<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="G109TC09" version="0.0.0" createppg="false" language="fi-FI" type="Modbus">
  <targetdetails deviceposition="TC09" targetposition="" target="Fredriksberg A" location="K1-KRS. LJH" address="Konepajankuja 1" city="Helsinki" postnumber="00510" contactperson="Iiro Taskinen" loadedtodevice="21.2.2018 9.38" loader="iiro.taskinen" deviceversion="2.2" />
  <groups>
    <group categorytype="1" name="Aika-asetukset">
      <point name="Vuosi" datetype="0" pointid="DTYEAR" pointtype="0" registertype="Holding" addressformat="U16" addressindex="2" readacceslevel="5" writeacceslevel="1" min="2008" max="2100" />
      <point name="Kuukausi" datetype="1" pointid="DTMONTH" pointtype="0" registertype="Holding" addressformat="U16" addressindex="3" enum="1=tammikuu;2=helmikuu;3=maaliskuu;4=huhtikuu;5=toukokuu;6=kesäkuu;7=heinäkuu;8=elokuu;9=syyskuu;10=lokakuu;11=marraskuu;12=joulukuu" readacceslevel="5" writeacceslevel="1" />
      <point name="Päivä" datetype="2" pointid="DTDAY" pointtype="0" registertype="Holding" addressformat="U16" addressindex="4" readacceslevel="5" writeacceslevel="1" />
      <point name="Tunti" datetype="3" pointid="DTHOUR" pointtype="0" registertype="Holding" addressformat="U16" addressindex="6" readacceslevel="5" writeacceslevel="1" />
      <point name="Minuutti" datetype="4" pointid="DTMINUTE" pointtype="0" registertype="Holding" addressformat="U16" addressindex="7" readacceslevel="5" writeacceslevel="1" />
      <point name="Viikonpäivä" datetype="5" pointid="DTDAYOFWEEK" pointtype="0" registertype="Holding" addressformat="U16" addressindex="5" enum="1=Maanantai;2=Tiistai;3=Keskiviikko;4=Torstai;5=Perjantai;6=Lauantai;7=Sunnuntai" readacceslevel="5" writeacceslevel="1" />
    </group>
    <group categorytype="2" name="Järjestelmäasetukset">
      <point name="Device version" pointid="SYSDEVVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="15" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="Application version" pointid="SYSAPPVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="16" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="IO-card version" pointid="SYSIOVERSION" pointtype="21" registertype="Holding" addressformat="U16" addressindex="17" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="Serialnumber" pointid="SYSSERIALNUMBER" pointtype="21" registertype="Holding" addressformat="U16" addressindex="18" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="65536" />
      <point name="SNMP enable" pointid="SYSSNMP" pointtype="21" registertype="Holding" addressformat="U16" addressindex="19" categorytype="3" readacceslevel="5" writeacceslevel="1" min="0" max="1" />
      <point name="FTP enable" pointid="SYSFTP" pointtype="21" registertype="Holding" addressformat="U16" addressindex="20" categorytype="3" readacceslevel="5" writeacceslevel="1" min="0" max="1" />
    </group>
    <group categorytype="2" name="Normaalit pisteet">
      <pointgroup name="Kaukokylmä tulo" technicalname="UI 1" channel="UI 1" group="Fyysiset pisteet" connectors="1;G0">
        <point name="Kaukokylmä tulo" pointid="TC09.G400.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Kaukokylmä tulo, ohjaustapa" pointid="TC09.G400.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="283" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kaukokylmä paluu" technicalname="UI 2" channel="UI 2" group="Fyysiset pisteet" connectors="2;G0">
        <point name="Kaukokylmä paluu" pointid="TC09.G400.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Kaukokylmä paluu, ohjaustapa" pointid="TC09.G400.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="284" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähdytys menovesi" technicalname="UI 3" channel="UI 3" group="Fyysiset pisteet" connectors="3;G0">
        <point name="IV-Jäähdytys menovesi" pointid="TC09.G401.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähdytys menovesi, ohjaustapa" pointid="TC09.G401.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="285" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähdytys paluuvesi" technicalname="UI 4" channel="UI 4" group="Fyysiset pisteet" connectors="4;G0">
        <point name="IV-Jäähdytys paluuvesi" pointid="TC09.G401.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähdytys paluuvesi, ohjaustapa" pointid="TC09.G401.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="286" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. verkoston paine" technicalname="UI 5" channel="UI 5" group="Fyysiset pisteet" connectors="5;G0">
        <point name="IV-Jäähd. verkoston paine" pointid="TC09.G401.PIE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6">
          <point name="IV-Jäähd. verkoston paine, ohjaustapa" pointid="TC09.G401.PIE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="287" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. Verkoston paine-ero" technicalname="UI 6" channel="UI 6" group="Fyysiset pisteet" connectors="6;G0">
        <point name="IV-Jäähd. Verkoston paine-ero" pointid="TC09.G401.PDIE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="400">
          <point name="IV-Jäähd. Verkoston paine-ero, ohjaustapa" pointid="TC09.G401.PDIE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="288" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. menovesi" technicalname="UI 7" channel="UI 7" group="Fyysiset pisteet" connectors="7;G0">
        <point name="Säteilyjäähd. menovesi" pointid="TC09.G402.TE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Säteilyjäähd. menovesi, ohjaustapa" pointid="TC09.G402.TE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="289" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. paluuvesi" technicalname="UI 8" channel="UI 8" group="Fyysiset pisteet" connectors="8;G0">
        <point name="Säteilyjäähd. paluuvesi" pointid="TC09.G402.TE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Säteilyjäähd. paluuvesi, ohjaustapa" pointid="TC09.G402.TE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="290" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. verkoston paine" technicalname="UI 9" channel="UI 9" group="Fyysiset pisteet" connectors="9;G0">
        <point name="Säteilyjäähd. verkoston paine" pointid="TC09.G402.PIE42.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="6">
          <point name="Säteilyjäähd. verkoston paine, ohjaustapa" pointid="TC09.G402.PIE42.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="291" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. verkoston paine-ero" technicalname="UI 10" channel="UI 10" group="Fyysiset pisteet" connectors="10;G0">
        <point name="Säteilyjäähd. verkoston paine-ero" pointid="TC09.G402.PDIE41.M" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="400">
          <point name="Säteilyjäähd. verkoston paine-ero, ohjaustapa" pointid="TC09.G402.PDIE41.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="292" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 1 tila" technicalname="UI 11" channel="UI 11" group="Fyysiset pisteet" connectors="11;G0">
        <point name="IV-Jäähd. pumppu 1 tila" pointid="TC09.G401.P01.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="221" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähd. pumppu 1 tila, ohjaustapa" pointid="TC09.G401.P01.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="293" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 1 häl." technicalname="UI 12" channel="UI 12" group="Fyysiset pisteet" connectors="12;G0">
        <point name="IV-Jäähd. pumppu 1 häl." pointid="TC09.G401.P01.A" pointtype="8" registertype="Holding" addressformat="S32" addressindex="223" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähd. pumppu 1 häl., ohjaustapa" pointid="TC09.G401.P01.A_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="294" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 2 tila" technicalname="UI 13" channel="UI 13" group="Fyysiset pisteet" connectors="13;G0">
        <point name="IV-Jäähd. pumppu 2 tila" pointid="TC09.G401.P02.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="225" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähd. pumppu 2 tila, ohjaustapa" pointid="TC09.G401.P02.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="295" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 2 häl." technicalname="UI 14" channel="UI 14" group="Fyysiset pisteet" connectors="14;G0">
        <point name="IV-Jäähd. pumppu 2 häl." pointid="TC09.G401.P02.A" pointtype="8" registertype="Holding" addressformat="S32" addressindex="227" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="IV-Jäähd. pumppu 2 häl., ohjaustapa" pointid="TC09.G401.P02.A_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="296" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. pumppu tila" technicalname="UI 15" channel="UI 15" group="Fyysiset pisteet" connectors="15;G0">
        <point name="Säteilyjäähd. pumppu tila" pointid="TC09.G402.P01.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="229" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Säteilyjäähd. pumppu tila, ohjaustapa" pointid="TC09.G402.P01.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="297" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. pumppu häl." technicalname="UI 16" channel="UI 16" group="Fyysiset pisteet" connectors="16;G0">
        <point name="Säteilyjäähd. pumppu häl." pointid="TC09.G402.P01.A" pointtype="8" registertype="Holding" addressformat="S32" addressindex="231" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Säteilyjäähd. pumppu häl., ohjaustapa" pointid="TC09.G402.P01.A_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="298" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Energiamittaus MWh" technicalname="DI 1" channel="DI 1" group="Fyysiset pisteet" connectors="21">
        <point name="Energiamittaus MWh" pointid="TC09.G400.QQ01.1.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="233" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+35">
          <point name="Energiamittaus MWh, ohjaustapa" pointid="TC09.G400.QQ01.1.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="299" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Energiamittaus m3" technicalname="DI 2" channel="DI 2" group="Fyysiset pisteet" connectors="22">
        <point name="Energiamittaus m3" pointid="TC09.G400.QQ01.2.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="235" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+33">
          <point name="Energiamittaus m3, ohjaustapa" pointid="TC09.G400.QQ01.2.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="300" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Internal power failure indication" technicalname="PFI" group="Fyysiset pisteet">
        <point name="Internal power failure indication" pointid="TC09.PFI.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="237" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Internal power failure indication, ohjaustapa" pointid="TC09.PFI.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="301" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 1" technicalname="AO 1" channel="AO 1" group="Fyysiset pisteet" connectors="61;G0">
        <point name="AO 1" pointid="TC09.AO 1.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="239" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 1, ohjaustapa" pointid="TC09.AO 1.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="302" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="AO 2" technicalname="AO 2" channel="AO 2" group="Fyysiset pisteet" connectors="62;G0">
        <point name="AO 2" pointid="TC09.AO 2.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="240" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="AO 2, ohjaustapa" pointid="TC09.AO 2.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="303" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 1 säätö" technicalname="AO 3" channel="AO 3" group="Fyysiset pisteet" connectors="63;G0">
        <point name="IV-Jäähd. pumppu 1 säätö" pointid="TC09.G401.P01.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="241" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Jäähd. pumppu 1 säätö, ohjaustapa" pointid="TC09.G401.P01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="304" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 2 säätö" technicalname="AO 4" channel="AO 4" group="Fyysiset pisteet" connectors="64;G0">
        <point name="IV-Jäähd. pumppu 2 säätö" pointid="TC09.G401.P02.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="242" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Jäähd. pumppu 2 säätö, ohjaustapa" pointid="TC09.G401.P02.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="305" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="säteilyjääh. pumppu säätö" technicalname="AO 5" channel="AO 5" group="Fyysiset pisteet" connectors="65;G0">
        <point name="säteilyjääh. pumppu säätö" pointid="TC09.G402.P01.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="243" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="säteilyjääh. pumppu säätö, ohjaustapa" pointid="TC09.G402.P01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="306" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. venttiili 1 säätö" technicalname="AO 6" channel="AO 6" group="Fyysiset pisteet" connectors="66;G0">
        <point name="IV-Jäähd. venttiili 1 säätö" pointid="TC09.G401.FV01.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="244" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Jäähd. venttiili 1 säätö, ohjaustapa" pointid="TC09.G401.FV01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="307" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 1" technicalname="TR 1" channel="TR 1" group="Fyysiset pisteet" connectors="42">
        <point name="TR 1" pointid="TC09.TR 1.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="245" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 1, ohjaustapa" pointid="TC09.TR 1.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="308" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 2" technicalname="TR 2" channel="TR 2" group="Fyysiset pisteet" connectors="43">
        <point name="TR 2" pointid="TC09.TR 2.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="246" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 2, ohjaustapa" pointid="TC09.TR 2.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="309" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 3" technicalname="TR 3" channel="TR 3" group="Fyysiset pisteet" connectors="44">
        <point name="TR 3" pointid="TC09.TR 3.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="247" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 3, ohjaustapa" pointid="TC09.TR 3.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="310" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="TR 4" technicalname="TR 4" channel="TR 4" group="Fyysiset pisteet" connectors="45">
        <point name="TR 4" pointid="TC09.TR 4.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="248" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="TR 4, ohjaustapa" pointid="TC09.TR 4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="311" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 1 ohj." technicalname="R1" channel="R1" group="Fyysiset pisteet" connectors="71;72">
        <point name="IV-Jäähd. pumppu 1 ohj." pointid="TC09.G401.P01.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="249" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="IV-Jäähd. pumppu 1 ohj., ohjaustapa" pointid="TC09.G401.P01.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="312" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. pumppu 2 ohj." technicalname="R2" channel="R2" group="Fyysiset pisteet" connectors="74;75">
        <point name="IV-Jäähd. pumppu 2 ohj." pointid="TC09.G401.P02.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="250" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="IV-Jäähd. pumppu 2 ohj., ohjaustapa" pointid="TC09.G401.P02.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="313" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. pumppu ohj." technicalname="R3" channel="R3" group="Fyysiset pisteet" connectors="77">
        <point name="Säteilyjäähd. pumppu ohj." pointid="TC09.G402.P01.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="251" categorytype="3" enum="0=Seis;1=Käy" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Säteilyjäähd. pumppu ohj., ohjaustapa" pointid="TC09.G402.P01.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="314" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R4" technicalname="R4" channel="R4" group="Fyysiset pisteet" connectors="79">
        <point name="R4" pointid="TC09.R4.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="252" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R4, ohjaustapa" pointid="TC09.R4.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="315" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R5" technicalname="R5" channel="R5" group="Fyysiset pisteet" connectors="81">
        <point name="R5" pointid="TC09.R5.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="253" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R5, ohjaustapa" pointid="TC09.R5.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="316" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="R6" technicalname="R6" channel="R6" group="Fyysiset pisteet" connectors="83">
        <point name="R6" pointid="TC09.R6.S" pointtype="9" registertype="Holding" addressformat="U16" addressindex="254" categorytype="3" enum="0=Off;1=On" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="R6, ohjaustapa" pointid="TC09.R6.S_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="317" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="JVP01 Lämpösuoja häl." technicalname="MB2_ADDR2_MOD1_C32_UI1" channel="MB2_ADDR2_MOD1_C32_UI1" group="Fyysiset pisteet" connectors="1;G0">
        <point name="JVP01 Lämpösuoja häl." pointid="TC09.JVP01.1.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="255" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="JVP01 Lämpösuoja häl., ohjaustapa" pointid="TC09.JVP01.1.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="318" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="JVP01 Pinta häl." technicalname="MB2_ADDR2_MOD1_C32_UI2" channel="MB2_ADDR2_MOD1_C32_UI2" group="Fyysiset pisteet" connectors="2;G0">
        <point name="JVP01 Pinta häl." pointid="TC09.JVP01.2.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="257" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="JVP01 Pinta häl., ohjaustapa" pointid="TC09.JVP01.2.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="319" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="PEK01 Lämpösuoja häl." technicalname="MB2_ADDR2_MOD1_C32_UI3" channel="MB2_ADDR2_MOD1_C32_UI3" group="Fyysiset pisteet" connectors="3;G0">
        <point name="PEK01 Lämpösuoja häl." pointid="TC09.PEK01.1.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="259" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="PEK01 Lämpösuoja häl., ohjaustapa" pointid="TC09.PEK01.1.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="320" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="PEK01 Pinta häl." technicalname="MB2_ADDR2_MOD1_C32_UI4" channel="MB2_ADDR2_MOD1_C32_UI4" group="Fyysiset pisteet" connectors="4;G0">
        <point name="PEK01 Pinta häl." pointid="TC09.PEK01.2.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="261" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="PEK01 Pinta häl., ohjaustapa" pointid="TC09.PEK01.2.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="321" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="REK01 Lämpösuoja häl." technicalname="MB2_ADDR2_MOD1_C32_UI5" channel="MB2_ADDR2_MOD1_C32_UI5" group="Fyysiset pisteet" connectors="5;G0">
        <point name="REK01 Lämpösuoja häl." pointid="TC09.REK01.1.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="263" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="REK01 Lämpösuoja häl., ohjaustapa" pointid="TC09.REK01.1.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="322" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="REK01 Pinta häl." technicalname="MB2_ADDR2_MOD1_C32_UI6" channel="MB2_ADDR2_MOD1_C32_UI6" group="Fyysiset pisteet" connectors="6;G0">
        <point name="REK01 Pinta häl." pointid="TC09.REK01.2.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="265" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="REK01 Pinta häl., ohjaustapa" pointid="TC09.REK01.2.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="323" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="HEK01 Lämpösuoja häl." technicalname="MB2_ADDR2_MOD1_C32_UI7" channel="MB2_ADDR2_MOD1_C32_UI7" group="Fyysiset pisteet" connectors="7;G0">
        <point name="HEK01 Lämpösuoja häl." pointid="TC09.HEK01.1.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="267" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="HEK01 Lämpösuoja häl., ohjaustapa" pointid="TC09.HEK01.1.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="324" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="HEK01 Pinta häl." technicalname="MB2_ADDR2_MOD1_C32_UI8" channel="MB2_ADDR2_MOD1_C32_UI8" group="Fyysiset pisteet" connectors="8;G0">
        <point name="HEK01 Pinta häl." pointid="TC09.HEK01.2.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="269" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="HEK01 Pinta häl., ohjaustapa" pointid="TC09.HEK01.2.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="325" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Ilmanpoistolaite häl." technicalname="MB2_ADDR2_MOD1_C32_UI10" channel="MB2_ADDR2_MOD1_C32_UI10" group="Fyysiset pisteet" connectors="10;G0">
        <point name="Ilmanpoistolaite häl." pointid="TC09.IPL01.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="271" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Ilmanpoistolaite häl., ohjaustapa" pointid="TC09.IPL01.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="326" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Palopelti LJH häl." technicalname="MB2_ADDR2_MOD1_C32_UI11" channel="MB2_ADDR2_MOD1_C32_UI11" group="Fyysiset pisteet" connectors="11;G0">
        <point name="Palopelti LJH häl." pointid="TC09.302PP15.21_15.17_17.17.I" pointtype="8" registertype="Holding" addressformat="S32" addressindex="273" categorytype="3" enum="0=Normaali;1=Hälytys" decimals="0" readacceslevel="5" writeacceslevel="1" min="-50" max="100">
          <point name="Palopelti LJH häl., ohjaustapa" pointid="TC09.302PP15.21_15.17_17.17.I_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="327" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Energiamittaus IV-jäähd. MWh" technicalname="MB2_ADDR2_MOD1_C32_UI15" channel="MB2_ADDR2_MOD1_C32_UI15" group="Fyysiset pisteet" connectors="15;G0">
        <point name="Energiamittaus IV-jäähd. MWh" pointid="TC09.G401.QQ42.1.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="275" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+21">
          <point name="Energiamittaus IV-jäähd. MWh, ohjaustapa" pointid="TC09.G401.QQ42.1.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="328" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Energiamittaus säteilijät MWh" technicalname="MB2_ADDR2_MOD1_C32_UI16" channel="MB2_ADDR2_MOD1_C32_UI16" group="Fyysiset pisteet" connectors="16;G0">
        <point name="Energiamittaus säteilijät MWh" pointid="TC09.G402.QQ42.2.P" pointtype="10" registertype="Holding" addressformat="U32" addressindex="277" categorytype="3" decimals="0" readacceslevel="5" writeacceslevel="1" min="0" max="1E+30">
          <point name="Energiamittaus säteilijät MWh, ohjaustapa" pointid="TC09.G402.QQ42.2.P_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="329" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. venttiili 2 säätö" technicalname="MB2_ADDR2_MOD1_C32_AO3" channel="MB2_ADDR2_MOD1_C32_AO3" group="Fyysiset pisteet" connectors="63;G0">
        <point name="IV-Jäähd. venttiili 2 säätö" pointid="TC09.G401.FV02.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="279" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Jäähd. venttiili 2 säätö, ohjaustapa" pointid="TC09.G401.FV02.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="330" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähd. venttiili 3 säätö" technicalname="MB2_ADDR2_MOD1_C32_AO4" channel="MB2_ADDR2_MOD1_C32_AO4" group="Fyysiset pisteet" connectors="64;G0">
        <point name="IV-Jäähd. venttiili 3 säätö" pointid="TC09.G401.FV03.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="280" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="IV-Jäähd. venttiili 3 säätö, ohjaustapa" pointid="TC09.G401.FV03.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="331" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjäähd. vent. 1 säätö" technicalname="MB2_ADDR2_MOD1_C32_AO5" channel="MB2_ADDR2_MOD1_C32_AO5" group="Fyysiset pisteet" connectors="65;G0">
        <point name="Säteilyjäähd. vent. 1 säätö" pointid="TC09.G402.FV01.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="281" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Säteilyjäähd. vent. 1 säätö, ohjaustapa" pointid="TC09.G402.FV01.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="332" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Säteilyjääh. vent. 2 säätö" technicalname="MB2_ADDR2_MOD1_C32_AO6" channel="MB2_ADDR2_MOD1_C32_AO6" group="Fyysiset pisteet" connectors="66;G0">
        <point name="Säteilyjääh. vent. 2 säätö" pointid="TC09.G402.FV02.C" pointtype="7" registertype="Holding" addressformat="U16" addressindex="282" categorytype="3" unit="%" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="100">
          <point name="Säteilyjääh. vent. 2 säätö, ohjaustapa" pointid="TC09.G402.FV02.C_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="333" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Ulkolämpötila väylältä" technicalname="TC09TE00IN">
        <point name="Ulkolämpötila väylältä" pointid="TC09.TE00.IN" pointtype="12" registertype="Holding" addressformat="S32" addressindex="456" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Kaukokylmä m3" technicalname="G400.QQ_012.Measure2" group="G400 Kaukokylmä" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="Kaukokylmä m3" pointid="TC09.G400.QQ01.2.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="335" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Kaukokylmä m3, ohjaustapa" pointid="TC09.G400.QQ01.2.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="356" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Kaukokylmä MWh" technicalname="G400.QQ_011.Measure2" group="G400 Kaukokylmä" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="Kaukokylmä MWh" pointid="TC09.G400.QQ01.1.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="337" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Kaukokylmä MWh, ohjaustapa" pointid="TC09.G400.QQ01.1.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="361" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Skaalaus imp/l" technicalname="G400.QQ_012.Setvalue22" group="G400 Kaukokylmä">
        <point name="Skaalaus imp/l" pointid="TC09.G400.QQ01.2.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="380" categorytype="3" unit="imp/l" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="Kaukokylmä m3 alkuarvo" technicalname="G400.QQ_012.Setvalue21" group="G400 Kaukokylmä" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="Kaukokylmä m3 alkuarvo" pointid="TC09.G400.QQ01.2.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="382" categorytype="3" unit="m3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G400.QQ_011.Setvalue22" group="G400 Kaukokylmä">
        <point name="Skaalaus imp/kwh" pointid="TC09.G400.QQ01.1.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="384" categorytype="3" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="Kaukokylmä MWh alkuarvo" technicalname="G400.QQ_011.Setvalue21" group="G400 Kaukokylmä" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="Kaukokylmä MWh alkuarvo" pointid="TC09.G400.QQ01.1.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="386" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Laskennall. menoveden asetusarvo" technicalname="G401.SupplyWaterSet" group="G401 Jäähdytys konvektorit/IV">
        <point name="Laskennall. menoveden asetusarvo" pointid="TC09.G401.TE41.M9" refpointid="TC09.G401.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="344" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Laskennall. menoveden asetusarvo, ohjaustapa" pointid="TC09.G401.TE41.M9_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="357" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Minimirajan vaikutus" technicalname="G401.MinLimitEffect" group="G401 Jäähdytys konvektorit/IV">
        <point name="Minimirajan vaikutus" pointid="TC09.G401.TE41.M10" refpointid="TC09.G401.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="346" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Jäähdytys" technicalname="G401.CoolingEnable" group="G401 Jäähdytys konvektorit/IV">
        <point name="Jäähdytys" pointid="TC09.G401.P01.M1" refpointid="TC09.G401.P01.S" pointtype="12" registertype="Holding" addressformat="U16" addressindex="348" categorytype="3" enum="0=Pois;1=Päällä" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Jäähdytys, ohjaustapa" pointid="TC09.G401.P01.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="358" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="PID säätimen lähtö" technicalname="G401.Measure" group="G401 Jäähdytys konvektorit/IV" description="PID säätimen lähtö">
        <point name="PID säätimen lähtö" pointid="TC09.G401.Measure.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="339" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="PID säätimen lähtö, ohjaustapa" pointid="TC09.G401.Measure.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="372" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Mittauksen poikkeama asetusarvosta" technicalname="G401.Measure2" group="G401 Jäähdytys konvektorit/IV" description="Mittauksen poikkeama asetusarvosta">
        <point name="Mittauksen poikkeama asetusarvosta" pointid="TC09.G401.Measure2.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="342" categorytype="3" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Mittauksen poikkeama asetusarvosta, ohjaustapa" pointid="TC09.G401.Measure2.M_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="373" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="IV-Jäähdytys energia" technicalname="G401.QQ4212.Measure2" group="G401 Jäähdytys konvektorit/IV" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="IV-Jäähdytys energia" pointid="TC09.G401.QQ42.1.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="349" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="IV-Jäähdytys energia, ohjaustapa" pointid="TC09.G401.QQ42.1.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="376" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Paine alarajahälytys" technicalname="G401.PressAlarmLowLimit" group="G401 Jäähdytys konvektorit/IV">
        <point name="Paine alarajahälytys" pointid="TC09.G401.PIE42.SP3" refpointid="TC09.G401.PIE42.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="362" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Paine ylärajahälytys" technicalname="G401.PressAlarmHighLimit" group="G401 Jäähdytys konvektorit/IV">
        <point name="Paine ylärajahälytys" pointid="TC09.G401.PIE42.SP4" refpointid="TC09.G401.PIE42.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="364" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Menoveden min.raja" technicalname="G401.SupplyWaterMin" group="G401 Jäähdytys konvektorit/IV">
        <point name="Menoveden min.raja" pointid="TC09.G401.TE41.SP16" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="374" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      </pointgroup>
      <pointgroup name="Menovesi P-alue" technicalname="G401.P_Area" group="G401 Jäähdytys konvektorit/IV" description="P-alue">
        <point name="Menovesi P-alue" pointid="TC09.G401.TE41.SP17" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="366" categorytype="3" unit="°C" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Menovesi I-aika (s)" technicalname="G401.I_Time" group="G401 Jäähdytys konvektorit/IV" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Menovesi I-aika (s)" pointid="TC09.G401.TE41.SP18" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="368" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Menovesi D-aika (s)" technicalname="G401.D_Time" group="G401 Jäähdytys konvektorit/IV" description="D-aika sekunteina">
        <point name="Menovesi D-aika (s)" pointid="TC09.G401.TE41.SP19" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="370" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="G401 Menovesiasetus" technicalname="G401.Setvalue" group="G401 Jäähdytys konvektorit/IV">
        <point name="G401 Menovesiasetus" pointid="TC09.G401.TE41.SP20" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="388" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      </pointgroup>
      <pointgroup name="G401 Ulkolämpöraja" technicalname="G401.Setvalue2" group="G401 Jäähdytys konvektorit/IV" description="Asetusarvo">
        <point name="G401 Ulkolämpöraja" pointid="TC09.G401.TE41.SP21" refpointid="TC09.G401.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="402" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      </pointgroup>
      <pointgroup name="Paine-ero P-alue" technicalname="G401.Setvalue3" group="G401 Jäähdytys konvektorit/IV" description="P-alue">
        <point name="Paine-ero P-alue" pointid="TC09.G401.P01.SP1" refpointid="TC09.G401.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="404" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Paine-ero I-aika (s)" technicalname="G401.Setvalue4" group="G401 Jäähdytys konvektorit/IV" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Paine-ero I-aika (s)" pointid="TC09.G401.P01.SP2" refpointid="TC09.G401.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="406" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Paine-ero D-aika (s)" technicalname="G401.Setvalue5" group="G401 Jäähdytys konvektorit/IV" description="D-aika sekunteina">
        <point name="Paine-ero D-aika (s)" pointid="TC09.G401.P01.SP3" refpointid="TC09.G401.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="408" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="G401 Paine-ero asetus" technicalname="G401.Setvalue6" group="G401 Jäähdytys konvektorit/IV">
        <point name="G401 Paine-ero asetus" pointid="TC09.G401.PDIE42.SP1" refpointid="TC09.G401.PDIE42.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="410" categorytype="3" unit="kpa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="250" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G401.QQ4212.Setvalue22" group="G401 Jäähdytys konvektorit/IV">
        <point name="Skaalaus imp/kwh" pointid="TC09.G401.QQ42.1.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="412" categorytype="3" unit="imp/kWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="IV-Jäähdytys alkuarvo" technicalname="G401.QQ4212.Setvalue21" group="G401 Jäähdytys konvektorit/IV" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="IV-Jäähdytys alkuarvo" pointid="TC09.G401.QQ42.1.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="414" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
      <pointgroup name="Laskennall. menoveden asetusarvo" technicalname="G402.SupplyWaterSet" group="G402 Jäähdytys säteilijät">
        <point name="Laskennall. menoveden asetusarvo" pointid="TC09.G402.TE41.M9" refpointid="TC09.G402.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="351" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="Laskennall. menoveden asetusarvo, ohjaustapa" pointid="TC09.G402.TE41.M9_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="377" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Minimirajan vaikutus" technicalname="G402.MinLimitEffect" group="G402 Jäähdytys säteilijät">
        <point name="Minimirajan vaikutus" pointid="TC09.G402.TE41.M10" refpointid="TC09.G402.TE41.M" pointtype="12" registertype="Holding" addressformat="S32" addressindex="353" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608" />
      </pointgroup>
      <pointgroup name="Jäähdytys" technicalname="G402.CoolingEnable" group="G402 Jäähdytys säteilijät">
        <point name="Jäähdytys" pointid="TC09.G402.P01.M1" refpointid="TC09.G402.P01.S" pointtype="12" registertype="Holding" addressformat="U16" addressindex="355" categorytype="3" enum="0=Pois;1=Päällä" decimals="0" readacceslevel="5" writeacceslevel="1">
          <point name="Jäähdytys, ohjaustapa" pointid="TC09.G402.P01.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="378" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="säteilyjäähd. energia" technicalname="G402.QQ4222.Measure2" group="G402 Jäähdytys säteilijät" description="Tulopulsseista skaalattu laskurin lähtöarvo (käyttöliittymässä näytettävä yksikkö)">
        <point name="säteilyjäähd. energia" pointid="TC09.G402.QQ42.2.M1" pointtype="12" registertype="Holding" addressformat="S32" addressindex="359" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="1" min="-8388608" max="8388608">
          <point name="säteilyjäähd. energia, ohjaustapa" pointid="TC09.G402.QQ42.2.M1_CM" pointtype="5" registertype="Holding" addressformat="U16" addressindex="379" categorytype="3" enum="0=Automaatti;1=Käsiajo" decimals="0" scaling="0" readacceslevel="5" writeacceslevel="1" />
        </point>
      </pointgroup>
      <pointgroup name="Paine alarajahälytys" technicalname="G402.PressAlarmLowLimit" group="G402 Jäähdytys säteilijät">
        <point name="Paine alarajahälytys" pointid="TC09.G402.PIE42.SP3" refpointid="TC09.G402.PIE42.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="416" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Paine ylärajahälytys" technicalname="G402.PressAlarmHighLimit" group="G402 Jäähdytys säteilijät">
        <point name="Paine ylärajahälytys" pointid="TC09.G402.PIE42.SP4" refpointid="TC09.G402.PIE42.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="418" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="16" />
      </pointgroup>
      <pointgroup name="Menoveden min.raja" technicalname="G402.SupplyWaterMin" group="G402 Jäähdytys säteilijät">
        <point name="Menoveden min.raja" pointid="TC09.G402.TE41.SP16" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="420" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      </pointgroup>
      <pointgroup name="Menovesi P-alue" technicalname="G402.P_Area" group="G402 Jäähdytys säteilijät" description="P-alue">
        <point name="Menovesi P-alue" pointid="TC09.G402.TE41.SP17" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="422" categorytype="3" unit="°C" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Menovesi I-aika (s)" technicalname="G402.I_Time" group="G402 Jäähdytys säteilijät" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Menovesi I-aika (s)" pointid="TC09.G402.TE41.SP18" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="424" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Menovesi D-aika (s)" technicalname="G402.D_Time" group="G402 Jäähdytys säteilijät" description="D-aika sekunteina">
        <point name="Menovesi D-aika (s)" pointid="TC09.G402.TE41.SP19" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="426" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="G402 Menovesiasetus" technicalname="G402.Setvalue" group="G402 Jäähdytys säteilijät">
        <point name="G402 Menovesiasetus" pointid="TC09.G402.TE41.SP20" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="428" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      </pointgroup>
      <pointgroup name="G402 Ulkolämpöraja" technicalname="G402.Setvalue2" group="G402 Jäähdytys säteilijät" description="Asetusarvo">
        <point name="G402 Ulkolämpöraja" pointid="TC09.G402.TE41.SP21" refpointid="TC09.G402.TE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="430" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      </pointgroup>
      <pointgroup name="Paine-ero P-alue" technicalname="G402.Setvalue3" group="G402 Jäähdytys säteilijät" description="P-alue">
        <point name="Paine-ero P-alue" pointid="TC09.G402.P01.SP1" refpointid="TC09.G402.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="432" categorytype="3" unit="kPa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      </pointgroup>
      <pointgroup name="Paine-ero I-aika (s)" technicalname="G402.Setvalue4" group="G402 Jäähdytys säteilijät" description="I-aika sekunteina. Huom. ei saa asettaa nollaksi. Pelkällä P tai PD -säädöllä säädön poikkeama voi kasvaa ajan kanssa suureksi. ">
        <point name="Paine-ero I-aika (s)" pointid="TC09.G402.P01.SP2" refpointid="TC09.G402.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="434" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      </pointgroup>
      <pointgroup name="Paine-ero D-aika (s)" technicalname="G402.Setvalue5" group="G402 Jäähdytys säteilijät" description="D-aika sekunteina">
        <point name="Paine-ero D-aika (s)" pointid="TC09.G402.P01.SP3" refpointid="TC09.G402.P01.C" pointtype="13" registertype="Holding" addressformat="S32" addressindex="436" categorytype="3" unit="s" decimals="0" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      </pointgroup>
      <pointgroup name="G402 Paine-ero asetus" technicalname="G402.Setvalue6" group="G402 Jäähdytys säteilijät">
        <point name="G402 Paine-ero asetus" pointid="TC09.G402.PDIE41.SP1" refpointid="TC09.G402.PDIE41.M" pointtype="13" registertype="Holding" addressformat="S32" addressindex="438" categorytype="3" unit="kpa" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="250" />
      </pointgroup>
      <pointgroup name="Skaalaus imp/kwh" technicalname="G402.QQ4222.Setvalue22" group="G402 Jäähdytys säteilijät">
        <point name="Skaalaus imp/kwh" pointid="TC09.G402.QQ42.2.SP1" pointtype="13" registertype="Holding" addressformat="S32" addressindex="440" categorytype="3" unit="imp/kwh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="1000" />
      </pointgroup>
      <pointgroup name="säteilijät alkuarvo" technicalname="G402.QQ4222.Setvalue21" group="G402 Jäähdytys säteilijät" description="Asetusarvotulo, jolla voidaan asettaa laskurilähdön alkuarvo">
        <point name="säteilijät alkuarvo" pointid="TC09.G402.QQ42.2.SP2" pointtype="13" registertype="Holding" addressformat="S32" addressindex="442" categorytype="3" unit="mWh" decimals="3" scaling="1000" readacceslevel="5" writeacceslevel="3" min="0" max="9999999" />
      </pointgroup>
    </group>
    <group categorytype="4" name="Hälytykset">
      <point name="Laitteen perus IO (MB1.BaseCard) ei vastaa" technicalname="BaseCard_Error" pointid="TC09.BaseCard_Error.A" addressindex="334" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="0" severity="1" alarmid="#A0" pointtype="14" />
      <point name="Laite MB2.MOD1_C32 osoitteessa 2 ei vastaa" technicalname="MB2_ADDR2_MOD1_C32__Error" pointid="TC09.MB2_ADDR2_MOD1_C32__Error.A" addressindex="341" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="1" severity="1" alarmid="#A1" pointtype="14" />
      <point name="JVP01 Lämpösuoja (JVP01 Lämpösuoja häl.)" technicalname="Alarm" pointid="TC09.JVP01.1.DA0" refpointid="TC09.JVP01.1.I" addressindex="390" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="2" severity="2" alarmid="#A2" pointtype="14" />
      <point name="JPV01 Pinnankorkeus (JVP01 Pinta häl.)" technicalname="Alarm2" pointid="TC09.JVP01.2.DA0" refpointid="TC09.JVP01.2.I" addressindex="391" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="3" severity="2" alarmid="#A3" pointtype="14" />
      <point name="PEK01 Lämpösuoja (PEK01 Lämpösuoja häl.)" technicalname="Alarm3" pointid="TC09.PEK01.1.DA0" refpointid="TC09.PEK01.1.I" addressindex="392" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="4" severity="2" alarmid="#A4" pointtype="14" />
      <point name="PEK01 Pinnankorkeus (PEK01 Pinta häl.)" technicalname="Alarm4" pointid="TC09.PEK01.2.DA0" refpointid="TC09.PEK01.2.I" addressindex="393" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="5" severity="2" alarmid="#A5" pointtype="14" />
      <point name="REK01 Lämpösuoja (REK01 Lämpösuoja häl.)" technicalname="Alarm5" pointid="TC09.REK01.1.DA0" refpointid="TC09.REK01.1.I" addressindex="394" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="6" severity="2" alarmid="#A6" pointtype="14" />
      <point name="REK01 Pinnankorkeus (REK01 Pinta häl.)" technicalname="Alarm6" pointid="TC09.REK01.2.DA0" refpointid="TC09.REK01.2.I" addressindex="395" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="7" severity="2" alarmid="#A7" pointtype="14" />
      <point name="HEK01 Lämpösuoja (HEK01 Lämpösuoja häl.)" technicalname="Alarm7" pointid="TC09.HEK01.1.DA0" refpointid="TC09.HEK01.1.I" addressindex="396" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="8" severity="2" alarmid="#A8" pointtype="14" />
      <point name="HEK01 Pinnankorkeus (HEK01 Pinta häl.)" technicalname="Alarm8" pointid="TC09.HEK01.2.DA0" refpointid="TC09.HEK01.2.I" addressindex="397" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="9" severity="2" alarmid="#A9" pointtype="14" />
      <point name="Ilmanpoistin hälytys (Ilmanpoistolaite häl.)" technicalname="Alarm9" pointid="TC09.IPL01.DA0" refpointid="TC09.IPL01.I" addressindex="398" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="10" severity="2" alarmid="#A10" pointtype="14" />
      <point name="Palopelti LJH Hälytys (Palopelti LJH häl.)" technicalname="Alarm10" pointid="TC09.302PP15.21_15.17_17.17.DA0" refpointid="TC09.302PP15.21_15.17_17.17.I" addressindex="399" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="11" severity="2" alarmid="#A11" pointtype="14" />
      <point name="Anturivika BaseCard Kaukokylmä tulo (Kaukokylmä tulo)" technicalname="SensorFaultAlarm_BaseCard_UI_1" pointid="TC09.G400.TE41.SE" refpointid="TC09.G400.TE41.M" addressindex="444" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="12" severity="2" alarmid="#A12" pointtype="14" />
      <point name="Anturivika BaseCard Kaukokylmä paluu (Kaukokylmä paluu)" technicalname="SensorFaultAlarm_BaseCard_UI_2" pointid="TC09.G400.TE42.SE" refpointid="TC09.G400.TE42.M" addressindex="445" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="13" severity="2" alarmid="#A13" pointtype="14" />
      <point name="Anturivika BaseCard IV-Jäähdytys menovesi (IV-Jäähdytys menovesi)" technicalname="SensorFaultAlarm_BaseCard_UI_3" pointid="TC09.G401.TE41.SE" refpointid="TC09.G401.TE41.M" addressindex="446" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="14" severity="2" alarmid="#A14" pointtype="14" />
      <point name="Anturivika BaseCard IV-Jäähdytys paluuvesi (IV-Jäähdytys paluuvesi)" technicalname="SensorFaultAlarm_BaseCard_UI_4" pointid="TC09.G401.TE42.SE" refpointid="TC09.G401.TE42.M" addressindex="447" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="15" severity="2" alarmid="#A15" pointtype="14" />
      <point name="Anturivika BaseCard Säteilyjäähd. menovesi (Säteilyjäähd. menovesi)" technicalname="SensorFaultAlarm_BaseCard_UI_7" pointid="TC09.G402.TE41.SE" refpointid="TC09.G402.TE41.M" addressindex="448" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="16" severity="2" alarmid="#A16" pointtype="14" />
      <point name="Anturivika BaseCard Säteilyjäähd. paluuvesi (Säteilyjäähd. paluuvesi)" technicalname="SensorFaultAlarm_BaseCard_UI_8" pointid="TC09.G402.TE42.SE" refpointid="TC09.G402.TE42.M" addressindex="449" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="17" severity="2" alarmid="#A17" pointtype="14" />
      <point name="G401.G401 Painehälytys" technicalname="G401.AnalogAlarm_A" pointid="TC09.G401.PIE42.A1" refpointid="TC09.G401.PIE42.M" addressindex="400" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="18" severity="1" alarmid="#A18" pointtype="14" />
      <point name="G401.G401 P1 Ristiriita" technicalname="G401.ContradictionAlarm_A" pointid="TC09.G401.P01.CA1" refpointid="TC09.G401.P01.I" addressindex="401" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="19" severity="1" alarmid="#A19" pointtype="14" />
      <point name="G401.G401 P2 Ristiriita" technicalname="G401.Alarm" pointid="TC09.G401.P02.CA1" refpointid="TC09.G401.P02.I" addressindex="450" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="20" severity="1" alarmid="#A20" pointtype="14" />
      <point name="G401.G401 P1 taajuusmuuttaja" technicalname="G401.BinaryAlarm_A" pointid="TC09.G401.P01.A1" refpointid="TC09.G401.P01.A" addressindex="451" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="21" severity="1" alarmid="#A21" pointtype="14" />
      <point name="G401.G401 P2 Taajuusmuuttaja" technicalname="G401.BinaryAlarm2_A" pointid="TC09.G401.P02.A1" refpointid="TC09.G401.P02.A" addressindex="452" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="22" severity="1" alarmid="#A22" pointtype="14" />
      <point name="G402.G402 Painehälytys" technicalname="G402.AnalogAlarm_A" pointid="TC09.G402.PIE42.A1" refpointid="TC09.G402.PIE42.M" addressindex="453" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="23" severity="1" alarmid="#A23" pointtype="14" />
      <point name="G402.G402 P1 Ristiriita" technicalname="G402.ContradictionAlarm_A" pointid="TC09.G402.P01.CA1" refpointid="TC09.G402.P01.I" addressindex="454" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="24" severity="1" alarmid="#A24" pointtype="14" />
      <point name="G402.G402 P1 taajuusmuuttaja" technicalname="G402.BinaryAlarm_A" pointid="TC09.G402.P01.A1" refpointid="TC09.G402.P01.A" addressindex="455" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="52" transferackindex="53" ackvalue="25" severity="1" alarmid="#A25" pointtype="14" />
    </group>
  </groups>
</controllertemplate>