<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="G307TC07" version="0.0.0" createppg="false" language="fi-FI" type="Modbus" addressindexstart="1">
  <groups>
    <group categorytype="2" name="Fyysiset pisteet" name_en="Physical points" name_fi="Fyysiset pisteet" name_sv="Fysiska punkter" name_et="Füüsilised punktid" name_ru="Физические точки" name_lv="Fiziskie punkti" name_tr="Fiziksel noktalar " name_pl="Punkt fizyczny">
      <point name="UI 1" name_en="UI 1" name_fi="Tuloilma LTO:n jälkeen" name_sv="UI 1" name_et="UI 1" name_ru="UI 1" name_lv="UI 1" name_tr="UI 1" name_pl="UI 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 2" name_en="UI 2" name_fi="Tuloilman lämpötila" name_sv="UI 2" name_et="UI 2" name_ru="UI 2" name_lv="UI 2" name_tr="UI 2" name_pl="UI 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 3" name_en="UI 3" name_fi="Poistoilman lämpötila" name_sv="UI 3" name_et="UI 3" name_ru="UI 3" name_lv="UI 3" name_tr="UI 3" name_pl="UI 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 4" name_en="UI 4" name_fi="Jäteilman lämpötila" name_sv="UI 4" name_et="UI 4" name_ru="UI 4" name_lv="UI 4" name_tr="UI 4" name_pl="UI 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 5" name_en="UI 5" name_fi="Tulosuodatin paine-ero" name_sv="UI 5" name_et="UI 5" name_ru="UI 5" name_lv="UI 5" name_tr="UI 5" name_pl="UI 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="UI 6" name_en="UI 6" name_fi="Poistosuodatin paine-ero" name_sv="UI 6" name_et="UI 6" name_ru="UI 6" name_lv="UI 6" name_tr="UI 6" name_pl="UI 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="UI 7" name_en="UI 7" name_fi="LTO:n paine-ero" name_sv="UI 7" name_et="UI 7" name_ru="UI 7" name_lv="UI 7" name_tr="UI 7" name_pl="UI 7" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="UI 8" name_en="UI 8" name_fi="Tuloilmamäärä" name_sv="UI 8" name_et="UI 8" name_ru="UI 8" name_lv="UI 8" name_tr="UI 8" name_pl="UI 8" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="2" unit="l/s" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="2000" type="0" iotype="1" />
      <point name="UI 9" name_en="UI 9" name_fi="Poistoilmamäärä" name_sv="UI 9" name_et="UI 9" name_ru="UI 9" name_lv="UI 9" name_tr="UI 9" name_pl="UI 9" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="2" unit="l/s" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="2000" type="0" iotype="1" />
      <point name="UI 10" name_en="UI 10" name_fi="LTO kiekko häl." name_sv="UI 10" name_et="UI 10" name_ru="UI 10" name_lv="UI 10" name_tr="UI 10" name_pl="UI 10" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="2" enum="0=Normaali;1=Hälytys" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="UI 11" name_en="UI 11" name_fi="Tulosuodatin 2 paine-ero" name_sv="UI 11" name_et="UI 11" name_ru="UI 11" name_lv="UI 11" name_tr="UI 11" name_pl="UI 11" pointtype="6" registertype="Holding" addressformat="S32" addressindex="221" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="UI 12" name_en="UI 12" name_fi="LP Paluuveden lämpötila" name_sv="UI 12" name_et="UI 12" name_ru="UI 12" name_lv="UI 12" name_tr="UI 12" name_pl="UI 12" pointtype="6" registertype="Holding" addressformat="S32" addressindex="223" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="1" />
      <point name="UI 13" name_en="UI 13" name_fi="Tulopuhallin liiketila tila" name_sv="UI 13" name_et="UI 13" name_ru="UI 13" name_lv="UI 13" name_tr="UI 13" name_pl="UI 13" pointtype="6" registertype="Holding" addressformat="S32" addressindex="225" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="UI 14" name_en="UI 14" name_fi="Tuloilma kanavapaine" name_sv="UI 14" name_et="UI 14" name_ru="UI 14" name_lv="UI 14" name_tr="UI 14" name_pl="UI 14" pointtype="6" registertype="Holding" addressformat="S32" addressindex="227" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="UI 15" name_en="UI 15" name_fi="Poistopuhallin liiketila tila" name_sv="UI 15" name_et="UI 15" name_ru="UI 15" name_lv="UI 15" name_tr="UI 15" name_pl="UI 15" pointtype="6" registertype="Holding" addressformat="S32" addressindex="229" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="UI 16" name_en="UI 16" name_fi="Poistoilma kanavapaine" name_sv="UI 16" name_et="UI 16" name_ru="UI 16" name_lv="UI 16" name_tr="UI 16" name_pl="UI 16" pointtype="6" registertype="Holding" addressformat="S32" addressindex="231" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="500" type="0" iotype="1" />
      <point name="DI 1" name_en="DI 1" name_fi="LP Pumppu tila" name_sv="DI 1" name_et="DI 1" name_ru="DI 1" name_lv="DI 1" name_tr="DI 1" name_pl="DI 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="233" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="DI 2" name_en="DI 2" name_fi="Jäätymissuoja häl." name_sv="DI 2" name_et="DI 2" name_ru="DI 2" name_lv="DI 2" name_tr="DI 2" name_pl="DI 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="235" categorytype="2" enum="0=Normaali;1=Hälytys" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="PFI" name_en="Internal power failure indication" name_fi="Internal power failure indication" name_sv="Internal power failure indication" name_et="Internal power failure indication" name_ru="Internal power failure indication" name_lv="Internal power failure indication" name_tr="Internal power failure indication" name_pl="Internal power failure indication" pointtype="6" registertype="Holding" addressformat="S32" addressindex="237" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="AO 1" name_en="AO 1" name_fi="LP venttiili säätö" name_sv="AO 1" name_et="AO 1" name_ru="AO 1" name_lv="AO 1" name_tr="AO 1" name_pl="AO 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="239" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 2" name_en="AO 2" name_fi="AO 2" name_sv="AO 2" name_et="AO 2" name_ru="AO 2" name_lv="AO 2" name_tr="AO 2" name_pl="AO 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="241" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 3" name_en="AO 3" name_fi="Tulopuh. liiketila säätö" name_sv="AO 3" name_et="AO 3" name_ru="AO 3" name_lv="AO 3" name_tr="AO 3" name_pl="AO 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="243" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 4" name_en="AO 4" name_fi="Poistopuh. liiketila säätö" name_sv="AO 4" name_et="AO 4" name_ru="AO 4" name_lv="AO 4" name_tr="AO 4" name_pl="AO 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="245" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 5" name_en="AO 5" name_fi="LTO Kiekko säätö" name_sv="AO 5" name_et="AO 5" name_ru="AO 5" name_lv="AO 5" name_tr="AO 5" name_pl="AO 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="247" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 6" name_en="AO 6" name_fi="JP venttiili säätö" name_sv="AO 6" name_et="AO 6" name_ru="AO 6" name_lv="AO 6" name_tr="AO 6" name_pl="AO 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="249" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="TR 1" name_en="TR 1" name_fi="Raitisilmapelti ohjaus" name_sv="TR 1" name_et="TR 1" name_ru="TR 1" name_lv="TR 1" name_tr="TR 1" name_pl="TR 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="251" categorytype="2" enum="0=Kiinni;1=Auki" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 2" name_en="TR 2" name_fi="Jäteilmapelti ohjaus" name_sv="TR 2" name_et="TR 2" name_ru="TR 2" name_lv="TR 2" name_tr="TR 2" name_pl="TR 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="253" categorytype="2" enum="0=Kiinni;1=Auki" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 3" name_en="TR 3" name_fi="TR 3" name_sv="TR 3" name_et="TR 3" name_ru="TR 3" name_lv="TR 3" name_tr="TR 3" name_pl="TR 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="255" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 4" name_en="TR 4" name_fi="TR 4" name_sv="TR 4" name_et="TR 4" name_ru="TR 4" name_lv="TR 4" name_tr="TR 4" name_pl="TR 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="257" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="R1" name_en="R1" name_fi="Tulopuh. liiketila ohj." name_sv="R1" name_et="R1" name_ru="R1" name_lv="R1" name_tr="R1" name_pl="R1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="259" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R2" name_en="R2" name_fi="Poistopuh. liiketila ohj." name_sv="R2" name_et="R2" name_ru="R2" name_lv="R2" name_tr="R2" name_pl="R2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="261" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R3" name_en="R3" name_fi="LTO Kiekko ohj." name_sv="R3" name_et="R3" name_ru="R3" name_lv="R3" name_tr="R3" name_pl="R3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="263" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R4" name_en="R4" name_fi="R4" name_sv="R4" name_et="R4" name_ru="R4" name_lv="R4" name_tr="R4" name_pl="R4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="265" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R5" name_en="R5" name_fi="R5" name_sv="R5" name_et="R5" name_ru="R5" name_lv="R5" name_tr="R5" name_pl="R5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="267" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R6" name_en="R6" name_fi="R6" name_sv="R6" name_et="R6" name_ru="R6" name_lv="R6" name_tr="R6" name_pl="R6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="269" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
    </group>
    <group categorytype="2" name="Asetusarvot" name_en="Setting values" name_fi="Asetusarvot" name_sv="Inställningar" name_et="Seadistused" name_ru="Уставочные значения" name_lv="Iestatīt vērtības" name_tr="Set değerleri" name_pl="Ustawienia">
      <point name="G307_Setvalue" name_en="Setpoint" name_fi="Tehonvaihtoraja" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="353" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="G307_Setvalue2" name_en="Enable/disable" name_fi="Ulkolämpörajoitus" name_sv="Aktivera/deaktivera" pointtype="3" registertype="Holding" addressformat="U16" addressindex="355" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="G307_ALARMS_PumpState_Setvalue" name_en="Alarm delay (s)" name_fi="Hälytysviive (s)" name_sv="Larm fördröjning (s)" name_et="Value 1 to add" name_ru="Value 1 to add" name_lv="Value 1 to add" name_tr="Alarm delay (s)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="356" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_EState_Setvalue" name_en="Alarm delay (s)" name_fi="Hälytysviive (s)" name_sv="Larm fördröjning (s)" name_et="Value 1 to add" name_ru="Value 1 to add" name_lv="Value 1 to add" name_tr="Alarm delay (s)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="358" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="240" />
      <point name="G307_ALARMS_SState_Setvalue" name_en="Alarm delay (s)" name_fi="Hälytysviive (s)" name_sv="Larm fördröjning (s)" name_et="Value 1 to add" name_ru="Value 1 to add" name_lv="Value 1 to add" name_tr="Alarm delay (s)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="360" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="240" />
      <point name="G307_ALARMS_SupplyTemp_Setvalue2" name_en="Alarm delay (min)" name_fi="Hälytysviive (min)" name_sv="Larm fördröjning (min)" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="Alarm delay (min)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="368" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_SupplyTemp_Setvalue3" name_en="Max deviation of Supply air temp." name_fi="Tuloilman lämpötilan max poikkeama" name_sv="Max avvikelse av Tilluftens temp." name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="Max deviation of Supply air temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="370" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_SupplyPressure_Setvalue2" name_en="Alarm delay (min)" name_fi="Hälytysviive (min)" name_sv="Larm fördröjning (min)" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="Alarm delay (min)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="378" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_SupplyPressure_Setvalue3" name_en="Max deviation of Supply air pressure" name_fi="Tuloilman paineen max poikkeama" name_sv="Max avvikelse av Tilluftens tryck" name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="Max deviation of Supply air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="380" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_RetWater_Setvalue2" name_en="Alarm delay (min)" name_fi="Hälytysviive (min)" name_sv="Larm fördröjning (min)" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="Alarm delay (min)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="372" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_RetWater_Setvalue3" name_en="Low limit of  heat.radiator return water" name_fi="LP Paluuveden alaraja" name_sv="Nedre gräns av värmebatteri returvatten" name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="Low limit of  heat.radiator return water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="374" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_RetWater_Setvalue4" name_en="High limit of  heat.radiator return water" name_fi="LP Paluuveden yläraja" name_sv="Högre gräns av värmebatteri returvatten" name_et="High limit for alarm activation" name_ru="High limit for alarm activation" name_lv="High limit for alarm activation" name_tr="High limit of  heat.radiator return water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="376" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_EFilter_SFFilterPDEMinMeasured" name_en="Pressure diff. of Extract filter, AHU min" name_fi="Poistosuod. yläraja, IV min" name_sv="Frånlluftfilterns tryckdifferens, LB min" name_et="Supply filter pressure difference, AHU min" name_ru="Supply filter pressure difference, AHU min" name_lv="Supply filter pressure difference, AHU min" name_tr="Pressure diff. of Extract filter, AHU min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="382" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_EFilter_SFFilterPDEMaxMeasured" name_en="Pressure diff. of Exhaus filter, AHU max" name_fi="Poistosuod. yläraja, IV max" name_sv="Frånluftfilterns tryckdifferens, LB max" name_et="Supply filter pressure difference, AHU max" name_ru="Supply filter pressure difference, AHU max" name_lv="Supply filter pressure difference, AHU max" name_tr="Pressure diff. of Exhaus filter, AHU max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="384" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_EFilter_Setvalue" name_en="Alarm delay of Extract filter" name_fi="Poistosuod. hälytysviive" name_sv="Larm fördröjning av Frånluftfilter" name_et="Alarm activation delay" name_ru="Alarm activation delay" name_lv="Alarm activation delay" name_tr="Alarm delay of Extract filter" pointtype="3" registertype="Holding" addressformat="S32" addressindex="386" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_EFilter_Setvalue2" name_en="Low limit for alarm activation" name_fi="Poistosuod. alaraja" name_sv="Nedre aktiveringsgränsen för larm" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="388" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_ExtPressure_Setvalue2" name_en="Alarm delay (min)" name_fi="Hälytysviive (min)" name_sv="Larm fördröjning (min)" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="Alarm delay (min)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="398" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_ExtPressure_Setvalue3" name_en="Max deviation of Extract air pressure" name_fi="Poistoilman paineen max poikkeama" name_sv="Max avvikelse av Frånluftens tryck" name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="Max deviation of Extract air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="400" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_SFilter_SFFilterPDEMinMeasured" name_en="Pressure diff. of Supply filter, AHU min" name_fi="Tulosuod. yläraja, IV min" name_sv="Tilluftfilterns tryckdifferens, LB min" name_et="Supply filter pressure difference, AHU min" name_ru="Supply filter pressure difference, AHU min" name_lv="Supply filter pressure difference, AHU min" name_tr="Pressure diff. of Supply filter, AHU min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="390" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_SFilter_SFFilterPDEMaxMeasured" name_en="Pressure diff. of Supply filter, AHU max" name_fi="Tulosuod. yläraja, IV max" name_sv="Tilluftfilterns tryckdifferens, LB max" name_et="Supply filter pressure difference, AHU max" name_ru="Supply filter pressure difference, AHU max" name_lv="Supply filter pressure difference, AHU max" name_tr="Pressure diff. of Supply filter, AHU max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="392" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_SFilter_Setvalue" name_en="Alarm delay of Supply filter" name_fi="Tulosuod. hälytysviive" name_sv="Larm fördröjning av Tilluftens filter" name_et="Alarm activation delay" name_ru="Alarm activation delay" name_lv="Alarm activation delay" name_tr="Alarm delay of Supply filter" pointtype="3" registertype="Holding" addressformat="S32" addressindex="394" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_SFilter_Setvalue2" name_en="Low limit for alarm activation" name_fi="Tulosuod. alaraja" name_sv="Nedre aktiveringsgränsen för larm" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="396" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_Freeze_Setvalue" name_en="Alarm delay of frost protection" name_fi="Jäätymissuojan hälytysviive" name_sv="Larm fördröjning av Frostskydd" name_et="Alarm activation delay in seconds" name_ru="Alarm activation delay in seconds" name_lv="Alarm activation delay in seconds" name_tr="Alarm delay of frost protection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="402" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="G307_ALARMS_SFilter2_SFFilterPDEMinMeasured" name_en="Pressure diff. of Supply filter, AHU min" name_fi="Tulosuod. 2 yläraja, IV min" name_sv="Tilluftfilterns tryckdifferens, LB min" name_et="Supply filter pressure difference, AHU min" name_ru="Supply filter pressure difference, AHU min" name_lv="Supply filter pressure difference, AHU min" name_tr="Pressure diff. of Supply filter, AHU min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="404" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_SFilter2_SFFilterPDEMaxMeasured" name_en="Pressure diff. of Supply filter, AHU max" name_fi="Tulosuod. 2 yläraja, IV max" name_sv="Tilluftfilterns tryckdifferens, LB max" name_et="Supply filter pressure difference, AHU max" name_ru="Supply filter pressure difference, AHU max" name_lv="Supply filter pressure difference, AHU max" name_tr="Pressure diff. of Supply filter, AHU max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="406" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="900" />
      <point name="G307_ALARMS_SFilter2_Setvalue" name_en="Alarm delay of Supply filter" name_fi="Tulosuod. 2 hälytysviive" name_sv="Larm fördröjning av Tilluftens filter" name_et="Alarm activation delay" name_ru="Alarm activation delay" name_lv="Alarm activation delay" name_tr="Alarm delay of Supply filter" pointtype="3" registertype="Holding" addressformat="S32" addressindex="408" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="59" />
      <point name="G307_ALARMS_SFilter2_Setvalue2" name_en="Low limit for alarm activation" name_fi="Tulosuod. 2 alaraja" name_sv="Nedre aktiveringsgränsen för larm" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="410" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ALARMS_Recovery_Setvalue" name_en="Alarm activation delay in seconds" name_fi="Hälytysviive (s)" name_sv="Larm aktiveringsfördröjning i sekunder" pointtype="3" registertype="Holding" addressformat="S32" addressindex="412" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="G307_Manager3_Setvalue" name_en="AHU control" name_fi="IV-koneen ohjaus" name_sv="LB-styrning" name_et="Select" name_ru="Select" name_lv="Select" name_tr="AHU control" pointtype="3" registertype="Holding" addressformat="S32" addressindex="414" categorytype="3" enum="0=Automaatti;1=Seis käsin;2=1/2 käsin;3=1/1 käsin" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="G307_Manager3_Setvalue2" name_en="AHU conflict delay" name_fi="IV-koneen ristiriitaviive" name_sv="LB Konflikt fördröjning" name_et="DelayTime" name_ru="DelayTime" name_lv="DelayTime" name_tr="AHU conflict delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="416" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="600" />
      <point name="G307_Manager3_Setvalue3" name_en="AHU start delay" name_fi="IV-koneen käynnistysviive" name_sv="LB-aggregatets start fördröjning" name_et="OnDelay" name_ru="OnDelay" name_lv="OnDelay" name_tr="AHU start delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="418" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="G307_Manager3_Setvalue4" name_en="AHU stop delay" name_fi="IV-koneen pysäytysviive" name_sv="LB-aggregatets stopp fördröjning" name_et="OffDelay" name_ru="OffDelay" name_lv="OffDelay" name_tr="AHU stop delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="420" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue" name_en="P-area of cooling " name_fi="P-alue Jäähdytys" name_sv="P-band av kylning" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of cooling " pointtype="3" registertype="Holding" addressformat="S32" addressindex="422" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue2" name_en="I-time of supply air " name_fi="I-aika Tuloilma" name_sv="I-tid av Tilluft" name_et="" name_ru="" name_lv="I-time in seconds" name_tr="I-time of supply air " pointtype="3" registertype="Holding" addressformat="S32" addressindex="424" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue3" name_en="P-area of HRU" name_fi="P-alue LTO" name_sv="P-band av VÅV" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of HRU" pointtype="3" registertype="Holding" addressformat="S32" addressindex="426" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue5" name_en="P-area of heating radiator" name_fi="P-alue lämmityspatteri" name_sv="P-band av värmebatteri" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of heating radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="428" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue4" name_en="P-area of cascade" name_fi="P-alue Kaskadisäätö" name_sv="P-band av kaskadstyrning" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of cascade" pointtype="3" registertype="Holding" addressformat="S32" addressindex="430" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="200" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue6" name_en="I-time of cascade" name_fi="I-aika Kaskadisäätö" name_sv="I-tid av kaskadstyrning" name_et="" name_ru="" name_lv="I-time in seconds" name_tr="I-time of cascade" pointtype="3" registertype="Holding" addressformat="S32" addressindex="432" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="1000" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue8" name_en="Supply air minimum" name_fi="Tuloilman minimi" name_sv="Tilluftens min. temperatur" name_et="Output value when input value is In1" name_ru="Output value when input value is In1" name_lv="Output value when input value is In1" name_tr="Supply air minimum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="434" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue9" name_en="Supply air maximum" name_fi="Tuloilman maksimi" name_sv="Tilluftens max temperatur" name_et="Out2" name_ru="Out2" name_lv="Out2" name_tr="Supply air maximum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="436" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="15" max="30" />
      <point name="G307_ExhaustTempControl_TEMP3_Setvalue10" name_en="Zero energy zone" name_fi="Nollaenergia alue" name_sv="Värde 1 som man vill addera" name_et="Value 1 to add" name_ru="Value 1 to add" name_lv="Value 1 to add" name_tr="Value 1 to add" pointtype="3" registertype="Holding" addressformat="S32" addressindex="438" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G307_ExhaustTempControl_TEMP3_ExtractAirTempSetValue" name_en="Extract air temp. setting value" name_fi="Poistoilman asetusarvo" name_sv="Frånlufts temperaturens inställningsvärde" name_et="SetPoint" name_ru="SetPoint" name_lv="SetPoint" name_tr="Extract air temp. setting value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="440" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="G307_ExhaustTempControl_RecoveryPreHeat_Setvalue" name_en="P-area of HRU Supply air" name_fi="P-alue, LTO Tuloilma" name_sv="P-band av VÅV Tilluft" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of HRU Supply air" pointtype="3" registertype="Holding" addressformat="S32" addressindex="442" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_ExhaustTempControl_RecoveryPreHeat_Setvalue2" name_en="I-time of HRU Supply air" name_fi="I-aika , LTO Tuloilma" name_sv="I-tid av VÅV Tilluft" name_et="" name_ru="" name_lv="I-time in seconds" name_tr="I-time of HRU Supply air" pointtype="3" registertype="Holding" addressformat="S32" addressindex="444" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G307_ExhaustTempControl_RecoveryPreHeat_Setvalue3" name_en="HRU supply air setting value" name_fi="LTO tuloilman asetusarvo" name_sv="VÅV Tilluftens inställningsvärde" name_et="SetPoint" name_ru="SetPoint" name_lv="SetPoint" name_tr="HRU supply air setting value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="446" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="G307_ExhaustTempControl_Cooling_OutTempPermit_Setvalue" name_en="Outdoor temp.permit for cooling" name_fi="Ulkoilmalupa jäähdytykselle" name_sv="Utetemp. tillstånd för kylmaskin" name_et="Setpoint" name_ru="Setpoint" name_lv="Setpoint" name_tr="Outdoor temp.permit for cooling" pointtype="3" registertype="Holding" addressformat="S32" addressindex="448" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="30" />
      <point name="G307_ExhaustTempControl_Cooling_TempPermit_Setvalue" name_en="Cooling hysteresis" name_fi="Jäähdytyksen eroalue" name_sv="Kylning hysteresis" name_et="Setpoint" name_ru="Setpoint" name_lv="Setpoint" name_tr="Cooling hysteresis" pointtype="3" registertype="Holding" addressformat="S32" addressindex="450" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue" name_en="Output value when input value is In1" name_fi="LTO:n sulatusraja, IV min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="452" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue2" name_en="Out2" name_fi="LTO:n sulatusraja, IV max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="454" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue3" name_en="HRU defrost hysteresis" name_fi="LTO:n sulatuksen eroalue" name_sv="VÅV avfrostining hysteres" name_et="Value 1 to add" name_ru="Value 1 to add" name_lv="Value 1 to add" name_tr="HRU defrost hysteresis" pointtype="3" registertype="Holding" addressformat="S32" addressindex="456" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="500" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue4" name_en="HRU state during defrost" name_fi="LTO:n sulatusasento" name_sv="VÅV tillstånd under avfrostning " name_et="Output value when input value is In1" name_ru="Output value when input value is In1" name_lv="Output value when input value is In1" name_tr="HRU state during defrost" pointtype="3" registertype="Holding" addressformat="S32" addressindex="458" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue5" name_en="HRU defrostning time" name_fi="LTO Sulatusjakson aika" name_sv="VÅV avfrostning tid" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="HRU defrostning time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="460" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="60" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue6" name_en="Frost prevention outdoor temp. limit " name_fi="Ulkoilmaraja huurteenestolle" name_sv="Frostskydd utetemp. gräns " name_et="Setpoint" name_ru="Setpoint" name_lv="Setpoint" name_tr="Frost prevention outdoor temp. limit " pointtype="3" registertype="Holding" addressformat="S32" addressindex="462" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-30" max="20" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Setvalue7" name_en="Defrosting maximum number" name_fi="Sulatuskertojen maksimi määrä" name_sv="Avfrostning maximal antal " name_et="B1" name_ru="B1" name_lv="B1" name_tr="Defrosting maximum number" pointtype="3" registertype="Holding" addressformat="S32" addressindex="464" categorytype="3" unit="kpl" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G307_ExhaustTempControl_HeatingFluid_P_RetWaterCtrl" name_en="P-area, heating radiator return water" name_fi="P-alue, lämmityspatterin paluuvesi" name_sv="P-band, returvatten av värmebatteri " name_et="P-area, preheating radioator return water" name_ru="P-area, preheating radioator return water" name_lv="P-area, heating radioator return water" name_tr="P-area, heating radiator return water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="466" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_ExhaustTempControl_HeatingFluid_I_RetWaterCtrl" name_en="I-time, heating radioator return water" name_fi="I-aika, lämmityspatterin paluuvesi" name_sv="I-tid, returvatten av värmebatteri" name_et="I-time, return water temperature" name_ru="I-time, return water temperature" name_lv="I-time, heating radioator return water" name_tr="I-time, heating radioator return water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="468" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Setvalue" name_en="Return water setting when AHU runs" name_fi="Paluuvesi käy asetus" name_sv="Returvat. inst.värde när LB är i drift" name_et="Minimum limit for Output" name_ru="Minimum limit for Output" name_lv="Minimum limit for Output" name_tr="Return water setting when AHU runs" pointtype="3" registertype="Holding" addressformat="S32" addressindex="470" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="50" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Setvalue2" name_en="Return w. setting when AHU is stopped" name_fi="Paluuvesi seis asetus" name_sv="Returvat. inst.värde när LB är stopped" name_et="Maximum limit for Output" name_ru="Maximum limit for Output" name_lv="Maximum limit for Output" name_tr="Return w. setting when AHU is stopped" pointtype="3" registertype="Holding" addressformat="S32" addressindex="472" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="50" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Setvalue3" name_en="Heating radiator value time of changing setting" name_fi="Lämm.patterin asetuksen muutosaika" name_sv="Förändringstid av värmebat. inst. värde" name_et="Value to be multiplied" name_ru="Value to be multiplied" name_lv="Value to be multiplied" name_tr="Heating radiator value time of changing setting" pointtype="3" registertype="Holding" addressformat="S32" addressindex="474" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G307_ExhaustTempControl_RecoveryCool_Setvalue" name_en="Hysteresis of HRU ON (cool.energy)" name_fi="Eroalue LTO päälle (jäähd.energia)" name_sv="Hysteres av VÅV På (Kylenergi)" name_et="Value B" name_ru="Value B" name_lv="Value B" name_tr="Hysteresis of HRU ON (cool.energy)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="476" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="10" />
      <point name="G307_ExhaustTempControl_RecoveryCool_Setvalue2" name_en="Hysteresis of  HRU OFF (cool.energy)" name_fi="Eroalue  LTO pois päälltä (jäähd.energia)" name_sv="Hysteres av VÅV Av (Kylenergi)" name_et="Value B" name_ru="Value B" name_lv="Value B" name_tr="Hysteresis of  HRU OFF (cool.energy)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="478" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="5" />
      <point name="G307_ExhaustTempControl_RecoveryEfficiency_Setvalue" name_en="HRU efficiency min limit" name_fi="LTO Hyötysuhde alaraja" name_sv="VÅV verkningsgrad nedre gräns" name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="HRU efficiency min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="480" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_ExhaustTempControl_RecoveryEfficiency_Setvalue2" name_en="Alarm activation delay" name_fi="LTO Hyötysuhde hälytysviive" name_sv="Larm aktiveringsfördröjning i sekunder" pointtype="3" registertype="Holding" addressformat="S32" addressindex="482" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="G307_ExhaustTempControl_RecoveryStartUp_Setvalue" name_en="HRU's position start-up situation" name_fi="LTO:n asento käynnistystilanteessa" name_sv="VÅV position uppstart situation" name_et="Input1" name_ru="Input1" name_lv="Input1" name_tr="HRU's position start-up situation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="484" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_SFanPE2_Setvalue" name_en="P-area of supply air pressure" name_fi="P-alue Tuloilman paine" name_sv="P-band av tillufts tryck" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of supply air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="486" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_SFanPE2_Setvalue2" name_en="I-time of supply air pressure" name_fi="I-aika Tuloilman paine" name_sv="I-tid av tilluftens tryck" name_et="" name_ru="" name_lv="I-time in seconds" name_tr="I-time of supply air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="488" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G307_SFanPE2_Setvalue3" name_en="Maximum speed of Frequence converter " name_fi="Tulopuh. maksiminopeus" name_sv="Max. hastighet av frekvensomformare" name_et="Output value when input value is In1" name_ru="Output value when input value is In1" name_lv="Output value when input value is In1" name_tr="Maximum speed of Frequence converter " pointtype="3" registertype="Holding" addressformat="S32" addressindex="490" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_SFanPE2_Setvalue4" name_en="Minimum speed of Frequence converter " name_fi="Tulopuh. miniminopeus" name_sv="Min. hastighet av frekvensomformare" name_et="Output value when input value is In1" name_ru="Output value when input value is In1" name_lv="Output value when input value is In1" name_tr="Minimum speed of Frequence converter " pointtype="3" registertype="Holding" addressformat="S32" addressindex="492" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_SFanPE2_Setvalue5" name_en="Supply air min. pressure " name_fi="Tuloilman minimipaine" name_sv="Tilluftens min tryck" name_et="Input0" name_ru="Input0" name_lv="Input0" name_tr="Supply air min. pressure " pointtype="3" registertype="Holding" addressformat="S32" addressindex="494" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_SFanPE2_Setvalue6" name_en="Supply air max pressure" name_fi="Tuloilman maksimipaine" name_sv="Tilluftens max tryck" name_et="Input1" name_ru="Input1" name_lv="Input1" name_tr="Supply air max pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="496" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_EFanPE2_Setvalue" name_en="P-area of Extract air pressure" name_fi="P-alue, Poistoilma paine" name_sv="P-band av Frånluftens tryck" name_et="" name_ru="" name_lv="P-area" name_tr="P-area of Extract air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="498" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G307_EFanPE2_Setvalue2" name_en="I-time of Extract air pressure" name_fi="I-aika,  Poistoilma paine" name_sv="I-tid av Frånluftens tryck" name_et="" name_ru="" name_lv="I-time in seconds" name_tr="I-time of Extract air pressure" pointtype="3" registertype="Holding" addressformat="S32" addressindex="500" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G307_EFanPE2_Setvalue3" name_en="Min. pressure of Extract air " name_fi="Poistoilman minimipaine" name_sv="Frånluftens min. tryck" name_et="Input0" name_ru="Input0" name_lv="Input0" name_tr="Min. pressure of Extract air " pointtype="3" registertype="Holding" addressformat="S32" addressindex="502" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_EFanPE2_Setvalue4" name_en="Max pressure of Extract air " name_fi="Poistoilman maksimipaine" name_sv="Fränluftens max tryck" name_et="Input1" name_ru="Input1" name_lv="Input1" name_tr="Max pressure of Extract air " pointtype="3" registertype="Holding" addressformat="S32" addressindex="504" categorytype="3" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2500" />
      <point name="G307_EFanPE2_Setvalue5" name_en="Output value when input value is In1" name_fi="Poistopuh. miniminopeus" pointtype="3" registertype="Holding" addressformat="S32" addressindex="506" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G307_EFanPE2_Setvalue6" name_en="Out2" name_fi="Poistopuh. maksiminopeus" pointtype="3" registertype="Holding" addressformat="S32" addressindex="508" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
    </group>
    <group categorytype="2" name="Mittaukset" name_en="Measurements" name_fi="Mittaukset" name_sv="Mätningar" name_et="Mõõtmised" name_ru="Измерения" name_lv="Mērījumi" name_tr="Ölçümler " name_pl="Pomiary">
      <point name="TC07TE00IN" name_en="Outdoor temperature" name_fi="Ulkolämpötila väylältä" name_sv="Utetemperatur" name_et="Välistemperatuur" name_ru="" name_lv="" name_tr="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="362" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="TC07EMSIN" name_en="Emergency STOP" name_fi="IV-Pysäytys väylältä" name_sv="Nöd STOPP" name_et="" name_ru="" name_lv="" name_tr="" pointtype="10" registertype="Holding" addressformat="U16" addressindex="364" categorytype="2" enum="0=Ei aktiivinen;1=Aktiivinen" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_Measure" name_en="Output3" name_fi="Ulkolämpörajoitus aktiivinen" name_sv="Termostat utgång" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="U16" addressindex="311" categorytype="2" enum="0=Ei;1=Kyllä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_ALARMS_EFilter_SFFilterAlarmLimit" name_en="Alarm limit of Calculated supply filter " name_fi="Poistosuod. laskenn. hälytysraja" name_sv="Beräknad larmgräns av Frånluftfilter" name_et="Calculated supply filter alarm limit" name_ru="Calculated supply filter alarm limit" name_lv="Calculated supply filter alarm limit" name_tr="Alarm limit of Calculated supply filter " pointtype="10" registertype="Holding" addressformat="S32" addressindex="312" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ALARMS_SFilter_SFFilterAlarmLimit" name_en="Calculated alarm limit of supply filter" name_fi="Tulosuod. laskennall. hälytysraja" name_sv="Beräknad larmgräns av Tilluftens filter" name_et="Calculated supply filter alarm limit" name_ru="Calculated supply filter alarm limit" name_lv="Calculated supply filter alarm limit" name_tr="Calculated alarm limit of supply filter" pointtype="10" registertype="Holding" addressformat="S32" addressindex="314" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ALARMS_SFilter2_SFFilterAlarmLimit" name_en="Calculated alarm limit of supply filter" name_fi="Tulosuod. 2 laskennall. hälytysraja" name_sv="Beräknad larmgräns av Tilluftens filter" name_et="Calculated supply filter alarm limit" name_ru="Calculated supply filter alarm limit" name_lv="Calculated supply filter alarm limit" name_tr="Calculated alarm limit of supply filter" pointtype="10" registertype="Holding" addressformat="S32" addressindex="316" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_Manager3_Measure" name_en="State" name_fi="Tila" name_sv="Läge" name_et="StateOut" name_ru="StateOut" name_lv="StateOut" name_tr="State" pointtype="10" registertype="Holding" addressformat="S32" addressindex="318" categorytype="2" enum="0=Seis;1=Päällä;2=1/1 ohjaus" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_Manager3_Measure2" name_en="Control" name_fi="Ohjaus" name_sv="Styrning" name_et="StateOut" name_ru="StateOut" name_lv="StateOut" name_tr="Control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="320" categorytype="2" enum="0=Seis;1=Päällä;2=1/1 ohjaus" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_Manager3_Measure3" name_en="State of AHU " name_fi="IV-koneen tila" name_sv="Läge av LB-aggregat" name_et="Output" name_ru="Output" name_lv="Output" name_tr="State of AHU " pointtype="10" registertype="Holding" addressformat="S32" addressindex="322" categorytype="2" enum="-1=Seis Ristiriitaisesti;0=Seis;1=Käynnistymässä;2=1/2;3=1/1;4=Pysähtymässä;5=Päällä Ristiriitaisesti" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ExhaustTempControl_TEMP3_SupplyAirCalcSetValue" name_en="Supply air calculated setting value" name_fi="Tuloilman laskennallinen asetusarvo" name_sv="Tillufts beräknad inställningsvärde" name_et="Output" name_ru="Output" name_lv="Output" name_tr="Supply air calculated setting value" pointtype="10" registertype="Holding" addressformat="S32" addressindex="324" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ExhaustTempControl_Cooling_OutTempPermit_Measure" name_en="Outdoor temp.permit for cooling" name_fi="Ulkolämpötilalupa jäähdytykselle" name_sv="Utetemp. tillstånd för kylmaskin" name_et="" name_ru="" name_lv="Output3" name_tr="Outdoor temp.permit for cooling" pointtype="10" registertype="Holding" addressformat="U16" addressindex="326" categorytype="2" enum="0=Estetty;1=Sallittu" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_ExhaustTempControl_Cooling_TempPermit_Measure" name_en="Extract air permit for cooling" name_fi="Poistolämpö lupa jäähdytykselle" name_sv="Frånluft tillstånd för kylmaskin" name_et="" name_ru="" name_lv="Output3" name_tr="Extract air permit for cooling" pointtype="10" registertype="Holding" addressformat="U16" addressindex="327" categorytype="2" enum="0=Estetty;1=Sallittu" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_HRUCalDefFrotLimit" name_en="Calculated defrost limit " name_fi="Laskennallinen sulatusraja" name_sv="Beräknat avfrostning gräns " name_et="Output" name_ru="Output" name_lv="Output" name_tr="Calculated defrost limit " pointtype="10" registertype="Holding" addressformat="S32" addressindex="328" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Measure" name_en="Outdoor temp. permit for frost prevention" name_fi="Ulkoilmalupa huurteenesto" name_sv="Utetemp. tillstånd för frostskydd " name_et="" name_ru="" name_lv="Output3" name_tr="Outdoor temp. permit for frost prevention" pointtype="10" registertype="Holding" addressformat="U16" addressindex="330" categorytype="2" enum="0=Estetty;1=Sallittu" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Measure2" name_en="HRU Frost prevention" name_fi="LTO Huurteen esto" name_sv="VÅV Frostskydd" name_et="Result of logical OR operation" name_ru="Result of logical OR operation" name_lv="Result of logical OR operation" name_tr="HRU Frost prevention" pointtype="10" registertype="Holding" addressformat="U16" addressindex="331" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Measure" name_en="State of heating phase" name_sv="Läge av värmesteg" name_fi="Lämmitysportaan tila" name_et="Input number where maximum value locates" name_ru="Input number where maximum value locates" name_lv="Input number where maximum value locates" name_tr="State of heating phase" pointtype="10" registertype="Holding" addressformat="S32" addressindex="332" categorytype="2" enum="1=Normaali säätö;2=Paluuvesirajoitus;3=Ennakointi" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Measure2" name_en="Calculated value of heat.radiator return water" name_fi="Paluuveden laskennall. asetus" name_sv="Beräknad inst. värde av värmebatteri returvatten" name_et="Output signal" name_ru="Output signal" name_lv="Output signal" name_tr="Calculated value of heat.radiator return water" pointtype="10" registertype="Holding" addressformat="S32" addressindex="334" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_ExhaustTempControl_RecoveryEfficiency_Measure" name_en="Minumum value" name_fi="Hyötysuhde LTO" name_sv="Minimum värdet" name_et="Minumum value" name_ru="Minumum value" name_lv="Minumum value" name_tr="Minumum value" pointtype="10" registertype="Holding" addressformat="S32" addressindex="336" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_SFanPE2_SPressureSet" name_en="Supply air calculated pressure setting" name_fi="Tuloilman laskennal. paineasetus" name_sv="Tilluftens beräknad tryck inställning" name_et="Output" name_ru="Output" name_lv="Output" name_tr="Supply air calculated pressure setting" pointtype="10" registertype="Holding" addressformat="S32" addressindex="338" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G307_EFanPE2_EPressureSet" name_en="Extract air calculater pressure setting" name_fi="Poistoilman laskennal. paineasetus" name_sv="Frånluftens beräknad tryck inställning" name_et="Output" name_ru="Output" name_lv="Output" name_tr="Extract air calculater pressure setting" pointtype="10" registertype="Holding" addressformat="S32" addressindex="340" categorytype="2" unit="Pa" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
    </group>
    <group categorytype="1" name="Käsiajo" name_en="Manual control" name_fi="Käsiajo" name_sv="Manuell styrning" name_et="käsijuhtimisrežiim" name_ru="Ручной режим" name_lv="Rokas vadība" name_tr="Manuel kontrol " name_pl="Sterowanie ręczne">
      <point name="UI 1_mc" name_en="UI 1 Manual control" name_fi="Tuloilma LTO:n jälkeen Käsiajo" name_sv="UI 1 Manuell styrning" name_et="UI 1 käsijuhtimisrežiim" name_ru="UI 1 Ручной режим" name_lv="UI 1 Rokas vadība" name_tr="UI 1 Manuel kontrol " name_pl="UI 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="271" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 2_mc" name_en="UI 2 Manual control" name_fi="Tuloilman lämpötila Käsiajo" name_sv="UI 2 Manuell styrning" name_et="UI 2 käsijuhtimisrežiim" name_ru="UI 2 Ручной режим" name_lv="UI 2 Rokas vadība" name_tr="UI 2 Manuel kontrol " name_pl="UI 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="272" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 3_mc" name_en="UI 3 Manual control" name_fi="Poistoilman lämpötila Käsiajo" name_sv="UI 3 Manuell styrning" name_et="UI 3 käsijuhtimisrežiim" name_ru="UI 3 Ручной режим" name_lv="UI 3 Rokas vadība" name_tr="UI 3 Manuel kontrol " name_pl="UI 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="273" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 4_mc" name_en="UI 4 Manual control" name_fi="Jäteilman lämpötila Käsiajo" name_sv="UI 4 Manuell styrning" name_et="UI 4 käsijuhtimisrežiim" name_ru="UI 4 Ручной режим" name_lv="UI 4 Rokas vadība" name_tr="UI 4 Manuel kontrol " name_pl="UI 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="274" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 5_mc" name_en="UI 5 Manual control" name_fi="Tulosuodatin paine-ero Käsiajo" name_sv="UI 5 Manuell styrning" name_et="UI 5 käsijuhtimisrežiim" name_ru="UI 5 Ручной режим" name_lv="UI 5 Rokas vadība" name_tr="UI 5 Manuel kontrol " name_pl="UI 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="275" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 6_mc" name_en="UI 6 Manual control" name_fi="Poistosuodatin paine-ero Käsiajo" name_sv="UI 6 Manuell styrning" name_et="UI 6 käsijuhtimisrežiim" name_ru="UI 6 Ручной режим" name_lv="UI 6 Rokas vadība" name_tr="UI 6 Manuel kontrol " name_pl="UI 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="276" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 7_mc" name_en="UI 7 Manual control" name_fi="LTO:n paine-ero Käsiajo" name_sv="UI 7 Manuell styrning" name_et="UI 7 käsijuhtimisrežiim" name_ru="UI 7 Ручной режим" name_lv="UI 7 Rokas vadība" name_tr="UI 7 Manuel kontrol " name_pl="UI 7 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="277" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 8_mc" name_en="UI 8 Manual control" name_fi="Tuloilmamäärä Käsiajo" name_sv="UI 8 Manuell styrning" name_et="UI 8 käsijuhtimisrežiim" name_ru="UI 8 Ручной режим" name_lv="UI 8 Rokas vadība" name_tr="UI 8 Manuel kontrol " name_pl="UI 8 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="278" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 9_mc" name_en="UI 9 Manual control" name_fi="Poistoilmamäärä Käsiajo" name_sv="UI 9 Manuell styrning" name_et="UI 9 käsijuhtimisrežiim" name_ru="UI 9 Ручной режим" name_lv="UI 9 Rokas vadība" name_tr="UI 9 Manuel kontrol " name_pl="UI 9 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="279" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 10_mc" name_en="UI 10 Manual control" name_fi="LTO kiekko häl. Käsiajo" name_sv="UI 10 Manuell styrning" name_et="UI 10 käsijuhtimisrežiim" name_ru="UI 10 Ручной режим" name_lv="UI 10 Rokas vadība" name_tr="UI 10 Manuel kontrol " name_pl="UI 10 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="280" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 11_mc" name_en="UI 11 Manual control" name_fi="Tulosuodatin 2 paine-ero Käsiajo" name_sv="UI 11 Manuell styrning" name_et="UI 11 käsijuhtimisrežiim" name_ru="UI 11 Ручной режим" name_lv="UI 11 Rokas vadība" name_tr="UI 11 Manuel kontrol " name_pl="UI 11 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="281" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 12_mc" name_en="UI 12 Manual control" name_fi="LP Paluuveden lämpötila Käsiajo" name_sv="UI 12 Manuell styrning" name_et="UI 12 käsijuhtimisrežiim" name_ru="UI 12 Ручной режим" name_lv="UI 12 Rokas vadība" name_tr="UI 12 Manuel kontrol " name_pl="UI 12 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="282" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 13_mc" name_en="UI 13 Manual control" name_fi="Tulopuhallin liiketila tila Käsiajo" name_sv="UI 13 Manuell styrning" name_et="UI 13 käsijuhtimisrežiim" name_ru="UI 13 Ручной режим" name_lv="UI 13 Rokas vadība" name_tr="UI 13 Manuel kontrol " name_pl="UI 13 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="283" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 14_mc" name_en="UI 14 Manual control" name_fi="Tuloilma kanavapaine Käsiajo" name_sv="UI 14 Manuell styrning" name_et="UI 14 käsijuhtimisrežiim" name_ru="UI 14 Ручной режим" name_lv="UI 14 Rokas vadība" name_tr="UI 14 Manuel kontrol " name_pl="UI 14 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="284" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 15_mc" name_en="UI 15 Manual control" name_fi="Poistopuhallin liiketila tila Käsiajo" name_sv="UI 15 Manuell styrning" name_et="UI 15 käsijuhtimisrežiim" name_ru="UI 15 Ручной режим" name_lv="UI 15 Rokas vadība" name_tr="UI 15 Manuel kontrol " name_pl="UI 15 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="285" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 16_mc" name_en="UI 16 Manual control" name_fi="Poistoilma kanavapaine Käsiajo" name_sv="UI 16 Manuell styrning" name_et="UI 16 käsijuhtimisrežiim" name_ru="UI 16 Ручной режим" name_lv="UI 16 Rokas vadība" name_tr="UI 16 Manuel kontrol " name_pl="UI 16 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="286" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 1_mc" name_en="DI 1 Manual control" name_fi="LP Pumppu tila Käsiajo" name_sv="DI 1 Manuell styrning" name_et="DI 1 käsijuhtimisrežiim" name_ru="DI 1 Ручной режим" name_lv="DI 1 Rokas vadība" name_tr="DI 1 Manuel kontrol " name_pl="DI 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="287" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 2_mc" name_en="DI 2 Manual control" name_fi="Jäätymissuoja häl. Käsiajo" name_sv="DI 2 Manuell styrning" name_et="DI 2 käsijuhtimisrežiim" name_ru="DI 2 Ручной режим" name_lv="DI 2 Rokas vadība" name_tr="DI 2 Manuel kontrol " name_pl="DI 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="288" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="PFI_mc" name_en="Internal power failure indication Manual control" name_fi="Internal power failure indication Käsiajo" name_sv="Internal power failure indication Manuell styrning" name_et="Internal power failure indication käsijuhtimisrežiim" name_ru="Internal power failure indication Ручной режим" name_lv="Internal power failure indication Rokas vadība" name_tr="Internal power failure indication Manuel kontrol " name_pl="Internal power failure indication Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="289" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 1_mc" name_en="AO 1 Manual control" name_fi="LP venttiili säätö Käsiajo" name_sv="AO 1 Manuell styrning" name_et="AO 1 käsijuhtimisrežiim" name_ru="AO 1 Ручной режим" name_lv="AO 1 Rokas vadība" name_tr="AO 1 Manuel kontrol " name_pl="AO 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="290" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 2_mc" name_en="AO 2 Manual control" name_fi="AO 2 Käsiajo" name_sv="AO 2 Manuell styrning" name_et="AO 2 käsijuhtimisrežiim" name_ru="AO 2 Ручной режим" name_lv="AO 2 Rokas vadība" name_tr="AO 2 Manuel kontrol " name_pl="AO 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="291" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 3_mc" name_en="AO 3 Manual control" name_fi="Tulopuh. liiketila säätö Käsiajo" name_sv="AO 3 Manuell styrning" name_et="AO 3 käsijuhtimisrežiim" name_ru="AO 3 Ручной режим" name_lv="AO 3 Rokas vadība" name_tr="AO 3 Manuel kontrol " name_pl="AO 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="292" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 4_mc" name_en="AO 4 Manual control" name_fi="Poistopuh. liiketila säätö Käsiajo" name_sv="AO 4 Manuell styrning" name_et="AO 4 käsijuhtimisrežiim" name_ru="AO 4 Ручной режим" name_lv="AO 4 Rokas vadība" name_tr="AO 4 Manuel kontrol " name_pl="AO 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="293" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 5_mc" name_en="AO 5 Manual control" name_fi="LTO Kiekko säätö Käsiajo" name_sv="AO 5 Manuell styrning" name_et="AO 5 käsijuhtimisrežiim" name_ru="AO 5 Ручной режим" name_lv="AO 5 Rokas vadība" name_tr="AO 5 Manuel kontrol " name_pl="AO 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="294" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 6_mc" name_en="AO 6 Manual control" name_fi="JP venttiili säätö Käsiajo" name_sv="AO 6 Manuell styrning" name_et="AO 6 käsijuhtimisrežiim" name_ru="AO 6 Ручной режим" name_lv="AO 6 Rokas vadība" name_tr="AO 6 Manuel kontrol " name_pl="AO 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="295" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 1_mc" name_en="TR 1 Manual control" name_fi="Raitisilmapelti ohjaus Käsiajo" name_sv="TR 1 Manuell styrning" name_et="TR 1 käsijuhtimisrežiim" name_ru="TR 1 Ручной режим" name_lv="TR 1 Rokas vadība" name_tr="TR 1 Manuel kontrol " name_pl="TR 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="296" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 2_mc" name_en="TR 2 Manual control" name_fi="Jäteilmapelti ohjaus Käsiajo" name_sv="TR 2 Manuell styrning" name_et="TR 2 käsijuhtimisrežiim" name_ru="TR 2 Ручной режим" name_lv="TR 2 Rokas vadība" name_tr="TR 2 Manuel kontrol " name_pl="TR 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="297" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 3_mc" name_en="TR 3 Manual control" name_fi="TR 3 Käsiajo" name_sv="TR 3 Manuell styrning" name_et="TR 3 käsijuhtimisrežiim" name_ru="TR 3 Ручной режим" name_lv="TR 3 Rokas vadība" name_tr="TR 3 Manuel kontrol " name_pl="TR 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="298" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 4_mc" name_en="TR 4 Manual control" name_fi="TR 4 Käsiajo" name_sv="TR 4 Manuell styrning" name_et="TR 4 käsijuhtimisrežiim" name_ru="TR 4 Ручной режим" name_lv="TR 4 Rokas vadība" name_tr="TR 4 Manuel kontrol " name_pl="TR 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="299" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R1_mc" name_en="R1 Manual control" name_fi="Tulopuh. liiketila ohj. Käsiajo" name_sv="R1 Manuell styrning" name_et="R1 käsijuhtimisrežiim" name_ru="R1 Ручной режим" name_lv="R1 Rokas vadība" name_tr="R1 Manuel kontrol " name_pl="R1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="300" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R2_mc" name_en="R2 Manual control" name_fi="Poistopuh. liiketila ohj. Käsiajo" name_sv="R2 Manuell styrning" name_et="R2 käsijuhtimisrežiim" name_ru="R2 Ручной режим" name_lv="R2 Rokas vadība" name_tr="R2 Manuel kontrol " name_pl="R2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="301" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R3_mc" name_en="R3 Manual control" name_fi="LTO Kiekko ohj. Käsiajo" name_sv="R3 Manuell styrning" name_et="R3 käsijuhtimisrežiim" name_ru="R3 Ручной режим" name_lv="R3 Rokas vadība" name_tr="R3 Manuel kontrol " name_pl="R3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="302" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R4_mc" name_en="R4 Manual control" name_fi="R4 Käsiajo" name_sv="R4 Manuell styrning" name_et="R4 käsijuhtimisrežiim" name_ru="R4 Ручной режим" name_lv="R4 Rokas vadība" name_tr="R4 Manuel kontrol " name_pl="R4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="303" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R5_mc" name_en="R5 Manual control" name_fi="R5 Käsiajo" name_sv="R5 Manuell styrning" name_et="R5 käsijuhtimisrežiim" name_ru="R5 Ручной режим" name_lv="R5 Rokas vadība" name_tr="R5 Manuel kontrol " name_pl="R5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="304" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R6_mc" name_en="R6 Manual control" name_fi="R6 Käsiajo" name_sv="R6 Manuell styrning" name_et="R6 käsijuhtimisrežiim" name_ru="R6 Ручной режим" name_lv="R6 Rokas vadība" name_tr="R6 Manuel kontrol " name_pl="R6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="305" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_Measure_mc" name_en="Output3 Manual control" name_fi="Ulkolämpörajoitus aktiivinen Käsiajo" name_sv="Termostat utgång Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="342" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ALARMS_EFilter_SFFilterAlarmLimit_mc" name_en="Alarm limit of Calculated supply filter  Manual control" name_fi="Poistosuod. laskenn. hälytysraja Käsiajo" name_sv="Beräknad larmgräns av Frånluftfilter Manuell styrning" name_et="Calculated supply filter alarm limit käsijuhtimisrežiim" name_ru="Calculated supply filter alarm limit Ручной режим" name_lv="Calculated supply filter alarm limit Rokas vadība" name_tr="Alarm limit of Calculated supply filter  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="343" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ALARMS_SFilter_SFFilterAlarmLimit_mc" name_en="Calculated alarm limit of supply filter Manual control" name_fi="Tulosuod. laskennall. hälytysraja Käsiajo" name_sv="Beräknad larmgräns av Tilluftens filter Manuell styrning" name_et="Calculated supply filter alarm limit käsijuhtimisrežiim" name_ru="Calculated supply filter alarm limit Ручной режим" name_lv="Calculated supply filter alarm limit Rokas vadība" name_tr="Calculated alarm limit of supply filter Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="344" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ALARMS_SFilter2_SFFilterAlarmLimit_mc" name_en="Calculated alarm limit of supply filter Manual control" name_fi="Tulosuod. 2 laskennall. hälytysraja Käsiajo" name_sv="Beräknad larmgräns av Tilluftens filter Manuell styrning" name_et="Calculated supply filter alarm limit käsijuhtimisrežiim" name_ru="Calculated supply filter alarm limit Ручной режим" name_lv="Calculated supply filter alarm limit Rokas vadība" name_tr="Calculated alarm limit of supply filter Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="345" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_Manager3_Measure3_mc" name_en="State of AHU  Manual control" name_fi="IV-koneen tila Käsiajo" name_sv="Läge av LB-aggregat Manuell styrning" name_et="Output käsijuhtimisrežiim" name_ru="Output Ручной режим" name_lv="Output Rokas vadība" name_tr="State of AHU  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="346" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_Cooling_OutTempPermit_Measure_mc" name_en="Outdoor temp.permit for cooling Manual control" name_fi="Ulkolämpötilalupa jäähdytykselle Käsiajo" name_sv="Utetemp. tillstånd för kylmaskin Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" name_lv="Output3 Rokas vadība" name_tr="Outdoor temp.permit for cooling Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="347" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_Cooling_TempPermit_Measure_mc" name_en="Extract air permit for cooling Manual control" name_fi="Poistolämpö lupa jäähdytykselle Käsiajo" name_sv="Frånluft tillstånd för kylmaskin Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" name_lv="Output3 Rokas vadība" name_tr="Extract air permit for cooling Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="348" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_HRUCalDefFrotLimit_mc" name_en="Calculated defrost limit  Manual control" name_fi="Laskennallinen sulatusraja Käsiajo" name_sv="Beräknat avfrostning gräns  Manuell styrning" name_et="Output käsijuhtimisrežiim" name_ru="Output Ручной режим" name_lv="Output Rokas vadība" name_tr="Calculated defrost limit  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="349" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_Measure2_mc" name_en="HRU Frost prevention Manual control" name_fi="LTO Huurteen esto Käsiajo" name_sv="VÅV Frostskydd Manuell styrning" name_et="Result of logical OR operation käsijuhtimisrežiim" name_ru="Result of logical OR operation Ручной режим" name_lv="Result of logical OR operation Rokas vadība" name_tr="HRU Frost prevention Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="350" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_HeatingFluid_Measure2_mc" name_en="Calculated value of heat.radiator return water Manual control" name_fi="Paluuveden laskennall. asetus Käsiajo" name_sv="Beräknad inst. värde av värmebatteri returvatten Manuell styrning" name_et="Output signal käsijuhtimisrežiim" name_ru="Output signal Ручной режим" name_lv="Output signal Rokas vadība" name_tr="Calculated value of heat.radiator return water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="351" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G307_ExhaustTempControl_RecoveryEfficiency_Measure_mc" name_en="Minumum value Manual control" name_fi="Hyötysuhde LTO Käsiajo" name_sv="Minimum värdet Manuell styrning" name_et="Minumum value käsijuhtimisrežiim" name_ru="Minumum value Ручной режим" name_lv="Minumum value Rokas vadība" name_tr="Minumum value Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="352" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
    </group>
    <group categorytype="4" name="Hälytykset" name_en="Alarms" name_fi="Hälytykset" name_sv="Larm" name_et="Alarmid" name_ru="Аварийные сигналы" name_lv="Trauksmes" name_tr="Alarmlar " name_pl="Alarmy">
      <point name="BaseCard_Error" name_en="Device's base IO (MB1.BaseCard) not response" name_fi="Laitteen perus IO (MB1.BaseCard) ei vastaa" name_sv="Enhetens basen IO (MB1.BaseCard) svarar inte" name_et="Seade põhi IO (MB1.BaseCard) ei vasta" name_ru="Устройство MB1.BaseCard не отвечает " name_lv="Ierīces base IO (MB1.BaseCard) nav atbildes" name_tr="Cihazın temel IO (MB1.BaseCard) yanıt yok" name_pl="Urządzenie główne IO (MB1.BaseCard) nie odpowiada" pointid="TC07.BaseCard_Error.A" addressindex="306" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="0" severity="1" alarmid="#A0" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_1" name_en="Sensor fault BaseCard UI 1" name_fi="Anturivika TE02 Tuloilma LTO:n jälkeen" name_sv="Sensorfel BaseCard UI 1" name_et="Sensori viga BaseCard UI 1" name_ru="Неисправность датчика BaseCard UI 1" name_lv="Sensora kļūda BaseCard UI 1" name_tr="Sensör hatası  BaseCard UI 1" name_pl="Błąd czujnika BaseCard UI 1" pointid="TC07.TE02.SE" refpointid="TC07.G307.TE02.M" addressindex="307" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="1" severity="2" alarmid="#A1" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_2" name_en="Sensor fault BaseCard UI 2" name_fi="Anturivika TE10 Tuloilman lämpö" name_sv="Sensorfel BaseCard UI 2" name_et="Sensori viga BaseCard UI 2" name_ru="Неисправность датчика BaseCard UI 2" name_lv="Sensora kļūda BaseCard UI 2" name_tr="Sensör hatası  BaseCard UI 2" name_pl="Błąd czujnika BaseCard UI 2" pointid="TC07.TE10.SE" refpointid="TC07.G307.TE10.M" addressindex="308" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="2" severity="2" alarmid="#A2" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_3" name_en="Sensor fault BaseCard UI 3" name_fi="Anturivika TE19 Poistoilman lämpö" name_sv="Sensorfel BaseCard UI 3" name_et="Sensori viga BaseCard UI 3" name_ru="Неисправность датчика BaseCard UI 3" name_lv="Sensora kļūda BaseCard UI 3" name_tr="Sensör hatası  BaseCard UI 3" name_pl="Błąd czujnika BaseCard UI 3" pointid="TC07.TE19.SE" refpointid="TC07.G307.TE19.M" addressindex="309" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="3" severity="2" alarmid="#A3" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_4" name_en="Sensor fault BaseCard UI 4" name_fi="Anturivika TE21 Poistoilma LTO:n jälkeen" name_sv="Sensorfel BaseCard UI 4" name_et="Sensori viga BaseCard UI 4" name_ru="Неисправность датчика BaseCard UI 4" name_lv="Sensora kļūda BaseCard UI 4" name_tr="Sensör hatası  BaseCard UI 4" name_pl="Błąd czujnika BaseCard UI 4" pointid="TC07.TE21.SE" refpointid="TC07.G307.TE21.M" addressindex="310" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="4" severity="2" alarmid="#A4" pointtype="14" />
      <point name="G307_ALARMS_EMS_A" name_en="AHU-Emergence stop" name_fi="IV-Hätäseis" name_sv="LB Nödstopp" name_et="" name_ru="" name_lv="" name_tr="AHU-Emergence stop" pointid="TC07.G307.A1" addressindex="510" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="5" severity="1" alarmid="#A5" pointtype="14" />
      <point name="G307_ALARMS_PumpState_BinaryAlarm_A" name_en="Pump of heating radiator" name_fi="LP Pumppu" name_sv="Värmebatteri Pump" name_et="Application" name_ru="Application" name_lv="Application" name_tr="Pump of heating radiator" pointid="TC07.G307.P04.CA1" addressindex="511" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="6" severity="1" alarmid="#A6" pointtype="14" />
      <point name="G307_ALARMS_EState_ContradictionAlarm_A" name_en="Frequence converter of Extract air" name_fi="Poistopuhallin ristiriita" name_sv="Frånluftens frekvensomformare" name_et="" name_ru="" name_lv="" name_tr="Frequence converter of Extract air" pointid="TC07.G307.PF01.CA1" addressindex="512" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="7" severity="1" alarmid="#A7" pointtype="14" />
      <point name="G307_ALARMS_SState_ContradictionAlarm_A" name_en="Frequence converter of Supply air" name_fi="Tulopuhallin ristiriita" name_sv="Tilluftens frekvensomformare" name_et="" name_ru="" name_lv="" name_tr="Frequence converter of Supply air" pointid="TC07.G307.TF01.CA1" addressindex="513" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="8" severity="1" alarmid="#A8" pointtype="14" />
      <point name="G307_ALARMS_SupplyTemp_LowLimit_A" name_en="Low limit of Supply air temperature " name_fi="Tuloilman lämpötilan alaraja" name_sv="Låggräns av tilluftens temp." name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Low limit of Supply air temperature " pointid="TC07.G307.TE10.LL1" addressindex="516" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="9" severity="2" alarmid="#A9" pointtype="14" />
      <point name="G307_ALARMS_SupplyTemp_HighLimit_A" name_en="High limit of Supply air temperature " name_fi="Tuloilman lämpötilan yläraja" name_sv="Höggräns av tilluftens temp." name_et="AnalogAlarm2" name_ru="AnalogAlarm2" name_lv="AnalogAlarm2" name_tr="High limit of Supply air temperature " pointid="TC07.G307.TE10.HL1" addressindex="517" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="10" severity="2" alarmid="#A10" pointtype="14" />
      <point name="G307_ALARMS_SupplyPressure_LowLimit_A" name_en="Low limit of Supply air pressure" name_fi="Tuloilman paineen alaraja" name_sv="Låggräns av tilluftens tryck" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Low limit of Supply air pressure" pointid="TC07.G307.PIE10.LL1" addressindex="520" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="11" severity="2" alarmid="#A11" pointtype="14" />
      <point name="G307_ALARMS_SupplyPressure_HighLimit_A" name_en="High limit of Supply air pressure" name_fi="Tuloilman paineen yläraja" name_sv="Höggräns av tilluftens tryck" name_et="AnalogAlarm2" name_ru="AnalogAlarm2" name_lv="AnalogAlarm2" name_tr="High limit of Supply air pressure" pointid="TC07.G307.PIE10.HL1" addressindex="521" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="12" severity="2" alarmid="#A12" pointtype="14" />
      <point name="G307_ALARMS_RetWater_LowLimit_A" name_en="Low limit of  heat.radiator return water" name_fi="LP Paluuveden alaraja" name_sv="Nedre gräns av värmebatteri returvatten" name_et="" name_ru="Low limit for alarm activation" name_lv="Low limit for alarm activation" name_tr="Low limit of  heat.radiator return water" pointid="TC07.G307.TE04.LL1" addressindex="518" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="13" severity="1" alarmid="#A13" pointtype="14" />
      <point name="G307_ALARMS_RetWater_HighLimit_A" name_en="High limit of  heat.radiator return water" name_fi="LP Paluuveden yläraja" name_sv="Högre gräns av värmebatteri returvatten" name_et="High limit for alarm activation" name_ru="High limit for alarm activation" name_lv="High limit for alarm activation" name_tr="High limit of  heat.radiator return water" pointid="TC07.G307.TE04.HL1" addressindex="519" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="14" severity="2" alarmid="#A14" pointtype="14" />
      <point name="G307_ALARMS_EFilter_SupplyFilterAlarm_A" name_en="Extract air filter alarm" name_fi="Poistosuodatin yläraja" name_sv="Frånluftsfilter larm" name_et="Extract air filter alarm" name_ru="Extract air filter alarm" name_lv="Extract air filter alarm" name_tr="Extract air filter alarm" pointid="TC07.G307.PDIE20.HL1" addressindex="522" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="15" severity="3" alarmid="#A15" pointtype="14" />
      <point name="G307_ALARMS_EFilter_Alarm" name_en="Extract air filter alarm" name_fi="Poistosuodatin alaraja" name_sv="Frånluftsfilter larm" name_et="Extract air filter alarm" name_ru="Extract air filter alarm" name_lv="Extract air filter alarm" name_tr="Extract air filter alarm" pointid="TC07.G307.PDIE20.LL1" addressindex="523" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="16" severity="3" alarmid="#A16" pointtype="14" />
      <point name="G307_ALARMS_ExtPressure_LowLimit_A" name_en="Low limit of Extract air pressure" name_fi="Poistoilman paineen alaraja" name_sv="Låggräns av frånluftens tryck" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Low limit of Extract air pressure" pointid="TC07.G307.PIE19.LL1" addressindex="526" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="17" severity="2" alarmid="#A17" pointtype="14" />
      <point name="G307_ALARMS_ExtPressure_HighLimit_A" name_en="High limit of Extract air pressure" name_fi="Poistoilman paineen yläraja" name_sv="Höggräns av frånluftens tryck" name_et="AnalogAlarm2" name_ru="AnalogAlarm2" name_lv="AnalogAlarm2" name_tr="High limit of Extract air pressure" pointid="TC07.G307.PIE19.HL1" addressindex="527" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="18" severity="2" alarmid="#A18" pointtype="14" />
      <point name="G307_ALARMS_SFilter_SupplyFilterAlarm_A" name_en="Supply air filter alarm" name_fi="Tulosuodatin yläraja" name_sv="Tilluftsfilter larm" name_et="Supply air filter alarm" name_ru="Supply air filter alarm" name_lv="Supply air filter alarm" name_tr="Supply air filter alarm" pointid="TC07.G307.PDIE01.1.HL1" addressindex="524" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="19" severity="3" alarmid="#A19" pointtype="14" />
      <point name="G307_ALARMS_SFilter_Alarm" name_en="Supply air filter alarm" name_fi="Tulosuodatin alaraja" name_sv="Tilluftsfilter larm" name_et="Supply air filter alarm" name_ru="Supply air filter alarm" name_lv="Supply air filter alarm" name_tr="Supply air filter alarm" pointid="TC07.G307.PDIE01.1.LL1" addressindex="525" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="20" severity="3" alarmid="#A20" pointtype="14" />
      <point name="G307_ALARMS_FireRisk_STempFR_A" name_en="Fire danger of Supply air" name_fi="Tuloilman palovaara" name_sv="Brandrisk av Tilluft" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Fire danger of Supply air" pointid="TC07.G307.TE10.HHL1" addressindex="528" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="21" severity="1" alarmid="#A21" pointtype="14" />
      <point name="G307_ALARMS_FireRisk_ETempFR_A" name_en="Fire risk of Extract air" name_fi="Poistoilman palovaara" name_sv="Brand risk av Frånluft" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Fire risk of Extract air" pointid="TC07.G307.TE19.HHL1" addressindex="529" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="22" severity="1" alarmid="#A22" pointtype="14" />
      <point name="G307_ALARMS_Freeze_BinaryAlarm_A" name_en="Frost protection" name_fi="Jäätymissuoja" name_sv="Frostskydd" name_et="Application" name_ru="Application" name_lv="Application" name_tr="Frost protection" pointid="TC07.G307.TZA04.A1" addressindex="531" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="23" severity="1" alarmid="#A23" pointtype="14" />
      <point name="G307_ALARMS_ExtTemp_LowLimit_A" name_en="Low limit of Extract air temperature" name_fi="Poistoilman lämpötilan alaraja" name_sv="Låggräns av frånluftens temp." name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="Low limit of Extract air temperature" pointid="TC07.G307.TE19.LL1" addressindex="532" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="24" severity="2" alarmid="#A24" pointtype="14" />
      <point name="G307_ALARMS_ExtTemp_HighLimit_A" name_en="High limit of Extract air temperature" name_fi="Poistoilman lämpötilan yläraja" name_sv="Höggräns av frånluftens temp." name_et="AnalogAlarm2" name_ru="AnalogAlarm2" name_lv="AnalogAlarm2" name_tr="High limit of Extract air temperature" pointid="TC07.G307.TE19.HL1" addressindex="533" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="25" severity="2" alarmid="#A25" pointtype="14" />
      <point name="G307_ALARMS_SFilter2_SupplyFilterAlarm_A" name_en="Supply air filter alarm" name_fi="Tulosuodatin yläraja" name_sv="Tilluftsfilter larm" name_et="Supply air filter alarm" name_ru="Supply air filter alarm" name_lv="Supply air filter alarm" name_tr="Supply air filter alarm" pointid="TC07.G307.PDIE01.2.HL1" addressindex="534" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="26" severity="3" alarmid="#A26" pointtype="14" />
      <point name="G307_ALARMS_SFilter2_Alarm" name_en="Supply air filter alarm" name_fi="Tulosuodatin alaraja" name_sv="Tilluftsfilter larm" name_et="Supply air filter alarm" name_ru="Supply air filter alarm" name_lv="Supply air filter alarm" name_tr="Supply air filter alarm" pointid="TC07.G307.PDIE01.2.LL1" addressindex="535" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="27" severity="3" alarmid="#A27" pointtype="14" />
      <point name="G307_ALARMS_Recovery_BinaryAlarm_A" name_en="BinaryAlarm" name_fi="LTO-Kiekko hälytys" name_sv="BinaryAlarm" name_et="BinaryAlarm" name_ru="BinaryAlarm" name_lv="BinaryAlarm" name_tr="BinaryAlarm" name_pl="BinaryAlarm" pointid="TC07.G307.SC02.A1" addressindex="536" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="28" severity="1" alarmid="#A28" pointtype="14" />
      <point name="G307_ExhaustTempControl_RecoveryDefrostPDE_RecoveryAlarm_A" name_en="Max duration of Frost prevention ON" name_fi="Huurtumisen esto päällä maksimi ajan" name_sv="Max längd av Frost protection på" name_et="BinaryAlarm" name_ru="BinaryAlarm" name_lv="BinaryAlarm" name_tr="Max duration of Frost prevention ON" pointid="TC07.G307.PDIE02.HL1" addressindex="537" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="29" severity="2" alarmid="#A29" pointtype="14" />
      <point name="G307_ExhaustTempControl_RecoveryEfficiency_AnalogAlarm_A" name_en="HRU efficience " name_fi="LTO Hyötysuhde" name_sv="VÅV Återvinning" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="HRU efficience " pointid="TC07.G307.LL1" refpointid="TC07.G307.TE19.M2" addressindex="538" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="30" severity="1" alarmid="#A30" pointtype="14" />
    </group>
  </groups>
</controllertemplate>