<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="G108TC08" version="0.0.0" createppg="false" language="fi-FI" type="Modbus">
  <targetdetails deviceposition="TC08" targetposition="" target="Fredriksberg A" location="LJH" address="Konepajankuja 1" city="Helsinki" postnumber="00510" contactperson="Iiro Taskinen" loadedtodevice="19.2.2018 10.17" loader="iiro.taskinen" deviceversion="2.2" />
  <groups>
    <group categorytype="1" name="Aika-asetukset">
      <point name="Vuosi" datetype="0" pointid="DTYEAR" pointtype="0" registertype="Holding" addressformat="U16" addressindex="2" readacceslevel="5" writeacceslevel="1" min="2008" max="2100" />
      <point name="Kuukausi" datetype="1" pointid="DTMONTH" pointtype="0" registertype="Holding" addressformat="U16" addressindex="3" enum="1=tammikuu;2=helmikuu;3=maaliskuu;4=huhtikuu;5=toukokuu;6=kesäkuu;7=heinäkuu;8=elokuu;9=syyskuu;10=lokakuu;11=marraskuu;12=joulukuu" readacceslevel="5" writeacceslevel="1" />
      <point name="Päivä" datetype="2" pointid="DTDAY" pointtype="0" registertype="Holding" addressformat="U16" addressindex="4" readacceslevel="5" writeacceslevel="1" />
      <point name="Tunti" datetype="3" pointid="DTHOUR" pointtype="0" registertype="Holding" addressformat="U16" addressindex="6" readacceslevel="5" writeacceslevel="1" />
      <point name="Minuutti" datetype="4" pointid="DTMINUTE" pointtype="0" registertype="Holding" addressformat="U16" addressindex="7" readacceslevel="5" writeacceslevel="1" />
      <point name="Viikonpäivä" datetype="5" pointid="DTDAYOFWEEK" pointtype="0" registertype="Holding" addressformat="U16" addressindex="5" enum="1=Maanantai;2=Tiistai;3=Keskiviikko;4=Torstai;5=Perjantai;6=Lauantai;7=Sunnuntai" readacceslevel="5" writeacceslevel="1" />
    </group>
    <group categorytype="2" name="Järjestelmäasetukset">
      <point name="Device version" pointid="SYSDEVVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="15" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="Application version" pointid="SYSAPPVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="16" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="IO-card version" pointid="SYSIOVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="17" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="Serialnumber" pointid="SYSSERIALNUMBER" pointtype="21" registertype="Holding" addressformat="U16" addressindex="18" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="SNMP enable" pointid="SYSSNMP" pointtype="21" registertype="Holding" addressformat="U16" addressindex="19" categorytype="3" readacceslevel="5" writeacceslevel="1" min="0" max="1" />
      <point name="FTP enable" pointid="SYSFTP" pointtype="21" registertype="Holding" addressformat="U16" addressindex="20" categorytype="3" readacceslevel="5" writeacceslevel="1" min="0" max="1" />
    </group>
    <group categorytype="2" name="Normaalit pisteet">
      <pointgroup name="Ulkovaloisuus" technicalname="UI 1" channel="UI 1" group="Fyysiset pisteet" connectors="1;G0">
        <point name="Ulkovaloisuus" pointid="TC08.XE00.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="3" unit="lx" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="1000">
          <point name="Ulkovaloisuus, ohjaustapa" pointid="TC08.XE00.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="373" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Ulkolämpötila" technicalname="UI 2" channel="UI 2" group="Fyysiset pisteet" connectors="2;G0">
        <point name="Ulkolämpötila" pointid="TC08.TE00.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="50">
          <point name="Ulkolämpötila, ohjaustapa" pointid="TC08.TE00.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="374" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kaukolämpö tulo" technicalname="UI 3" channel="UI 3" group="Fyysiset pisteet" connectors="3;G0">
        <point name="Kaukolämpö tulo" pointid="TC08.G100.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Kaukolämpö tulo, ohjaustapa" pointid="TC08.G100.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="375" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kaukolämpö paluu" technicalname="UI 4" channel="UI 4" group="Fyysiset pisteet" connectors="4;G0">
        <point name="Kaukolämpö paluu" pointid="TC08.G100.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Kaukolämpö paluu, ohjaustapa" pointid="TC08.G100.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="376" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Lämmin käyttövesi" technicalname="UI 5" channel="UI 5" group="Fyysiset pisteet" connectors="5;G0">
        <point name="Lämmin käyttövesi" pointid="TC08.G201.TE31.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Lämmin käyttövesi, ohjaustapa" pointid="TC08.G201.TE31.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="377" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttöveden kierto" technicalname="UI 6" channel="UI 6" group="Fyysiset pisteet" connectors="6;G0">
        <point name="Käyttöveden kierto" pointid="TC08.G201.TE32.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Käyttöveden kierto, ohjaustapa" pointid="TC08.G201.TE32.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="378" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kylmä käyttövesi" technicalname="UI 7" channel="UI 7" group="Fyysiset pisteet" connectors="7;G0">
        <point name="Kylmä käyttövesi" pointid="TC08.G201.TE33.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Kylmä käyttövesi, ohjaustapa" pointid="TC08.G201.TE33.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="379" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto meno" technicalname="UI 8" channel="UI 8" group="Fyysiset pisteet" connectors="8;G0">
        <point name="Patteriverkosto meno" pointid="TC08.G101.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Patteriverkosto meno, ohjaustapa" pointid="TC08.G101.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="380" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto paluu" technicalname="UI 9" channel="UI 9" group="Fyysiset pisteet" connectors="9;G0">
        <point name="Patteriverkosto paluu" pointid="TC08.G101.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Patteriverkosto paluu, ohjaustapa" pointid="TC08.G101.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="381" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto meno" technicalname="UI 10" channel="UI 10" group="Fyysiset pisteet" connectors="10;G0">
        <point name="IV-Verkosto meno" pointid="TC08.G102.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Verkosto meno, ohjaustapa" pointid="TC08.G102.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="382" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto paluu" technicalname="UI 11" channel="UI 11" group="Fyysiset pisteet" connectors="11;G0">
        <point name="IV-Verkosto paluu" pointid="TC08.G102.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="221" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Verkosto paluu, ohjaustapa" pointid="TC08.G102.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="383" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="UI 12" technicalname="UI 12" channel="UI 12" group="Fyysiset pisteet" connectors="12;G0">
        <point name="UI 12" pointid="TC08.UI 12.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="223" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="UI 12, ohjaustapa" pointid="TC08.UI 12.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="384" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Vesimäärä VM33.1" technicalname="UI 13" channel="UI 13" group="Fyysiset pisteet" connectors="13;G0">
        <point name="Vesimäärä VM33.1" pointid="TC08.G201.VM33.1.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="225" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+18">
          <point name="Vesimäärä VM33.1, ohjaustapa" pointid="TC08.G201.VM33.1.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="385" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Vesimäärä VM33.2" technicalname="UI 14" channel="UI 14" group="Fyysiset pisteet" connectors="14;G0">
        <point name="Vesimäärä VM33.2" pointid="TC08.G201.VM33.2.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="227" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+25">
          <point name="Vesimäärä VM33.2, ohjaustapa" pointid="TC08.G201.VM33.2.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="386" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="KL-Energia MWh" technicalname="UI 15" channel="UI 15" group="Fyysiset pisteet" connectors="15;G0">
        <point name="KL-Energia MWh" pointid="TC08.G100.QQ01_E.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="229" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+30">
          <point name="KL-Energia MWh, ohjaustapa" pointid="TC08.G100.QQ01_E.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="387" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="KL-Energia m3" technicalname="UI 16" channel="UI 16" group="Fyysiset pisteet" connectors="16;G0">
        <point name="KL-Energia m3" pointid="TC08.G100.QQ01_V.P" pointtype="10" registertype="Holding" addressformat="S32" addressindex="231" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+21">
          <point name="KL-Energia m3, ohjaustapa" pointid="TC08.G100.QQ01_V.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="388" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttövesi pumppu häl." technicalname="DI 1" channel="DI 1" group="Fyysiset pisteet" connectors="21">
        <point name="Käyttövesi pumppu häl." pointid="TC08.G201.P01_AL.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="233" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Käyttövesi pumppu häl., ohjaustapa" pointid="TC08.G201.P01_AL.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="389" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttövesi pumppu tila" technicalname="DI 2" channel="DI 2" group="Fyysiset pisteet" connectors="22">
        <point name="Käyttövesi pumppu tila" pointid="TC08.G201.P01_IND.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="235" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Käyttövesi pumppu tila, ohjaustapa" pointid="TC08.G201.P01_IND.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="390" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Internal power failure indication" technicalname="PFI" group="Fyysiset pisteet">
        <point name="Internal power failure indication" pointid="TC08.PFI.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="237" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Internal power failure indication, ohjaustapa" pointid="TC08.PFI.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="391" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto pumppu säätö" technicalname="AO 1" channel="AO 1" group="Fyysiset pisteet" connectors="61;G0">
        <point name="Patteriverkosto pumppu säätö" pointid="TC08.G101.P01.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="239" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Patteriverkosto pumppu säätö, ohjaustapa" pointid="TC08.G101.P01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="392" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto pumppu säätö" technicalname="AO 2" channel="AO 2" group="Fyysiset pisteet" connectors="62;G0">
        <point name="IV-Verkosto pumppu säätö" pointid="TC08.G102.P01.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="241" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Verkosto pumppu säätö, ohjaustapa" pointid="TC08.G102.P01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="393" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttövesi venttiili säätö" technicalname="AO 3" channel="AO 3" group="Fyysiset pisteet" connectors="63;G0">
        <point name="Käyttövesi venttiili säätö" pointid="TC08.G201.FV01.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="243" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Käyttövesi venttiili säätö, ohjaustapa" pointid="TC08.G201.FV01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="394" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto venttiili säätö" technicalname="AO 4" channel="AO 4" group="Fyysiset pisteet" connectors="64;G0">
        <point name="Patteriverkosto venttiili säätö" pointid="TC08.G101.FV01.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="245" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Patteriverkosto venttiili säätö, ohjaustapa" pointid="TC08.G101.FV01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="395" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto venttiili 1 säätö" technicalname="AO 5" channel="AO 5" group="Fyysiset pisteet" connectors="65;G0">
        <point name="IV-Verkosto venttiili 1 säätö" pointid="TC08.G102.FV01.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="247" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Verkosto venttiili 1 säätö, ohjaustapa" pointid="TC08.G102.FV01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="396" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto venttiili 2 säätö" technicalname="AO 6" channel="AO 6" group="Fyysiset pisteet" connectors="66;G0">
        <point name="IV-Verkosto venttiili 2 säätö" pointid="TC08.G102.FV02.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="249" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Verkosto venttiili 2 säätö, ohjaustapa" pointid="TC08.G102.FV02.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="397" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 1" technicalname="TR 1" channel="TR 1" group="Fyysiset pisteet" connectors="42">
        <point name="TR 1" pointid="TC08.TR 1.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="251" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 1, ohjaustapa" pointid="TC08.TR 1.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="398" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Jäähd. Vent. Moot. LJH ohj." technicalname="TR 2" channel="TR 2" group="Fyysiset pisteet" connectors="43">
        <point name="Jäähd. Vent. Moot. LJH ohj." pointid="TC08.G410.FV16.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="253" categorytype="3" enum="0=Pois;1=Päällä" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Jäähd. Vent. Moot. LJH ohj., ohjaustapa" pointid="TC08.G410.FV16.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="399" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 3" technicalname="TR 3" channel="TR 3" group="Fyysiset pisteet" connectors="44">
        <point name="TR 3" pointid="TC08.TR 3.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="255" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 3, ohjaustapa" pointid="TC08.TR 3.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="400" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 4" technicalname="TR 4" channel="TR 4" group="Fyysiset pisteet" connectors="45">
        <point name="TR 4" pointid="TC08.TR 4.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="257" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 4, ohjaustapa" pointid="TC08.TR 4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="401" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto pumppu ohjaus" technicalname="R1" channel="R1" group="Fyysiset pisteet" connectors="71;72">
        <point name="Patteriverkosto pumppu ohjaus" pointid="TC08.G101.P01.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="259" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Patteriverkosto pumppu ohjaus, ohjaustapa" pointid="TC08.G101.P01.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="402" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto pumppu ohjaus" technicalname="R2" channel="R2" group="Fyysiset pisteet" connectors="74;75">
        <point name="IV-Verkosto pumppu ohjaus" pointid="TC08.G102.P01.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="261" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="IV-Verkosto pumppu ohjaus, ohjaustapa" pointid="TC08.G102.P01.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="403" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R3" technicalname="R3" channel="R3" group="Fyysiset pisteet" connectors="77">
        <point name="R3" pointid="TC08.R3.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="263" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R3, ohjaustapa" pointid="TC08.R3.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="404" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R4" technicalname="R4" channel="R4" group="Fyysiset pisteet" connectors="79">
        <point name="R4" pointid="TC08.R4.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="265" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R4, ohjaustapa" pointid="TC08.R4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="405" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R5" technicalname="R5" channel="R5" group="Fyysiset pisteet" connectors="81">
        <point name="R5" pointid="TC08.R5.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="267" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R5, ohjaustapa" pointid="TC08.R5.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="406" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R6" technicalname="R6" channel="R6" group="Fyysiset pisteet" connectors="83">
        <point name="R6" pointid="TC08.R6.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="269" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R6, ohjaustapa" pointid="TC08.R6.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="407" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto pumppu häl." technicalname="MB2_ADDR2_MOD1_C32_UI1" channel="MB2_ADDR2_MOD1_C32_UI1" group="Fyysiset pisteet" connectors="1;G0">
        <point name="Patteriverkosto pumppu häl." pointid="TC08.G101.P01_AL.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="271" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Patteriverkosto pumppu häl., ohjaustapa" pointid="TC08.G101.P01_AL.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="408" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto pumppu tila" technicalname="MB2_ADDR2_MOD1_C32_UI2" channel="MB2_ADDR2_MOD1_C32_UI2" group="Fyysiset pisteet" connectors="2;G0">
        <point name="Patteriverkosto pumppu tila" pointid="TC08.G101.P01_IND.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="273" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Patteriverkosto pumppu tila, ohjaustapa" pointid="TC08.G101.P01_IND.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="409" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto pumppu häl." technicalname="MB2_ADDR2_MOD1_C32_UI3" channel="MB2_ADDR2_MOD1_C32_UI3" group="Fyysiset pisteet" connectors="3;G0">
        <point name="IV-Verkosto pumppu häl." pointid="TC08.G102.P01_AL.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="275" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Verkosto pumppu häl., ohjaustapa" pointid="TC08.G102.P01_AL.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="410" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto pumppu tila" technicalname="MB2_ADDR2_MOD1_C32_UI4" channel="MB2_ADDR2_MOD1_C32_UI4" group="Fyysiset pisteet" connectors="4;G0">
        <point name="IV-Verkosto pumppu tila" pointid="TC08.G102.P01_IND.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="277" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Verkosto pumppu tila, ohjaustapa" pointid="TC08.G102.P01_IND.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="411" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttövesi painelähetin VARAUS" technicalname="MB2_ADDR2_MOD1_C32_UI5" channel="MB2_ADDR2_MOD1_C32_UI5" group="Fyysiset pisteet" connectors="5;G0">
        <point name="Käyttövesi painelähetin VARAUS" pointid="TC08.G201.PIE33.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="279" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="16">
          <point name="Käyttövesi painelähetin VARAUS, ohjaustapa" pointid="TC08.G201.PIE33.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="412" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto painelähetin" technicalname="MB2_ADDR2_MOD1_C32_UI6" channel="MB2_ADDR2_MOD1_C32_UI6" group="Fyysiset pisteet" connectors="6;G0">
        <point name="Patteriverkosto painelähetin" pointid="TC08.G101.PIE01.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="281" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6">
          <point name="Patteriverkosto painelähetin, ohjaustapa" pointid="TC08.G101.PIE01.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="413" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto paine-ero" technicalname="MB2_ADDR2_MOD1_C32_UI7" channel="MB2_ADDR2_MOD1_C32_UI7" group="Fyysiset pisteet" connectors="7;G0">
        <point name="Patteriverkosto paine-ero" pointid="TC08.G101.PDIE02.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="283" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="2.5">
          <point name="Patteriverkosto paine-ero, ohjaustapa" pointid="TC08.G101.PDIE02.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="414" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto painelähetin" technicalname="MB2_ADDR2_MOD1_C32_UI8" channel="MB2_ADDR2_MOD1_C32_UI8" group="Fyysiset pisteet" connectors="8;G0">
        <point name="IV-Verkosto painelähetin" pointid="TC08.G102.PIE01.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="285" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6">
          <point name="IV-Verkosto painelähetin, ohjaustapa" pointid="TC08.G102.PIE01.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="415" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto paine-erolähetin" technicalname="MB2_ADDR2_MOD1_C32_UI9" channel="MB2_ADDR2_MOD1_C32_UI9" group="Fyysiset pisteet" connectors="9;G0">
        <point name="IV-Verkosto paine-erolähetin" pointid="TC08.G102.PDIE02.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="287" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="2.5">
          <point name="IV-Verkosto paine-erolähetin, ohjaustapa" pointid="TC08.G102.PDIE02.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="416" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Huonelämpötila LJH" technicalname="MB2_ADDR2_MOD1_C32_UI10" channel="MB2_ADDR2_MOD1_C32_UI10" group="Fyysiset pisteet" connectors="10;G0">
        <point name="Huonelämpötila LJH" pointid="TC08.G410.TE16.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="289" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Huonelämpötila LJH, ohjaustapa" pointid="TC08.G410.TE16.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="417" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="UI 11" technicalname="MB2_ADDR2_MOD1_C32_UI11" channel="MB2_ADDR2_MOD1_C32_UI11" group="Fyysiset pisteet" connectors="11;G0">
        <point name="UI 11" pointid="TC08.MB2_ADDR2_MOD1_C32_UI11.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="291" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="UI 11, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_UI11.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="418" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="UI 12" technicalname="MB2_ADDR2_MOD1_C32_UI12" channel="MB2_ADDR2_MOD1_C32_UI12" group="Fyysiset pisteet" connectors="12;G0">
        <point name="UI 12" pointid="TC08.MB2_ADDR2_MOD1_C32_UI12.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="293" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="UI 12, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_UI12.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="419" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyttövesi energiamittaus" technicalname="MB2_ADDR2_MOD1_C32_UI13" channel="MB2_ADDR2_MOD1_C32_UI13" group="Fyysiset pisteet" connectors="13;G0">
        <point name="Käyttövesi energiamittaus" pointid="TC08.G201.QQ31.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="295" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+26">
          <point name="Käyttövesi energiamittaus, ohjaustapa" pointid="TC08.G201.QQ31.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="420" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto energiamittaus" technicalname="MB2_ADDR2_MOD1_C32_UI14" channel="MB2_ADDR2_MOD1_C32_UI14" group="Fyysiset pisteet" connectors="14;G0">
        <point name="Patteriverkosto energiamittaus" pointid="TC08.G101.QQ42.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="297" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+22">
          <point name="Patteriverkosto energiamittaus, ohjaustapa" pointid="TC08.G101.QQ42.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="421" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto energiamittaus" technicalname="MB2_ADDR2_MOD1_C32_UI15" channel="MB2_ADDR2_MOD1_C32_UI15" group="Fyysiset pisteet" connectors="15;G0">
        <point name="IV-Verkosto energiamittaus" pointid="TC08.G102.QQ42.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="299" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+17">
          <point name="IV-Verkosto energiamittaus, ohjaustapa" pointid="TC08.G102.QQ42.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="422" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="UI 16" technicalname="MB2_ADDR2_MOD1_C32_UI16" channel="MB2_ADDR2_MOD1_C32_UI16" group="Fyysiset pisteet" connectors="16;G0">
        <point name="UI 16" pointid="TC08.MB2_ADDR2_MOD1_C32_UI16.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="301" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="UI 16, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_UI16.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="423" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Jäähd. konvektori LJH säätö" technicalname="MB2_ADDR2_MOD1_C32_AO1" channel="MB2_ADDR2_MOD1_C32_AO1" group="Fyysiset pisteet" connectors="61;G0">
        <point name="Jäähd. konvektori LJH säätö" pointid="TC08.G410.PKN16.0.023.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="303" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Jäähd. konvektori LJH säätö, ohjaustapa" pointid="TC08.G410.PKN16.0.023.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="424" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 2" technicalname="MB2_ADDR2_MOD1_C32_AO2" channel="MB2_ADDR2_MOD1_C32_AO2" group="Fyysiset pisteet" connectors="62;G0">
        <point name="AO 2" pointid="TC08.MB2_ADDR2_MOD1_C32_AO2.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="305" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 2, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_AO2.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="425" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 3" technicalname="MB2_ADDR2_MOD1_C32_AO3" channel="MB2_ADDR2_MOD1_C32_AO3" group="Fyysiset pisteet" connectors="63;G0">
        <point name="AO 3" pointid="TC08.MB2_ADDR2_MOD1_C32_AO3.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="307" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 3, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_AO3.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="426" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 4" technicalname="MB2_ADDR2_MOD1_C32_AO4" channel="MB2_ADDR2_MOD1_C32_AO4" group="Fyysiset pisteet" connectors="64;G0">
        <point name="AO 4" pointid="TC08.MB2_ADDR2_MOD1_C32_AO4.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="309" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 4, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_AO4.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="427" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 5" technicalname="MB2_ADDR2_MOD1_C32_AO5" channel="MB2_ADDR2_MOD1_C32_AO5" group="Fyysiset pisteet" connectors="65;G0">
        <point name="AO 5" pointid="TC08.MB2_ADDR2_MOD1_C32_AO5.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="311" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 5, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_AO5.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="428" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 6" technicalname="MB2_ADDR2_MOD1_C32_AO6" channel="MB2_ADDR2_MOD1_C32_AO6" group="Fyysiset pisteet" connectors="66;G0">
        <point name="AO 6" pointid="TC08.MB2_ADDR2_MOD1_C32_AO6.C" pointtype="7" registertype="Holding" addressformat="S32" addressindex="313" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 6, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_AO6.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="429" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 1" technicalname="MB2_ADDR2_MOD1_C32_TR1" channel="MB2_ADDR2_MOD1_C32_TR1" group="Fyysiset pisteet" connectors="42">
        <point name="TR 1" pointid="TC08.MB2_ADDR2_MOD1_C32_TR1.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="315" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 1, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_TR1.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="430" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 2" technicalname="MB2_ADDR2_MOD1_C32_TR2" channel="MB2_ADDR2_MOD1_C32_TR2" group="Fyysiset pisteet" connectors="43">
        <point name="TR 2" pointid="TC08.MB2_ADDR2_MOD1_C32_TR2.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="317" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 2, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_TR2.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="431" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 3" technicalname="MB2_ADDR2_MOD1_C32_TR3" channel="MB2_ADDR2_MOD1_C32_TR3" group="Fyysiset pisteet" connectors="44">
        <point name="TR 3" pointid="TC08.MB2_ADDR2_MOD1_C32_TR3.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="319" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 3, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_TR3.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="432" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 4" technicalname="MB2_ADDR2_MOD1_C32_TR4" channel="MB2_ADDR2_MOD1_C32_TR4" group="Fyysiset pisteet" connectors="45">
        <point name="TR 4" pointid="TC08.MB2_ADDR2_MOD1_C32_TR4.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="321" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 4, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_TR4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="433" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R1" technicalname="MB2_ADDR2_MOD1_C32_R1" channel="MB2_ADDR2_MOD1_C32_R1" group="Fyysiset pisteet" connectors="71;72">
        <point name="R1" pointid="TC08.MB2_ADDR2_MOD1_C32_R1.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="323" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R1, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R1.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="434" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R2" technicalname="MB2_ADDR2_MOD1_C32_R2" channel="MB2_ADDR2_MOD1_C32_R2" group="Fyysiset pisteet" connectors="74;75">
        <point name="R2" pointid="TC08.MB2_ADDR2_MOD1_C32_R2.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="325" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R2, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R2.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="435" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R3" technicalname="MB2_ADDR2_MOD1_C32_R3" channel="MB2_ADDR2_MOD1_C32_R3" group="Fyysiset pisteet" connectors="77">
        <point name="R3" pointid="TC08.MB2_ADDR2_MOD1_C32_R3.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="327" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R3, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R3.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="436" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R4" technicalname="MB2_ADDR2_MOD1_C32_R4" channel="MB2_ADDR2_MOD1_C32_R4" group="Fyysiset pisteet" connectors="79">
        <point name="R4" pointid="TC08.MB2_ADDR2_MOD1_C32_R4.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="329" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R4, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="437" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R5" technicalname="MB2_ADDR2_MOD1_C32_R5" channel="MB2_ADDR2_MOD1_C32_R5" group="Fyysiset pisteet" connectors="81">
        <point name="R5" pointid="TC08.MB2_ADDR2_MOD1_C32_R5.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="331" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R5, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R5.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="438" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R6" technicalname="MB2_ADDR2_MOD1_C32_R6" channel="MB2_ADDR2_MOD1_C32_R6" group="Fyysiset pisteet" connectors="83">
        <point name="R6" pointid="TC08.MB2_ADDR2_MOD1_C32_R6.S" pointtype="9" registertype="Holding" addressformat="S32" addressindex="333" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R6, ohjaustapa" pointid="TC08.MB2_ADDR2_MOD1_C32_R6.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="439" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Käyrän mukaan" technicalname="G101.CurveOut" group="Patteriverkosto" description="Käyrältä laskettu menoveden asetusarvo">
        <point name="Käyrän mukaan" pointid="TC08.G101.TE41.M4" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="335" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Käyrän mukaan, ohjaustapa" pointid="TC08.G101.TE41.M4_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="440" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Laskennall. menoveden asetusarvo" technicalname="G101.SupplyWaterSet" group="Patteriverkosto">
        <point name="Laskennall. menoveden asetusarvo" pointid="TC08.G101.TE41.M5" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="337" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Laskennall. menoveden asetusarvo, ohjaustapa" pointid="TC08.G101.TE41.M5_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="441" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Pudotus aikaohjelmalla" technicalname="G101.DropEffect" group="Patteriverkosto">
        <point name="Pudotus aikaohjelmalla" pointid="TC08.G101.TE41.M3" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="339" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Suuntaissiirto" technicalname="G101.ParallelShiftEffect" group="Patteriverkosto">
        <point name="Suuntaissiirto" pointid="TC08.G101.TE41.M2" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="341" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Suuntaissiirto, ohjaustapa" pointid="TC08.G101.TE41.M2_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="442" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Minimirajan vaikutus" technicalname="G101.MinLimitEffect" group="Patteriverkosto">
        <point name="Minimirajan vaikutus" pointid="TC08.G101.TE41.M6" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="343" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Maksimirajan vaikutus" technicalname="G101.MaxLimitEffect" group="Patteriverkosto">
        <point name="Maksimirajan vaikutus" pointid="TC08.G101.TE41.M7" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="345" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Syyskuivauksen vaikutus" technicalname="G101.AutumnDryEff" group="Patteriverkosto">
        <point name="Syyskuivauksen vaikutus" pointid="TC08.G101.TE41.M8" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="347" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Syyskuivauksen vaikutus, ohjaustapa" pointid="TC08.G101.TE41.M8_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="443" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Huonekompensoinnin vaikutus" technicalname="G101.Measure" group="Patteriverkosto">
        <point name="Huonekompensoinnin vaikutus" pointid="TC08.G101.TE41.M1" refpointid="TC08.G101.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="349" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Huonekompensoinnin vaikutus, ohjaustapa" pointid="TC08.G101.TE41.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="444" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kesäpysäytystila" technicalname="G101.Measure4" group="Patteriverkosto" description="Lähtö">
        <point name="Kesäpysäytystila" pointid="TC08.G101.TE00.M1" refpointid="TC08.TE00.M" pointtype="12" registertype="Holding" addressformat="U16" addressindex="351" categorytype="3" enum="0=Pois;1=Päällä" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Kesäpysäytystila, ohjaustapa" pointid="TC08.G101.TE00.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="353" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Patteriverkosto energia" technicalname="G101.EnergyMeter.Measure2" group="Patteriverkosto" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="Patteriverkosto energia" pointid="TC08.G101.QQ42.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="618" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Patteriverkosto energia, ohjaustapa" pointid="TC08.G101.QQ42.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="624" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="P-alue" technicalname="G101.P_Area" group="Patteriverkosto" description="P-alue">
        <point name="P-alue" pointid="TC08.G101.TE41.SP1" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="453" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="I-aika" technicalname="G101.I_Time" group="Patteriverkosto" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="I-aika" pointid="TC08.G101.TE41.SP2" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="455" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="D-aika" technicalname="G101.D_Time" group="Patteriverkosto" description="D-aika sekunteina">
        <point name="D-aika" pointid="TC08.G101.TE41.SP3" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="457" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Out1" technicalname="G101.Setvalue4" group="Patteriverkosto" description="Menoveden lämpötila -20C:n ulkolämpötilassa">
        <point name="Out1" pointid="TC08.G101.TE41.SP4" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="459" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In2" technicalname="G101.Setvalue5" group="Patteriverkosto" description="Käyrän ulkolämpötilapiste 2">
        <point name="In2" pointid="TC08.G101.TE00.SP5" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="461" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out2" technicalname="G101.Setvalue6" group="Patteriverkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 2">
        <point name="Out2" pointid="TC08.G101.TE41.SP5" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="463" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In3" technicalname="G101.Setvalue7" group="Patteriverkosto" description="Käyrän ulkolämpötilapiste 3">
        <point name="In3" pointid="TC08.G101.TE00.SP6" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="465" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out3" technicalname="G101.Setvalue8" group="Patteriverkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 3">
        <point name="Out3" pointid="TC08.G101.TE41.SP6" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="467" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In4" technicalname="G101.Setvalue9" group="Patteriverkosto" description="Käyrän ulkolämpötilapiste 4">
        <point name="In4" pointid="TC08.G101.TE00.SP7" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="469" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out4" technicalname="G101.Setvalue10" group="Patteriverkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 4">
        <point name="Out4" pointid="TC08.G101.TE41.SP7" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="471" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Out5" technicalname="G101.Setvalue11" group="Patteriverkosto" description="Menoveden lämpötila 20C:n ulkolämpötilassa">
        <point name="Out5" pointid="TC08.G101.TE41.SP8" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="473" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Minimiraja" technicalname="G101.Setvalue12" group="Patteriverkosto" description="Lähtö rajoitetaan minimissä tähän arvoon">
        <point name="Minimiraja" pointid="TC08.G101.TE41.SP9" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="475" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Maksimiraja" technicalname="G101.Setvalue13" group="Patteriverkosto" description="Lähtö rajoitetaan maksimissa tähän arvoon">
        <point name="Maksimiraja" pointid="TC08.G101.TE41.SP10" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="477" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Pudotuksen määrä" technicalname="G101.DropAmout" group="Patteriverkosto">
        <point name="Pudotuksen määrä" pointid="TC08.G101.TE41.SP11" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="479" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      </pointgroup>
      <pointgroup name="Suuntaissiirto" technicalname="G101.ParallelShift" group="Patteriverkosto">
        <point name="Suuntaissiirto" pointid="TC08.G101.TE41.SP12" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="481" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="10" />
      </pointgroup>
      <pointgroup name="Verkoston paine alaraja" technicalname="G101.PressAlarmLowLimit" group="Patteriverkosto">
        <point name="Verkoston paine alaraja" pointid="TC08.G101.PIE01.SP2" refpointid="TC08.G101.PIE01.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="483" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Verkoston paine yläraja" technicalname="G101.PressAlarmHighLimit" group="Patteriverkosto">
        <point name="Verkoston paine yläraja" pointid="TC08.G101.PIE01.SP1" refpointid="TC08.G101.PIE01.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="485" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytysraja" technicalname="G101.DeviationAlarmLimit" group="Patteriverkosto">
        <point name="Poikkeamahälytysraja" pointid="TC08.G101.TE41.SP13" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="487" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytyksen viive" technicalname="G101.DeviationAlarmDelay" group="Patteriverkosto">
        <point name="Poikkeamahälytyksen viive" pointid="TC08.G101.TE41.SP14" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="489" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      </pointgroup>
      <pointgroup name="Syyskuivaus" technicalname="G101.AutumnDrySet" group="Patteriverkosto">
        <point name="Syyskuivaus" pointid="TC08.G101.TE41.SP15" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="491" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      </pointgroup>
      <pointgroup name="Huonelämpötilan tavoite" technicalname="G101.Setvalue" group="Patteriverkosto">
        <point name="Huonelämpötilan tavoite" pointid="TC08.G101.TE41.SP16" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="493" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="18" max="24" />
      </pointgroup>
      <pointgroup name="Huonekompensointisuhde" technicalname="G101.Setvalue2" group="Patteriverkosto">
        <point name="Huonekompensointisuhde" pointid="TC08.G101.TE41.SP17" refpointid="TC08.G101.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="495" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      </pointgroup>
      <pointgroup name="Pumpun P-alue" technicalname="G101.Setvalue3" group="Patteriverkosto" description="P-alue">
        <point name="Pumpun P-alue" pointid="TC08.G101.PDIE02.SP4" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="497" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Pumpun I-aika (s)" technicalname="G101.Setvalue14" group="Patteriverkosto" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Pumpun I-aika (s)" pointid="TC08.G101.PDIE02.SP5" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="499" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Pumpun D-aika (s)" technicalname="G101.Setvalue15" group="Patteriverkosto" description="D-aika sekunteina">
        <point name="Pumpun D-aika (s)" pointid="TC08.G101.PDIE02.SP6" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="501" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Pumpun paineen asetusarvo" technicalname="G101.Setvalue16" group="Patteriverkosto">
        <point name="Pumpun paineen asetusarvo" pointid="TC08.G101.PDIE02.SP3" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="503" categorytype="3" unit="kpa" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="250" />
      </pointgroup>
      <pointgroup name="Kesäpysäytysraja" technicalname="G101.Setvalue17" group="Patteriverkosto" description="Asetusarvo">
        <point name="Kesäpysäytysraja" pointid="TC08.G101.TE00.SP1" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="369" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      </pointgroup>
      <pointgroup name="Kesäpysäytyksen eroalue" technicalname="G101.Setvalue18" group="Patteriverkosto">
        <point name="Kesäpysäytyksen eroalue" pointid="TC08.G101.TE00.SP8" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="371" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="10" />
      </pointgroup>
      <pointgroup name="Pumpun paine hälytysviive" technicalname="G101.Setvalue19" group="Patteriverkosto">
        <point name="Pumpun paine hälytysviive" pointid="TC08.G101.PDIE02.SP1" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="445" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="60" />
      </pointgroup>
      <pointgroup name="P. Paineen max. poikkeama" technicalname="G101.Setvalue20" group="Patteriverkosto">
        <point name="P. Paineen max. poikkeama" pointid="TC08.G101.PDIE02.SP2" refpointid="TC08.G101.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="451" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G101.EnergyMeter.Setvalue22" group="Patteriverkosto">
        <point name="Skaalaus imp/kwh" pointid="TC08.G101.QQ42.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="627" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="PV-Energia alkuarvo" technicalname="G101.EnergyMeter.Setvalue21" group="Patteriverkosto" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="PV-Energia alkuarvo" pointid="TC08.G101.QQ42.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="629" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="KV kulutus" technicalname="G201.WaterMeasures.Measure2" group="Lämmin käyttövesi" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="KV kulutus" pointid="TC08.G201.VM33.1.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="639" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="KV kulutus, ohjaustapa" pointid="TC08.G201.VM33.1.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="641" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="LV kulutus" technicalname="G201.WaterMeasures.Measure" group="Lämmin käyttövesi" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="LV kulutus" pointid="TC08.G201.VM33.1.M2" pointtype="12" registertype="Holding" addressformat="S32" addressindex="646" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="LV kulutus, ohjaustapa" pointid="TC08.G201.VM33.1.M2_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="648" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="LV energia" technicalname="G201.EnergyMeter.Measure2" group="Lämmin käyttövesi" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="LV energia" pointid="TC08.G201.QQ31.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="620" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="LV energia, ohjaustapa" pointid="TC08.G201.QQ31.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="625" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="P-alue" technicalname="G201.PSetvalue" group="Lämmin käyttövesi" description="P-alue">
        <point name="P-alue" pointid="TC08.G201.TE31.SP1" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="505" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="I-aika" technicalname="G201.ISetvalue" group="Lämmin käyttövesi" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="I-aika" pointid="TC08.G201.TE31.SP2" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="507" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="D-aika" technicalname="G201.DSetvalue" group="Lämmin käyttövesi" description="D-aika sekunteina">
        <point name="D-aika" pointid="TC08.G201.TE31.SP3" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="509" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Asetusarvo" technicalname="G201.Setvalue" group="Lämmin käyttövesi" description="Käyttöveden asetusarvo">
        <point name="Asetusarvo" pointid="TC08.G201.TE31.SP4" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="511" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      </pointgroup>
      <pointgroup name="Ennakoinnin P-alkue" technicalname="G201.AnticPSetvalue" group="Lämmin käyttövesi">
        <point name="Ennakoinnin P-alkue" pointid="TC08.G201.TE32.SP1" refpointid="TC08.G201.TE32.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="513" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="50" max="250" />
      </pointgroup>
      <pointgroup name="Pika-ajo" technicalname="G201.BPSetvalue" group="Lämmin käyttövesi">
        <point name="Pika-ajo" pointid="TC08.G201.TE32.SP2" refpointid="TC08.G201.TE32.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="515" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="LV Ylilämpöhäl. viive" technicalname="G201.DHWAlarmDelay" group="Lämmin käyttövesi">
        <point name="LV Ylilämpöhäl. viive" pointid="TC08.G201.TE31.SP5" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="517" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      </pointgroup>
      <pointgroup name="LV Ylilämpö hälytysraja" technicalname="G201.DHWMaxAlarm" group="Lämmin käyttövesi">
        <point name="LV Ylilämpö hälytysraja" pointid="TC08.G201.TE31.SP6" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="519" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="65" max="120" />
      </pointgroup>
      <pointgroup name="Moottorin ajoaika" technicalname="G201.MotorDriveTime" group="Lämmin käyttövesi" description="Moottorin ajoaika sekunteina">
        <point name="Moottorin ajoaika" pointid="TC08.G201.FV01.SP1" refpointid="TC08.G201.FV01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="521" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytysraja" technicalname="G201.MaxDeviation" group="Lämmin käyttövesi">
        <point name="Poikkeamahälytysraja" pointid="TC08.G201.TE31.SP7" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="523" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytyksen viive" technicalname="G201.DeviationAlamrDelay" group="Lämmin käyttövesi">
        <point name="Poikkeamahälytyksen viive" pointid="TC08.G201.TE31.SP8" refpointid="TC08.G201.TE31.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="525" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="600" />
      </pointgroup>
      <pointgroup name="LV Skaalaus imp/l" technicalname="G201.WaterMeasures.Setvalue22" group="Lämmin käyttövesi">
        <point name="LV Skaalaus imp/l" pointid="TC08.G201.VM33.1.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="642" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="KV kulutus alkuarvo" technicalname="G201.WaterMeasures.Setvalue21" group="Lämmin käyttövesi" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="KV kulutus alkuarvo" pointid="TC08.G201.VM33.1.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="644" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="KV Skaalaus imp/l" technicalname="G201.WaterMeasures.Setvalue" group="Lämmin käyttövesi">
        <point name="KV Skaalaus imp/l" pointid="TC08.G201.VM33.2.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="649" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="LV kulutus alkuarvo" technicalname="G201.WaterMeasures.Setvalue2" group="Lämmin käyttövesi" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="LV kulutus alkuarvo" pointid="TC08.G201.VM33.2.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="651" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G201.EnergyMeter.Setvalue22" group="Lämmin käyttövesi">
        <point name="Skaalaus imp/kwh" pointid="TC08.G201.QQ31.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="631" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="LV Energia alkuarvo" technicalname="G201.EnergyMeter.Setvalue21" group="Lämmin käyttövesi" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="LV Energia alkuarvo" pointid="TC08.G201.QQ31.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="633" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="LJH Jäähd. P-alue" technicalname="G410.Setvalue" group="G410 LJH Jäähdytys" description="P-alue">
        <point name="LJH Jäähd. P-alue" pointid="TC08.G410.TE16.SP2" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="674" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="LJH Jäähd. I-aika" technicalname="G410.Setvalue2" group="G410 LJH Jäähdytys" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="LJH Jäähd. I-aika" pointid="TC08.G410.TE16.SP3" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="676" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="LJH Lämpötilan asetus" technicalname="G410.Setvalue4" group="G410 LJH Jäähdytys">
        <point name="LJH Lämpötilan asetus" pointid="TC08.G410.TE16.SP1" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="678" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="30" />
      </pointgroup>
      <pointgroup name="LJH Konvektoripuh. min-nopeus" technicalname="G410.Setvalue3" group="G410 LJH Jäähdytys">
        <point name="LJH Konvektoripuh. min-nopeus" pointid="TC08.G410.PKN16.0.023.SP1" refpointid="TC08.G410.PKN16.0.023.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="680" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="LJH Konvektoripuh. max-nopeus" technicalname="G410.Setvalue5" group="G410 LJH Jäähdytys">
        <point name="LJH Konvektoripuh. max-nopeus" pointid="TC08.G410.PKN16.0.023.SP2" refpointid="TC08.G410.PKN16.0.023.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="682" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="LJH Lämpötila alaraja" technicalname="G410.Setvalue6" group="G410 LJH Jäähdytys">
        <point name="LJH Lämpötila alaraja" pointid="TC08.G410.TE16.SP4" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="684" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      </pointgroup>
      <pointgroup name="LJH Lämpötila yläraja" technicalname="G410.Setvalue7" group="G410 LJH Jäähdytys">
        <point name="LJH Lämpötila yläraja" pointid="TC08.G410.TE16.SP5" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="686" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      </pointgroup>
      <pointgroup name="LJH Lämpötila hälytysviive" technicalname="G410.Setvalue8" group="G410 LJH Jäähdytys">
        <point name="LJH Lämpötila hälytysviive" pointid="TC08.G410.TE16.SP6" refpointid="TC08.G410.TE16.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="688" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      </pointgroup>
      <pointgroup name="KL energia" technicalname="DHMeasures.EnergyMeter.Measure2" group="Kaukolämpö" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="KL energia" pointid="TC08.G100.QQ01_E.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="653" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="KL energia, ohjaustapa" pointid="TC08.G100.QQ01_E.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="657" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="KL Vesimäärä" technicalname="DHMeasures.WaterMeasure.Measure2" group="Kaukolämpö" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="KL Vesimäärä" pointid="TC08.G100.QQ01_V.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="655" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="KL Vesimäärä, ohjaustapa" pointid="TC08.G100.QQ01_V.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="658" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kaukolämpö hälytysviive" technicalname="DHMeasures.Setvalue" group="Kaukolämpö">
        <point name="Kaukolämpö hälytysviive" pointid="TC08.G100.TE41.SP1" refpointid="TC08.G100.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="659" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      </pointgroup>
      <pointgroup name="Kaukolämpö hälytysraja" technicalname="DHMeasures.Setvalue2" group="Kaukolämpö">
        <point name="Kaukolämpö hälytysraja" pointid="TC08.G100.TE41.SP2" refpointid="TC08.G100.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="661" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="DHMeasures.EnergyMeter.Setvalue22" group="Kaukolämpö">
        <point name="Skaalaus imp/kwh" pointid="TC08.G100.QQ01_E.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="663" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="KL Energia alkuarvo" technicalname="DHMeasures.EnergyMeter.Setvalue21" group="Kaukolämpö" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="KL Energia alkuarvo" pointid="TC08.G100.QQ01_E.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="665" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/l" technicalname="DHMeasures.WaterMeasure.Setvalue22" group="Kaukolämpö">
        <point name="Skaalaus imp/l" pointid="TC08.G100.QQ01_V.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="667" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="KL Vesimäärä alkuarvo" technicalname="DHMeasures.WaterMeasure.Setvalue21" group="Kaukolämpö" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="KL Vesimäärä alkuarvo" pointid="TC08.G100.QQ01_V.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="669" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Käyrän mukaan" technicalname="G102.CurveOut" group="IV-Verkosto" description="Käyrältä laskettu menoveden asetusarvo">
        <point name="Käyrän mukaan" pointid="TC08.G102.TE41.M4" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="355" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Käyrän mukaan, ohjaustapa" pointid="TC08.G102.TE41.M4_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="447" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Laskennall. menoveden asetusarvo" technicalname="G102.SupplyWaterSet" group="IV-Verkosto">
        <point name="Laskennall. menoveden asetusarvo" pointid="TC08.G102.TE41.M5" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="357" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Laskennall. menoveden asetusarvo, ohjaustapa" pointid="TC08.G102.TE41.M5_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="448" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Pudotus aikaohjelmalla" technicalname="G102.DropEffect" group="IV-Verkosto">
        <point name="Pudotus aikaohjelmalla" pointid="TC08.G102.TE41.M3" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="359" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Suuntaissiirto" technicalname="G102.ParallelShiftEffect" group="IV-Verkosto">
        <point name="Suuntaissiirto" pointid="TC08.G102.TE41.M2" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="361" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Suuntaissiirto, ohjaustapa" pointid="TC08.G102.TE41.M2_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="449" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Minimirajan vaikutus" technicalname="G102.MinLimitEffect" group="IV-Verkosto">
        <point name="Minimirajan vaikutus" pointid="TC08.G102.TE41.M6" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="363" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Maksimirajan vaikutus" technicalname="G102.MaxLimitEffect" group="IV-Verkosto">
        <point name="Maksimirajan vaikutus" pointid="TC08.G102.TE41.M7" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="365" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Syyskuivauksen vaikutus" technicalname="G102.AutumnDryEff" group="IV-Verkosto">
        <point name="Syyskuivauksen vaikutus" pointid="TC08.G102.TE41.M8" refpointid="TC08.G102.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="367" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Syyskuivauksen vaikutus, ohjaustapa" pointid="TC08.G102.TE41.M8_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="450" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kesäpysäytystila" technicalname="G102.Measure3" group="IV-Verkosto" description="Lähtö">
        <point name="Kesäpysäytystila" pointid="TC08.G102.TE00.M1" refpointid="TC08.TE00.M" pointtype="12" registertype="Holding" addressformat="U16" addressindex="352" categorytype="3" enum="0=Pois;1=Päällä" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Kesäpysäytystila, ohjaustapa" pointid="TC08.G102.TE00.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="354" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Verkosto energia" technicalname="G102.EnergyMeter.Measure2" group="IV-Verkosto" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="IV-Verkosto energia" pointid="TC08.G102.QQ42.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="622" categorytype="3" unit="mWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="IV-Verkosto energia, ohjaustapa" pointid="TC08.G102.QQ42.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="626" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="P-alue" technicalname="G102.P_Area" group="IV-Verkosto" description="P-alue">
        <point name="P-alue" pointid="TC08.G102.TE41.SP1" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="527" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="I-aika" technicalname="G102.I_Time" group="IV-Verkosto" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="I-aika" pointid="TC08.G102.TE41.SP2" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="529" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="D-aika" technicalname="G102.D_Time" group="IV-Verkosto" description="D-aika sekunteina">
        <point name="D-aika" pointid="TC08.G102.TE41.SP3" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="531" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Out1" technicalname="G102.Setvalue4" group="IV-Verkosto" description="Menoveden lämpötila -20C:n ulkolämpötilassa">
        <point name="Out1" pointid="TC08.G102.TE41.SP4" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="533" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In2" technicalname="G102.Setvalue5" group="IV-Verkosto" description="Käyrän ulkolämpötilapiste 2">
        <point name="In2" pointid="TC08.G102.TE00.SP5" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="535" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out2" technicalname="G102.Setvalue6" group="IV-Verkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 2">
        <point name="Out2" pointid="TC08.G102.TE41.SP5" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="537" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In3" technicalname="G102.Setvalue7" group="IV-Verkosto" description="Käyrän ulkolämpötilapiste 3">
        <point name="In3" pointid="TC08.G102.TE00.SP6" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="539" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out3" technicalname="G102.Setvalue8" group="IV-Verkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 3">
        <point name="Out3" pointid="TC08.G102.TE41.SP6" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="541" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="In4" technicalname="G102.Setvalue9" group="IV-Verkosto" description="Käyrän ulkolämpötilapiste 4">
        <point name="In4" pointid="TC08.G102.TE00.SP7" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="543" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      </pointgroup>
      <pointgroup name="Out4" technicalname="G102.Setvalue10" group="IV-Verkosto" description="Menoveden lämpötila käyrän ulkolämpötilapisteessä 4">
        <point name="Out4" pointid="TC08.G102.TE41.SP7" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="545" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Out5" technicalname="G102.Setvalue11" group="IV-Verkosto" description="Menoveden lämpötila 20C:n ulkolämpötilassa">
        <point name="Out5" pointid="TC08.G102.TE41.SP8" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="547" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Minimiraja" technicalname="G102.Setvalue12" group="IV-Verkosto" description="Lähtö rajoitetaan minimissä tähän arvoon">
        <point name="Minimiraja" pointid="TC08.G102.TE41.SP9" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="549" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Maksimiraja" technicalname="G102.Setvalue13" group="IV-Verkosto" description="Lähtö rajoitetaan maksimissa tähän arvoon">
        <point name="Maksimiraja" pointid="TC08.G102.TE41.SP10" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="551" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Pudotuksen määrä" technicalname="G102.DropAmout" group="IV-Verkosto">
        <point name="Pudotuksen määrä" pointid="TC08.G102.TE41.SP11" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="553" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      </pointgroup>
      <pointgroup name="Suuntaissiirto" technicalname="G102.ParallelShift" group="IV-Verkosto">
        <point name="Suuntaissiirto" pointid="TC08.G102.TE41.SP12" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="555" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="10" />
      </pointgroup>
      <pointgroup name="Paine alarajahälytys" technicalname="G102.PressAlarmLowLimit" group="IV-Verkosto">
        <point name="Paine alarajahälytys" pointid="TC08.G102.PIE01.SP2" refpointid="TC08.G102.PIE01.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="557" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Paine ylärajahälytys" technicalname="G102.PressAlarmHighLimit" group="IV-Verkosto">
        <point name="Paine ylärajahälytys" pointid="TC08.G102.PIE01.SP1" refpointid="TC08.G102.PIE01.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="559" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytysraja" technicalname="G102.DeviationAlarmLimit" group="IV-Verkosto">
        <point name="Poikkeamahälytysraja" pointid="TC08.G102.TE41.SP13" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="561" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      </pointgroup>
      <pointgroup name="Poikkeamahälytyksen viive" technicalname="G102.DeviationAlarmDelay" group="IV-Verkosto">
        <point name="Poikkeamahälytyksen viive" pointid="TC08.G102.TE41.SP14" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="563" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      </pointgroup>
      <pointgroup name="Syyskuivaus" technicalname="G102.AutumnDrySet" group="IV-Verkosto">
        <point name="Syyskuivaus" pointid="TC08.G102.TE41.SP15" refpointid="TC08.G102.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="565" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      </pointgroup>
      <pointgroup name="Pumpun P-alue" technicalname="G102.Setvalue" group="IV-Verkosto" description="P-alue">
        <point name="Pumpun P-alue" pointid="TC08.G102.PDIE02.SP1" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="567" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Pumpun I-aika (s)" technicalname="G102.Setvalue2" group="IV-Verkosto" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Pumpun I-aika (s)" pointid="TC08.G102.PDIE02.SP2" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="569" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Pumpun D-aika (s)" technicalname="G102.Setvalue3" group="IV-Verkosto" description="D-aika sekunteina">
        <point name="Pumpun D-aika (s)" pointid="TC08.G102.PDIE02.SP3" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="571" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="Kesäpysäytysraja" technicalname="G102.Setvalue14" group="IV-Verkosto" description="Asetusarvo">
        <point name="Kesäpysäytysraja" pointid="TC08.G102.TE00.SP1" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="599" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      </pointgroup>
      <pointgroup name="Kesäpysäytys eroalue" technicalname="G102.Setvalue15" group="IV-Verkosto">
        <point name="Kesäpysäytys eroalue" pointid="TC08.G102.TE00.SP8" refpointid="TC08.TE00.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="601" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      </pointgroup>
      <pointgroup name="Pumpun paineen asetusarvo" technicalname="G102.Setvalue16" group="IV-Verkosto">
        <point name="Pumpun paineen asetusarvo" pointid="TC08.G102.PDIE02.SP4" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="603" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="50" max="250" />
      </pointgroup>
      <pointgroup name="Pumpun paine hälytysviive" technicalname="G102.Setvalue17" group="IV-Verkosto">
        <point name="Pumpun paine hälytysviive" pointid="TC08.G102.PDIE02.SP5" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="605" categorytype="3" unit="min" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="60" />
      </pointgroup>
      <pointgroup name="P. paineen max. poikkeama" technicalname="G102.Setvalue18" group="IV-Verkosto">
        <point name="P. paineen max. poikkeama" pointid="TC08.G102.PDIE02.SP6" refpointid="TC08.G102.PDIE02.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="607" categorytype="3" unit="kpa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G102.EnergyMeter.Setvalue22" group="IV-Verkosto">
        <point name="Skaalaus imp/kwh" pointid="TC08.G102.QQ42.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="635" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="IV-Energia alkuarvo" technicalname="G102.EnergyMeter.Setvalue21" group="IV-Verkosto" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="IV-Energia alkuarvo" pointid="TC08.G102.QQ42.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="637" categorytype="3" unit="mWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="G102FV01 ajoaika" technicalname="G102.MotorDriving2.t_OpenMotor1" group="IV-Verkosto" description="Ajoaika laidasta laitaan sekunteina">
        <point name="G102FV01 ajoaika" pointid="TC08.FV01.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="573" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      </pointgroup>
      <pointgroup name="G102FV01 valinta" technicalname="G102.MotorDriving2.ActuatorConf" group="IV-Verkosto" description="Toimilaitteen valinta. 0=0-10V, 1=2-10V, 2=10-0V, 3=10-2V">
        <point name="G102FV01 valinta" pointid="G102.MotorDriving2.ActuatorConf" pointtype="13" registertype="Holding" addressformat="S32" addressindex="575" categorytype="3" enum="0=0-10V;1=2-10V;2=10-0V;3=10-2V" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="3" />
      </pointgroup>
      <pointgroup name="G102FV02 valinta" technicalname="G102.MotorDriving2.Setvalue" group="IV-Verkosto" description="Toimilaitteen valinta. 0=0-10V, 1=2-10V, 2=10-0V, 3=10-2V">
        <point name="G102FV02 valinta" pointid="G102.MotorDriving2.Setvalue" pointtype="13" registertype="Holding" addressformat="S32" addressindex="577" categorytype="3" enum="0=0-10V;1=2-10V;2=10-0V;3=10-2V" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="3" />
      </pointgroup>
      <pointgroup name="G102FV02 ajoaika" technicalname="G102.MotorDriving2.t_OpenMotor2" group="IV-Verkosto" description="Ajoaika auki suuntaan sekunteina">
        <point name="G102FV02 ajoaika" pointid="TC08.G102.FV02.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="579" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      </pointgroup>
    </group>
    <group categorytype="4" name="Hälytykset">
      <point name="Laitteen perus IO (MB1.BaseCard) ei vastaa" technicalname="BaseCard_Error" pointid="TC08.BaseCard_Error.A" addressindex="581" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="0" severity="1" alarmid="#A0" pointtype="14" />
      <point name="Anturivika TE31 Lämmin käyttövesi (Lämmin käyttövesi)" technicalname="SensorFaultAlarm_BaseCard_UI_5" pointid="TC08.G201.TE31.SE" refpointid="TC08.G201.TE31.M" addressindex="584" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="1" severity="2" alarmid="#A1" pointtype="14" />
      <point name="Laite MB2.MOD1_C32 osoitteessa 2 ei vastaa" technicalname="MB2_ADDR2_MOD1_C32__Error" pointid="TC08.MB2_ADDR2_MOD1_C32__Error.A" addressindex="585" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="2" severity="1" alarmid="#A2" pointtype="14" />
      <point name="Anturivika TE41 Patteriverkosto meno (Patteriverkosto meno)" technicalname="SensorFaultAlarm_BaseCard_UI_8" pointid="TC08.G101.TE41.SE" refpointid="TC08.G101.TE41.M" addressindex="609" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="3" severity="2" alarmid="#A3" pointtype="14" />
      <point name="Anturivika TE42 Patteriverkosto paluu (Patteriverkosto paluu)" technicalname="SensorFaultAlarm_BaseCard_UI_9" pointid="TC08.G101.TE42.SE" refpointid="TC08.G101.TE42.M" addressindex="610" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="4" severity="2" alarmid="#A4" pointtype="14" />
      <point name="Anturivika TE32 Käyttöveden kierto (Käyttöveden kierto)" technicalname="SensorFaultAlarm_BaseCard_UI_6" pointid="TC08.G201.TE32.SE" refpointid="TC08.G201.TE32.M" addressindex="611" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="5" severity="2" alarmid="#A5" pointtype="14" />
      <point name="Anturivika TE33 Kylmä käyttövesi (Kylmä käyttövesi)" technicalname="SensorFaultAlarm_BaseCard_UI_7" pointid="TC08.G201.TE33.SE" refpointid="TC08.G201.TE33.M" addressindex="612" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="6" severity="2" alarmid="#A6" pointtype="14" />
      <point name="Anturivika TE41 IV-Verkosto meno (IV-Verkosto meno)" technicalname="SensorFaultAlarm_BaseCard_UI_10" pointid="TC08.G102.TE41.SE" refpointid="TC08.G102.TE41.M" addressindex="613" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="7" severity="2" alarmid="#A7" pointtype="14" />
      <point name="Anturivika TE42 IV-Verkosto paluu (IV-Verkosto paluu)" technicalname="SensorFaultAlarm_BaseCard_UI_11" pointid="TC08.G102.TE42.SE" refpointid="TC08.G102.TE42.M" addressindex="614" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="8" severity="2" alarmid="#A8" pointtype="14" />
      <point name="Anturivika TE41 Kaukolämpö tulo (Kaukolämpö tulo)" technicalname="SensorFaultAlarm_BaseCard_UI_3" pointid="TC08.TE41.SE" refpointid="TC08.G100.TE41.M" addressindex="582" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="9" severity="2" alarmid="#A9" pointtype="14" />
      <point name="Anturivika TE42 Kaukolämpö paluu (Kaukolämpö paluu)" technicalname="SensorFaultAlarm_BaseCard_UI_4" pointid="TC08.TE42.SE" refpointid="TC08.G100.TE42.M" addressindex="583" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="10" severity="2" alarmid="#A10" pointtype="14" />
      <point name="Laite MBTCP.VAK1 väylässä ModbusTCP ei vastaa" technicalname="MBTCP_ADDR172_16_100_20_VAK1__Error" pointid="TC08.MBTCP_ADDR172_16_100_20_VAK1__Error.A" addressindex="672" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="11" severity="1" alarmid="#A11" pointtype="14" />
      <point name="Anturivika TE16 Huonelämpötila LJH (Huonelämpötila LJH)" technicalname="SensorFaultAlarm_MOD1_C32_UI_10" pointid="TC08.TE16.SE" refpointid="TC08.G410.TE16.M" addressindex="673" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="12" severity="2" alarmid="#A12" pointtype="14" />
      <point name="G101.Patteriverkosto pumppu ristiriita" technicalname="G101.ContradictionAlarm_A" pointid="TC08.G101.P01_IND.A1" refpointid="TC08.G101.P01_IND.I" addressindex="586" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="13" severity="1" alarmid="#A13" pointtype="14" />
      <point name="G101.Painehäl. Patteriverkosto" technicalname="G101.AnalogAlarm_A" pointid="TC08.G101.PIE01.A1" refpointid="TC08.G101.PIE01.M" addressindex="587" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="14" severity="1" alarmid="#A14" pointtype="14" />
      <point name="G101.Jäätymisvaara patteriverkosto" technicalname="G101.Alarm" pointid="TC08.G101.TE41.A1" refpointid="TC08.G101.TE41.M" addressindex="588" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="15" severity="1" alarmid="#A15" pointtype="14" />
      <point name="G101.Poikkeamahäl. patteriverkosto" technicalname="G101.DeviationAlarm_A" pointid="TC08.G101.TE41.A2" refpointid="TC08.G101.TE41.M" addressindex="589" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="16" severity="1" alarmid="#A16" pointtype="14" />
      <point name="G101.Patteriverkosto pumppu vika" technicalname="G101.BinaryAlarm_A" pointid="TC08.G101.P01_AL.A1" refpointid="TC08.G101.P01_AL.I" addressindex="590" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="17" severity="1" alarmid="#A17" pointtype="14" />
      <point name="G101.Patteriverk. pumpun painepoikkeama" technicalname="G101.Alarm2" pointid="TC08.G101.PDIE02.A1" refpointid="TC08.G101.PDIE02.M" addressindex="615" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="18" severity="1" alarmid="#A18" pointtype="14" />
      <point name="G201.Ylilämpöhälytys käyttövesi laaj." technicalname="G201.AnalogAlarm_A" pointid="TC08.G201.TE31.A1" refpointid="TC08.G201.TE31.M" addressindex="591" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="19" severity="1" alarmid="#A19" pointtype="14" />
      <point name="G201.poikkeamahälytys käyttövesi laaj." technicalname="G201.DeviationAlarm_A" pointid="TC08.G201.TE31.A2" refpointid="TC08.G201.TE31.M" addressindex="592" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="20" severity="2" alarmid="#A20" pointtype="14" />
      <point name="G201.Käyttövesi kiertopumppu VIKA" technicalname="G201.BinaryAlarm_A" pointid="TC08.G201.P01_AL.A2" refpointid="TC08.G201.P01_AL.I" addressindex="593" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="21" severity="1" alarmid="#A21" pointtype="14" />
      <point name="G201.Käyttövesi kiertopumppu SEIS" technicalname="G201.ContradictionAlarm_A" pointid="TC08.G201.P01_IND.A1" refpointid="TC08.G201.P01_IND.I" addressindex="616" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="22" severity="1" alarmid="#A22" pointtype="14" />
      <point name="G410.LJH Lämpötila alaraja" technicalname="G410.AnalogAlarm_A" pointid="TC08.G410.TE16.LL1" refpointid="TC08.G410.TE16.M" addressindex="690" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="23" severity="1" alarmid="#A23" pointtype="14" />
      <point name="G410.LJH Lämpötila yläraja" technicalname="G410.AnalogAlarm2_A" pointid="TC08.G410.TE16.HL2" refpointid="TC08.G410.TE16.M" addressindex="691" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="24" severity="1" alarmid="#A24" pointtype="14" />
      <point name="DHMeasures.Kaukolämpö alaraja" technicalname="DHMeasures.AnalogAlarm_A" pointid="TC08.G100.TE41.A1" refpointid="TC08.G100.TE41.M" addressindex="671" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="25" severity="1" alarmid="#A25" pointtype="14" />
      <point name="G102.IV-Verkosto pumppu ristiriita" technicalname="G102.ContradictionAlarm_A" pointid="TC08.G102.P01_IND.A1" refpointid="TC08.G102.P01_IND.I" addressindex="594" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="26" severity="1" alarmid="#A26" pointtype="14" />
      <point name="G102.Painehäl. IV-Verkosto" technicalname="G102.AnalogAlarm_A" pointid="TC08.G102.PIE01.A1" refpointid="TC08.G102.PIE01.M" addressindex="595" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="27" severity="1" alarmid="#A27" pointtype="14" />
      <point name="G102.Jäätymisvaara IV-Verkosto" technicalname="G102.Alarm" pointid="TC08.G102.TE41.A1" refpointid="TC08.G102.TE41.M" addressindex="596" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="28" severity="1" alarmid="#A28" pointtype="14" />
      <point name="G102.Poikkeamahäl. IV-Verkosto" technicalname="G102.DeviationAlarm_A" pointid="TC08.G102.TE41.A2" refpointid="TC08.G102.TE41.M" addressindex="597" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="29" severity="1" alarmid="#A29" pointtype="14" />
      <point name="G102.IV-Verkosto pumppu VIKA" technicalname="G102.BinaryAlarm_A" pointid="TC08.G102.P01_AL.A1" refpointid="TC08.G102.P01_AL.I" addressindex="598" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="30" severity="1" alarmid="#A30" pointtype="14" />
      <point name="G102.IV-Verkosto pumpun painepoikkeama" technicalname="G102.Alarm2" pointid="TC08.G102.PDIE02.A1" refpointid="TC08.G102.PDIE02.M" addressindex="617" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="31" severity="1" alarmid="#A31" pointtype="14" />
    </group>
    <group categorytype="5" name="Aikaohjelmat">
      <timeprogram name="Pudotusohjelma" technicalname="G101.DropProgram">
        <point name="Viikko-ohjelma: Pudotusohjelma" pointtype="15" timeprogramtype="1" registertype="Holding" addressindex="10003" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="1" pointid="TC08.G101.TP1_WS">
          <status group="1" name="Ei käytössä" value="-1" hiddenvalue="true" notusedvalue="true" />
          <status group="1" name="Pois" value="0" defaultvalue="true" />
          <status group="1" name="Päällä" value="1" />
        </point>
        <point name="Erikoispäivät: Pudotusohjelma" pointtype="17" timeprogramtype="2" registertype="Holding" addressindex="10243" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" daycount="7" group="1" pointid="TC08.G101.TP2_SP">
          <status group="1" name="Pois" value="0" />
          <status group="1" name="Päällä" value="1" />
        </point>
        <point name="Poikkeuskalenteri: Pudotusohjelma" pointtype="16" timeprogramtype="3" registertype="Holding" addressindex="10123" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="1" pointid="TC08.G101.TP3_ES">
          <status group="1" name="Ei käytössä" value="255" />
          <status group="1" name="Arvo" value="0">
            <enum name="Automaatti" value="-1" />
            <enum name="Pois" value="0" />
            <enum name="Päällä" value="1" />
          </status>
          <status group="1" name="Maanantai" value="1" />
          <status group="1" name="Tiistai" value="2" />
          <status group="1" name="Keskiviikko" value="3" />
          <status group="1" name="Torstai" value="4" />
          <status group="1" name="Perjantai" value="5" />
          <status group="1" name="Lauantai" value="6" />
          <status group="1" name="Sunnuntai" value="7" />
          <status group="1" name="Erikoispäivä 1" value="8" />
          <status group="1" name="Erikoispäivä 2" value="9" />
          <status group="1" name="Erikoispäivä 3" value="10" />
          <status group="1" name="Erikoispäivä 4" value="11" />
          <status group="1" name="Erikoispäivä 5" value="12" />
          <status group="1" name="Erikoispäivä 6" value="13" />
          <status group="1" name="Erikoispäivä 7" value="14" />
        </point>
        <point name="G101.Pudotusohjelma Nykyinen arvo" pointid="TC08.G101.TP" pointtype="18" registertype="Holding" addressformat="S16" addressindex="10001" categorytype="3" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1">
          <point name="Pudotusohjelma, ohjaustapa" pointid="TC08.G101.TP_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="10002" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </timeprogram>
      <timeprogram name="G410 LJH Jäähdytys" technicalname="G410.Timeprogram">
        <point name="Viikko-ohjelma: G410 LJH Jäähdytys" pointtype="15" timeprogramtype="1" registertype="Holding" addressindex="10727" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="2" pointid="TC08.G410.PKN16.0.023.TP11_WS">
          <status group="2" name="Ei käytössä" value="-1" hiddenvalue="true" notusedvalue="true" />
          <status group="2" name="Seis" value="0" defaultvalue="true" />
          <status group="2" name="Käy" value="1" />
        </point>
        <point name="Erikoispäivät: G410 LJH Jäähdytys" pointtype="17" timeprogramtype="2" registertype="Holding" addressindex="10967" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" daycount="7" group="2" pointid="TC08.G410.PKN16.0.023.TP12_SP">
          <status group="2" name="Seis" value="0" />
          <status group="2" name="Käy" value="1" />
        </point>
        <point name="Poikkeuskalenteri: G410 LJH Jäähdytys" pointtype="16" timeprogramtype="3" registertype="Holding" addressindex="10847" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="2" pointid="TC08.G410.PKN16.0.023.TP13_ES">
          <status group="2" name="Ei käytössä" value="255" />
          <status group="2" name="Arvo" value="0">
            <enum name="Automaatti" value="-1" />
            <enum name="Seis" value="0" />
            <enum name="Käy" value="1" />
          </status>
          <status group="2" name="Maanantai" value="1" />
          <status group="2" name="Tiistai" value="2" />
          <status group="2" name="Keskiviikko" value="3" />
          <status group="2" name="Torstai" value="4" />
          <status group="2" name="Perjantai" value="5" />
          <status group="2" name="Lauantai" value="6" />
          <status group="2" name="Sunnuntai" value="7" />
          <status group="2" name="Erikoispäivä 1" value="8" />
          <status group="2" name="Erikoispäivä 2" value="9" />
          <status group="2" name="Erikoispäivä 3" value="10" />
          <status group="2" name="Erikoispäivä 4" value="11" />
          <status group="2" name="Erikoispäivä 5" value="12" />
          <status group="2" name="Erikoispäivä 6" value="13" />
          <status group="2" name="Erikoispäivä 7" value="14" />
        </point>
        <point name="G410.G410 LJH Jäähdytys Nykyinen arvo" pointid="TC08.G410.PKN16.0.023.TP1" refpointid="TC08.G410.PKN16.0.023.C" pointtype="18" registertype="Holding" addressformat="S16" addressindex="10725" categorytype="3" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1">
          <point name="G410 LJH Jäähdytys, ohjaustapa" pointid="TC08.G410.PKN16.0.023.TP1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="10726" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </timeprogram>
      <timeprogram name="Pudotusohjelma" technicalname="G102.DropProgram">
        <point name="Viikko-ohjelma: Pudotusohjelma" pointtype="15" timeprogramtype="1" registertype="Holding" addressindex="10365" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="3" pointid="TC08.G102.TP1_WS">
          <status group="3" name="Ei käytössä" value="-1" hiddenvalue="true" notusedvalue="true" />
          <status group="3" name="Pois" value="0" defaultvalue="true" />
          <status group="3" name="Päällä" value="1" />
        </point>
        <point name="Erikoispäivät: Pudotusohjelma" pointtype="17" timeprogramtype="2" registertype="Holding" addressindex="10605" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" daycount="7" group="3" pointid="TC08.G102.TP2_SP">
          <status group="3" name="Pois" value="0" />
          <status group="3" name="Päällä" value="1" />
        </point>
        <point name="Poikkeuskalenteri: Pudotusohjelma" pointtype="16" timeprogramtype="3" registertype="Holding" addressindex="10485" addressmultiple="120" readacceslevel="5" writeacceslevel="3" pointcount="30" group="3" pointid="TC08.G102.TP3_ES">
          <status group="3" name="Ei käytössä" value="255" />
          <status group="3" name="Arvo" value="0">
            <enum name="Automaatti" value="-1" />
            <enum name="Pois" value="0" />
            <enum name="Päällä" value="1" />
          </status>
          <status group="3" name="Maanantai" value="1" />
          <status group="3" name="Tiistai" value="2" />
          <status group="3" name="Keskiviikko" value="3" />
          <status group="3" name="Torstai" value="4" />
          <status group="3" name="Perjantai" value="5" />
          <status group="3" name="Lauantai" value="6" />
          <status group="3" name="Sunnuntai" value="7" />
          <status group="3" name="Erikoispäivä 1" value="8" />
          <status group="3" name="Erikoispäivä 2" value="9" />
          <status group="3" name="Erikoispäivä 3" value="10" />
          <status group="3" name="Erikoispäivä 4" value="11" />
          <status group="3" name="Erikoispäivä 5" value="12" />
          <status group="3" name="Erikoispäivä 6" value="13" />
          <status group="3" name="Erikoispäivä 7" value="14" />
        </point>
        <point name="G102.Pudotusohjelma Nykyinen arvo" pointid="TC08.G102.TP" pointtype="18" registertype="Holding" addressformat="S16" addressindex="10363" categorytype="3" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1">
          <point name="Pudotusohjelma, ohjaustapa" pointid="TC08.G102.TP_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="10364" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </timeprogram>
    </group>
  </groups>
</controllertemplate>