<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="G108TC08" version="0.0.0" createppg="false" language="fi-FI" type="Modbus" addressindexstart="1">
  <groups>
    <group categorytype="2" name="Fyysiset pisteet" name_en="Physical points" name_fi="Fyysiset pisteet" name_sv="Fysiska punkter" name_et="Füüsilised punktid" name_ru="Физические точки" name_lv="Fiziskie punkti" name_tr="Fiziksel noktalar " name_pl="Punkt fizyczny">
      <point name="UI 1" name_en="UI 1" name_fi="Ulkovaloisuus" name_sv="UI 1" name_et="UI 1" name_ru="UI 1" name_lv="UI 1" name_tr="UI 1" name_pl="UI 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="2" unit="lx" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="1000" type="0" iotype="1" />
      <point name="UI 2" name_en="UI 2" name_fi="Ulkolämpötila" name_sv="UI 2" name_et="UI 2" name_ru="UI 2" name_lv="UI 2" name_tr="UI 2" name_pl="UI 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="50" type="0" iotype="1" />
      <point name="UI 3" name_en="UI 3" name_fi="Kaukolämpö tulo" name_sv="UI 3" name_et="UI 3" name_ru="UI 3" name_lv="UI 3" name_tr="UI 3" name_pl="UI 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 4" name_en="UI 4" name_fi="Kaukolämpö paluu" name_sv="UI 4" name_et="UI 4" name_ru="UI 4" name_lv="UI 4" name_tr="UI 4" name_pl="UI 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 5" name_en="UI 5" name_fi="Lämmin käyttövesi" name_sv="UI 5" name_et="UI 5" name_ru="UI 5" name_lv="UI 5" name_tr="UI 5" name_pl="UI 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 6" name_en="UI 6" name_fi="Käyttöveden kierto" name_sv="UI 6" name_et="UI 6" name_ru="UI 6" name_lv="UI 6" name_tr="UI 6" name_pl="UI 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 7" name_en="UI 7" name_fi="Kylmä käyttövesi" name_sv="UI 7" name_et="UI 7" name_ru="UI 7" name_lv="UI 7" name_tr="UI 7" name_pl="UI 7" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 8" name_en="UI 8" name_fi="Patteriverkosto meno" name_sv="UI 8" name_et="UI 8" name_ru="UI 8" name_lv="UI 8" name_tr="UI 8" name_pl="UI 8" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 9" name_en="UI 9" name_fi="Patteriverkosto paluu" name_sv="UI 9" name_et="UI 9" name_ru="UI 9" name_lv="UI 9" name_tr="UI 9" name_pl="UI 9" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 10" name_en="UI 10" name_fi="IV-Verkosto meno" name_sv="UI 10" name_et="UI 10" name_ru="UI 10" name_lv="UI 10" name_tr="UI 10" name_pl="UI 10" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 11" name_en="UI 11" name_fi="IV-Verkosto paluu" name_sv="UI 11" name_et="UI 11" name_ru="UI 11" name_lv="UI 11" name_tr="UI 11" name_pl="UI 11" pointtype="6" registertype="Holding" addressformat="S32" addressindex="221" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 12" name_en="UI 12" name_fi="UI 12" name_sv="UI 12" name_et="UI 12" name_ru="UI 12" name_lv="UI 12" name_tr="UI 12" name_pl="UI 12" pointtype="6" registertype="Holding" addressformat="S32" addressindex="223" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="UI 13" name_en="UI 13" name_fi="Vesimäärä VM33.1" name_sv="UI 13" name_et="UI 13" name_ru="UI 13" name_lv="UI 13" name_tr="UI 13" name_pl="UI 13" pointtype="6" registertype="Holding" addressformat="U32" addressindex="225" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+18" type="2" iotype="1" />
      <point name="UI 14" name_en="UI 14" name_fi="Vesimäärä VM33.2" name_sv="UI 14" name_et="UI 14" name_ru="UI 14" name_lv="UI 14" name_tr="UI 14" name_pl="UI 14" pointtype="6" registertype="Holding" addressformat="U32" addressindex="227" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+25" type="2" iotype="1" />
      <point name="UI 15" name_en="UI 15" name_fi="KL-Energia MWh" name_sv="UI 15" name_et="UI 15" name_ru="UI 15" name_lv="UI 15" name_tr="UI 15" name_pl="UI 15" pointtype="6" registertype="Holding" addressformat="U32" addressindex="229" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+30" type="2" iotype="1" />
      <point name="UI 16" name_en="UI 16" name_fi="KL-Energia m3" name_sv="UI 16" name_et="UI 16" name_ru="UI 16" name_lv="UI 16" name_tr="UI 16" name_pl="UI 16" pointtype="6" registertype="Holding" addressformat="S32" addressindex="231" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+21" type="2" iotype="1" />
      <point name="DI 1" name_en="DI 1" name_fi="Käyttövesi pumppu häl." name_sv="DI 1" name_et="DI 1" name_ru="DI 1" name_lv="DI 1" name_tr="DI 1" name_pl="DI 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="233" categorytype="2" enum="0=Normaali;1=Hälytys" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="DI 2" name_en="DI 2" name_fi="Käyttövesi pumppu tila" name_sv="DI 2" name_et="DI 2" name_ru="DI 2" name_lv="DI 2" name_tr="DI 2" name_pl="DI 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="235" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="PFI" name_en="Internal power failure indication" name_fi="Internal power failure indication" name_sv="Internal power failure indication" name_et="Internal power failure indication" name_ru="Internal power failure indication" name_lv="Internal power failure indication" name_tr="Internal power failure indication" name_pl="Internal power failure indication" pointtype="6" registertype="Holding" addressformat="S32" addressindex="237" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="AO 1" name_en="AO 1" name_fi="Patteriverkosto pumppu säätö" name_sv="AO 1" name_et="AO 1" name_ru="AO 1" name_lv="AO 1" name_tr="AO 1" name_pl="AO 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="239" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 2" name_en="AO 2" name_fi="IV-Verkosto pumppu säätö" name_sv="AO 2" name_et="AO 2" name_ru="AO 2" name_lv="AO 2" name_tr="AO 2" name_pl="AO 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="241" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 3" name_en="AO 3" name_fi="Käyttövesi venttiili säätö" name_sv="AO 3" name_et="AO 3" name_ru="AO 3" name_lv="AO 3" name_tr="AO 3" name_pl="AO 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="243" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 4" name_en="AO 4" name_fi="Patteriverkosto venttiili säätö" name_sv="AO 4" name_et="AO 4" name_ru="AO 4" name_lv="AO 4" name_tr="AO 4" name_pl="AO 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="245" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 5" name_en="AO 5" name_fi="IV-Verkosto venttiili 1 säätö" name_sv="AO 5" name_et="AO 5" name_ru="AO 5" name_lv="AO 5" name_tr="AO 5" name_pl="AO 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="247" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 6" name_en="AO 6" name_fi="IV-Verkosto venttiili 2 säätö" name_sv="AO 6" name_et="AO 6" name_ru="AO 6" name_lv="AO 6" name_tr="AO 6" name_pl="AO 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="249" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="TR 1" name_en="TR 1" name_fi="TR 1" name_sv="TR 1" name_et="TR 1" name_ru="TR 1" name_lv="TR 1" name_tr="TR 1" name_pl="TR 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="251" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 2" name_en="TR 2" name_fi="Jäähd. Vent. Moot. LJH ohj." name_sv="TR 2" name_et="TR 2" name_ru="TR 2" name_lv="TR 2" name_tr="TR 2" name_pl="TR 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="253" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 3" name_en="TR 3" name_fi="TR 3" name_sv="TR 3" name_et="TR 3" name_ru="TR 3" name_lv="TR 3" name_tr="TR 3" name_pl="TR 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="255" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 4" name_en="TR 4" name_fi="TR 4" name_sv="TR 4" name_et="TR 4" name_ru="TR 4" name_lv="TR 4" name_tr="TR 4" name_pl="TR 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="257" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="R1" name_en="R1" name_fi="Patteriverkosto pumppu ohjaus" name_sv="R1" name_et="R1" name_ru="R1" name_lv="R1" name_tr="R1" name_pl="R1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="259" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R2" name_en="R2" name_fi="IV-Verkosto pumppu ohjaus" name_sv="R2" name_et="R2" name_ru="R2" name_lv="R2" name_tr="R2" name_pl="R2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="261" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R3" name_en="R3" name_fi="R3" name_sv="R3" name_et="R3" name_ru="R3" name_lv="R3" name_tr="R3" name_pl="R3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="263" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R4" name_en="R4" name_fi="R4" name_sv="R4" name_et="R4" name_ru="R4" name_lv="R4" name_tr="R4" name_pl="R4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="265" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R5" name_en="R5" name_fi="R5" name_sv="R5" name_et="R5" name_ru="R5" name_lv="R5" name_tr="R5" name_pl="R5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="267" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R6" name_en="R6" name_fi="R6" name_sv="R6" name_et="R6" name_ru="R6" name_lv="R6" name_tr="R6" name_pl="R6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="269" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_UI1" name_en="UI 1" name_fi="Patteriverkosto pumppu häl." name_sv="UI 1" name_et="UI 1" name_ru="UI 1" name_lv="UI 1" name_tr="UI 1" name_pl="UI 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="271" categorytype="2" enum="0=Normaali;1=Hälytys" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI2" name_en="UI 2" name_fi="Patteriverkosto pumppu tila" name_sv="UI 2" name_et="UI 2" name_ru="UI 2" name_lv="UI 2" name_tr="UI 2" name_pl="UI 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="273" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI3" name_en="UI 3" name_fi="IV-Verkosto pumppu häl." name_sv="UI 3" name_et="UI 3" name_ru="UI 3" name_lv="UI 3" name_tr="UI 3" name_pl="UI 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="275" categorytype="2" enum="0=Normaali;1=Hälytys" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI4" name_en="UI 4" name_fi="IV-Verkosto pumppu tila" name_sv="UI 4" name_et="UI 4" name_ru="UI 4" name_lv="UI 4" name_tr="UI 4" name_pl="UI 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="277" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="1" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI5" name_en="UI 5" name_fi="Käyttövesi painelähetin VARAUS" name_sv="UI 5" name_et="UI 5" name_ru="UI 5" name_lv="UI 5" name_tr="UI 5" name_pl="UI 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="279" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="16" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI6" name_en="UI 6" name_fi="Patteriverkosto painelähetin" name_sv="UI 6" name_et="UI 6" name_ru="UI 6" name_lv="UI 6" name_tr="UI 6" name_pl="UI 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="281" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI7" name_en="UI 7" name_fi="Patteriverkosto paine-ero" name_sv="UI 7" name_et="UI 7" name_ru="UI 7" name_lv="UI 7" name_tr="UI 7" name_pl="UI 7" pointtype="6" registertype="Holding" addressformat="S32" addressindex="283" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="2.5" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI8" name_en="UI 8" name_fi="IV-Verkosto painelähetin" name_sv="UI 8" name_et="UI 8" name_ru="UI 8" name_lv="UI 8" name_tr="UI 8" name_pl="UI 8" pointtype="6" registertype="Holding" addressformat="S32" addressindex="285" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI9" name_en="UI 9" name_fi="IV-Verkosto paine-erolähetin" name_sv="UI 9" name_et="UI 9" name_ru="UI 9" name_lv="UI 9" name_tr="UI 9" name_pl="UI 9" pointtype="6" registertype="Holding" addressformat="S32" addressindex="287" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="2.5" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI10" name_en="UI 10" name_fi="Huonelämpötila LJH" name_sv="UI 10" name_et="UI 10" name_ru="UI 10" name_lv="UI 10" name_tr="UI 10" name_pl="UI 10" pointtype="6" registertype="Holding" addressformat="S32" addressindex="289" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI11" name_en="UI 11" name_fi="UI 11" name_sv="UI 11" name_et="UI 11" name_ru="UI 11" name_lv="UI 11" name_tr="UI 11" name_pl="UI 11" pointtype="6" registertype="Holding" addressformat="S32" addressindex="291" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI12" name_en="UI 12" name_fi="UI 12" name_sv="UI 12" name_et="UI 12" name_ru="UI 12" name_lv="UI 12" name_tr="UI 12" name_pl="UI 12" pointtype="6" registertype="Holding" addressformat="S32" addressindex="293" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI13" name_en="UI 13" name_fi="Käyttövesi energiamittaus" name_sv="UI 13" name_et="UI 13" name_ru="UI 13" name_lv="UI 13" name_tr="UI 13" name_pl="UI 13" pointtype="6" registertype="Holding" addressformat="U32" addressindex="295" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+26" type="2" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI14" name_en="UI 14" name_fi="Patteriverkosto energiamittaus" name_sv="UI 14" name_et="UI 14" name_ru="UI 14" name_lv="UI 14" name_tr="UI 14" name_pl="UI 14" pointtype="6" registertype="Holding" addressformat="U32" addressindex="297" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+22" type="2" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI15" name_en="UI 15" name_fi="IV-Verkosto energiamittaus" name_sv="UI 15" name_et="UI 15" name_ru="UI 15" name_lv="UI 15" name_tr="UI 15" name_pl="UI 15" pointtype="6" registertype="Holding" addressformat="U32" addressindex="299" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+17" type="2" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_UI16" name_en="UI 16" name_fi="UI 16" name_sv="UI 16" name_et="UI 16" name_ru="UI 16" name_lv="UI 16" name_tr="UI 16" name_pl="UI 16" pointtype="6" registertype="Holding" addressformat="S32" addressindex="301" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100" type="0" iotype="1" />
      <point name="MB2_ADDR2_MOD1_C32_AO1" name_en="AO 1" name_fi="Jäähd. konvektori LJH säätö" name_sv="AO 1" name_et="AO 1" name_ru="AO 1" name_lv="AO 1" name_tr="AO 1" name_pl="AO 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="303" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_AO2" name_en="AO 2" name_fi="AO 2" name_sv="AO 2" name_et="AO 2" name_ru="AO 2" name_lv="AO 2" name_tr="AO 2" name_pl="AO 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="305" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_AO3" name_en="AO 3" name_fi="AO 3" name_sv="AO 3" name_et="AO 3" name_ru="AO 3" name_lv="AO 3" name_tr="AO 3" name_pl="AO 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="307" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_AO4" name_en="AO 4" name_fi="AO 4" name_sv="AO 4" name_et="AO 4" name_ru="AO 4" name_lv="AO 4" name_tr="AO 4" name_pl="AO 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="309" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_AO5" name_en="AO 5" name_fi="AO 5" name_sv="AO 5" name_et="AO 5" name_ru="AO 5" name_lv="AO 5" name_tr="AO 5" name_pl="AO 5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="311" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_AO6" name_en="AO 6" name_fi="AO 6" name_sv="AO 6" name_et="AO 6" name_ru="AO 6" name_lv="AO 6" name_tr="AO 6" name_pl="AO 6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="313" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_TR1" name_en="TR 1" name_fi="TR 1" name_sv="TR 1" name_et="TR 1" name_ru="TR 1" name_lv="TR 1" name_tr="TR 1" name_pl="TR 1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="315" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_TR2" name_en="TR 2" name_fi="TR 2" name_sv="TR 2" name_et="TR 2" name_ru="TR 2" name_lv="TR 2" name_tr="TR 2" name_pl="TR 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="317" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_TR3" name_en="TR 3" name_fi="TR 3" name_sv="TR 3" name_et="TR 3" name_ru="TR 3" name_lv="TR 3" name_tr="TR 3" name_pl="TR 3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="319" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_TR4" name_en="TR 4" name_fi="TR 4" name_sv="TR 4" name_et="TR 4" name_ru="TR 4" name_lv="TR 4" name_tr="TR 4" name_pl="TR 4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="321" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R1" name_en="R1" name_fi="R1" name_sv="R1" name_et="R1" name_ru="R1" name_lv="R1" name_tr="R1" name_pl="R1" pointtype="6" registertype="Holding" addressformat="S32" addressindex="323" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R2" name_en="R2" name_fi="R2" name_sv="R2" name_et="R2" name_ru="R2" name_lv="R2" name_tr="R2" name_pl="R2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="325" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R3" name_en="R3" name_fi="R3" name_sv="R3" name_et="R3" name_ru="R3" name_lv="R3" name_tr="R3" name_pl="R3" pointtype="6" registertype="Holding" addressformat="S32" addressindex="327" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R4" name_en="R4" name_fi="R4" name_sv="R4" name_et="R4" name_ru="R4" name_lv="R4" name_tr="R4" name_pl="R4" pointtype="6" registertype="Holding" addressformat="S32" addressindex="329" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R5" name_en="R5" name_fi="R5" name_sv="R5" name_et="R5" name_ru="R5" name_lv="R5" name_tr="R5" name_pl="R5" pointtype="6" registertype="Holding" addressformat="S32" addressindex="331" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="MB2_ADDR2_MOD1_C32_R6" name_en="R6" name_fi="R6" name_sv="R6" name_et="R6" name_ru="R6" name_lv="R6" name_tr="R6" name_pl="R6" pointtype="6" registertype="Holding" addressformat="S32" addressindex="333" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
    </group>
    <group categorytype="2" name="Asetusarvot" name_en="Setting values" name_fi="Asetusarvot" name_sv="Inställningar" name_et="Seadistused" name_ru="Уставочные значения" name_lv="Iestatīt vērtības" name_tr="Set değerleri" name_pl="Ustawienia">
      <point name="G101_P_Area" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="453" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G101_I_Time" name_en="I-time" name_fi="I-aika" name_sv="I-tid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="455" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G101_D_Time" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="457" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue4" name_en="Out1" name_fi="Out1" pointtype="3" registertype="Holding" addressformat="S32" addressindex="459" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue5" name_en="In2" name_fi="In2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="461" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G101_Setvalue6" name_en="Out2" name_fi="Out2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="463" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue7" name_en="In3" name_fi="In3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="465" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G101_Setvalue8" name_en="Out3" name_fi="Out3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="467" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue9" name_en="In4" name_fi="In4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="469" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G101_Setvalue10" name_en="Out4" name_fi="Out4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="471" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue11" name_en="Out5" name_fi="Out5" pointtype="3" registertype="Holding" addressformat="S32" addressindex="473" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue12" name_en="Min" name_fi="Minimiraja" pointtype="3" registertype="Holding" addressformat="S32" addressindex="475" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue13" name_en="Max" name_fi="Maksimiraja" pointtype="3" registertype="Holding" addressformat="S32" addressindex="477" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_DropAmout" name_en="Drop effect" name_fi="Pudotuksen määrä" name_sv="Sänkning effekt" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="479" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="G101_ParallelShift" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="481" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="10" />
      <point name="G101_PressAlarmLowLimit" name_en="Pressure meas. lower limit alarm" name_fi="Verkoston paine alaraja" name_sv="Tryckmätning lågnivålarm" name_et="Press. meas.lower limit alarm" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="483" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      <point name="G101_PressAlarmHighLimit" name_en="Pressure meas. upper limit alarm" name_fi="Verkoston paine yläraja" name_sv="Tryckmätning högnivålarm" name_et="Press. meas.upper limit alarm" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="485" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      <point name="G101_DeviationAlarmLimit" name_en="Deviation alarm limit" name_fi="Poikkeamahälytysraja" name_sv="Avvikelselarm gräns" pointtype="3" registertype="Holding" addressformat="S32" addressindex="487" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      <point name="G101_DeviationAlarmDelay" name_en="Deviation alarm delay" name_fi="Poikkeamahälytyksen viive" name_sv="Avvikelselarmets fördröjning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="489" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="G101_AutumnDrySet" name_en="Autumn drying" name_fi="Syyskuivaus" name_sv="Hösttorkning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="491" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G101_Setvalue" name_en="Value to subract from" name_fi="Huonelämpötilan tavoite" name_sv="Värde A" pointtype="3" registertype="Holding" addressformat="S32" addressindex="493" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="18" max="24" />
      <point name="G101_Setvalue2" name_en="B1" name_fi="Huonekompensointisuhde" name_sv="Multiplikator 1" pointtype="3" registertype="Holding" addressformat="S32" addressindex="495" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G101_Setvalue3" name_en="P-area" name_fi="Pumpun P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="497" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G101_Setvalue14" name_en="I-time in seconds" name_fi="Pumpun I-aika (s)" name_sv="I-tid i sekunder" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="499" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G101_Setvalue15" name_en="D-time in seconds" name_fi="Pumpun D-aika (s)" name_sv="D-tid i sekunder" pointtype="3" registertype="Holding" addressformat="S32" addressindex="501" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_Setvalue16" name_en="SetPoint" name_fi="Pumpun paineen asetusarvo" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="503" categorytype="3" unit="kpa" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="250" />
      <point name="G101_Setvalue17" name_en="Setpoint" name_fi="Kesäpysäytysraja" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="369" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="G101_Setvalue18" name_en="Hysteresis" name_fi="Kesäpysäytyksen eroalue" name_sv="Hysteresis" pointtype="3" registertype="Holding" addressformat="S32" addressindex="371" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="10" />
      <point name="G101_Setvalue19" name_en="Value to be multiplied" name_fi="Pumpun paine hälytysviive" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="445" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="60" />
      <point name="G101_Setvalue20" name_en="Deviation alarm" name_fi="P. Paineen max. poikkeama" name_sv="Den maximala tillåtna avvikelse" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="451" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G101_EnergyMeter_Setvalue22" name_en="In/Base scaling ratio" name_fi="Skaalaus imp/kwh" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="627" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="G101_EnergyMeter_Setvalue21" name_en="Counter initial value" name_fi="PV-Energia alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="629" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G201_PSetvalue" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="505" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G201_ISetvalue" name_en="I" name_fi="I-aika" pointtype="3" registertype="Holding" addressformat="S32" addressindex="507" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G201_DSetvalue" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="509" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G201_Setvalue" name_en="Setpoint" name_fi="Asetusarvo" name_sv="Inställningsvärde" name_et="SetPoint" name_ru="SetPoint" pointtype="3" registertype="Holding" addressformat="S32" addressindex="511" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="95" />
      <point name="G201_AnticPSetvalue" name_en="AnticipP" name_fi="Ennakoinnin P-alkue" name_sv="AnticipP" name_et="AnticipP" name_ru="AnticipP" pointtype="3" registertype="Holding" addressformat="S32" addressindex="513" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="50" max="250" />
      <point name="G201_BPSetvalue" name_en="BoostPower" name_fi="Pika-ajo" name_sv="BoostPower" name_et="BoostPower" name_ru="BoostPower" pointtype="3" registertype="Holding" addressformat="S32" addressindex="515" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G201_DHWAlarmDelay" name_en="HW Over heating alarm delay" name_fi="LV Ylilämpöhäl. viive" name_sv="TV Överhettning larm fördröjn." name_et="Entry delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="517" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="G201_DHWMaxAlarm" name_en="HW Over heating alarm limit" name_fi="LV Ylilämpö hälytysraja" name_sv="TV Överhettning  larm gräns" name_et="High limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="519" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="65" max="120" />
      <point name="G201_MotorDriveTime" name_en="Actuator running time" name_fi="Moottorin ajoaika" name_sv="Ställdonets driftstid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="521" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="G201_MaxDeviation" name_en="Deviation alarm limit" name_fi="Poikkeamahälytysraja" name_sv="Avvikelselarmgräns" name_et="Deviation alarm limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="523" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="G201_DeviationAlamrDelay" name_en="Deviation alarm delay" name_fi="Poikkeamahälytyksen viive" name_sv="Avvikelselarmets fördröjning" name_et="Deviation alarm delay" name_ru="Deviation alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="525" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="600" />
      <point name="G201_WaterMeasures_Setvalue22" name_en="In/Base scaling ratio" name_fi="LV Skaalaus imp/l" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="642" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="G201_WaterMeasures_Setvalue21" name_en="Counter initial value" name_fi="KV kulutus alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="644" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G201_WaterMeasures_Setvalue" name_en="In/Base scaling ratio" name_fi="KV Skaalaus imp/l" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="649" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="G201_WaterMeasures_Setvalue2" name_en="Counter initial value" name_fi="LV kulutus alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="651" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G201_EnergyMeter_Setvalue22" name_en="In/Base scaling ratio" name_fi="Skaalaus imp/kwh" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="631" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="G201_EnergyMeter_Setvalue21" name_en="Counter initial value" name_fi="LV Energia alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="633" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G410_Setvalue" name_en="P-area" name_fi="LJH Jäähd. P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="674" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G410_Setvalue2" name_en="I-time in seconds" name_fi="LJH Jäähd. I-aika" name_sv="I-tid i sekunder" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="676" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G410_Setvalue4" name_en="SetPoint" name_fi="LJH Lämpötilan asetus" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="678" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="30" />
      <point name="G410_Setvalue3" name_en="Minimum limit of Output" name_fi="LJH Konvektoripuh. min-nopeus" name_sv="Minimigräns för Output" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="680" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G410_Setvalue5" name_en="Maximum limit of Output" name_fi="LJH Konvektoripuh. max-nopeus" name_sv="Maximigräns för Output" pointtype="3" registertype="Holding" addressformat="S32" addressindex="682" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G410_Setvalue6" name_en="Low limit for alarm activation" name_fi="LJH Lämpötila alaraja" name_sv="Nedre aktiveringsgränsen för larm" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="684" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      <point name="G410_Setvalue7" name_en="High limit for alarm activation" name_fi="LJH Lämpötila yläraja" name_sv="Högre aktiveringsgränsen för larm" pointtype="3" registertype="Holding" addressformat="S32" addressindex="686" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      <point name="G410_Setvalue8" name_en="Value to be multiplied" name_fi="LJH Lämpötila hälytysviive" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="688" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="DHMeasures_Setvalue" name_en="Value to be multiplied" name_fi="Kaukolämpö hälytysviive" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="659" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="DHMeasures_Setvalue2" name_en="Low limit for alarm activation" name_fi="Kaukolämpö hälytysraja" name_sv="Nedre aktiveringsgränsen för larm" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="661" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHMeasures_EnergyMeter_Setvalue22" name_en="In/Base scaling ratio" name_fi="Skaalaus imp/kwh" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="663" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="DHMeasures_EnergyMeter_Setvalue21" name_en="Counter initial value" name_fi="KL Energia alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="665" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="DHMeasures_WaterMeasure_Setvalue22" name_en="In/Base scaling ratio" name_fi="Skaalaus imp/l" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="667" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="DHMeasures_WaterMeasure_Setvalue21" name_en="Counter initial value" name_fi="KL Vesimäärä alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="669" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G102_P_Area" name_en="P-area" name_fi="P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="527" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G102_I_Time" name_en="I-time" name_fi="I-aika" name_sv="I-tid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="529" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G102_D_Time" name_en="D-time" name_fi="D-aika" name_sv="D-tid" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="531" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue4" name_en="Out1" name_fi="Out1" pointtype="3" registertype="Holding" addressformat="S32" addressindex="533" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue5" name_en="In2" name_fi="In2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="535" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G102_Setvalue6" name_en="Out2" name_fi="Out2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="537" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue7" name_en="In3" name_fi="In3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="539" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G102_Setvalue8" name_en="Out3" name_fi="Out3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="541" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue9" name_en="In4" name_fi="In4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="543" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-50" max="50" />
      <point name="G102_Setvalue10" name_en="Out4" name_fi="Out4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="545" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue11" name_en="Out5" name_fi="Out5" pointtype="3" registertype="Holding" addressformat="S32" addressindex="547" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue12" name_en="Min" name_fi="Minimiraja" pointtype="3" registertype="Holding" addressformat="S32" addressindex="549" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue13" name_en="Max" name_fi="Maksimiraja" pointtype="3" registertype="Holding" addressformat="S32" addressindex="551" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_DropAmout" name_en="Drop effect" name_fi="Pudotuksen määrä" name_sv="Sänkning effekt" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="553" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="G102_ParallelShift" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="555" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="10" />
      <point name="G102_PressAlarmLowLimit" name_en="Pressure meas. lower limit alarm" name_fi="Paine alarajahälytys" name_sv="Tryckmätning lågnivålarm" name_et="Press. meas.lower limit alarm" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="557" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      <point name="G102_PressAlarmHighLimit" name_en="Pressure meas. upper limit alarm" name_fi="Paine ylärajahälytys" name_sv="Tryckmätning högnivålarm" name_et="Press. meas.upper limit alarm" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="559" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      <point name="G102_DeviationAlarmLimit" name_en="Deviation alarm limit" name_fi="Poikkeamahälytysraja" name_sv="Avvikelselarm gräns" pointtype="3" registertype="Holding" addressformat="S32" addressindex="561" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      <point name="G102_DeviationAlarmDelay" name_en="Deviation alarm delay" name_fi="Poikkeamahälytyksen viive" name_sv="Avvikelselarmets fördröjning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="563" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="G102_AutumnDrySet" name_en="Autumn drying" name_fi="Syyskuivaus" name_sv="Hösttorkning" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="565" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G102_Setvalue" name_en="P-area" name_fi="Pumpun P-alue" name_sv="P-band" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="567" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="G102_Setvalue2" name_en="I-time in seconds" name_fi="Pumpun I-aika (s)" name_sv="I-tid i sekunder" name_et="" name_ru="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="569" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="G102_Setvalue3" name_en="D-time in seconds" name_fi="Pumpun D-aika (s)" name_sv="D-tid i sekunder" pointtype="3" registertype="Holding" addressformat="S32" addressindex="571" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="G102_Setvalue14" name_en="Setpoint" name_fi="Kesäpysäytysraja" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="599" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="G102_Setvalue15" name_en="Hysteresis" name_fi="Kesäpysäytys eroalue" name_sv="Hysteresis" pointtype="3" registertype="Holding" addressformat="S32" addressindex="601" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="G102_Setvalue16" name_en="SetPoint" name_fi="Pumpun paineen asetusarvo" name_sv="Börvärdet" pointtype="3" registertype="Holding" addressformat="S32" addressindex="603" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="50" max="250" />
      <point name="G102_Setvalue17" name_en="Value to be multiplied" name_fi="Pumpun paine hälytysviive" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="605" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="60" />
      <point name="G102_Setvalue18" name_en="Deviation alarm" name_fi="P. paineen max. poikkeama" name_sv="Den maximala tillåtna avvikelse" name_et="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="607" categorytype="3" unit="kpa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      <point name="G102_EnergyMeter_Setvalue22" name_en="In/Base scaling ratio" name_fi="Skaalaus imp/kwh" name_sv="In/Base scalning relation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="635" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      <point name="G102_EnergyMeter_Setvalue21" name_en="Counter initial value" name_fi="IV-Energia alkuarvo" name_sv="Initialvärde för räknare" pointtype="3" registertype="Holding" addressformat="S32" addressindex="637" categorytype="3" unit="mWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      <point name="G102_MotorDriving2_t_OpenMotor1" name_en="Motor drive time" name_fi="G102FV01 ajoaika" name_sv="Motor driv tid" pointtype="3" registertype="Holding" addressformat="S32" addressindex="573" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      <point name="G102_MotorDriving2_ActuatorConf" name_en="Actuator select" name_fi="G102FV01 valinta" name_sv="Ställdon selekt" pointtype="3" registertype="Holding" addressformat="S32" addressindex="575" categorytype="3" enum="0=0-10V;1=2-10V;2=10-0V;3=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="3" />
      <point name="G102_MotorDriving2_Setvalue" name_en="Select" name_fi="G102FV02 valinta" name_sv="Select" name_et="Select" name_ru="Select" name_lv="Select" pointtype="3" registertype="Holding" addressformat="S32" addressindex="577" categorytype="3" enum="0=0-10V;1=2-10V;2=10-0V;3=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="3" />
      <point name="G102_MotorDriving2_t_OpenMotor2" name_en="Drive time to open direction" name_fi="G102FV02 ajoaika" name_sv="Drifttid  till öppet i sekunder" pointtype="3" registertype="Holding" addressformat="S32" addressindex="579" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
    </group>
    <group categorytype="2" name="Mittaukset" name_en="Measurements" name_fi="Mittaukset" name_sv="Mätningar" name_et="Mõõtmised" name_ru="Измерения" name_lv="Mērījumi" name_tr="Ölçümler " name_pl="Pomiary">
      <point name="G101_CurveOut" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurvan" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="335" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_SupplyWaterSet" name_en="Calculated supply water setting" name_fi="Laskennall. menoveden asetusarvo" name_sv="Beräknad inst.värde för framledningstemp." name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="337" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_DropEffect" name_en="Drop by time program" name_fi="Pudotus aikaohjelmalla" name_sv="Sänkning av tid styrning" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="339" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_ParallelShiftEffect" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="341" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_MinLimitEffect" name_en="Min limit effect" name_fi="Minimirajan vaikutus" name_sv="Minimigränsens effekt" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="343" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_MaxLimitEffect" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Max.gränsens effekt" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="345" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_AutumnDryEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkning " name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="347" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_Measure" name_en="Output" name_fi="Huonekompensoinnin vaikutus" name_sv="Output" name_et="Output" name_ru="Output" name_lv="Output" name_tr="Output" name_pl="Output" pointtype="10" registertype="Holding" addressformat="S32" addressindex="349" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G101_Measure4" name_en="Output3" name_fi="Kesäpysäytystila" name_sv="Termostat utgång" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="U16" addressindex="351" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G101_EnergyMeter_Measure2" name_en="Counter output" name_fi="Patteriverkosto energia" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="618" categorytype="2" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G201_WaterMeasures_Measure2" name_en="Counter output" name_fi="KV kulutus" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="639" categorytype="2" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G201_WaterMeasures_Measure" name_en="Counter output" name_fi="LV kulutus" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="646" categorytype="2" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G201_EnergyMeter_Measure2" name_en="Counter output" name_fi="LV energia" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="620" categorytype="2" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="DHMeasures_EnergyMeter_Measure2" name_en="Counter output" name_fi="KL energia" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="653" categorytype="2" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="DHMeasures_WaterMeasure_Measure2" name_en="Counter output" name_fi="KL Vesimäärä" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="655" categorytype="2" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_CurveOut" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurvan" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="355" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_SupplyWaterSet" name_en="Calculated supply water setting" name_fi="Laskennall. menoveden asetusarvo" name_sv="Beräknad inst.värde för framledningstemp." name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="357" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_DropEffect" name_en="Drop by time program" name_fi="Pudotus aikaohjelmalla" name_sv="Sänkning av tid styrning" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="359" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_ParallelShiftEffect" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="361" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_MinLimitEffect" name_en="Min limit effect" name_fi="Minimirajan vaikutus" name_sv="Minimigränsens effekt" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="363" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_MaxLimitEffect" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Max.gränsens effekt" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="365" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_AutumnDryEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkning " name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="S32" addressindex="367" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="G102_Measure3" name_en="Output3" name_fi="Kesäpysäytystila" name_sv="Termostat utgång" name_et="" name_ru="" pointtype="10" registertype="Holding" addressformat="U16" addressindex="352" categorytype="2" enum="0=Pois;1=Päällä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="G102_EnergyMeter_Measure2" name_en="Counter output" name_fi="IV-Verkosto energia" name_sv="Skalad utgångsvärde av räknare" pointtype="10" registertype="Holding" addressformat="S32" addressindex="622" categorytype="2" unit="mWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
    </group>
    <group categorytype="1" name="Käsiajo" name_en="Manual control" name_fi="Käsiajo" name_sv="Manuell styrning" name_et="käsijuhtimisrežiim" name_ru="Ручной режим" name_lv="Rokas vadība" name_tr="Manuel kontrol " name_pl="Sterowanie ręczne">
      <point name="UI 1_mc" name_en="UI 1 Manual control" name_fi="Ulkovaloisuus Käsiajo" name_sv="UI 1 Manuell styrning" name_et="UI 1 käsijuhtimisrežiim" name_ru="UI 1 Ручной режим" name_lv="UI 1 Rokas vadība" name_tr="UI 1 Manuel kontrol " name_pl="UI 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="373" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 2_mc" name_en="UI 2 Manual control" name_fi="Ulkolämpötila Käsiajo" name_sv="UI 2 Manuell styrning" name_et="UI 2 käsijuhtimisrežiim" name_ru="UI 2 Ручной режим" name_lv="UI 2 Rokas vadība" name_tr="UI 2 Manuel kontrol " name_pl="UI 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="374" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 3_mc" name_en="UI 3 Manual control" name_fi="Kaukolämpö tulo Käsiajo" name_sv="UI 3 Manuell styrning" name_et="UI 3 käsijuhtimisrežiim" name_ru="UI 3 Ручной режим" name_lv="UI 3 Rokas vadība" name_tr="UI 3 Manuel kontrol " name_pl="UI 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="375" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 4_mc" name_en="UI 4 Manual control" name_fi="Kaukolämpö paluu Käsiajo" name_sv="UI 4 Manuell styrning" name_et="UI 4 käsijuhtimisrežiim" name_ru="UI 4 Ручной режим" name_lv="UI 4 Rokas vadība" name_tr="UI 4 Manuel kontrol " name_pl="UI 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="376" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 5_mc" name_en="UI 5 Manual control" name_fi="Lämmin käyttövesi Käsiajo" name_sv="UI 5 Manuell styrning" name_et="UI 5 käsijuhtimisrežiim" name_ru="UI 5 Ручной режим" name_lv="UI 5 Rokas vadība" name_tr="UI 5 Manuel kontrol " name_pl="UI 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="377" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 6_mc" name_en="UI 6 Manual control" name_fi="Käyttöveden kierto Käsiajo" name_sv="UI 6 Manuell styrning" name_et="UI 6 käsijuhtimisrežiim" name_ru="UI 6 Ручной режим" name_lv="UI 6 Rokas vadība" name_tr="UI 6 Manuel kontrol " name_pl="UI 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="378" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 7_mc" name_en="UI 7 Manual control" name_fi="Kylmä käyttövesi Käsiajo" name_sv="UI 7 Manuell styrning" name_et="UI 7 käsijuhtimisrežiim" name_ru="UI 7 Ручной режим" name_lv="UI 7 Rokas vadība" name_tr="UI 7 Manuel kontrol " name_pl="UI 7 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="379" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 8_mc" name_en="UI 8 Manual control" name_fi="Patteriverkosto meno Käsiajo" name_sv="UI 8 Manuell styrning" name_et="UI 8 käsijuhtimisrežiim" name_ru="UI 8 Ручной режим" name_lv="UI 8 Rokas vadība" name_tr="UI 8 Manuel kontrol " name_pl="UI 8 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="380" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 9_mc" name_en="UI 9 Manual control" name_fi="Patteriverkosto paluu Käsiajo" name_sv="UI 9 Manuell styrning" name_et="UI 9 käsijuhtimisrežiim" name_ru="UI 9 Ручной режим" name_lv="UI 9 Rokas vadība" name_tr="UI 9 Manuel kontrol " name_pl="UI 9 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="381" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 10_mc" name_en="UI 10 Manual control" name_fi="IV-Verkosto meno Käsiajo" name_sv="UI 10 Manuell styrning" name_et="UI 10 käsijuhtimisrežiim" name_ru="UI 10 Ручной режим" name_lv="UI 10 Rokas vadība" name_tr="UI 10 Manuel kontrol " name_pl="UI 10 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="382" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 11_mc" name_en="UI 11 Manual control" name_fi="IV-Verkosto paluu Käsiajo" name_sv="UI 11 Manuell styrning" name_et="UI 11 käsijuhtimisrežiim" name_ru="UI 11 Ручной режим" name_lv="UI 11 Rokas vadība" name_tr="UI 11 Manuel kontrol " name_pl="UI 11 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="383" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 12_mc" name_en="UI 12 Manual control" name_fi="UI 12 Käsiajo" name_sv="UI 12 Manuell styrning" name_et="UI 12 käsijuhtimisrežiim" name_ru="UI 12 Ручной режим" name_lv="UI 12 Rokas vadība" name_tr="UI 12 Manuel kontrol " name_pl="UI 12 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="384" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 13_mc" name_en="UI 13 Manual control" name_fi="Vesimäärä VM33.1 Käsiajo" name_sv="UI 13 Manuell styrning" name_et="UI 13 käsijuhtimisrežiim" name_ru="UI 13 Ручной режим" name_lv="UI 13 Rokas vadība" name_tr="UI 13 Manuel kontrol " name_pl="UI 13 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="385" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 14_mc" name_en="UI 14 Manual control" name_fi="Vesimäärä VM33.2 Käsiajo" name_sv="UI 14 Manuell styrning" name_et="UI 14 käsijuhtimisrežiim" name_ru="UI 14 Ручной режим" name_lv="UI 14 Rokas vadība" name_tr="UI 14 Manuel kontrol " name_pl="UI 14 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="386" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 15_mc" name_en="UI 15 Manual control" name_fi="KL-Energia MWh Käsiajo" name_sv="UI 15 Manuell styrning" name_et="UI 15 käsijuhtimisrežiim" name_ru="UI 15 Ручной режим" name_lv="UI 15 Rokas vadība" name_tr="UI 15 Manuel kontrol " name_pl="UI 15 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="387" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 16_mc" name_en="UI 16 Manual control" name_fi="KL-Energia m3 Käsiajo" name_sv="UI 16 Manuell styrning" name_et="UI 16 käsijuhtimisrežiim" name_ru="UI 16 Ручной режим" name_lv="UI 16 Rokas vadība" name_tr="UI 16 Manuel kontrol " name_pl="UI 16 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="388" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 1_mc" name_en="DI 1 Manual control" name_fi="Käyttövesi pumppu häl. Käsiajo" name_sv="DI 1 Manuell styrning" name_et="DI 1 käsijuhtimisrežiim" name_ru="DI 1 Ручной режим" name_lv="DI 1 Rokas vadība" name_tr="DI 1 Manuel kontrol " name_pl="DI 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="389" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 2_mc" name_en="DI 2 Manual control" name_fi="Käyttövesi pumppu tila Käsiajo" name_sv="DI 2 Manuell styrning" name_et="DI 2 käsijuhtimisrežiim" name_ru="DI 2 Ручной режим" name_lv="DI 2 Rokas vadība" name_tr="DI 2 Manuel kontrol " name_pl="DI 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="390" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="PFI_mc" name_en="Internal power failure indication Manual control" name_fi="Internal power failure indication Käsiajo" name_sv="Internal power failure indication Manuell styrning" name_et="Internal power failure indication käsijuhtimisrežiim" name_ru="Internal power failure indication Ручной режим" name_lv="Internal power failure indication Rokas vadība" name_tr="Internal power failure indication Manuel kontrol " name_pl="Internal power failure indication Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="391" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 1_mc" name_en="AO 1 Manual control" name_fi="Patteriverkosto pumppu säätö Käsiajo" name_sv="AO 1 Manuell styrning" name_et="AO 1 käsijuhtimisrežiim" name_ru="AO 1 Ручной режим" name_lv="AO 1 Rokas vadība" name_tr="AO 1 Manuel kontrol " name_pl="AO 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="392" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 2_mc" name_en="AO 2 Manual control" name_fi="IV-Verkosto pumppu säätö Käsiajo" name_sv="AO 2 Manuell styrning" name_et="AO 2 käsijuhtimisrežiim" name_ru="AO 2 Ручной режим" name_lv="AO 2 Rokas vadība" name_tr="AO 2 Manuel kontrol " name_pl="AO 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="393" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 3_mc" name_en="AO 3 Manual control" name_fi="Käyttövesi venttiili säätö Käsiajo" name_sv="AO 3 Manuell styrning" name_et="AO 3 käsijuhtimisrežiim" name_ru="AO 3 Ручной режим" name_lv="AO 3 Rokas vadība" name_tr="AO 3 Manuel kontrol " name_pl="AO 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="394" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 4_mc" name_en="AO 4 Manual control" name_fi="Patteriverkosto venttiili säätö Käsiajo" name_sv="AO 4 Manuell styrning" name_et="AO 4 käsijuhtimisrežiim" name_ru="AO 4 Ручной режим" name_lv="AO 4 Rokas vadība" name_tr="AO 4 Manuel kontrol " name_pl="AO 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="395" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 5_mc" name_en="AO 5 Manual control" name_fi="IV-Verkosto venttiili 1 säätö Käsiajo" name_sv="AO 5 Manuell styrning" name_et="AO 5 käsijuhtimisrežiim" name_ru="AO 5 Ручной режим" name_lv="AO 5 Rokas vadība" name_tr="AO 5 Manuel kontrol " name_pl="AO 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="396" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 6_mc" name_en="AO 6 Manual control" name_fi="IV-Verkosto venttiili 2 säätö Käsiajo" name_sv="AO 6 Manuell styrning" name_et="AO 6 käsijuhtimisrežiim" name_ru="AO 6 Ручной режим" name_lv="AO 6 Rokas vadība" name_tr="AO 6 Manuel kontrol " name_pl="AO 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="397" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 1_mc" name_en="TR 1 Manual control" name_fi="TR 1 Käsiajo" name_sv="TR 1 Manuell styrning" name_et="TR 1 käsijuhtimisrežiim" name_ru="TR 1 Ручной режим" name_lv="TR 1 Rokas vadība" name_tr="TR 1 Manuel kontrol " name_pl="TR 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="398" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 2_mc" name_en="TR 2 Manual control" name_fi="Jäähd. Vent. Moot. LJH ohj. Käsiajo" name_sv="TR 2 Manuell styrning" name_et="TR 2 käsijuhtimisrežiim" name_ru="TR 2 Ручной режим" name_lv="TR 2 Rokas vadība" name_tr="TR 2 Manuel kontrol " name_pl="TR 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="399" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 3_mc" name_en="TR 3 Manual control" name_fi="TR 3 Käsiajo" name_sv="TR 3 Manuell styrning" name_et="TR 3 käsijuhtimisrežiim" name_ru="TR 3 Ручной режим" name_lv="TR 3 Rokas vadība" name_tr="TR 3 Manuel kontrol " name_pl="TR 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="400" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 4_mc" name_en="TR 4 Manual control" name_fi="TR 4 Käsiajo" name_sv="TR 4 Manuell styrning" name_et="TR 4 käsijuhtimisrežiim" name_ru="TR 4 Ручной режим" name_lv="TR 4 Rokas vadība" name_tr="TR 4 Manuel kontrol " name_pl="TR 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="401" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R1_mc" name_en="R1 Manual control" name_fi="Patteriverkosto pumppu ohjaus Käsiajo" name_sv="R1 Manuell styrning" name_et="R1 käsijuhtimisrežiim" name_ru="R1 Ручной режим" name_lv="R1 Rokas vadība" name_tr="R1 Manuel kontrol " name_pl="R1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="402" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R2_mc" name_en="R2 Manual control" name_fi="IV-Verkosto pumppu ohjaus Käsiajo" name_sv="R2 Manuell styrning" name_et="R2 käsijuhtimisrežiim" name_ru="R2 Ручной режим" name_lv="R2 Rokas vadība" name_tr="R2 Manuel kontrol " name_pl="R2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="403" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R3_mc" name_en="R3 Manual control" name_fi="R3 Käsiajo" name_sv="R3 Manuell styrning" name_et="R3 käsijuhtimisrežiim" name_ru="R3 Ручной режим" name_lv="R3 Rokas vadība" name_tr="R3 Manuel kontrol " name_pl="R3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="404" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R4_mc" name_en="R4 Manual control" name_fi="R4 Käsiajo" name_sv="R4 Manuell styrning" name_et="R4 käsijuhtimisrežiim" name_ru="R4 Ручной режим" name_lv="R4 Rokas vadība" name_tr="R4 Manuel kontrol " name_pl="R4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="405" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R5_mc" name_en="R5 Manual control" name_fi="R5 Käsiajo" name_sv="R5 Manuell styrning" name_et="R5 käsijuhtimisrežiim" name_ru="R5 Ручной режим" name_lv="R5 Rokas vadība" name_tr="R5 Manuel kontrol " name_pl="R5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="406" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="R6_mc" name_en="R6 Manual control" name_fi="R6 Käsiajo" name_sv="R6 Manuell styrning" name_et="R6 käsijuhtimisrežiim" name_ru="R6 Ручной режим" name_lv="R6 Rokas vadība" name_tr="R6 Manuel kontrol " name_pl="R6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="407" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI1_mc" name_en="UI 1 Manual control" name_fi="Patteriverkosto pumppu häl. Käsiajo" name_sv="UI 1 Manuell styrning" name_et="UI 1 käsijuhtimisrežiim" name_ru="UI 1 Ручной режим" name_lv="UI 1 Rokas vadība" name_tr="UI 1 Manuel kontrol " name_pl="UI 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="408" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI2_mc" name_en="UI 2 Manual control" name_fi="Patteriverkosto pumppu tila Käsiajo" name_sv="UI 2 Manuell styrning" name_et="UI 2 käsijuhtimisrežiim" name_ru="UI 2 Ручной режим" name_lv="UI 2 Rokas vadība" name_tr="UI 2 Manuel kontrol " name_pl="UI 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="409" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI3_mc" name_en="UI 3 Manual control" name_fi="IV-Verkosto pumppu häl. Käsiajo" name_sv="UI 3 Manuell styrning" name_et="UI 3 käsijuhtimisrežiim" name_ru="UI 3 Ручной режим" name_lv="UI 3 Rokas vadība" name_tr="UI 3 Manuel kontrol " name_pl="UI 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="410" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI4_mc" name_en="UI 4 Manual control" name_fi="IV-Verkosto pumppu tila Käsiajo" name_sv="UI 4 Manuell styrning" name_et="UI 4 käsijuhtimisrežiim" name_ru="UI 4 Ручной режим" name_lv="UI 4 Rokas vadība" name_tr="UI 4 Manuel kontrol " name_pl="UI 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="411" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI5_mc" name_en="UI 5 Manual control" name_fi="Käyttövesi painelähetin VARAUS Käsiajo" name_sv="UI 5 Manuell styrning" name_et="UI 5 käsijuhtimisrežiim" name_ru="UI 5 Ручной режим" name_lv="UI 5 Rokas vadība" name_tr="UI 5 Manuel kontrol " name_pl="UI 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="412" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI6_mc" name_en="UI 6 Manual control" name_fi="Patteriverkosto painelähetin Käsiajo" name_sv="UI 6 Manuell styrning" name_et="UI 6 käsijuhtimisrežiim" name_ru="UI 6 Ручной режим" name_lv="UI 6 Rokas vadība" name_tr="UI 6 Manuel kontrol " name_pl="UI 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="413" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI7_mc" name_en="UI 7 Manual control" name_fi="Patteriverkosto paine-ero Käsiajo" name_sv="UI 7 Manuell styrning" name_et="UI 7 käsijuhtimisrežiim" name_ru="UI 7 Ручной режим" name_lv="UI 7 Rokas vadība" name_tr="UI 7 Manuel kontrol " name_pl="UI 7 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="414" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI8_mc" name_en="UI 8 Manual control" name_fi="IV-Verkosto painelähetin Käsiajo" name_sv="UI 8 Manuell styrning" name_et="UI 8 käsijuhtimisrežiim" name_ru="UI 8 Ручной режим" name_lv="UI 8 Rokas vadība" name_tr="UI 8 Manuel kontrol " name_pl="UI 8 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="415" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI9_mc" name_en="UI 9 Manual control" name_fi="IV-Verkosto paine-erolähetin Käsiajo" name_sv="UI 9 Manuell styrning" name_et="UI 9 käsijuhtimisrežiim" name_ru="UI 9 Ручной режим" name_lv="UI 9 Rokas vadība" name_tr="UI 9 Manuel kontrol " name_pl="UI 9 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="416" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI10_mc" name_en="UI 10 Manual control" name_fi="Huonelämpötila LJH Käsiajo" name_sv="UI 10 Manuell styrning" name_et="UI 10 käsijuhtimisrežiim" name_ru="UI 10 Ручной режим" name_lv="UI 10 Rokas vadība" name_tr="UI 10 Manuel kontrol " name_pl="UI 10 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="417" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI11_mc" name_en="UI 11 Manual control" name_fi="UI 11 Käsiajo" name_sv="UI 11 Manuell styrning" name_et="UI 11 käsijuhtimisrežiim" name_ru="UI 11 Ручной режим" name_lv="UI 11 Rokas vadība" name_tr="UI 11 Manuel kontrol " name_pl="UI 11 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="418" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI12_mc" name_en="UI 12 Manual control" name_fi="UI 12 Käsiajo" name_sv="UI 12 Manuell styrning" name_et="UI 12 käsijuhtimisrežiim" name_ru="UI 12 Ручной режим" name_lv="UI 12 Rokas vadība" name_tr="UI 12 Manuel kontrol " name_pl="UI 12 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="419" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI13_mc" name_en="UI 13 Manual control" name_fi="Käyttövesi energiamittaus Käsiajo" name_sv="UI 13 Manuell styrning" name_et="UI 13 käsijuhtimisrežiim" name_ru="UI 13 Ручной режим" name_lv="UI 13 Rokas vadība" name_tr="UI 13 Manuel kontrol " name_pl="UI 13 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="420" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI14_mc" name_en="UI 14 Manual control" name_fi="Patteriverkosto energiamittaus Käsiajo" name_sv="UI 14 Manuell styrning" name_et="UI 14 käsijuhtimisrežiim" name_ru="UI 14 Ручной режим" name_lv="UI 14 Rokas vadība" name_tr="UI 14 Manuel kontrol " name_pl="UI 14 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="421" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI15_mc" name_en="UI 15 Manual control" name_fi="IV-Verkosto energiamittaus Käsiajo" name_sv="UI 15 Manuell styrning" name_et="UI 15 käsijuhtimisrežiim" name_ru="UI 15 Ручной режим" name_lv="UI 15 Rokas vadība" name_tr="UI 15 Manuel kontrol " name_pl="UI 15 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="422" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_UI16_mc" name_en="UI 16 Manual control" name_fi="UI 16 Käsiajo" name_sv="UI 16 Manuell styrning" name_et="UI 16 käsijuhtimisrežiim" name_ru="UI 16 Ручной режим" name_lv="UI 16 Rokas vadība" name_tr="UI 16 Manuel kontrol " name_pl="UI 16 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="423" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO1_mc" name_en="AO 1 Manual control" name_fi="Jäähd. konvektori LJH säätö Käsiajo" name_sv="AO 1 Manuell styrning" name_et="AO 1 käsijuhtimisrežiim" name_ru="AO 1 Ручной режим" name_lv="AO 1 Rokas vadība" name_tr="AO 1 Manuel kontrol " name_pl="AO 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="424" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO2_mc" name_en="AO 2 Manual control" name_fi="AO 2 Käsiajo" name_sv="AO 2 Manuell styrning" name_et="AO 2 käsijuhtimisrežiim" name_ru="AO 2 Ручной режим" name_lv="AO 2 Rokas vadība" name_tr="AO 2 Manuel kontrol " name_pl="AO 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="425" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO3_mc" name_en="AO 3 Manual control" name_fi="AO 3 Käsiajo" name_sv="AO 3 Manuell styrning" name_et="AO 3 käsijuhtimisrežiim" name_ru="AO 3 Ручной режим" name_lv="AO 3 Rokas vadība" name_tr="AO 3 Manuel kontrol " name_pl="AO 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="426" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO4_mc" name_en="AO 4 Manual control" name_fi="AO 4 Käsiajo" name_sv="AO 4 Manuell styrning" name_et="AO 4 käsijuhtimisrežiim" name_ru="AO 4 Ручной режим" name_lv="AO 4 Rokas vadība" name_tr="AO 4 Manuel kontrol " name_pl="AO 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="427" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO5_mc" name_en="AO 5 Manual control" name_fi="AO 5 Käsiajo" name_sv="AO 5 Manuell styrning" name_et="AO 5 käsijuhtimisrežiim" name_ru="AO 5 Ручной режим" name_lv="AO 5 Rokas vadība" name_tr="AO 5 Manuel kontrol " name_pl="AO 5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="428" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_AO6_mc" name_en="AO 6 Manual control" name_fi="AO 6 Käsiajo" name_sv="AO 6 Manuell styrning" name_et="AO 6 käsijuhtimisrežiim" name_ru="AO 6 Ручной режим" name_lv="AO 6 Rokas vadība" name_tr="AO 6 Manuel kontrol " name_pl="AO 6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="429" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_TR1_mc" name_en="TR 1 Manual control" name_fi="TR 1 Käsiajo" name_sv="TR 1 Manuell styrning" name_et="TR 1 käsijuhtimisrežiim" name_ru="TR 1 Ручной режим" name_lv="TR 1 Rokas vadība" name_tr="TR 1 Manuel kontrol " name_pl="TR 1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="430" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_TR2_mc" name_en="TR 2 Manual control" name_fi="TR 2 Käsiajo" name_sv="TR 2 Manuell styrning" name_et="TR 2 käsijuhtimisrežiim" name_ru="TR 2 Ручной режим" name_lv="TR 2 Rokas vadība" name_tr="TR 2 Manuel kontrol " name_pl="TR 2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="431" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_TR3_mc" name_en="TR 3 Manual control" name_fi="TR 3 Käsiajo" name_sv="TR 3 Manuell styrning" name_et="TR 3 käsijuhtimisrežiim" name_ru="TR 3 Ручной режим" name_lv="TR 3 Rokas vadība" name_tr="TR 3 Manuel kontrol " name_pl="TR 3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="432" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_TR4_mc" name_en="TR 4 Manual control" name_fi="TR 4 Käsiajo" name_sv="TR 4 Manuell styrning" name_et="TR 4 käsijuhtimisrežiim" name_ru="TR 4 Ручной режим" name_lv="TR 4 Rokas vadība" name_tr="TR 4 Manuel kontrol " name_pl="TR 4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="433" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R1_mc" name_en="R1 Manual control" name_fi="R1 Käsiajo" name_sv="R1 Manuell styrning" name_et="R1 käsijuhtimisrežiim" name_ru="R1 Ручной режим" name_lv="R1 Rokas vadība" name_tr="R1 Manuel kontrol " name_pl="R1 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="434" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R2_mc" name_en="R2 Manual control" name_fi="R2 Käsiajo" name_sv="R2 Manuell styrning" name_et="R2 käsijuhtimisrežiim" name_ru="R2 Ручной режим" name_lv="R2 Rokas vadība" name_tr="R2 Manuel kontrol " name_pl="R2 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="435" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R3_mc" name_en="R3 Manual control" name_fi="R3 Käsiajo" name_sv="R3 Manuell styrning" name_et="R3 käsijuhtimisrežiim" name_ru="R3 Ручной режим" name_lv="R3 Rokas vadība" name_tr="R3 Manuel kontrol " name_pl="R3 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="436" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R4_mc" name_en="R4 Manual control" name_fi="R4 Käsiajo" name_sv="R4 Manuell styrning" name_et="R4 käsijuhtimisrežiim" name_ru="R4 Ручной режим" name_lv="R4 Rokas vadība" name_tr="R4 Manuel kontrol " name_pl="R4 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="437" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R5_mc" name_en="R5 Manual control" name_fi="R5 Käsiajo" name_sv="R5 Manuell styrning" name_et="R5 käsijuhtimisrežiim" name_ru="R5 Ручной режим" name_lv="R5 Rokas vadība" name_tr="R5 Manuel kontrol " name_pl="R5 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="438" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="MB2_ADDR2_MOD1_C32_R6_mc" name_en="R6 Manual control" name_fi="R6 Käsiajo" name_sv="R6 Manuell styrning" name_et="R6 käsijuhtimisrežiim" name_ru="R6 Ручной режим" name_lv="R6 Rokas vadība" name_tr="R6 Manuel kontrol " name_pl="R6 Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="439" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_CurveOut_mc" name_en="According to curve Manual control" name_fi="Käyrän mukaan Käsiajo" name_sv="Enligt kurvan Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="440" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_SupplyWaterSet_mc" name_en="Calculated supply water setting Manual control" name_fi="Laskennall. menoveden asetusarvo Käsiajo" name_sv="Beräknad inst.värde för framledningstemp. Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="441" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_ParallelShiftEffect_mc" name_en="Parallel shift Manual control" name_fi="Suuntaissiirto Käsiajo" name_sv="Parallellförskjutning Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="442" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_AutumnDryEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkning  Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="443" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_Measure_mc" name_en="Output Manual control" name_fi="Huonekompensoinnin vaikutus Käsiajo" name_sv="Output Manuell styrning" name_et="Output käsijuhtimisrežiim" name_ru="Output Ручной режим" name_lv="Output Rokas vadība" name_tr="Output Manuel kontrol " name_pl="Output Sterowanie ręczne" pointtype="3" registertype="Holding" addressformat="U16" addressindex="444" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_Measure4_mc" name_en="Output3 Manual control" name_fi="Kesäpysäytystila Käsiajo" name_sv="Termostat utgång Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="353" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G101_EnergyMeter_Measure2_mc" name_en="Counter output Manual control" name_fi="Patteriverkosto energia Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="624" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G201_WaterMeasures_Measure2_mc" name_en="Counter output Manual control" name_fi="KV kulutus Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="641" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G201_WaterMeasures_Measure_mc" name_en="Counter output Manual control" name_fi="LV kulutus Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="648" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G201_EnergyMeter_Measure2_mc" name_en="Counter output Manual control" name_fi="LV energia Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="625" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DHMeasures_EnergyMeter_Measure2_mc" name_en="Counter output Manual control" name_fi="KL energia Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="657" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DHMeasures_WaterMeasure_Measure2_mc" name_en="Counter output Manual control" name_fi="KL Vesimäärä Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="658" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_CurveOut_mc" name_en="According to curve Manual control" name_fi="Käyrän mukaan Käsiajo" name_sv="Enligt kurvan Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="447" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_SupplyWaterSet_mc" name_en="Calculated supply water setting Manual control" name_fi="Laskennall. menoveden asetusarvo Käsiajo" name_sv="Beräknad inst.värde för framledningstemp. Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="448" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_ParallelShiftEffect_mc" name_en="Parallel shift Manual control" name_fi="Suuntaissiirto Käsiajo" name_sv="Parallellförskjutning Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="449" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_AutumnDryEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkning  Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="450" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_Measure3_mc" name_en="Output3 Manual control" name_fi="Kesäpysäytystila Käsiajo" name_sv="Termostat utgång Manuell styrning" name_et=" käsijuhtimisrežiim" name_ru=" Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="354" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="G102_EnergyMeter_Measure2_mc" name_en="Counter output Manual control" name_fi="IV-Verkosto energia Käsiajo" name_sv="Skalad utgångsvärde av räknare Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="626" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
    </group>
    <group categorytype="4" name="Hälytykset" name_en="Alarms" name_fi="Hälytykset" name_sv="Larm" name_et="Alarmid" name_ru="Аварийные сигналы" name_lv="Trauksmes" name_tr="Alarmlar " name_pl="Alarmy">
      <point name="BaseCard_Error" name_en="Device's base IO (MB1.BaseCard) not response" name_fi="Laitteen perus IO (MB1.BaseCard) ei vastaa" name_sv="Enhetens basen IO (MB1.BaseCard) svarar inte" name_et="Seade põhi IO (MB1.BaseCard) ei vasta" name_ru="Устройство MB1.BaseCard не отвечает " name_lv="Ierīces base IO (MB1.BaseCard) nav atbildes" name_tr="Cihazın temel IO (MB1.BaseCard) yanıt yok" name_pl="Urządzenie główne IO (MB1.BaseCard) nie odpowiada" pointid="TC08.BaseCard_Error.A" addressindex="581" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="0" severity="1" alarmid="#A0" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_5" name_en="Sensor fault BaseCard UI 5" name_fi="Anturivika TE31 Lämmin käyttövesi" name_sv="Sensorfel BaseCard UI 5" name_et="Sensori viga BaseCard UI 5" name_ru="Неисправность датчика BaseCard UI 5" name_lv="Sensora kļūda BaseCard UI 5" name_tr="Sensör hatası  BaseCard UI 5" name_pl="Błąd czujnika BaseCard UI 5" pointid="TC08.G201.TE31.SE" refpointid="TC08.G201.TE31.M" addressindex="584" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="1" severity="2" alarmid="#A1" pointtype="14" />
      <point name="MB2_ADDR2_MOD1_C32__Error" name_en="Device MB2.MOD1_C32 in address 2 not response" name_fi="Laite MB2.MOD1_C32 osoitteessa 2 ei vastaa" name_sv="Enhet MB2.MOD1_C32 i adress 2 svarar inte" name_et="Seade MB2.MOD1_C32 aadressil 2 ei vasta" name_ru="Устройство MB2.MOD1_C32 по адресу 2 не отвечает " name_lv="Ierīce MB2.MOD1_C32 adresē 2 nav atbildes" name_tr="Cihaz MB2.MOD1_C32 adres 2 yanıt yok " name_pl="Urządzenie MB2.MOD1_C32 na adresie 2 nie odpowiada" pointid="TC08.MB2_ADDR2_MOD1_C32__Error.A" addressindex="585" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="2" severity="1" alarmid="#A2" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_8" name_en="Sensor fault BaseCard UI 8" name_fi="Anturivika TE41 Patteriverkosto meno" name_sv="Sensorfel BaseCard UI 8" name_et="Sensori viga BaseCard UI 8" name_ru="Неисправность датчика BaseCard UI 8" name_lv="Sensora kļūda BaseCard UI 8" name_tr="Sensör hatası  BaseCard UI 8" name_pl="Błąd czujnika BaseCard UI 8" pointid="TC08.G101.TE41.SE" refpointid="TC08.G101.TE41.M" addressindex="609" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="3" severity="2" alarmid="#A3" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_9" name_en="Sensor fault BaseCard UI 9" name_fi="Anturivika TE42 Patteriverkosto paluu" name_sv="Sensorfel BaseCard UI 9" name_et="Sensori viga BaseCard UI 9" name_ru="Неисправность датчика BaseCard UI 9" name_lv="Sensora kļūda BaseCard UI 9" name_tr="Sensör hatası  BaseCard UI 9" name_pl="Błąd czujnika BaseCard UI 9" pointid="TC08.G101.TE42.SE" refpointid="TC08.G101.TE42.M" addressindex="610" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="4" severity="2" alarmid="#A4" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_6" name_en="Sensor fault BaseCard UI 6" name_fi="Anturivika TE32 Käyttöveden kierto" name_sv="Sensorfel BaseCard UI 6" name_et="Sensori viga BaseCard UI 6" name_ru="Неисправность датчика BaseCard UI 6" name_lv="Sensora kļūda BaseCard UI 6" name_tr="Sensör hatası  BaseCard UI 6" name_pl="Błąd czujnika BaseCard UI 6" pointid="TC08.G201.TE32.SE" refpointid="TC08.G201.TE32.M" addressindex="611" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="5" severity="2" alarmid="#A5" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_7" name_en="Sensor fault BaseCard UI 7" name_fi="Anturivika TE33 Kylmä käyttövesi" name_sv="Sensorfel BaseCard UI 7" name_et="Sensori viga BaseCard UI 7" name_ru="Неисправность датчика BaseCard UI 7" name_lv="Sensora kļūda BaseCard UI 7" name_tr="Sensör hatası  BaseCard UI 7" name_pl="Błąd czujnika BaseCard UI 7" pointid="TC08.G201.TE33.SE" refpointid="TC08.G201.TE33.M" addressindex="612" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="6" severity="2" alarmid="#A6" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_10" name_en="Sensor fault BaseCard UI 10" name_fi="Anturivika TE41 IV-Verkosto meno" name_sv="Sensorfel BaseCard UI 10" name_et="Sensori viga BaseCard UI 10" name_ru="Неисправность датчика BaseCard UI 10" name_lv="Sensora kļūda BaseCard UI 10" name_tr="Sensör hatası  BaseCard UI 10" name_pl="Błąd czujnika BaseCard UI 10" pointid="TC08.G102.TE41.SE" refpointid="TC08.G102.TE41.M" addressindex="613" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="7" severity="2" alarmid="#A7" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_11" name_en="Sensor fault BaseCard UI 11" name_fi="Anturivika TE42 IV-Verkosto paluu" name_sv="Sensorfel BaseCard UI 11" name_et="Sensori viga BaseCard UI 11" name_ru="Неисправность датчика BaseCard UI 11" name_lv="Sensora kļūda BaseCard UI 11" name_tr="Sensör hatası  BaseCard UI 11" name_pl="Błąd czujnika BaseCard UI 11" pointid="TC08.G102.TE42.SE" refpointid="TC08.G102.TE42.M" addressindex="614" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="8" severity="2" alarmid="#A8" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_3" name_en="Sensor fault BaseCard UI 3" name_fi="Anturivika TE41 Kaukolämpö tulo" name_sv="Sensorfel BaseCard UI 3" name_et="Sensori viga BaseCard UI 3" name_ru="Неисправность датчика BaseCard UI 3" name_lv="Sensora kļūda BaseCard UI 3" name_tr="Sensör hatası  BaseCard UI 3" name_pl="Błąd czujnika BaseCard UI 3" pointid="TC08.TE41.SE" refpointid="TC08.G100.TE41.M" addressindex="582" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="9" severity="2" alarmid="#A9" pointtype="14" />
      <point name="SensorFaultAlarm_BaseCard_UI_4" name_en="Sensor fault BaseCard UI 4" name_fi="Anturivika TE42 Kaukolämpö paluu" name_sv="Sensorfel BaseCard UI 4" name_et="Sensori viga BaseCard UI 4" name_ru="Неисправность датчика BaseCard UI 4" name_lv="Sensora kļūda BaseCard UI 4" name_tr="Sensör hatası  BaseCard UI 4" name_pl="Błąd czujnika BaseCard UI 4" pointid="TC08.TE42.SE" refpointid="TC08.G100.TE42.M" addressindex="583" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="10" severity="2" alarmid="#A10" pointtype="14" />
      <point name="MBTCP_ADDR172_16_100_20_VAK1__Error" name_en="Device MBTCP.VAK1 in bus ModbusTCP not response" name_fi="Laite MBTCP.VAK1 väylässä ModbusTCP ei vastaa" name_sv="Enhet MBTCP.VAK1 i buss ModbusTCP svarar inte" name_et="Seade MBTCP.VAK1 buss ModbusTCP ei vasta" name_ru="Устройство MBTCP.VAK1 по адресу ModbusTCP не отвечает " name_lv="Ierīce MBTCP.VAK1 in bus ModbusTCP nav atbildes" name_tr="Cihaz MBTCP.VAK1 adresModbusTCP yanıt yok " name_pl="Urządzenie MBTCP.VAK1 na magistrali ModbusTCP nie odpowiada" pointid="TC08.MBTCP_ADDR172_16_100_20_VAK1__Error.A" addressindex="672" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="11" severity="1" alarmid="#A11" pointtype="14" />
      <point name="SensorFaultAlarm_MOD1_C32_UI_10" name_en="Sensor fault MOD1_C32 UI 10" name_fi="Anturivika TE16 Huonelämpötila LJH" name_sv="Sensorfel MOD1_C32 UI 10" name_et="Sensori viga MOD1_C32 UI 10" name_ru="Неисправность датчика MOD1_C32 UI 10" name_lv="Sensora kļūda MOD1_C32 UI 10" name_tr="Sensör hatası  MOD1_C32 UI 10" name_pl="Błąd czujnika MOD1_C32 UI 10" pointid="TC08.TE16.SE" refpointid="TC08.G410.TE16.M" addressindex="673" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="12" severity="2" alarmid="#A12" pointtype="14" />
      <point name="G101_ContradictionAlarm_A" name_en="Contradiction alarm" name_fi="Patteriverkosto pumppu ristiriita" name_sv="Konfliktlarm" name_et="" name_ru="" pointid="TC08.G101.P01_IND.A1" refpointid="TC08.G101.P01_IND.I" addressindex="586" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="13" severity="1" alarmid="#A13" pointtype="14" />
      <point name="G101_AnalogAlarm_A" name_en="Pressure alarm" name_fi="Painehäl. Patteriverkosto" name_sv="Trycklarm" name_et="" name_ru="" pointid="TC08.G101.PIE01.A1" refpointid="TC08.G101.PIE01.M" addressindex="587" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="14" severity="1" alarmid="#A14" pointtype="14" />
      <point name="G101_Alarm" name_en="Freeze risk" name_fi="Jäätymisvaara patteriverkosto" name_sv="Frysrisk" name_et="" name_ru="" pointid="TC08.G101.TE41.A1" refpointid="TC08.G101.TE41.M" addressindex="588" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="15" severity="1" alarmid="#A15" pointtype="14" />
      <point name="G101_DeviationAlarm_A" name_en="Deviation alarm" name_fi="Poikkeamahäl. patteriverkosto" name_sv="Avvikelselarm" name_et="" name_ru="" pointid="TC08.G101.TE41.A2" refpointid="TC08.G101.TE41.M" addressindex="589" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="16" severity="1" alarmid="#A16" pointtype="14" />
      <point name="G101_BinaryAlarm_A" name_en="BinaryAlarm" name_fi="Patteriverkosto pumppu vika" name_sv="BinaryAlarm" name_et="BinaryAlarm" name_ru="BinaryAlarm" name_lv="BinaryAlarm" name_tr="BinaryAlarm" name_pl="BinaryAlarm" pointid="TC08.G101.P01_AL.A1" refpointid="TC08.G101.P01_AL.I" addressindex="590" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="17" severity="1" alarmid="#A17" pointtype="14" />
      <point name="G101_Alarm2" name_en="DeviationAlarm" name_fi="Patteriverk. pumpun painepoikkeama" name_sv="DeviationAlarm" name_et="DeviationAlarm" name_ru="DeviationAlarm" name_lv="DeviationAlarm" name_tr="DeviationAlarm" name_pl="DeviationAlarm" pointid="TC08.G101.PDIE02.A1" refpointid="TC08.G101.PDIE02.M" addressindex="615" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="18" severity="1" alarmid="#A18" pointtype="14" />
      <point name="G201_AnalogAlarm_A" name_en="HW Overheating alarm" name_fi="Ylilämpöhälytys käyttövesi laaj." name_sv="TV Överhettningslarm" name_et="AnalogAlarm" pointid="TC08.G201.TE31.A1" refpointid="TC08.G201.TE31.M" addressindex="591" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="19" severity="1" alarmid="#A19" pointtype="14" />
      <point name="G201_DeviationAlarm_A" name_en="DHW deviation alarm" name_fi="poikkeamahälytys käyttövesi laaj." name_sv="TVV avvikelselarm" name_et="DHW deviation alarm" name_ru="DHW deviation alarm" pointid="TC08.G201.TE31.A2" refpointid="TC08.G201.TE31.M" addressindex="592" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="20" severity="2" alarmid="#A20" pointtype="14" />
      <point name="G201_BinaryAlarm_A" name_en="BinaryAlarm" name_fi="Käyttövesi kiertopumppu VIKA" name_sv="BinaryAlarm" name_et="BinaryAlarm" name_ru="BinaryAlarm" name_lv="BinaryAlarm" name_tr="BinaryAlarm" name_pl="BinaryAlarm" pointid="TC08.G201.P01_AL.A2" refpointid="TC08.G201.P01_AL.I" addressindex="593" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="21" severity="1" alarmid="#A21" pointtype="14" />
      <point name="G201_ContradictionAlarm_A" name_en="ContradictionAlarm" name_fi="Käyttövesi kiertopumppu SEIS" name_sv="ContradictionAlarm" name_et="ContradictionAlarm" name_ru="ContradictionAlarm" name_lv="ContradictionAlarm" name_tr="ContradictionAlarm" name_pl="ContradictionAlarm" pointid="TC08.G201.P01_IND.A1" refpointid="TC08.G201.P01_IND.I" addressindex="616" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="22" severity="1" alarmid="#A22" pointtype="14" />
      <point name="G410_AnalogAlarm_A" name_en="AnalogAlarm" name_fi="LJH Lämpötila alaraja" name_sv="AnalogAlarm" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="AnalogAlarm" name_pl="AnalogAlarm" pointid="TC08.G410.TE16.LL1" refpointid="TC08.G410.TE16.M" addressindex="690" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="23" severity="1" alarmid="#A23" pointtype="14" />
      <point name="G410_AnalogAlarm2_A" name_en="AnalogAlarm2" name_fi="LJH Lämpötila yläraja" name_sv="AnalogAlarm2" name_et="AnalogAlarm2" name_ru="AnalogAlarm2" name_lv="AnalogAlarm2" name_tr="AnalogAlarm2" name_pl="AnalogAlarm2" pointid="TC08.G410.TE16.HL2" refpointid="TC08.G410.TE16.M" addressindex="691" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="24" severity="1" alarmid="#A24" pointtype="14" />
      <point name="DHMeasures_AnalogAlarm_A" name_en="AnalogAlarm" name_fi="Kaukolämpö alaraja" name_sv="AnalogAlarm" name_et="AnalogAlarm" name_ru="AnalogAlarm" name_lv="AnalogAlarm" name_tr="AnalogAlarm" name_pl="AnalogAlarm" pointid="TC08.G100.TE41.A1" refpointid="TC08.G100.TE41.M" addressindex="671" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="25" severity="1" alarmid="#A25" pointtype="14" />
      <point name="G102_ContradictionAlarm_A" name_en="Contradiction alarm" name_fi="IV-Verkosto pumppu ristiriita" name_sv="Konfliktlarm" name_et="" name_ru="" pointid="TC08.G102.P01_IND.A1" refpointid="TC08.G102.P01_IND.I" addressindex="594" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="26" severity="1" alarmid="#A26" pointtype="14" />
      <point name="G102_AnalogAlarm_A" name_en="Pressure alarm" name_fi="Painehäl. IV-Verkosto" name_sv="Trycklarm" name_et="" name_ru="" pointid="TC08.G102.PIE01.A1" refpointid="TC08.G102.PIE01.M" addressindex="595" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="27" severity="1" alarmid="#A27" pointtype="14" />
      <point name="G102_Alarm" name_en="Freeze risk" name_fi="Jäätymisvaara IV-Verkosto" name_sv="Frysrisk" name_et="" name_ru="" pointid="TC08.G102.TE41.A1" refpointid="TC08.G102.TE41.M" addressindex="596" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="28" severity="1" alarmid="#A28" pointtype="14" />
      <point name="G102_DeviationAlarm_A" name_en="Deviation alarm" name_fi="Poikkeamahäl. IV-Verkosto" name_sv="Avvikelselarm" name_et="" name_ru="" pointid="TC08.G102.TE41.A2" refpointid="TC08.G102.TE41.M" addressindex="597" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="29" severity="1" alarmid="#A29" pointtype="14" />
      <point name="G102_BinaryAlarm_A" name_en="BinaryAlarm" name_fi="IV-Verkosto pumppu VIKA" name_sv="BinaryAlarm" name_et="BinaryAlarm" name_ru="BinaryAlarm" name_lv="BinaryAlarm" name_tr="BinaryAlarm" name_pl="BinaryAlarm" pointid="TC08.G102.P01_AL.A1" refpointid="TC08.G102.P01_AL.I" addressindex="598" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="30" severity="1" alarmid="#A30" pointtype="14" />
      <point name="G102_Alarm2" name_en="DeviationAlarm" name_fi="IV-Verkosto pumpun painepoikkeama" name_sv="DeviationAlarm" name_et="DeviationAlarm" name_ru="DeviationAlarm" name_lv="DeviationAlarm" name_tr="DeviationAlarm" name_pl="DeviationAlarm" pointid="TC08.G102.PDIE02.A1" refpointid="TC08.G102.PDIE02.M" addressindex="617" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="58" transferackindex="59" ackvalue="31" severity="1" alarmid="#A31" pointtype="14" />
    </group>
  </groups>
</controllertemplate>