<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="H23" version="1.2.0" createppg="false" language="fi-FI" type="Modbus" addressindexstart="1">
  <groups>
    <group categorytype="2" name="Fyysiset pisteet">
      <point name="UI 1" name_en="Outdoor temp." name_fi="Ulkolämpötila" name_sv="Utetemperatur" name_et="Välistemperatuur" name_ru="Наружная темп." name_lv="Ārgaisa temp." name_tr="Outdoor temp." pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 2" name_en="H1 Supply water" name_fi="L1 Menovesi" name_ru="О1 Подача" name_sv="V1 Framledningsv." name_et="K1 Küttevesi" name_lv="A1 Turpgaitas" name_tr="H1 Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 3" name_en="H1 Return water" name_fi="L1 Paluuvesi" name_ru="O1 Темп. обратной воды" name_sv="V1 Returvatten" name_et="K1 Tagastusvesi" name_lv="A1 Atgaitas temperatūra" name_tr="H1 Return water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 4" name_en="H1 Room temperature" name_fi="L1 Huonelämpötila" name_sv="V1 Rumstemperatur" name_et="M4" name_ru="M4" name_lv="M4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 5" name_en="H2 Supply water" name_fi="L2 Menovesi" name_ru="О2 Подача" name_sv="V2 Framledningsv." name_et="K2 Küttevesi" name_lv="A2 Turpgaitas" name_tr="H2 Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 6" name_en="H2 Return water" name_fi="L2 Paluuvesi" name_ru="H2 Return water" name_sv="V2 Returvattnet" name_et="H2 Return water" name_lv="H2 Return water" name_tr="H2 Return water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 7" name_en="H2 Room temperature" name_fi="L2 Huonelämpötila" name_sv="V2 Rumstemperatur" name_et="M7" name_ru="M7" name_lv="M7" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 8" name_en="DHW Supply water" name_fi="LV Menovesi" name_ru="ГВС Подача" name_sv="TV Framledningsv." name_et="TV  Küttevesi" name_lv="K.ŪD. Turpgaita" name_tr="DHW Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 9" name_en="DHW Circulation water" name_fi="LV Kiertovesi" name_ru="ГВС Темп. циркуляц.воды" name_sv="TV Cirkulationsvattnets temp." name_et="TV Ringlusvesi" name_lv="K.ŪD Cirkulācijas ūd." name_tr="DHW Circulation water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="DI 1" name_en="Digital input 1 status" name_fi="Digitaalitulon 1 tila" name_sv="Digital ingång 1 läge" name_et="" name_ru="Статус цифр.входа 1" name_lv="Digitālās ievades 1 statuss" name_tr="Digital input 1 status" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="DI 2" name_en="Digital input 2 status" name_fi="Digitaalitulon 2 tila" name_sv="Digital ingång 2 läge" name_et="" name_ru="Статус цифр.входа 2" name_lv="Digitālās ievades 2 statuss" name_tr="Digital input 2 status" pointtype="6" registertype="Holding" addressformat="S32" addressindex="221" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="AO 1" name_en="DHW Valve control, V" name_fi="LV Venttiilin ohjaus, V" name_sv="TV Ventilens styrning, V" name_et="DHW Valve control, V" name_ru="DHW Valve control, V" name_lv="DHW Valve control, V" name_tr="DHW Valve control, V" pointtype="6" registertype="Holding" addressformat="S32" addressindex="225" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 2" name_en="H1 Valve control, V" name_fi="L1 Venttiilin ohjaus, V" name_sv="V1 Ventilens styrning, V" name_et="H1 Valve control, V" name_ru="H1 Valve control, V" name_lv="H1 Valve control, V" name_tr="H1 Valve control, V" pointtype="6" registertype="Holding" addressformat="S32" addressindex="227" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 3" name_en="H2 Valve control, V" name_fi="L2 Venttiilin ohjaus, V" name_sv="V2 Ventilens styrning, V" name_et="H2 Valve control, V" name_ru="H2 Valve control, V" pointtype="6" registertype="Holding" addressformat="S32" addressindex="229" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="TR 1" name_en="TR1 Control" name_fi="TR1 Ohjaus" name_sv="TR1 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="231" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 2" name_en="TR2 control" name_fi="TR2 Ohjaus" name_sv="TR2 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="233" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 3" name_en="TR3 Control" name_fi="TR3 Ohjaus" name_sv="TR3 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="235" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 4" name_en="TR4 Control" name_fi="TR4 Ohjaus" name_sv="TR4 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="237" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 5" name_en="TR5 Control" name_fi="TR5 Ohjaus" name_sv="TR5 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="239" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 6" name_en="TR6 Control" name_fi="TR6 Ohjaus" name_sv="TR6 Styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="241" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="R1" name_en="DHW Pump control" name_fi="LV Pumpun ohjaus" name_sv="TV Pump styrning" pointtype="6" registertype="Holding" addressformat="S32" addressindex="243" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R2" name_en="H1 Pump control" name_fi="L1 Pumpun ohjaus" name_sv="V1 Pump styrning" name_et="H1 Pump control" name_ru="H1 Pump control" name_lv="H1 Pump control" pointtype="6" registertype="Holding" addressformat="S32" addressindex="245" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R3" name_en="H2 Pump control" name_fi="L2 Pumpun ohjaus" name_sv="V2 Pump styrning" name_et="H2 Pump control" name_ru="H2 Pump control" name_lv="H2 Pump control" name_tr="H2 Pump control" pointtype="6" registertype="Holding" addressformat="S32" addressindex="247" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
    </group>
    <group categorytype="2" name="Asetusarvot">
      <point name="HomeAwaySw" name_en="Home-Away-control" name_fi="Kotona-Poissa -ohjaus" name_ru="Управл. Дома-Не дома" name_sv="Hemma-Borta-styrning" name_et="Kodus-Eemal-juhtimine" name_lv="Mājās - Ārpus mājām - vadība" name_tr="Home-Away-control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="399" categorytype="3" enum="0=Poissa;1=Kotona" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="SMSNoNetworkAlarm_GSMFailureAlarmInUse" name_en="Communication alarm" name_fi="Modeemin kuuluvuushälytys" name_sv="Kommunikationlarm" name_et="" name_ru="Авария связи с модемом" name_lv="Komunikācijas trauksme" name_tr="Communication alarm" pointtype="3" registertype="Holding" addressformat="U16" addressindex="715" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="MeasurementsSel_H2DelayedRoomTemp_RoomMeasDelay" name_en="Room temp.measurement delay" name_fi="Huonel. mittauksen hidastusaika" name_sv="Rumstemp.mätningens fördröjning" name_et="Toatemperatuuri mõõtmise viivitus" name_ru="Отлож.вр.измер.темп.наруж.возд." name_lv="Telpas temp. mērījuma aizkave" name_tr="Room temp.measurement delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="424" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="6" />
      <point name="MeasurementsSel_H1DelayedRoomTemp_RoomMeasDelay" name_en="Room temp.measurement delay" name_fi="Huonel. mittauksen hidastusaika" name_sv="Rumstemp.mätningens fördröjning" name_et="Toatemperatuuri mõõtmise viivitus" name_ru="Отлож.вр.измер.темп.наруж.возд." name_lv="Telpas temp. mērījuma aizkave" name_tr="Room temp.measurement delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="426" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="6" />
      <point name="MeasurementsSel_DelayedOutTemp_OutdoorMeasDelay" name_en="Outdoor temperature delay" name_fi="Ulkolämpötilan hidastus" name_sv="Utetemperatur fördröjdning" name_et="" name_ru="Отлож.измер.темп.наруж.возд." name_lv="Ārgaisa temp. aizkave" name_tr="Outdoor temperature delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="430" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="6" />
      <point name="AlarmSettings_DI1AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="432" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_DI2AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="434" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M1AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="436" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M1AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="438" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M1AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="440" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M2AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="442" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M2AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="444" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M2AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="446" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M3AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="448" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M3AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="450" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M3AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="452" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M4AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="454" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M4AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="456" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M4AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="458" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M5AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="460" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M5AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="462" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M5AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="464" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M6AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="466" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M6AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="468" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M6AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="470" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M7AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="472" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M7AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="474" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M7AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="476" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M8AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="478" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M8AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="480" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M8AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="482" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_M9AlarmLowLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="484" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M9AlarmHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="486" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="AlarmSettings_M9AlarmDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="488" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_AlarmsEnable" name_en="Alarms" name_fi="Hälytykset" name_sv="Larm" name_et="Alarmid" name_ru="Аварийные сигналы" name_lv="Trauksmes" name_tr="Alarms" pointtype="3" registertype="Holding" addressformat="U16" addressindex="490" categorytype="3" enum="0=Estetty;1=Sallittu" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="AlarmSettings_DHWSupplyAlrDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="526" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_DHWSupplyAlrHiLimit" name_en="Alarm max limit" name_fi="Hälytyksen yläraja" name_sv="Larm max.gräns" name_et="Alarm ülempiir" name_ru="Верхний предел аварии" name_lv="Trauksmes maks. robeža" name_tr="Alarm max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="530" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="AlarmSettings_H1DeviationAlrDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="663" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_H1DeviationAlrLimit" name_en="Max. deviation from setting" name_fi="Maks.poikkeama asetusarvosta" name_sv="Maximal tillåten avvikelse" name_et="" name_ru="Макс.отклонение от устав.знач." name_lv="Maks. deviācija no iestatījuma" name_tr="Max. deviation from setting" pointtype="3" registertype="Holding" addressformat="S32" addressindex="671" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="100" />
      <point name="AlarmSettings_H2DeviationAlrDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="524" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_H2DeviationAlrLimit" name_en="Max. deviation from setting" name_fi="Maks.poikkeama asetusarvosta" name_sv="Maximal tillåten avvikelse" name_et="" name_ru="Макс.отклонение от устав.знач." name_lv="Maks. deviācija no iestatījuma" name_tr="Max. deviation from setting" pointtype="3" registertype="Holding" addressformat="S32" addressindex="567" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="100" />
      <point name="AlarmSettings_H1RetWaterAlrDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="569" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_H1RetWaterAlrLoLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="573" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="100" />
      <point name="AlarmSettings_H2RetWaterAlrDelay" name_en="Alarm delay" name_fi="Hälytysviive" name_sv="Larmfördröjning" name_et="" name_ru="Задержка авар.сигнала" name_lv="Trauksmes aizkaves laiks" name_tr="Alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="575" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="AlarmSettings_H2RetWaterAlrLoLimit" name_en="Alarm min limit" name_fi="Hälytyksen alaraja" name_sv="Larm min.gräns" name_et="Alarm alampiir" name_ru="Нижний предел аварии" name_lv="Trauksmes min. robeža" name_tr="Alarm min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="665" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="100" />
      <point name="DHW_Control_P_area" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="P-area" name_ru="Зона P" name_lv="P-ala" name_tr="P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="587" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="600" />
      <point name="DHW_Control_I_time" name_en="I-time" name_fi="I-aika" name_sv="I-tid" name_et="I-time" name_ru="Время I" name_lv="I-aeg" name_tr="I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="589" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="DHW_Control_D_time" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="D-aeg" name_ru="Время D" name_lv="D-laiks" name_tr="D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="591" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="DHW_Control_HW_Setpoint" name_en="Domestic hot water setting value" name_fi="Käyttöveden asetusarvo" name_sv="TV Inställningsvärde" name_et="Kodune kuuma vee seadeväärtus" name_ru="Уставочное значение ГВС" name_lv="Mājas karstā ūdens temp. iestat. vērtība" name_tr="Domestic hot water setting value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="593" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHW_Control_BoostPowerSetpoint" name_en="HW Quick run" name_fi="LV Pika-ajo" name_sv="TV Snabbkörn" name_et="BoostPower" name_ru="HW Quick run" pointtype="3" registertype="Holding" addressformat="S32" addressindex="595" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHW_Control_AnticipPSetpoint" name_en="AnticipP" name_fi="LV ennakointi" name_sv="AnticipP" name_et="AnticipP" name_ru="AnticipP" pointtype="3" registertype="Holding" addressformat="S32" addressindex="597" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="250" />
      <point name="H1HeatingControl_P_band" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="P-area" name_ru="Зона P" name_lv="P-apgablas" name_tr="P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="491" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="600" />
      <point name="H1HeatingControl_I_time" name_en="I-time" name_fi="I-aika" name_sv="I-tid" name_et="I-time" name_ru="Время I" name_lv="I-laiks" name_tr="I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="493" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="H1HeatingControl_PumpStopLimit" name_en="Pump stop limit/summer stop" name_fi="Pumpun pys.raja/kesäpys." name_sv="Pump stopp gräns/Sommar stopp" name_et="Pump stop limit/summer stop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="495" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      <point name="H1HeatingControl_RoomTempSetValue" name_en="Room temp set" name_fi="Huonelämpötilan asetus" pointtype="3" registertype="Holding" addressformat="S32" addressindex="497" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="35" />
      <point name="H1HeatingControl_DTime" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="D-tid" name_ru="Время D" name_lv="D-laiks" name_tr="D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="607" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H1HeatingControl_TempDrop_TempDropSetValue" name_en="Night drop" name_fi="Lämmönpudotus" name_sv="Natt sänkning" name_et="Night drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="500" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_Out1" name_en="Out1" name_fi="Out1" name_sv="Out1" name_et="Out1" name_ru="Out1" name_lv="Out1" name_tr="Out1" pointtype="3" registertype="Holding" addressformat="S32" addressindex="502" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_In2" name_en="In2" name_fi="In2" name_sv="In2" name_et="In2" name_ru="In2" name_lv="In2" name_tr="In2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="504" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-15" max="-5" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_Out2" name_en="Out2" name_fi="Out2" name_sv="Out2" name_et="Out2" name_ru="Out2" name_lv="Out2" name_tr="Out2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="506" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_In3" name_en="In3" name_fi="In3" name_sv="In3" name_et="In3" name_ru="In3" name_lv="In3" name_tr="In3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="508" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-5" max="5" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_Out3" name_en="Out3" name_fi="Out3" name_sv="Out3" name_et="Out3" name_ru="Out3" name_lv="Out3" name_tr="Out3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="510" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_In4" name_en="In4" name_fi="In4" name_sv="In4" name_et="In4" name_ru="In4" name_lv="In4" name_tr="In4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="512" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="15" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_Out4" name_en="Out4" name_fi="Out4" name_sv="Out4" name_et="Out4" name_ru="Out4" name_lv="Out4" name_tr="Out4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="514" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_Out5" name_en="Out5" name_fi="Out5" name_sv="Out5" name_et="Out5" name_ru="Out5" name_lv="Out5" name_tr="Out5" pointtype="3" registertype="Holding" addressformat="S32" addressindex="516" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_p_Min" name_en="Supply water min limit" name_fi="Menoveden minimiraja" name_sv="Framledningsvatten min gräns" name_et="Supply water min limit" name_ru="Мин.значение воды на подаче" name_lv="Turpgaitas temp. min. robeža" name_tr="Supply water min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="518" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      <point name="H1HeatingControl_OutDoorComp_Curve5_p_Max" name_en="Supply water max limit" name_fi="Menoveden maksimiraja" name_sv="Framledningsvatten max gräns" name_et="Supply water max limit" name_ru="Макс.значение воды на подаче" name_lv="Turpgaitas temp. maks. robeža" name_tr="Supply water max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="520" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      <point name="H1HeatingControl_RetWaterComp_RetWatCompFactor" name_en="Return water compensation ratio" name_fi="Paluuveden kompensointisuhde" name_sv="Returvattnets komp. förhållande" name_et="Tagastusvee kompenseerimne" name_ru="Компенсация обратной воды" name_lv="Atgaitas ūd. kompensācijas koeficients" name_tr="Return water compensation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="522" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H1HeatingControl_RoomComp_RoomCompRatio" name_en="Room compensation ratio" name_fi="Huonekompensointisuhde" name_sv="Rumskompenseringförhållande" name_et="Toa kompenseerimise suhtarv" name_ru="Коэфф. Комн. Компенс." name_lv="Telpas kompensācijas koeficients" name_tr="Room compensation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="528" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H1HeatingControl_RoomComp_RoomCompMinLimit" name_en="Minimum limit" name_fi="Minimiraja" name_sv="minimivärdet" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="678" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="H1HeatingControl_RoomComp_RoomCompMaxLimit" name_en="Maximum limit" name_fi="Maksimiraja" name_sv="Maximivärdet" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="680" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="H2HeatingControl_P_band" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="P-area" name_ru="Зона P" name_lv="P-apgablas" name_tr="P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="535" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="600" />
      <point name="H2HeatingControl_I_time" name_en="I-time" name_fi="I-aika" name_sv="I-tid" name_et="I-time" name_ru="Время I" name_lv="I-laiks" name_tr="I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="548" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="H2HeatingControl_PumpStopLimit" name_en="Pump stop limit/summer stop" name_fi="Pumpun pys.raja/kesäpys." name_sv="Pump stopp gräns/Sommar stopp" name_et="Pump stop limit/summer stop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="550" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      <point name="H2HeatingControl_RoomTempSetValue" name_en="Room temp set" name_fi="Huonelämpötilan asetus" pointtype="3" registertype="Holding" addressformat="S32" addressindex="552" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="35" />
      <point name="H2HeatingControl_DTime" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="D-tid" name_ru="Время D" name_lv="D-laiks" name_tr="D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="554" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H2HeatingControl_TempDrop_TempDropSetValue" name_en="Night drop" name_fi="Lämmönpudotus" name_sv="Natt sänkning" name_et="Night drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="556" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_Out1" name_en="Out1" name_fi="Out1" name_sv="Out1" name_et="Out1" name_ru="Out1" name_lv="Out1" name_tr="Out1" pointtype="3" registertype="Holding" addressformat="S32" addressindex="558" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_In2" name_en="In2" name_fi="In2" name_sv="In2" name_et="In2" name_ru="In2" name_lv="In2" name_tr="In2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="560" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-15" max="-5" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_Out2" name_en="Out2" name_fi="Out2" name_sv="Out2" name_et="Out2" name_ru="Out2" name_lv="Out2" name_tr="Out2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="562" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_In3" name_en="In3" name_fi="In3" name_sv="In3" name_et="In3" name_ru="In3" name_lv="In3" name_tr="In3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="564" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-5" max="5" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_Out3" name_en="Out3" name_fi="Out3" name_sv="Out3" name_et="Out3" name_ru="Out3" name_lv="Out3" name_tr="Out3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="571" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_In4" name_en="In4" name_fi="In4" name_sv="In4" name_et="In4" name_ru="In4" name_lv="In4" name_tr="In4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="577" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="15" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_Out4" name_en="Out4" name_fi="Out4" name_sv="Out4" name_et="Out4" name_ru="Out4" name_lv="Out4" name_tr="Out4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="579" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_Out5" name_en="Out5" name_fi="Out5" name_sv="Out5" name_et="Out5" name_ru="Out5" name_lv="Out5" name_tr="Out5" pointtype="3" registertype="Holding" addressformat="S32" addressindex="581" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_p_Min" name_en="Supply water min limit" name_fi="Menoveden minimiraja" name_sv="Framledningsvatten min gräns" name_et="Supply water min limit" name_ru="Мин.значение воды на подаче" name_lv="Turpgaitas temp. min. robeža" name_tr="Supply water min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="583" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      <point name="H2HeatingControl_OutDoorComp_Curve5_p_Max" name_en="Supply water max limit" name_fi="Menoveden maksimiraja" name_sv="Framledningsvatten max gräns" name_et="Supply water max limit" name_ru="Макс.значение воды на подаче" name_lv="Turpgaitas temp. maks. robeža" name_tr="Supply water max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="585" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      <point name="H2HeatingControl_RetWaterComp_RetWatCompFactor" name_en="Return water compensation ratio" name_fi="Paluuveden kompensointisuhde" name_sv="Returvattnets komp. förhållande" name_et="Tagastusvee kompenseerimne" name_ru="Компенсация обратной воды" name_lv="Atgaitas ūd. kompensācijas koeficients" name_tr="Return water compensation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="599" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H2HeatingControl_RoomComp_RoomCompRatio" name_en="Room compensation ratio" name_fi="Huonekompensointisuhde" name_sv="Rumskompenseringförhållande" name_et="Toa kompenseerimise suhtarv" name_ru="Коэфф. Комн. Компенс." name_lv="Telpas kompensācijas koeficients" name_tr="Room compensation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="601" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="H2HeatingControl_RoomComp_RoomCompMinLimit" name_en="Minimum limit" name_fi="Minimiraja" name_sv="minimivärdet" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="603" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="H2HeatingControl_RoomComp_RoomCompMaxLimit" name_en="Maximum limit" name_fi="Maksimiraja" name_sv="Maximivärdet" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="605" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="DHWMotorCtrl_DHWActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор привода" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="544" categorytype="3" enum="0=Ei käytössä;1=3-piste;2=0-10V;3=2-10V;4=10-0V;5=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="5" />
      <point name="DHWMotorCtrl_t_Open" name_en="Actuator running time open" name_fi="Toimilaitteen ajoaika auki" name_sv="Ställdon gångtid, öppna" name_et="Aktuaatori tööaeg avatud" name_ru="Время откр.привода" name_lv="Izpildmehānisma atvēršanās laiks" name_tr="Actuator running time open" pointtype="3" registertype="Holding" addressformat="S32" addressindex="546" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="DHWMotorCtrl_t_Close" name_en="Actuator running time close" name_fi="Toimilaitteen ajoaika kiinni" name_sv="Ställdon gångtid, stänga" name_et="Aktuaatori tööaeg suletud" name_ru="Время закр.привода" name_lv="Izpildmehānisma aizvēršanās laiks" name_tr="Actuator running time close" pointtype="3" registertype="Holding" addressformat="S32" addressindex="629" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="DHWMotorCtrl_HeatingCircuitMode" name_en="DHW Control mode" name_fi="LV Ohjaustapa" name_sv="TV Styrsätt" name_et="DHW Control mode" name_ru="DHW Control mode" name_lv="DHW Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="631" categorytype="3" enum="0=Automaatti;1=Käsiajo sähköinen;2=Käsiajo mekaaninen" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="H1MotorCtrl_H1ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор привода" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="698" categorytype="3" enum="0=Ei käytössä;1=3-piste;2=0-10V;3=2-10V;4=10-0V;5=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="5" />
      <point name="H1MotorCtrl_t_Open" name_en="Actuator running time open" name_fi="Toimilaitteen ajoaika auki" name_sv="Ställdon gångtid, öppna" name_et="Aktuaatori tööaeg avatud" name_ru="Время откр.привода" name_lv="Izpildmehānisma atvēršanās laiks" name_tr="Actuator running time open" pointtype="3" registertype="Holding" addressformat="S32" addressindex="700" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H1MotorCtrl_t_Close" name_en="Actuator running time close" name_fi="Toimilaitteen ajoaika kiinni" name_sv="Ställdon gångtid, stänga" name_et="Aktuaatori tööaeg suletud" name_ru="Время закр.привода" name_lv="Izpildmehānisma aizvēršanās laiks" name_tr="Actuator running time close" pointtype="3" registertype="Holding" addressformat="S32" addressindex="702" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H1MotorCtrl_HeatingCircuitMode" name_en="H1 Control mode" name_fi="L1 Ohjaustapa" name_sv="V1 Styrsätt" name_et="H1 Control mode" name_ru="H1 Control mode" name_lv="H1 Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="704" categorytype="3" enum="0=Automaatti;1=Käsiajo sähköinen;2=Käsiajo mekaaninen" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="H2MotorCtrl_t_Open" name_en="Actuator running time open" name_fi="Toimilaitteen ajoaika auki" name_sv="Ställdon gångtid, öppna" name_et="Aktuaatori tööaeg avatud" name_ru="Время откр.привода" name_lv="Izpildmehānisma atvēršanās laiks" name_tr="Actuator running time open" pointtype="3" registertype="Holding" addressformat="S32" addressindex="395" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H2MotorCtrl_t_Close" name_en="Actuator running time close" name_fi="Toimilaitteen ajoaika kiinni" name_sv="Ställdon gångtid, stänga" name_et="Aktuaatori tööaeg suletud" name_ru="Время закр.привода" name_lv="Izpildmehānisma aizvēršanās laiks" name_tr="Actuator running time close" pointtype="3" registertype="Holding" addressformat="S32" addressindex="538" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H2MotorCtrl_HeatingCircuitMode" name_en="H2 Control mode" name_fi="L2 Ohjaustapa" name_sv="V2 Styrsätt" name_et="H2 Control mode" name_ru="H2 Control mode" name_lv="H2 Control mode" name_tr="H2 Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="540" categorytype="3" enum="0=Automaatti;1=Käsiajo sähköinen;2=Käsiajo mekaaninen" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="H2MotorCtrl_H2ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор привода" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="542" categorytype="3" enum="0=Ei käytössä;1=3-piste;2=0-10V;3=2-10V;4=10-0V;5=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="5" />
    </group>
    <group categorytype="2" name="Mittaukset">
      <point name="DigitalInputsSel_DI1Stat" name_en="DI 1 status" name_fi="DI 1 tila" name_sv="DI 1 status" name_et="DI 1 status" name_ru="DI 1 status" name_lv="DI 1 status" pointtype="10" registertype="Holding" addressformat="U16" addressindex="667" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="DigitalInputsSel_DI2Stat" name_en="DI 2 status" name_fi="DI 2 tila" name_sv="DI 2 status" name_et="DI 2 status" name_ru="DI 2 status" name_lv="DI 2 status" pointtype="10" registertype="Holding" addressformat="U16" addressindex="668" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="BusInputs_OutdoorTempFromBus" name_en="Outdoor temperature from bus" name_fi="Ulkolämpötila väylältä" name_sv="Utetemperatur från bus" name_et="Outdoor temperature from bus" name_ru="Outdoor temperature from bus" name_lv="Outdoor temperature from bus" name_tr="Outdoor temperature from bus" pointtype="10" registertype="Holding" addressformat="S32" addressindex="256" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="BusInputs_H1RoomTempFromBus" name_en="H1 Room temperature from bus" name_fi="L1 Huonelämpötila väylältä" name_sv="V1 Rumstemperatur från bus" name_et="H1 Room temperature from bus" name_ru="H1 Room temperature from bus" name_lv="H1 Room temperature from bus" name_tr="H1 Room temperature from bus" pointtype="10" registertype="Holding" addressformat="S32" addressindex="258" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="BusInputs_H2RoomTempFromBus" name_en="H2 Room temperature from bus" name_fi="L2 Huonelämpötila väylältä" name_sv="V2 Rumstemperatur från bus" name_et="H2 Room temperature from bus" name_ru="H2 Room temperature from bus" pointtype="10" registertype="Holding" addressformat="S32" addressindex="260" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_M7FreeMeas" name_en="M7 Measurement" name_fi="M7 Mittaus" name_sv="M7 Mätning" name_ru="Измерение M7" name_et="M7 Mõõtmine" name_lv="Mērīj. M7" name_tr="M7 Measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="263" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_M6FreeMeas" name_en="M6 Measurement" name_fi="M6 Mittaus" name_sv="M6 Mätning" name_ru="Измерение M6" name_et="M6 Mõõtmine" name_lv="Mērīj. M6" name_tr="M6 Measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="265" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_M5FreeMeas" name_en="M5 Measurement" name_fi="M5 Mittaus" name_sv="M5 Mätning" name_ru="Измерение M5" name_et="M5 Mõõtmine" name_lv="Mērīj. M5" name_tr="M5 Measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="267" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_OutDoorTempMeas" name_en="Outdoor temperature" name_fi="Ulkolämpötila" name_sv="Utetemperatur" name_et="Välistemperatuur" name_ru="Outdoor temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="269" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_H1RoomTempMeas" name_en="H1 Room temperature" name_fi="L1 Huonelämpötila" name_sv="V1 Rumstemperatur" name_et="K1 Toatemperatuur" name_ru="О1 Комнатная температура" name_lv="A1 Telpas temperatūra" name_tr="H1 Room temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="271" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_H2RoomTempMeas" name_en="H2 Room temperature" name_fi="L2 Huonelämpötila" name_sv="V2 Rumstemperatur" name_et="K2 Toatemperatuur" name_ru="О2 Комнатная температура" name_lv="A2 Telpas temperatūra" name_tr="H2 Room temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="273" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" />
      <point name="MeasurementsSel_H1RoomTempDelayed" name_en="H1 Room temperature filtered" name_fi="L1 Hidastettu huonelämpötila" name_sv="V1 Rumstemperatur filtrerades" pointtype="10" registertype="Holding" addressformat="S32" addressindex="275" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="MeasurementsSel_H2RoomTempDelayed" name_en="H2 Room temperature filtered" name_fi="L2 Hidastettu huonelämpötila" name_sv="V2 Rumstemperatur filtrerades" pointtype="10" registertype="Holding" addressformat="S32" addressindex="277" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="MeasurementsSel_OutdoorTempDelayed" name_en="Outdoor temperature filtered" name_fi="Hidastettu ulkolämpötila" name_sv="Utetemperatur filtrerades" pointtype="10" registertype="Holding" addressformat="S32" addressindex="279" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="MeasurementsSel_H2DelayedRoomTemp_H2DelayedRoomTempEff" name_en="Filtering effect" name_fi="Hidastuksen vaikutus" name_sv="Filtering effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="620" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="MeasurementsSel_H1DelayedRoomTemp_H1DelayedRoomTempEff" name_en="Filtering effect" name_fi="Hidastuksen vaikutus" name_sv="Filtering effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="618" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="MeasurementsSel_DelayedOutTemp_DelayedOutTempEff" name_en="Filtering effect" name_fi="Hidastuksen vaikutus" name_sv="Filtering effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="622" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="AlarmSettings_DI1_AlarmName" name_en="Switch alarm" name_fi="Kosketinhälytys" name_sv="Koppling larm" name_et="Lüliti alarm" name_ru="Авария по контакту" name_lv="Trauksmes relejs" name_tr="Switch alarm" pointtype="10" registertype="Holding" addressformat="U16" addressindex="281" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="AlarmSettings_DI2_AlarmName" name_en="Switch alarm" name_fi="Kosketinhälytys" name_sv="Koppling larm" name_et="Lüliti alarm" name_ru="Авария по контакту" name_lv="Trauksmes relejs" pointtype="10" registertype="Holding" addressformat="U16" addressindex="282" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="DHW_Control_DHWControlOut" name_en="DHW Control" name_fi="LV Ohjaus" name_sv="TV Kontroll" pointtype="10" registertype="Holding" addressformat="S32" addressindex="327" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_ControlOutValue" name_en="Supply water control output" name_fi="Säädön ulostulo" name_sv="Tillop vatten kontroll styrning" pointtype="10" registertype="Holding" addressformat="S32" addressindex="283" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="H1HeatingControl_H1CalculatedSupplySet" name_en="Calculated supply water setting" name_fi="Laskennall. menoveden asetusarvo" name_sv="Beräknad framledningstemp." name_et="Calculated supply water setting" pointtype="10" registertype="Holding" addressformat="S32" addressindex="285" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_CurveSetpoint" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurva" name_et="Küttevesi vastavalt küttekõverale" name_ru="В соответствии с кривой" name_lv="Pēc līknes" name_tr="According to curve" pointtype="10" registertype="Holding" addressformat="S32" addressindex="287" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_RoomCompEff" name_en="Room compensation" name_fi="Huonekomp. vaikutus menoveteen" name_sv="Rumskompensation" name_et="Room compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="289" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_RetWaterCompEff" name_en="Return water compensation" name_fi="Paluuvesikomp. vaikutus" name_sv="Påverkan av returvattnets kompens." name_et="Return water compensation" name_ru="Компенс. по обратной воде" name_lv="Return water compensation" name_tr="Return water compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="291" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_H1SummerStop" name_en="Summer stop" name_fi="Kesäpysäytys" name_sv="Sommarfunktion" name_et="" name_ru="" name_lv="" pointtype="10" registertype="Holding" addressformat="U16" addressindex="293" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="H1HeatingControl_TempDropEff" name_en="Effect of temperature drop" name_fi="Lämmönpudotuksen vaikutus" name_sv="Påverkan av temperatursänkningen" name_ru="Воздействие понижения температуры" name_lv="Temp. pazeminājuma ietekme" pointtype="10" registertype="Holding" addressformat="S32" addressindex="294" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_HeatingMinLimitEff" name_en="Min limit effect" name_sv="Påverkan av min.gränsen" name_fi="Minimirajan vaikutus" name_et="Alampiiri mõju" name_ru="Воздействие мин. ограничения" name_lv="Min. robežas ietekme" name_tr="Min limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="296" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_HeatingMaxLimitEff" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Påverkan av max.gränsen" name_et="Ülempiiri mõju" name_ru="Воздействие макс. ограничения" name_lv="Maks. robežas ietekme" name_tr="Max limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="298" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1HeatingControl_TempDrop_TempDropModes" name_en="Temperature drop status" name_fi="Lämmönpudotuksen tila" name_sv="Temperatursänkning status" name_et="" name_ru="Статус режима пониж.темпер." name_lv="Temp. pazeminājuma stāvoklis" name_tr="Temperature drop status" pointtype="10" registertype="Holding" addressformat="S32" addressindex="300" categorytype="2" enum="0=Ei pudotusta;1=Poissa ohj.;2=Aikaohj.;3=Poissa ohj. / Aikaohj." scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_ControlOutValue" name_en="Supply water control output" name_fi="Säädön ulostulo" name_sv="Tillop vatten kontroll styrning" pointtype="10" registertype="Holding" addressformat="S32" addressindex="310" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="H2HeatingControl_CurveSetpoint" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurva" name_et="Küttevesi vastavalt küttekõverale" name_ru="В соответствии с кривой" name_lv="Pēc līknes" name_tr="According to curve" pointtype="10" registertype="Holding" addressformat="S32" addressindex="312" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_RoomCompEff" name_en="Room compensation" name_fi="Huonekomp. vaikutus menoveteen" name_sv="Rumskompensation" name_et="Room compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="314" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_RetWaterCompEff" name_en="Return water compensation" name_fi="Paluuvesikomp. vaikutus" name_sv="Påverkan av returvattnets kompens." name_et="Return water compensation" name_ru="Компенс. по обратной воде" name_lv="Return water compensation" name_tr="Return water compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="316" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_TempDropEff" name_en="Effect of temperature drop" name_fi="Lämmönpudotuksen vaikutus" name_sv="Påverkan av temperatursänkningen" name_ru="Воздействие понижения температуры" name_lv="Temp. pazeminājuma ietekme" pointtype="10" registertype="Holding" addressformat="S32" addressindex="318" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_HeatingMinLimitEff" name_en="Min limit effect" name_sv="Påverkan av min.gränsen" name_fi="Minimirajan vaikutus" name_et="Alampiiri mõju" name_ru="Воздействие мин. ограничения" name_lv="Min. robežas ietekme" name_tr="Min limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="320" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_HeatingMaxLimitEff" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Påverkan av max.gränsen" name_et="Ülempiiri mõju" name_ru="Воздействие макс. ограничения" name_lv="Maks. robežas ietekme" name_tr="Max limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="322" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_H2CalculatedSupplySet" name_en="Limited output value" name_fi="Laskenn. menoveden astetusarvo" name_sv="Begränsad utgångsvärde" pointtype="10" registertype="Holding" addressformat="S32" addressindex="615" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2HeatingControl_H2SummerStop" name_en="H2 Summer function" name_fi="L2 Kesätoiminto" name_sv="V2 Sommarfunktion" name_et="H2 Summer function" name_ru="H2 Summer function" name_lv="H2 Summer function" name_tr="H2 Summer function" pointtype="10" registertype="Holding" addressformat="U16" addressindex="537" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="H2HeatingControl_TempDrop_TempDropModes" name_en="Temperature drop status" name_fi="Lämmönpudotuksen tila" name_sv="Temperatursänkning status" name_et="" name_ru="Статус режима пониж.темпер." name_lv="Temp. pazeminājuma stāvoklis" name_tr="Temperature drop status" pointtype="10" registertype="Holding" addressformat="S32" addressindex="329" categorytype="2" enum="0=Ei pudotusta;1=Poissa ohj.;2=Aikaohj.;3=Poissa ohj. / Aikaohj." scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="DHWMotorCtrl_ActuatorControlV" name_en="Actuator position, V" name_fi="Toimilaitteen asento, V" name_sv="Ställdonets läge, V" name_et="Actuator position, V" name_ru="Actuator position, V" pointtype="10" registertype="Holding" addressformat="S32" addressindex="381" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="DHWMotorCtrl_ActuatorControl3p" name_en="Actuator position, 3p" name_fi="Toimilaitteen asento, 3p" name_sv="Ställdonets läge, 3p" name_et="Actuator position, 3p" name_ru="Actuator position, 3p" name_lv="Actuator position, 3p" pointtype="10" registertype="Holding" addressformat="S32" addressindex="383" categorytype="2" enum="0=Kiinni;1=-;2=Auki" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="2" />
      <point name="H1MotorCtrl_ActuatorControlV" name_en="Actuator position, V" name_fi="Toimilaitteen asento, V" name_sv="Ställdonets läge, V" name_et="Actuator position, V" name_ru="Actuator position, V" name_lv="Actuator position, V" pointtype="10" registertype="Holding" addressformat="S32" addressindex="613" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="H1MotorCtrl_ActuatorControl3p" name_en="Actuator position, 3p" name_fi="Toimilaitteen asento, 3p" name_sv="Ställdonets läge, 3p" name_et="Actuator position, 3p" name_ru="Actuator position, 3p" name_lv="Actuator position, 3p" pointtype="10" registertype="Holding" addressformat="S32" addressindex="696" categorytype="2" enum="0=Kiinni;1=-;2=Auki" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="2" />
      <point name="H2MotorCtrl_ActuatorControlV" name_en="Actuator position, V" name_fi="Toimilaitteen asento, V" name_sv="Ställdonets läge, V" name_et="Actuator position, V" name_ru="Actuator position, V" pointtype="10" registertype="Holding" addressformat="S32" addressindex="306" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="H2MotorCtrl_ActuatorControl3p" name_en="Actuator position, 3p" name_fi="Toimilaitteen asento, 3p" name_sv="Ställdonets läge, 3p" name_et="Actuator position, 3p" name_ru="Actuator position, 3p" name_lv="Actuator position, 3p" pointtype="10" registertype="Holding" addressformat="S32" addressindex="308" categorytype="2" enum="0=Kiinni;1=-;2=Auki" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="2" />
      <point name="OutputsSel_H1PumpCtrl" name_en="H1 Pump control" name_fi="L1 Pumpun ohjaus" name_sv="V1 Pump styrning" name_et="H1 Pump control" name_ru="H1 Pump control" name_lv="H1 Pump control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="609" categorytype="2" enum="0=Pois;1=Päällä" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="OutputsSel_H2PumpCtrl" name_en="H2 Pump control" name_fi="L2 Pumpun ohjaus" name_sv="V2 Pump styrning" name_et="H2 Pump control" name_ru="H2 Pump control" name_lv="H2 Pump control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="611" categorytype="2" enum="0=Pois;1=Päällä" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="OutputsSel_DHWPumpCtrl" name_en="DHW Pump control" name_fi="LV Pumpun ohjaus" name_sv="TV Pump styrning" name_et="DHW Pump control" name_ru="DHW Pump control" name_lv="DHW Pump control" pointtype="10" registertype="Holding" addressformat="U16" addressindex="385" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
    </group>
    <group categorytype="1" name="Käsiajo">
      <point name="UI 1_mc" name_en="Outdoor temp. Manual control" name_fi="Ulkolämpötila Käsiajo" name_sv="Utetemperatur Manuell styrning" name_et="Välistemperatuur käsijuhtimisrežiim" name_ru="Наружная темп. Ручной режим" name_lv="Ārgaisa temp. Rokas vadība" name_tr="Outdoor temp. Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="341" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 2_mc" name_en="H1 Supply water Manual control" name_fi="L1 Menovesi Käsiajo" name_ru="О1 Подача Ручной режим" name_sv="V1 Framledningsv. Manuell styrning" name_et="K1 Küttevesi käsijuhtimisrežiim" name_lv="A1 Turpgaitas Rokas vadība" name_tr="H1 Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="342" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 3_mc" name_en="H1 Return water Manual control" name_fi="L1 Paluuvesi Käsiajo" name_ru="O1 Темп. обратной воды Ручной режим" name_sv="V1 Returvatten Manuell styrning" name_et="K1 Tagastusvesi käsijuhtimisrežiim" name_lv="A1 Atgaitas temperatūra Rokas vadība" name_tr="H1 Return water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="343" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 4_mc" name_en="H1 Room temperature Manual control" name_fi="L1 Huonelämpötila Käsiajo" name_sv="V1 Rumstemperatur Manuell styrning" name_et="M4 käsijuhtimisrežiim" name_ru="M4 Ручной режим" name_lv="M4 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="344" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 5_mc" name_en="H2 Supply water Manual control" name_fi="L2 Menovesi Käsiajo" name_ru="О2 Подача Ручной режим" name_sv="V2 Framledningsv. Manuell styrning" name_et="K2 Küttevesi käsijuhtimisrežiim" name_lv="A2 Turpgaitas Rokas vadība" name_tr="H2 Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="345" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 6_mc" name_en="H2 Return water Manual control" name_fi="L2 Paluuvesi Käsiajo" name_ru="H2 Return water Ручной режим" name_sv="V2 Returvattnet Manuell styrning" name_et="H2 Return water käsijuhtimisrežiim" name_lv="H2 Return water Rokas vadība" name_tr="H2 Return water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="346" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 7_mc" name_en="H2 Room temperature Manual control" name_fi="L2 Huonelämpötila Käsiajo" name_sv="V2 Rumstemperatur Manuell styrning" name_et="M7 käsijuhtimisrežiim" name_ru="M7 Ручной режим" name_lv="M7 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="347" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 8_mc" name_en="DHW Supply water Manual control" name_fi="LV Menovesi Käsiajo" name_ru="ГВС Подача Ручной режим" name_sv="TV Framledningsv. Manuell styrning" name_et="TV  Küttevesi käsijuhtimisrežiim" name_lv="K.ŪD. Turpgaita Rokas vadība" name_tr="DHW Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="348" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 9_mc" name_en="DHW Circulation water Manual control" name_fi="LV Kiertovesi Käsiajo" name_ru="ГВС Темп. циркуляц.воды Ручной режим" name_sv="TV Cirkulationsvattnets temp. Manuell styrning" name_et="TV Ringlusvesi käsijuhtimisrežiim" name_lv="K.ŪD Cirkulācijas ūd. Rokas vadība" name_tr="DHW Circulation water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="349" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 1_mc" name_en="Digital input 1 status Manual control" name_fi="Digitaalitulon 1 tila Käsiajo" name_sv="Digital ingång 1 läge Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru="Статус цифр.входа 1 Ручной режим" name_lv="Digitālās ievades 1 statuss Rokas vadība" name_tr="Digital input 1 status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="350" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 2_mc" name_en="Digital input 2 status Manual control" name_fi="Digitaalitulon 2 tila Käsiajo" name_sv="Digital ingång 2 läge Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru="Статус цифр.входа 2 Ручной режим" name_lv="Digitālās ievades 2 statuss Rokas vadība" name_tr="Digital input 2 status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="351" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 1_mc" name_en="DHW Valve control, V Manual control" name_fi="LV Venttiilin ohjaus, V Käsiajo" name_sv="TV Ventilens styrning, V Manuell styrning" name_et="DHW Valve control, V käsijuhtimisrežiim" name_ru="DHW Valve control, V Ручной режим" name_lv="DHW Valve control, V Rokas vadība" name_tr="DHW Valve control, V Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="353" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 2_mc" name_en="H1 Valve control, V Manual control" name_fi="L1 Venttiilin ohjaus, V Käsiajo" name_sv="V1 Ventilens styrning, V Manuell styrning" name_et="H1 Valve control, V käsijuhtimisrežiim" name_ru="H1 Valve control, V Ручной режим" name_lv="H1 Valve control, V Rokas vadība" name_tr="H1 Valve control, V Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="354" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 3_mc" name_en="H2 Valve control, V Manual control" name_fi="L2 Venttiilin ohjaus, V Käsiajo" name_sv="V2 Ventilens styrning, V Manuell styrning" name_et="H2 Valve control, V käsijuhtimisrežiim" name_ru="H2 Valve control, V Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="355" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 1_mc" name_en="TR1 Control Manual control" name_fi="TR1 Ohjaus Käsiajo" name_sv="TR1 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="356" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 2_mc" name_en="TR2 control Manual control" name_fi="TR2 Ohjaus Käsiajo" name_sv="TR2 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="357" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 3_mc" name_en="TR3 Control Manual control" name_fi="TR3 Ohjaus Käsiajo" name_sv="TR3 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="358" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 4_mc" name_en="TR4 Control Manual control" name_fi="TR4 Ohjaus Käsiajo" name_sv="TR4 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="359" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 5_mc" name_en="TR5 Control Manual control" name_fi="TR5 Ohjaus Käsiajo" name_sv="TR5 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="360" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 6_mc" name_en="TR6 Control Manual control" name_fi="TR6 Ohjaus Käsiajo" name_sv="TR6 Styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="361" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R1_mc" name_en="DHW Pump control Manual control" name_fi="LV Pumpun ohjaus Käsiajo" name_sv="TV Pump styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="362" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R2_mc" name_en="H1 Pump control Manual control" name_fi="L1 Pumpun ohjaus Käsiajo" name_sv="V1 Pump styrning Manuell styrning" name_et="H1 Pump control käsijuhtimisrežiim" name_ru="H1 Pump control Ручной режим" name_lv="H1 Pump control Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="363" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R3_mc" name_en="H2 Pump control Manual control" name_fi="L2 Pumpun ohjaus Käsiajo" name_sv="V2 Pump styrning Manuell styrning" name_et="H2 Pump control käsijuhtimisrežiim" name_ru="H2 Pump control Ручной режим" name_lv="H2 Pump control Rokas vadība" name_tr="H2 Pump control Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="364" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DigitalInputsSel_DI1Stat_mc" name_en="DI 1 status Manual control" name_fi="DI 1 tila Käsiajo" name_sv="DI 1 status Manuell styrning" name_et="DI 1 status käsijuhtimisrežiim" name_ru="DI 1 status Ручной режим" name_lv="DI 1 status Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="669" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DigitalInputsSel_DI2Stat_mc" name_en="DI 2 status Manual control" name_fi="DI 2 tila Käsiajo" name_sv="DI 2 status Manuell styrning" name_et="DI 2 status käsijuhtimisrežiim" name_ru="DI 2 status Ручной режим" name_lv="DI 2 status Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="670" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_M7FreeMeas_mc" name_en="M7 Measurement Manual control" name_fi="M7 Mittaus Käsiajo" name_sv="M7 Mätning Manuell styrning" name_ru="Измерение M7 Ручной режим" name_et="M7 Mõõtmine käsijuhtimisrežiim" name_lv="Mērīj. M7 Rokas vadība" name_tr="M7 Measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="369" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_M6FreeMeas_mc" name_en="M6 Measurement Manual control" name_fi="M6 Mittaus Käsiajo" name_sv="M6 Mätning Manuell styrning" name_ru="Измерение M6 Ручной режим" name_et="M6 Mõõtmine käsijuhtimisrežiim" name_lv="Mērīj. M6 Rokas vadība" name_tr="M6 Measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="370" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_M5FreeMeas_mc" name_en="M5 Measurement Manual control" name_fi="M5 Mittaus Käsiajo" name_sv="M5 Mätning Manuell styrning" name_ru="Измерение M5 Ручной режим" name_et="M5 Mõõtmine käsijuhtimisrežiim" name_lv="Mērīj. M5 Rokas vadība" name_tr="M5 Measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="371" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_OutdoorTempDelayed_mc" name_en="Outdoor temperature filtered Manual control" name_fi="Hidastettu ulkolämpötila Käsiajo" name_sv="Utetemperatur filtrerades Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="372" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_H2DelayedRoomTemp_H2DelayedRoomTempEff_mc" name_en="Filtering effect Manual control" name_fi="Hidastuksen vaikutus Käsiajo" name_sv="Filtering effect Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="688" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_H1DelayedRoomTemp_H1DelayedRoomTempEff_mc" name_en="Filtering effect Manual control" name_fi="Hidastuksen vaikutus Käsiajo" name_sv="Filtering effect Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="624" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MeasurementsSel_DelayedOutTemp_DelayedOutTempEff_mc" name_en="Filtering effect Manual control" name_fi="Hidastuksen vaikutus Käsiajo" name_sv="Filtering effect Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="689" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AlarmSettings_DI1_AlarmName_mc" name_en="Switch alarm Manual control" name_fi="Kosketinhälytys Käsiajo" name_sv="Koppling larm Manuell styrning" name_et="Lüliti alarm käsijuhtimisrežiim" name_ru="Авария по контакту Ручной режим" name_lv="Trauksmes relejs Rokas vadība" name_tr="Switch alarm Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="691" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AlarmSettings_DI2_AlarmName_mc" name_en="Switch alarm Manual control" name_fi="Kosketinhälytys Käsiajo" name_sv="Koppling larm Manuell styrning" name_et="Lüliti alarm käsijuhtimisrežiim" name_ru="Авария по контакту Ручной режим" name_lv="Trauksmes relejs Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="692" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DHW_Control_DHWControlOut_mc" name_en="DHW Control Manual control" name_fi="LV Ohjaus Käsiajo" name_sv="TV Kontroll Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="391" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_ControlOutValue_mc" name_en="Supply water control output Manual control" name_fi="Säädön ulostulo Käsiajo" name_sv="Tillop vatten kontroll styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="373" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_H1CalculatedSupplySet_mc" name_en="Calculated supply water setting Manual control" name_fi="Laskennall. menoveden asetusarvo Käsiajo" name_sv="Beräknad framledningstemp. Manuell styrning" name_et="Calculated supply water setting käsijuhtimisrežiim" pointtype="3" registertype="Holding" addressformat="U16" addressindex="374" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_RetWaterCompEff_mc" name_en="Return water compensation Manual control" name_fi="Paluuvesikomp. vaikutus Käsiajo" name_sv="Påverkan av returvattnets kompens. Manuell styrning" name_et="Return water compensation käsijuhtimisrežiim" name_ru="Компенс. по обратной воде Ручной режим" name_lv="Return water compensation Rokas vadība" name_tr="Return water compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="375" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_H1SummerStop_mc" name_en="Summer stop Manual control" name_fi="Kesäpysäytys Käsiajo" name_sv="Sommarfunktion Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" name_lv=" Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="376" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_TempDropEff_mc" name_en="Effect of temperature drop Manual control" name_fi="Lämmönpudotuksen vaikutus Käsiajo" name_sv="Påverkan av temperatursänkningen Manuell styrning" name_ru="Воздействие понижения температуры Ручной режим" name_lv="Temp. pazeminājuma ietekme Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="377" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_HeatingMinLimitEff_mc" name_en="Min limit effect Manual control" name_sv="Påverkan av min.gränsen Manuell styrning" name_fi="Minimirajan vaikutus Käsiajo" name_et="Alampiiri mõju käsijuhtimisrežiim" name_ru="Воздействие мин. ограничения Ручной режим" name_lv="Min. robežas ietekme Rokas vadība" name_tr="Min limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="378" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_HeatingMaxLimitEff_mc" name_en="Max limit effect Manual control" name_fi="Maksimirajan vaikutus Käsiajo" name_sv="Påverkan av max.gränsen Manuell styrning" name_et="Ülempiiri mõju käsijuhtimisrežiim" name_ru="Воздействие макс. ограничения Ручной режим" name_lv="Maks. robežas ietekme Rokas vadība" name_tr="Max limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="379" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1HeatingControl_TempDrop_TempDropModes_mc" name_en="Temperature drop status Manual control" name_fi="Lämmönpudotuksen tila Käsiajo" name_sv="Temperatursänkning status Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru="Статус режима пониж.темпер. Ручной режим" name_lv="Temp. pazeminājuma stāvoklis Rokas vadība" name_tr="Temperature drop status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="380" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_ControlOutValue_mc" name_en="Supply water control output Manual control" name_fi="Säädön ulostulo Käsiajo" name_sv="Tillop vatten kontroll styrning Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="331" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_RetWaterCompEff_mc" name_en="Return water compensation Manual control" name_fi="Paluuvesikomp. vaikutus Käsiajo" name_sv="Påverkan av returvattnets kompens. Manuell styrning" name_et="Return water compensation käsijuhtimisrežiim" name_ru="Компенс. по обратной воде Ручной режим" name_lv="Return water compensation Rokas vadība" name_tr="Return water compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="332" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_TempDropEff_mc" name_en="Effect of temperature drop Manual control" name_fi="Lämmönpudotuksen vaikutus Käsiajo" name_sv="Påverkan av temperatursänkningen Manuell styrning" name_ru="Воздействие понижения температуры Ручной режим" name_lv="Temp. pazeminājuma ietekme Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="333" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_HeatingMinLimitEff_mc" name_en="Min limit effect Manual control" name_sv="Påverkan av min.gränsen Manuell styrning" name_fi="Minimirajan vaikutus Käsiajo" name_et="Alampiiri mõju käsijuhtimisrežiim" name_ru="Воздействие мин. ограничения Ручной режим" name_lv="Min. robežas ietekme Rokas vadība" name_tr="Min limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="390" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_HeatingMaxLimitEff_mc" name_en="Max limit effect Manual control" name_fi="Maksimirajan vaikutus Käsiajo" name_sv="Påverkan av max.gränsen Manuell styrning" name_et="Ülempiiri mõju käsijuhtimisrežiim" name_ru="Воздействие макс. ограничения Ручной режим" name_lv="Maks. robežas ietekme Rokas vadība" name_tr="Max limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="392" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H2HeatingControl_TempDrop_TempDropModes_mc" name_en="Temperature drop status Manual control" name_fi="Lämmönpudotuksen tila Käsiajo" name_sv="Temperatursänkning status Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru="Статус режима пониж.темпер. Ручной режим" name_lv="Temp. pazeminājuma stāvoklis Rokas vadība" name_tr="Temperature drop status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="394" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1MotorCtrl_ActuatorControlV_mc" name_en="Actuator position, V Manual control" name_fi="Toimilaitteen asento, V Käsiajo" name_sv="Ställdonets läge, V Manuell styrning" name_et="Actuator position, V käsijuhtimisrežiim" name_ru="Actuator position, V Ручной режим" name_lv="Actuator position, V Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="255" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="H1MotorCtrl_ActuatorControl3p_mc" name_en="Actuator position, 3p Manual control" name_fi="Toimilaitteen asento, 3p Käsiajo" name_sv="Ställdonets läge, 3p Manuell styrning" name_et="Actuator position, 3p käsijuhtimisrežiim" name_ru="Actuator position, 3p Ручной режим" name_lv="Actuator position, 3p Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="324" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="OutputsSel_DHWPumpCtrl_mc" name_en="DHW Pump control Manual control" name_fi="LV Pumpun ohjaus Käsiajo" name_sv="TV Pump styrning Manuell styrning" name_et="DHW Pump control käsijuhtimisrežiim" name_ru="DHW Pump control Ручной режим" name_lv="DHW Pump control Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="389" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
    </group>
    <group categorytype="4" name="Hälytykset">
      <point name="SensorFaultAlarm__UI_1" name_en="Sensor fault M1" name_fi="Anturivika M1" name_sv="Givarefel M1" name_et="Anduri viga M1" name_ru="Неисправность датчика И1" name_lv="Sensora kļūda M1" name_tr="Sensor fault M1" pointid="SensorFaultAlarm__UI_1" refpointid="TE2B.M" addressindex="643" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1047" severity="2" alarmid="#A1047" pointtype="14" />
      <point name="SensorFaultAlarm__UI_2" name_en="Sensor fault M2" name_fi="Anturivika M2" name_sv="Sensorfel M2" name_et="Anduri viga M2" name_ru="Неисправность датчика И2" name_lv="Sensora kļūda M2" name_tr="Sensor fault M2" pointid="SensorFaultAlarm__UI_2" refpointid="TE2A.M" addressindex="644" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1048" severity="2" alarmid="#A1048" pointtype="14" />
      <point name="SensorFaultAlarm__UI_3" name_en="Sensor fault  M3" name_fi="Anturivika M3" name_sv="Sensorfel M3" name_et="Anduri viga M3" name_ru="Неисправность датчика И3" name_lv="Sensora kļūda M3" name_tr="Sensor fault  M3" pointid="SensorFaultAlarm__UI_3" refpointid="TE2C.M" addressindex="645" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1049" severity="2" alarmid="#A1049" pointtype="14" />
      <point name="SensorFaultAlarm__UI_4" name_en="Sensor fault M4" name_fi="Anturivika M4" name_sv="Sensorfel M4" name_et="Anduri viga M4" name_ru="Неисправность датчика И4" name_lv="Sensora kļūda M4" name_tr="Sensor fault M4" pointid="SensorFaultAlarm__UI_4" refpointid="H1.TE20.M" addressindex="646" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1050" severity="2" alarmid="#A1050" pointtype="14" />
      <point name="SensorFaultAlarm__UI_5" name_en="Sensor fault M5" name_fi="Anturivika M5" name_sv="Sensorfel M5" name_et="Anduri viga M5" name_ru="Неисправность датчика И5" name_lv="Sensora kļūda M5" name_tr="Sensor fault M5" pointid="SensorFaultAlarm__UI_5" refpointid="TE3A.M" addressindex="647" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1051" severity="2" alarmid="#A1051" pointtype="14" />
      <point name="SensorFaultAlarm__UI_6" name_en="Sensor fault M6" name_fi="Anturivika M6 " name_sv="Sensorfel M6" name_et="Anduri viga M6" name_ru="Неисправность датчика И6" name_lv="Sensora kļūda M6" name_tr="Sensor fault M6" pointid="SensorFaultAlarm__UI_6" refpointid="TE3C.M" addressindex="648" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1052" severity="2" alarmid="#A1052" pointtype="14" />
      <point name="SensorFaultAlarm__UI_7" name_en="Sensor fault  M7" name_fi="Anturivika M7" name_sv="Sensorfel M7" name_et="Anduri viga M7" name_ru="Неисправность датчика И7" name_lv="Sensora kļūda M7" name_tr="Sensor fault  M7" pointid="SensorFaultAlarm__UI_7" refpointid="H2.TE20.M" addressindex="649" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1053" severity="2" alarmid="#A1053" pointtype="14" />
      <point name="SensorFaultAlarm__UI_8" name_en="Sensor fault M8" name_fi="Anturivika M8" name_sv="Sensorfel M8" name_et="Anduri viga M8" name_ru="Неисправность датчика И8" name_lv="Sensora kļūda M8" name_tr="Sensor fault M8" pointid="SensorFaultAlarm__UI_8" refpointid="TE1A.M" addressindex="650" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1054" severity="2" alarmid="#A1054" pointtype="14" />
      <point name="SensorFaultAlarm__UI_9" name_en="Sensor fault  M9" name_fi="Anturivika M9" name_sv="Sensorfel M9" name_et="Anduri viga M9" name_ru="Неисправность датчика И9" name_lv="Sensora kļūda M9" name_tr="Sensor fault  M9" pointid="SensorFaultAlarm__UI_9" refpointid="TE1D.M" addressindex="651" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1055" severity="2" alarmid="#A1055" pointtype="14" />
      <point name="SMSNoNetworkAlarm_GsmNetworkAlarm_A" name_en="GSM modem fault alarm" name_fi="GSM modeemin vikahälytys" name_sv="GSM modem fellarm" name_et="" name_ru="Сигнал неисправности модема GSM" name_lv="GSM modema kļūdas trauksme" name_tr="GSM modem fault alarm" pointid="SMSNoNetworkAlarm.GsmNetworkAlarm_A" refpointid="SMSNoNetworkAlarm.GSmTextForAlarm" addressindex="716" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1056" severity="1" alarmid="#A1056" pointtype="14" />
      <point name="AlarmSettings_DI1Alarm_A" name_en="DI1 Alarm" name_fi="DI1 Hälytys" name_sv="DI1 Larm" name_et="DI1 Alarm" name_ru="DI1 Авария" name_lv="DI1 Trauksme" name_tr="DI1 Alarm" pointid="AlarmSettings.DI1Alarm_A" refpointid="DI1_AlarmName" addressindex="652" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1057" severity="1" alarmid="#A1057" pointtype="14" />
      <point name="AlarmSettings_DI2Alarm_A" name_en="DI2 Alarm" name_fi="DI2 Hälytys" name_sv="DI2 Larm" name_et="DI2 Alarm" name_ru="DI2 Авария" name_lv="DI2 Trauksme" name_tr="DI2 Alarm" pointid="AlarmSettings.DI2Alarm_A" refpointid="DI2_AlarmName" addressindex="653" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1058" severity="1" alarmid="#A1058" pointtype="14" />
      <point name="AlarmSettings_M1GeneralAlarm_A" name_en="M1 Alarm" name_fi="M1 Hälytys" name_sv="M1 Larm" name_et="M1 Alarm" name_ru="И1 Авария" name_lv="M1 Trauksme" name_tr="M1 Alarm" pointid="AlarmSettings.M1GeneralAlarm_A" refpointid="TE2B.M" addressindex="654" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1059" severity="1" alarmid="#A1059" pointtype="14" />
      <point name="AlarmSettings_M2GeneralAlarm_A" name_en="M2 Alarm" name_fi="M2 Hälytys" name_sv="M2 Larm" name_et="M2 Alarm" name_ru="И2 Авария" name_lv="M2 Trauksme" name_tr="M2 Alarm" pointid="AlarmSettings.M2GeneralAlarm_A" refpointid="TE2A.M" addressindex="655" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1060" severity="1" alarmid="#A1060" pointtype="14" />
      <point name="AlarmSettings_M3GeneralAlarm_A" name_en="M3 Alarm" name_fi="M3 Hälytys" name_sv="M3 Larm" name_et="M3 Alarm" name_ru="И3 Авария" name_lv="M3 Trauksme" name_tr="M3 Alarm" pointid="AlarmSettings.M3GeneralAlarm_A" refpointid="TE2C.M" addressindex="656" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1061" severity="1" alarmid="#A1061" pointtype="14" />
      <point name="AlarmSettings_M4GeneralAlarm_A" name_en="M4 Alarm" name_fi="M4 Hälytys" name_sv="M4 Larm" name_et="M4 Alarm" name_ru="И4 Авария" name_lv="M4 Trauksme" name_tr="M4 Alarm" pointid="AlarmSettings.M4GeneralAlarm_A" refpointid="H1.TE20.M" addressindex="657" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1062" severity="1" alarmid="#A1062" pointtype="14" />
      <point name="AlarmSettings_M5GeneralAlarm_A" name_en="M5 Alarm" name_fi="M5 Hälytys" name_sv="M5 Larm" name_et="M5 Alarm" name_ru="И5 Авария" name_lv="M5 Trauksme" name_tr="M5 Alarm" pointid="AlarmSettings.M5GeneralAlarm_A" refpointid="TE3A.M" addressindex="658" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1063" severity="1" alarmid="#A1063" pointtype="14" />
      <point name="AlarmSettings_M6GeneralAlarm_A" name_en="M6 Alarm" name_fi="M6 Hälytys" name_sv="M6 Larm" name_et="M6 Alarm" name_ru="И6 Авария" name_lv="M6Trauksme" name_tr="M6 Alarm" pointid="AlarmSettings.M6GeneralAlarm_A" refpointid="TE3C.M" addressindex="659" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1064" severity="1" alarmid="#A1064" pointtype="14" />
      <point name="AlarmSettings_M7GeneralAlarm_A" name_en="M7 Alarm" name_fi="M7 Hälytys" name_sv="M7 Larm" name_et="M7 Alarm" name_ru="И7 Авария" name_lv="M7 Trauksme" name_tr="M7 Alarm" pointid="AlarmSettings.M7GeneralAlarm_A" refpointid="H2.TE20.M" addressindex="660" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1065" severity="1" alarmid="#A1065" pointtype="14" />
      <point name="AlarmSettings_M8GeneralAlarm_A" name_en="M8 Alarm" name_fi="M8 Hälytys" name_sv="M8 Larm" name_et="M8 Alarm" name_ru="И8 вария" name_lv="M8 Trauksme" name_tr="M8 Alarm" pointid="AlarmSettings.M8GeneralAlarm_A" refpointid="TE1A.M" addressindex="661" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1066" severity="1" alarmid="#A1066" pointtype="14" />
      <point name="AlarmSettings_M9GeneralAlarm_A" name_en="M9 Alarm" name_fi="M9 Hälytys" name_sv="M9 Larm" name_et="M9 Alarm" name_ru="И9 Авария" name_lv="M9 Trauksme" name_tr="M9 Alarm" pointid="AlarmSettings.M9GeneralAlarm_A" refpointid="TE1D.M" addressindex="662" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1067" severity="1" alarmid="#A1067" pointtype="14" />
      <point name="AlarmSettings_DHWHighLimitAlarm_A" name_en="DHW Overheating alarm" name_fi="LV Ylärajahälytys" name_sv="TV Överhettningslarm" name_et="TV Ülekuumenemise alarm " name_ru="ГВС Авария по перегреву" name_lv="K.ŪD Pārkaršanas trauksme" name_tr="DHW Overheating alarm" pointid="AlarmSettings.DHWHighLimitAlarm_A" refpointid="TE1A.M" addressindex="532" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1068" severity="1" alarmid="#A1068" pointtype="14" />
      <point name="AlarmSettings_H1DeviationAlarm_A" name_en="H1 Supply water deviation alarm" name_fi="L1 Menoveden poikkeamahälytys" name_sv="V1 Framledn.vattnets avvikelselarm" name_et="K1 Küttevee hälbealarm" name_ru="O1 Сигн.несоотв. по воде на подаче" name_lv="A1 Trauksme par turpg. temp. novirzēm" name_tr="H1 Supply water deviation alarm" pointid="AlarmSettings.H1DeviationAlarm_A" addressindex="533" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1069" severity="1" alarmid="#A1069" pointtype="14" />
      <point name="AlarmSettings_H2DeviationAlarm_A" name_en="H2 Supply water deviation alarm" name_fi="L2 Menoveden poikkeamahälytys" name_sv="V2 Framledn.vattnets avvikelselarm" name_et="K2 Küttevee hälbealarm" name_ru="O2 Сигн.несоотв. по воде на подаче" name_lv="A2 Trauksme par turpg. temp. novirzēm" name_tr="H2 Supply water deviation alarm" pointid="AlarmSettings.H2DeviationAlarm_A" addressindex="673" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1070" severity="1" alarmid="#A1070" pointtype="14" />
      <point name="AlarmSettings_H1RetWaterLoLimitAlarm_A" name_en="H1 Return water low limit alarm" name_fi="L1 Paluuvesi alarajahälytys" name_sv="V1 Returvatten nedre gräns larm" name_et="K1 Tagastusvesi alumine piir alarm" name_ru="О1 Авария по нижн.пределу обр.воды" name_lv="A1 Atgaitas temp. zemākās temp. trauksme" name_tr="H1 Return water low limit alarm" pointid="AlarmSettings.H1RetWaterLoLimitAlarm_A" refpointid="TE2C.M" addressindex="674" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1071" severity="1" alarmid="#A1071" pointtype="14" />
      <point name="AlarmSettings_H2RetWaterLoLimitAlarm_A" name_en="H2 Return water low limit alarm" name_fi="L2 Paluuvesi alarajahälytys" name_sv="V2 Returvatten låg gräns larm" name_et="" name_ru="Сигнал неисправности модема GSM" name_lv="A2 Atgaitas temp. min. robežas trauksme" name_tr="H2 Return water low limit alarm" pointid="AlarmSettings.H2RetWaterLoLimitAlarm_A" refpointid="TE3C.M" addressindex="675" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="76" transferackindex="77" ackvalue="1072" severity="1" alarmid="#A1072" pointtype="14" />
    </group>
  </groups>
</controllertemplate>