<?xml version="1.0" encoding="utf-8"?>
<controllertemplate name="C203" version="1.5.0" createppg="false" language="fi-FI" type="Modbus" addressindexstart="1">
  <groups>
    <group categorytype="2" name="Fyysiset pisteet" name_en="Physical points" name_fi="Fyysiset pisteet" name_sv="Fysiska punkter" name_et="Füüsilised punktid" name_ru="Физические точки" name_lv="Fiziskie punkti" name_tr="Fiziksel noktalar ">
      <point name="UI 1" name_en="Outdoor temp." name_fi="Ulkolämpötila" name_sv="Utetemperatur" name_et="Välistemperatuur" name_ru="Наружная темп." name_lv="Ārgaisa temp." name_tr="Outdoor temp." pointtype="6" registertype="Holding" addressformat="S32" addressindex="201" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 2" name_en="H1 Supply water" name_fi="L1 Menovesi" name_sv="V1 Framledningsv." name_et="K1 Küttevesi" name_ru="O1 Подача" name_lv="A1 Turpgaitas" name_tr="Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="203" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 3" name_en="Return water" name_fi="Paluuvesi" name_sv="Returvatten" name_et="Tagastusvesi" name_ru="Темп. обратной воды " name_lv="Atgaitas temperatūra" name_tr="Return water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="205" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 4" name_en="UI 4" name_fi="UI 4" name_sv="UI 4" name_et="UI 4" name_ru="UI 4" name_lv="UI 4: Brīvais mērī./ A1 Telpas temp./ A1 Prim.kont. Atgaitas" pointtype="6" registertype="Holding" addressformat="S32" addressindex="207" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 5" name_en="H2 Supply water" name_fi="L2 Menovesi" name_sv="V2 Framledningsv." name_et="K2 Küttevesi" name_ru="O2 Подача" name_lv="A2 Turpgaitas" name_tr="Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="209" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 6" name_en="Return water" name_fi="Paluuvesi" name_sv="Returvatten" name_et="Tagastusvesi" name_ru="Темп. обратной воды " name_lv="Atgaitas temperatūra" name_tr="Return water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="211" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 7" name_en="UI 7" name_fi="UI 7" name_sv="UI 7" name_et="UI 7" name_ru="UI 7" name_lv="UI 7: Brīvais mērī./ A2 Telpas temp./ A2 Prim.kont. Atgaitas" pointtype="6" registertype="Holding" addressformat="S32" addressindex="213" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 8" name_en="DHW Supply water" name_fi="LV Menovesi" name_sv="TV Framledningsv." name_et="TV Küttevesi" name_ru="ГВС Подача" name_lv="K.ŪD. Turpgaitas" name_tr="Supply water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="215" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 9" name_en="Circulation water" name_fi="Kiertovesi " name_sv="Cirkulation " name_et="Ringlusvesi" name_ru="Циркуляционная вода" name_lv="Karstā ūdens cirkulācijas temp." name_tr="Circulation water" pointtype="6" registertype="Holding" addressformat="S32" addressindex="217" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 10" name_en="UI10" name_fi="UI10" name_sv="UI10" name_et="UI10" name_ru="UI 10" name_lv="UI10: Brīvais mērījums. / Trauksmes relejs" pointtype="6" registertype="Holding" addressformat="S32" addressindex="219" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 11" name_en="UI11" name_fi="UI11" name_sv="UI11" name_et="UI11" name_ru="UI 11" name_lv="UI11: Brīvais mērījums. / Trauksmes relejs" pointtype="6" registertype="Holding" addressformat="S32" addressindex="221" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="130" type="0" iotype="1" />
      <point name="UI 12" name_en="UI 12" name_fi="UI 12" name_sv="UI 12" name_et="UI 12" name_ru="UI 12" name_lv="UI 12: Brīvais mērīj. / Spiediena relejs/Spiediena devējs" pointtype="6" registertype="Holding" addressformat="S32" addressindex="223" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 13" name_en="UI 13" name_fi="UI 13" name_sv="UI 13" name_et="UI 13" name_ru="UI 13" name_lv="UI 13: Brīvais mērīj. / Spiediena relejs/Spiediena devējs" pointtype="6" registertype="Holding" addressformat="S32" addressindex="225" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 14" name_en="UI 14" name_fi="UI 14" name_sv="UI 14" name_et="UI 14" name_ru="UI 14" name_lv="UI 14: Vispārīgā kompensācija/ Mājās / Ārpus mājām – Slēdzis" pointtype="6" registertype="Holding" addressformat="S32" addressindex="227" categorytype="2" unit=" " decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 15" name_en="UI 15" name_fi="UI 15" name_sv="UI 15" name_et="UI 15" name_ru="UI 15" name_lv="UI 15:Trauksme/ Indikācija" pointtype="6" registertype="Holding" addressformat="S32" addressindex="229" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="UI 16" name_en="UI 16" name_fi="UI 16" name_sv="UI 16" name_et="UI 16" name_ru="UI 16" name_lv="UI 16: Trauksme/ Indikācija" pointtype="6" registertype="Holding" addressformat="S32" addressindex="231" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="140" type="0" iotype="1" />
      <point name="DI 1" name_en="DI 1" name_fi="DI 1" name_sv="DI 1" name_et="DI 1" name_ru="DI 1" name_lv="DI 1: Trauks./ Vispārīgā trauks./Ūdens tilpums/Enerģijamēr." pointtype="6" registertype="Holding" addressformat="U32" addressindex="407" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="0" type="2" iotype="1" />
      <point name="DI 2" name_en="DI 2" name_fi="DI 2" name_sv="DI 2" name_et="DI 2" name_ru="DI 2" name_lv="DI 2: Ūdens tilpums/Enerģijamērijum" pointtype="6" registertype="Holding" addressformat="U32" addressindex="945" categorytype="2" readacceslevel="5" writeacceslevel="1" min="0" max="1E+08" type="2" iotype="1" />
      <point name="AO 1" name_en="AO 1" name_fi="Moottoriohjaus, jänniteviesti" name_sv="AO 1" name_et="AO 1" name_ru="AO 1" name_lv="AO1: A1  Izpildmehānisma pozīcija" pointtype="6" registertype="Holding" addressformat="S32" addressindex="236" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 2" name_en="ValveCtrl2" name_fi="Moottoriohjaus, jänniteviesti 2" name_sv="ValveCtrl2" name_et="ValveCtrl2" name_lv="AO2: A1 Izpildmehānisma pozīcija 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="238" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 3" name_en="Valve control" name_fi="Moottoriohjaus, jänniteviesti" name_sv="Ventil styrning" name_lv="AO3: A2 Izpildmehānisma pozīcija" pointtype="6" registertype="Holding" addressformat="S32" addressindex="240" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 4" name_en="ValveCtrl2" name_fi="Moottoriohjaus, jänniteviesti 2" name_sv="ValveCtrl2" name_et="ValveCtrl2" name_lv="Rudens žāv. ietekme uz turpg. temp." pointtype="6" registertype="Holding" addressformat="S32" addressindex="242" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 5" name_en="Output " name_fi="Moottoriohjaus, jänniteviesti" name_lv="AO5: K.ŪD Izpildmehānisma pozīcija" pointtype="6" registertype="Holding" addressformat="S32" addressindex="244" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="AO 6" name_en="ValveCtrl2" name_fi="Moottoriohjaus, jänniteviesti 2" name_sv="ValveCtrl2" name_et="ValveCtrl2" name_lv="AO6: K.ŪD Izpildmehānisma pozīcija 2" pointtype="6" registertype="Holding" addressformat="S32" addressindex="246" categorytype="2" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" type="0" iotype="2" />
      <point name="TR 1" name_en="TR 1" name_fi="TR 1" name_sv="TR 1" name_et="TR 1" name_ru="TR 1" pointtype="6" registertype="Holding" addressformat="U16" addressindex="248" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TR 2" name_en="TR 2" name_fi="TR 2" name_sv="TR 2" name_et="TR 2" name_ru="TR 2" pointtype="6" registertype="Holding" addressformat="U16" addressindex="249" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="R1" name_en="Pump run permission" name_fi="P2 Ohjaus" name_sv="Pump drift lov" name_lv="CS2  Sūkņa vadība" pointtype="6" registertype="Holding" addressformat="U16" addressindex="250" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="R2" name_en="Pump run permission" name_fi="P3 Ohjaus" name_sv="Pump drift lov" name_lv="CS3  Sūkņa vadība" pointtype="6" registertype="Holding" addressformat="U16" addressindex="251" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" iotype="2" />
      <point name="TRS1" name_en="TRS1" name_fi="TRS1" name_sv="TRS1" name_et="TRS1" name_ru="TRS1" pointtype="6" registertype="Holding" addressformat="U16" addressindex="252" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
      <point name="TRS2" name_en="TRS2" name_fi="TRS2" name_sv="TRS2" name_et="TRS2" name_ru="TRS2" pointtype="6" registertype="Holding" addressformat="U16" addressindex="253" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="3" iotype="2" />
    </group>
    <group categorytype="2" name="Asetusarvot" name_en="Setting values" name_fi="Asetusarvot" name_sv="Inställningar" name_et="Seadistused" name_ru="Уставочные значения" name_lv="Iestatīt vērtības" name_tr="Set değerleri">
      <point name="H1InUse" name_en="H1 Control circuit" name_fi="L1 Säätöpiiri" name_sv="V1 Reglerkrets" name_et="H1 Control circuit" name_ru="H1 Control circuit" name_lv="A1 Kontūrs" pointtype="3" registertype="Holding" addressformat="U16" addressindex="262" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="H2InUse" name_en="H2 Control circuit" name_fi="L2 Säätöpiiri" name_sv="V2 Reglerkrets" name_et="H2 Control circuit" name_lv="A2 Kontūrs" pointtype="3" registertype="Holding" addressformat="U16" addressindex="278" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="DHWInUse" name_en="Domestic hot water control" name_fi="Käyttövesisäätö" name_sv="Tappvarmvattnets kontroll" name_et="Kodune kuuma vee juhtimine" name_ru="ГВС Регулир.контур" name_lv="Karstā ūdens kontūrs" name_tr="Domestic hot water control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="541" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_PArea" name_en="H1 P-area" name_fi="L1 P-alue" name_sv="V1 P-band" name_et="K1 P-ala" name_ru="О1 Зона Р" name_lv="A1 P-apgabals" name_tr="H1 P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="979" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="600" />
      <point name="HeatingControl1_ITime" name_en="H1 I-time" name_fi="L1 I-aika" name_sv="V1 I-tid" name_et="K1 I-aeg" name_ru="О1 Время I" name_lv="A1 I-laiks" name_tr="H1 I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="981" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="HeatingControl1_SupplyMaxChangeSpeed" name_en="H1 Supply w. max. speed of change" name_fi="L1 Menoveden max. muutosnop." name_sv="V1 Framledn. max. ändring" name_et="K1 Küttev. maks. muutumiskiirus" name_ru="О1 Макс.скор.изм.под.воды" name_lv="A1 Turpg. temp. izmaiņu ātrums" name_tr="H1 Supply w. max. speed of change" pointtype="3" registertype="Holding" addressformat="S32" addressindex="983" categorytype="3" unit="°C/min" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="5.0" />
      <point name="HeatingControl1_ParallShift" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="Paralleelnihe" name_ru="Параллельное смещение" name_lv="Paralēlā nobīde" name_tr="Parallel shift" pointtype="3" registertype="Holding" addressformat="S32" addressindex="985" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-15" max="15" />
      <point name="HeatingControl1_OperatingMode" name_en="Control mode" name_fi="Ohjaustapa" name_sv="Styrsätt" name_et="Juhtimisrežiim" name_ru="Способ управления" name_lv="Vadības režīms" name_tr="Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="987" categorytype="3" enum="0=Automaatti;1=Jatkuva normaalilämpö;2=Jatkuva lämmönpudotus;3=Jatkuva suuri lämmönpudotus;4=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl1_PumpSummerstopInUse" name_en="Pump summer stop" name_fi="Pumpun kesäpysäytys" name_sv="Pumpens sommarstopp" name_et="Pumba suvine seiskamine" name_ru="Отключ.насоса в летн.режиме" name_lv="Sūkņa vasaras apturēšana" name_tr="Pump summer stop" pointtype="3" registertype="Holding" addressformat="U16" addressindex="877" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_ParallShiftDampPoint" name_en="Parallel shift damping point" name_fi="Suuntaissiirron vaimennuspiste" name_sv="Dämning av parallellförskjutning" name_et="In1" name_ru="Attenuation of parallel shift" name_lv="A1 Paralēlās nobīd. slāpēšanas punkts" pointtype="3" registertype="Holding" addressformat="S32" addressindex="989" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_GenCompMin" name_en="General compensation min" name_fi="Yleiskompensoinnin aloitus" name_sv="Allmän kompensering min" name_et="Üldine min kompenseerimine" name_ru="Инициация общей компенсации" name_lv="Vispārīgās kompen. min." name_tr="General compensation min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="993" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_GenCompMax" name_en="General compensation max" name_fi="Yleiskompensointi maksimiin" name_sv="Allmän kompensering max" name_et="Üldine max kompenseerimine" name_ru="Макс.общая компенсация" name_lv="Vispārīgās komp. maks." name_tr="General compensation max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="995" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_GenCompMaxVal" name_en="General compensation max effect" name_fi="Yleiskompensoinnin maksimi" name_sv="Allmän kompenseringens max. effekt" name_et="Üldise kompenseerimise max mõju" name_ru="Макс.воздейств.общ.компенс." name_lv="Vispārīgās komp. maks. ietekme" name_tr="General compensation max effect" pointtype="3" registertype="Holding" addressformat="S32" addressindex="997" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_GenCompMinEff" name_en="H1 Compensation min effect" name_fi="L1 Kompensoinnin minimi" name_sv="V1 Kompenseringens min. effekt" name_et="K1 Kompenseerimise min mõju" name_ru="O1 Минимум компенсации" name_lv="A1 Vispārīgās komp. min. ietekme" name_tr="H1 Compensation min effect" pointtype="3" registertype="Holding" addressformat="S32" addressindex="999" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_RoomSetp" name_en="Room temperature setting" name_fi="Huonelämpötilan asetusarvo" name_sv="Rumstemp. inställningsvärde" name_et="Toatemperatuur seadistus" name_ru="Устав.знач.комнат.температуры" name_lv="Telpas temperatūras iestatījums" name_tr="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1001" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="50" />
      <point name="HeatingControl1_BusCompensationIn" name_en="Input" name_fi="Väyläkompensointi" name_sv="Input" name_et="Input" name_lv="Input A1  Tīkla kompensācija" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1003" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="HeatingControl1_BusCompMin" name_en="Bus compensation min" name_fi="Väyläkompensointi minimi" name_sv="Buss kompensering min" name_et="In1" name_ru="Bus compensation min" name_lv="Tīkla kompensācija min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1005" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-30" max="0" />
      <point name="HeatingControl1_BusCompMax" name_en="Bus compensation max" name_fi="Väyläkompensointi maksimi" name_sv="Buss kompensering max" name_et="In2" name_ru="Bus compensation max" name_lv="Tīkla kompensācija maks" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1007" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="HeatingControl1_AutumnDryInUse" name_en="Autumn drying" name_fi="Syyskuivaus" name_sv="Hösttorkning" name_et="Sügiskuivatus" name_ru="Режим осуш.осен.период" name_lv="Rudens žāvēšana" name_tr="Autumn drying" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1009" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_AutumDryFloor" name_en="Autumn dry effect on supply water" name_fi="Syyskuivauksen vaik. menoveteen" name_sv="Hösttorknings effekt på framl. vatten" name_et="Sügiskuivatuse mõju kütteveele " name_ru="Воздейс.реж.осуш.осен.на Т.подач." name_lv="Rudens žāv. ietekme uz turpg. temp." name_tr="Autumn dry effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1010" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_ValveSummerCutOff" name_en="Valve summer close" name_fi="Venttiilin kesäsulku" name_sv="Ventilens sommarstängning" name_et="Ventiili suvine sulgumine" name_ru="Перекрытие клап. в лет.реж." name_lv="Vārsta vasaras aizvēršana" name_tr="Valve summer close" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1013" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_SummerFuncTempLimit" name_en="Summer function outdoor t. limit" name_fi="Kesätoiminnon ulkol. raja" name_sv="Sommarfunktion utetemp. gräns" name_et="Suvefunktsiooni välistemp. piir" name_ru="Предел.знач.Т.нар.возд. в лет.реж." name_lv="Vasaras funkcijas ārgaisa temp. limits" name_tr="Summer function outd.limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1014" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      <point name="HeatingControl1_SummerFuncDisableLimit" name_en="Summer func. Inh. limit" name_fi="Kesätoiminnon estoraja" name_sv="Sommar funk.inhib.gräns" name_et="Suvefunktsiooni summutuspiir" name_ru="Предел.знач.блокировки лет.реж." name_lv="Vasaras funkc. izslēgšanas temp." name_tr="Summer func.inh.limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1020" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="20" />
      <point name="HeatingControl1_RetWaterCompInUse" name_en="H1 Return water compensation" name_fi="L1 Paluuvesikompensointi" name_sv="V1 Returvatten kompensering" name_et="K1 Tagastusvee kompens." name_ru="O1 Компенсация обратной воды" name_lv="A1 Atgaitas ūdens kompensācija" name_tr="H1 Return water compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1023" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_RoomCompInUseH1" name_en="Select" name_fi="Huonekompensointi" name_sv="Select" name_et="Select" name_lv="Telpas kompensācija Lietot" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1024" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_SerialValveCtrl" name_en="Select" name_fi="Sarjasäätö" name_sv="Select" name_et="Select" name_lv=" Izpildmehānisma 2 pozīcija" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1025" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_AutumnDryRoomSetp" name_en="Autumn drying" name_fi="Syyskuivaus" name_sv="Hösttorkning" name_et="" name_ru="" name_lv="Rudens žāvēšana" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1495" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="1.5" />
      <point name="HeatingControl1_AutumnDryRadiatorEff" name_en="Autumn dry effect on supply water" name_fi="Syyskuivauksen vaik. menoveteen" name_sv="Hösttorknings effekt på framl. vatten" name_et="Sügiskuivatuse mõju kütteveele " name_ru="Воздейс.реж.осуш.осен.на Т.подач." name_lv="Rudens žāv. ietekme uz turpg. temp." name_tr="Autumn dry effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1497" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl1_HAEnable" name_en="Home/Away control" name_fi="Kotona/Poissa ohjaus" name_sv="Hemma/Borta styrning" name_et="Kodus/eemal juhtimine" name_ru="Управление Дома/Не дома " name_lv="Mājās / Ārpus mājām vadība" name_tr="Home/Away control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="876" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_OutdoorTempForecSel" name_en="Outdoor temperature forecast" name_fi="Ulkolämpötilan ennustetieto" name_sv="Utetemperaturens prognos" name_et="Välistemp. ennustamine" name_ru="Прогноз по темп.наруж.возд." name_lv="Ārg. temp. prognoze" name_tr="Outdoor temperature forecast" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1501" categorytype="3" enum="0=Ei käytössä;1=Käytössä" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl1_GenCompInUse" name_en="General compensation" name_fi="Yleiskompensointi" name_sv="Allmän kompensering" name_et="Üldine kompenseerimine" name_lv="Vispārīgā kompensācija" name_ru="Общая компенсация" name_tr="General compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="962" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_BusCompInUse" name_en="Bus compensation" name_fi="Väyläkompensointi" name_sv="Busskompensering" name_et="Siini kompenseerimine" name_ru="Компенсация по шине" name_lv="Tīkla kompensācija" name_tr="Bus compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="963" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_BusCompFactor" name_en="Bus compensation factor" name_fi="Väyläkompensoinnin kerroin" name_sv="Buss kompenseringens faktor" name_et="B1" name_lv="Tīkla kompensācija koef." pointtype="3" registertype="Holding" addressformat="S32" addressindex="957" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl1_ManualPosition" name_en="H1 Manual position" name_fi="L1 Käsiajoasento" name_sv="V1 Manuell position" name_et="K1 Käsitsi positsioon" name_ru="O1 Положение ИМ в ручн.реж.управл." name_lv="A1 Rokas režīma pozīcija" name_tr="H1 Manual position" pointtype="3" registertype="Holding" addressformat="S32" addressindex="909" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_DTime" name_en="H1 D-time" name_fi="L1 D-aika" name_sv="V1 D-tid" name_et="K1 D-aeg" name_ru="О1 Время D" name_lv="A1 D-laiks" name_tr="H1 D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="682" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_GenCompFilter" name_en="Gen. compensation filtering" name_fi="Yleiskompensoinnin suodatus" name_sv="Allmän komp. filtertid" name_et="Kompenseerimise filtreerimine" name_ru="Фильтрация компенсации" name_lv="Kompensācijas filtrēšana" name_tr="Gen. compensation filtering" pointtype="3" registertype="Holding" addressformat="S32" addressindex="991" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="HeatingControl1_HeatingMode_L1" name_en="H1 Type of heating" name_fi="L1 Lämmitystapa" name_sv="V1 Typ av uppvärmning sätt" name_et="K1 Kütterežiim" name_ru="O1 Режим отопл." name_lv="A1 Kontūrs" name_tr="H1 Heating circuit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1080" categorytype="3" enum="0=Lattialämmitys;1=Patterilämmitys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_n_20" name_en="Output temperature when outdoor temperature is -20 °C" name_fi="Menoveden lämpötila kun ulkolämpötilan on -20 °C" name_sv="Framledn.vattnets temperatur när utetemperatur är -20 °C" name_et="K1 pealevoolu temp., kui välistemperatuur on -20 °C" name_ru="Т.на подаче при т.нар.возд. -20 °C" name_lv="Izvades temperatūra, kad ārgaisa temperatūra ir -20 °C" name_tr="Output temperature when outdoor temperature is -20 °C" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1301" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_in2" name_en="Curve outdoor temperature point 2" name_fi="Käyrän ulkolämpötilapiste 2" name_sv="punkt 2 utetemperatur" name_et="Küttekõvera välistemp. punkt 2" name_ru="Точка 2 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 2" name_tr="Curve outdoor temperature point 2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1303" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_out2" name_en="Heating water temperature at outdoor temperature point 2" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 2" name_sv="Framledn.vattnets temperatur  vid punkt 2 utetemperatur " name_et="Kütte pealevoolu temp. küttekõvera välistemp. punktis 2" name_ru="Т.на подаче в точ.2 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 2" name_tr="Heating water temperature at outdoor temperature point 2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1305" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_in3" name_en="Curve outdoor temperature point 3" name_fi="Käyrän ulkolämpötilapiste 3" name_sv="punkt 3 utetemperatur" name_et="Küttekõvera välistemp. punkt 3" name_ru="Точка 3 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 3" name_tr="Curve outdoor temperature point 3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1307" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_out3" name_en="Heating water temperature at outdoor temperature point 3" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 3" name_sv="Framledn.vattnets temperatur  vid punkt 3 utetemperatur" name_et="Kütte pealevoolu temperatuur küttekõvera välistemperatuuri punktis 3" name_ru="Т.на подаче в точ.3 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 3" name_tr="Heating water temperature at outdoor temperature point 3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1309" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_in4" name_en="Curve outdoor temperature point 4" name_fi="Käyrän ulkolämpötilapiste 4" name_sv="punkt 4 utetemperatur" name_et="Küttekõvera välistemperatuuri punkt 4" name_ru="Точка 4 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 4" name_tr="Curve outdoor temperature point 4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1311" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_out4" name_en="Heating water temperature at outdoor temperature point 4" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 4" name_sv="Framledn.vattnets vid punkt 4 utetemperatur" name_et="Kütte pealevoolu temp. küttekõvera välistemperatuuri punktis 4" name_ru="Т.на подаче в точ.4 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 4" name_tr="Heating water temperature at outdoor temperature point 4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1313" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_out5" name_en="Output temperature when outdoor temperature is +20 °C" name_fi="Menoveden lämpötila kun ulkolämpötilan on +20 °C" name_sv="Framledn.vattnets när utetemperatur är +20 °C" name_et="K1 pealevoolu temp., kui välistemperatuur on +20 °C" name_ru="Темп.подаче при т.нар.возд. +20 °C" name_lv="Izvades temperatūra, kad ārgaisa temperatūra ir +20 °C" name_tr="Output temperature when outdoor temperature is +20 °C" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1315" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_min_limit" name_en="Supply water minimum  value" name_fi="Menoveden lämpötilan minimiarvo" name_sv="Framledn.vattnets minimitemperatur" name_et="Kütte miinimum väärtus" name_ru="Миним.знач.темп.воды на подаче" name_lv="Izvades min. robeža" name_tr="Output minimum value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1317" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="20" max="60" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHReturnComp_max_limit" name_en="Supply water maximum value" name_fi="Menoveden lämpötilan maksimiarvo" name_sv="Framledn.vattnets maximitemperatur" name_et="Kütte maksimum väärtus" name_ru="Макс.знач.темп.воды на подаче" name_lv="Izvades maks. robeža" name_tr="Output maximum value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1319" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="50" max="70" />
      <point name="HeatingControl1_DHReturnTempComp_L1DhRetTempComp_P_value" name_en="H1 DH ret. water comp. P-area" name_fi="L1 KL paluulämpöt. kompens. P-alue" name_sv="V1 FJV returv. temp. komp. P-band" name_et="K1 KK tagasiv. temp. komp. P-arv" name_ru="О1 ЦТС зона Р компенс.Т.обр.воды" name_lv="A1 Prim. kont. atg. komp. P-apgabals" name_tr="H1 DH ret. water comp. P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1321" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="HeatingControl1_DHReturnTempComp_L1DhRetTempComp_I_time" name_en="H1 DH ret. water comp. I-time" name_fi="L1 KL paluulämpöt. kompens. I-aika" name_sv="V1 FJV returv. temp. komp. I-tid" name_et="K1 KK tagasiv. temp. komp. I-aeg" name_ru="О1 ЦТС время I компенс.Т.обр.воды" name_lv="A1 Prim. kont. atg. komp. I-laiks" name_tr="H1 DH ret. water comp. I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1323" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="HeatingControl1_DHReturnTempComp_L1DhReturnCompMAx" name_en="H1 DH return temp. max comp. " name_fi="L1 KL paluulämpötilan kompens. maks." name_sv="V1 FJV returtemp. max komp." name_et="K1 KK tagasiv. temp. max.kompens." name_ru="O1 ЦТС максимум компенс.Т.обр.воды" name_lv="A1 Prim. kont. atg. maks. komp." name_tr="H1 DH Return max comp " pointtype="3" registertype="Holding" addressformat="S32" addressindex="1325" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="50" />
      <point name="HeatingControl1_DHReturnTempComp_L1DHRetTempCompState" name_en="H1 DH return temp. comp." name_fi="L1 KL paluuvesikompensointi" name_sv="V1 FJV returtemp. komp." name_et="K1 KK tagasiv. temp. kompens." name_ru="О1 ЦТС компенсация обр.воды" name_lv="A1 Prim. kont. atg. kompensācija" name_tr="H1 DH return temp. comp" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1327" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_TimeControl2_OperatingModeAwayState" name_en="Temp.level on Away control" name_fi="Lämpötaso Poissa-ohjauksessa" name_sv="Temp. nivå på Borta status" name_et="Eemal-juhtimise temperatuuritase" name_ru="Темпер.режим управления Не дома" name_lv="Ārpus mājām rež. temp pazem." name_tr="Temp.level on Away control" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1026" categorytype="3" enum="2=Lämmönpud.;3=Suuri lämmönp." scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl1_TimeControl2_BigTempDropRadiator" name_en="Big temp. drop" name_fi="Suuri lämmönpudotus" name_sv="Stor temp.sänkning" name_et="Suur temperatuurilangus" name_ru="Значит.понижение темпер." name_lv="Lielais temp. pazeminājums" name_tr="Big temp. drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1030" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_SmallTempDropRadiator" name_en="Temp. drop" name_fi="Lämmönpudotus" name_sv="Temp. sänkning" name_et="Temp.langus" name_ru="Падение температуры" name_lv="Pazeminājums" name_tr="Temp. Drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1032" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_PreHeatingValueFloor" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framledn.vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1034" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl1_TimeControl2_SmallTempDropFloor" name_en="Temp. drop" name_fi="Lämmönpudotus" name_sv="Temp. sänkning" name_et="Temp.langus" name_ru="Падение температуры" name_lv="Pazeminājums" name_tr="Temp. Drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1038" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_BigTempDropFloor" name_en="Big temp. drop" name_fi="Suuri lämmönpudotus" name_sv="Stor temp.sänkning" name_et="Suur temperatuurilangus" name_ru="Значит.понижение темпер." name_lv="Lielais temp. pazeminājums" name_tr="Big temp. drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1040" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_PreHeatingTime" name_en="Pre-increase time" name_fi="Esikorotusaika" name_sv="Snabbhöjning tid" name_et="Eeltõstmise aeg" name_ru="О1 Время предподогрева" name_lv="Pirms-paaugstinājuma laiks" name_tr="Pre-increase time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1042" categorytype="3" unit="h" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="HeatingControl1_TimeControl2_PreHeatInUse" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framl. vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1095" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_TimeControl2_SmallTempDropRoom" name_en="Temp. drop room temp" name_fi="Lämmönpudotus huonel." name_sv="Temp. sänkning rumstemp." name_et="Temp.langus toatemp" name_ru="Падение температуры, Комнатная т." name_lv="Pazeminājums telpas temp." name_tr="Temp. drop room temp" pointtype="3" registertype="Holding" addressformat="S32" addressindex="725" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_BigTempDropRoom" name_en="Big temp. drop room temp." name_fi="Suuri lämmönpudotus huonel." name_sv="Stor temp.sänkning rumstemp." name_et="Suur temperatuurilangus toatemp." name_ru="Значит.понижение темпер. Комнатная т." name_lv="Lielais temp. pazeminājums telpas temp." name_tr="Big temp. drop room temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="727" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl1_TimeControl2_PreHeatingValueRadiator" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framledn.vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1082" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl1_ConstructionComp_OutTempDelayDec" name_en="Radiat. heat.delay on outd.temp dec." name_fi="Patterilämmityksen hidastus ulkol. laskiessa" name_sv="Rad.värme fördr.på utetemp.sjunkn." name_et="Building specific delay time" name_lv="Ārgaisa temp. aizkave tai samaz.(radiatoru apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="526" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_ConstructionComp_OutTempDelayInc" name_en="Radiat.heat.anticip.on outd.temp.incr." name_fi="Patterilämmityksen ennakointi ulkol. noustessa" name_sv="Rad.värme framförhålln.på utet.ökn." name_et="Building specific delay time" name_lv="Ārgaisa temp. aizkave tai paliel.(radiatoru apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="743" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_ConstructionComp_OutTempAnticInc" name_en="Building specific delay time" name_fi="Lattialämmityksen ennakointi ulkol. noustessa" name_sv="Buggnad specifik fördröjning tid" name_lv="Grīdas apk. prognoze temp. paliel. (grīdu apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="811" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_ConstructionComp_OutTempAnticDec" name_en="Building specific delay time" name_fi="Lattialämmityksen ennakointi ulkol. laskiessa" name_sv="Buggnad specifik fördröjning tid" name_lv="Grīdas apk. prognoze temp. samaz.(grīdu apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="813" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_RoomComp_RoomCompMaxEffectFloor" name_en="Input0" name_fi="Kompens. max vaikutus menoveteen" name_sv="Input0" name_et="Input0" name_lv="Telpas komp. maks. Ietekme uz turpg. t." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1048" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="HeatingControl1_RoomComp_RoomCompMaxEffectRadiator" name_en="A" name_fi="Kompens. max vaikutus menoveteen" name_sv="A" name_et="A" name_lv="Telpas komp. maks. Ietekme uz turpg. t." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1050" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="HeatingControl1_RoomComp_RoomCompRatioFloor" name_en="Input0" name_fi="Huonekompensointisuhde" name_sv="Input0" name_et="Input0" name_lv="Telpas kompensācijas koeficients" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1052" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl1_RoomComp_RoomCompRatioRadiator" name_en="Room compensation ratio" name_fi="Huonekompensointisuhde" name_sv="Rumskompensering" name_et="Room compensation ratio" name_lv="Telpas komp. maks. Ietekme uz turpg. t." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1054" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl1_RoomComp_RoomIMaxEffectFloor" name_en="I control's max effect on sup wat" name_fi="I-säädön max vaik. menoveteen" name_sv="I regler max.effekt på framl.vatten" name_et="Input1" name_lv="I-laika maks. ietekme uz turpg. temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1056" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_RoomComp_RoomITimeFloor" name_en="Room compensation adjustment time" name_fi="Huonekompens. korjausaika" name_sv="Rumskompenseringens justeringstid" name_et="Input1" name_ru="Room compensation adjustment time" name_lv="Telpas komp. laiks (I-laiks)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1060" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="7" />
      <point name="HeatingControl1_RoomComp_RoomITimeRadiator" name_en="Room compensation adjustment time" name_fi="Huonekompens. korjausaika" name_sv="Rumskompenseringens justeringstid" name_et="Input1" name_ru="Room compensation adjustment time" name_lv="Telpas komp. laiks (I-laiks)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1062" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="7" />
      <point name="HeatingControl1_RoomComp_RoomMeasDelay" name_en="B1" name_fi="Huonel. mitt. hidastusaika" name_sv="B1" name_et="B1" name_lv="Telpas temp. mērījuma aizkave" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1064" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl1_RoomComp_RoomIMaxEffectRadiatorL1" name_en="I control's max effect on sup wat" name_fi="I-säädön max vaik. menoveteen" name_sv="I regler max.effekt på framl.vatten" name_et="Input1" name_ru="I control's max effect on sup wat" name_lv="I-laika maks. ietekme uz turpg. temp." name_tr="I control's max effect on sup wat" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1086" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl1_OutdoorCompCurves_CurveTypeL1" name_en="Curve type" name_fi="Säätökäyrän tyyppi" name_sv="Typ av kurva" name_et="Kõvera tüüp" name_ru="Тип кривой регулирования" name_lv="Līknes tips" name_tr="Curve type" pointtype="3" registertype="Holding" addressformat="U16" addressindex="627" categorytype="3" enum="0=3-piste säätökäyrä;1=5-piste säätökäyrä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out_n20Radiator" name_en="Curve5p_Supply w._n20" name_fi="Käyrä5p_Menov._n20" name_sv="Kurva5p_Framl._n20" name_et="Kõver5p_küttevee_Välistemp.-20" name_ru="Кривая5p_Подача_Наружная т.20" name_lv="Līkne 5p_Turpg._n20" name_tr="Curve5p_Out_n20" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1068" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_n20Radiator" name_en="Curve3p_Supply w._n20 Radiator" name_fi="Käyrä3p_Menov._n20_patteril." name_sv="Kurva3p_Framl._n20 Radiator" name_et="Kõver3p_küttevee_Välistemp.-20 Radiaatork." name_ru="Кривая3p_Подача_n20_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa -20 radiatoru apkure" name_tr="Curve3p_Out_n20Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1084" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve_MinRadiator" name_en="Min. limit" name_fi="Minimiraja" name_sv="Min.gräns" name_et="Alampiir" name_ru="Мин.предел" name_lv="Min. robeža" name_tr="Min. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1088" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve_MaxRadiator" name_en="Max. limit" name_fi="Maksimiraja" name_sv="Max.gräns" name_et="Ülempiir" name_ru="Макс.предел" name_lv="Maks. robeža" name_tr="Max. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1090" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_0Radiator" name_en="Curve3p_Supply w._0 Radiator" name_fi="Käyrä3p_Menov._0_patteril." name_sv="Kurva3p_Framl._0 Radiator" name_et="Kõver3p_küttevee_0 Radiaatork." name_ru="Кривая3p_Подача_0_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa 0 radiatoru apkure" name_tr="Curve3p_Out_0Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1092" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_p20Radiator" name_en="Curve3p_Supply w._p20 Radiator" name_fi="Käyrä3p_Menov._p20_patteril." name_sv="Kurva3p_Framl._p20 Radiator" name_et="Kõver3p_küttevee_Välistemp.+20 Radiaatork." name_ru="Кривая3p_Подача_p20_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa +20_ radiatoru apkure" name_tr="Curve3p_Out_p20Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1441" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In2Radiator" name_en="Curve5p_Outdoor temp.2 Radiator" name_fi="Käyrä5p_Ulkol.2_patteril." name_sv="Kurva5p_Utet.2 Radiator" name_et="Kõver5p_Välistemp.2 Radiaatork." name_ru="Кривая5p_Наружная т.2_Радиаторное отопление" name_lv="Līkne 5p_Ārgaisa 2 radiatoru apkure" name_tr="Curve5p_In2Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1443" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out2Radiator" name_en="Curve5p_Supply w.2 Radiator" name_fi="Käyrä5p_Menov.2_patteril." name_sv="Kurva5p_Framl.2 Radiator" name_et="Kõver5p_küttevee 2 Radiaatork." name_ru="Кривая5p_Подача2_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 2 radiatoru apkure" name_tr="Curve5p_Out2Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1445" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In3Radiator" name_en="Curve5p_Outdoor temp.3 Radiator" name_fi="Käyrä5p_Ulkol.3_patteril." name_sv="Kurva5p_Utet.3 Radiator" name_et="Kõver5p_Välistemp.3 Radiaatork." name_ru="Кривая5p_Наружная т.3_Радиаторное отопление" name_lv="Līkne 5p_Ārgaisa 3_radiatoru apkure" name_tr="Curve5p_In3Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1447" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out3Radiator" name_en="Curve5p_Supply w.3 Radiator" name_fi="Käyrä5p_Menov.3_patteril." name_sv="Kurva5p_Framl.3 Radiator" name_et="Kõver5p_küttevee 3 Radiaatork." name_ru="Кривая5p_Подача3_Радиаторное отопление" name_lv="Līkne 5p_Turpg.3 radiatoru apkure" name_tr="Curve5p_Out3Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1449" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In4Radiator" name_en="Curve5p_Outdoor temp.4 Radiator" name_fi="Käyrä5p_Ulkol.4_patteril." name_sv="Kurva5p_Utet.4 Radiator" name_et="Kõver5p_Välistemp.4 Radiaatork." name_ru="Кривая5p_Наружная т.4_Радиаторное отопление" name_lv="Līkne 5p_Ārgaisa 4 radiatoru apkure" name_tr="Curve5p_In4Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1451" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out4Radiator" name_en="Curve5p_Supply w.4 Radiator" name_fi="Käyrä5p_Menov.4_patteril." name_sv="Kurva5p_Framl.4 Radiator" name_et="Kõver5p_küttevee 4 Radiaatork." name_ru="Кривая5p_Подача4_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 4 radiatoru apkure" name_tr="Curve5p_Out4Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1453" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out5Radiator" name_en="Curve5p_Supply w.5 Radiator" name_fi="Käyrä5p_Menov.5_patteril." name_sv="Kurva5p_Framl.5 Radiator" name_et="Kõver5p_küttevee 5 Radiaatork." name_ru="Кривая5p_Подача5_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 5 radiatoru apkure" name_tr="Curve5p_Out5Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1455" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_n20Floor" name_en="Curve3p_Supply w._n20Floor" name_fi="Käyrä3p_Menov._-20_Lattial." name_sv="Kurva3p_Framl._n20_Golv" name_et="Kõver3p_küttevee_n20 Põrandak." name_ru="Кривая 3p_Подача._Наружная темп.-20_Напольное отопление" name_lv="Līkne 3p_Turpg. n20 grīdu apkure" name_tr="Curve3p_Out_n20Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1457" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_0Floor" name_en="Curve3p_Supply w._0 Floor" name_fi="Käyrä3p_Menov._0 Lattial." name_sv="Kurva3p_Framl._0 Golv" name_et="Kõver3p_küttevee_Välistemp.0_Põrandak." name_ru="Кривая3p_Подача_Наружная т.0_напольный обогрев" name_lv="Līkne 3p_Turpg._Ārgaisa 0_ grīdu apkure" name_tr="Curve3p_Out_0Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1459" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve3p_Out_p20Floor" name_en="Curve3p_Supply w._p20 Floor" name_fi="Käyrä3p_Menov._p20_Lattial." name_sv="Kurva3p_Framl._p20 Golv" name_et="Kõver3p_küttevee_Välistemp.+20_Põrandak." name_ru="Кривая3p_Подача_Наружная т.+20_Напольный обогрев" name_lv="Līkne 3p_Turpg._Ārgaisa +20_ grīdu apkure" name_tr="Curve3p_Out_p20Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1461" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out_n20Floor" name_en="Curve5p_Supply w._n20Floor" name_fi="Käyrä5p_Menov._-20_Lattial." name_sv="Kurva5p_Framl._n20_Golv" name_et="Kõver5p_küttevee_n20 Põrandak." name_ru="Кривая 5p_Подача._Наружная темп.-20_Напольное отопление" name_lv="Līkne 5p_Turpg. n20 grīdu apkure" name_tr="Curve5p_Out_n20Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1463" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In2Floor" name_en="Curve5p_Outdoor temp.2 Floor" name_fi="Käyrä5p_Ulkol.2_Lattial." name_sv="Kurva5p_Utet.2 Golv" name_et="Kõver5p_Välistemp.2 Põrandak." name_ru="Кривая5p_Наружная т.2_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa 2 grīdu apkure" name_tr="Curve5p_In2Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1465" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out2Floor" name_en="Curve5p_Supply w.2 Floor" name_fi="Käyrä5p_Menov.2_Lattial." name_sv="Kurva5p_Framl.2 Golv" name_et="Kõver5p_küttevee 2 Põrandak." name_ru="Кривая5p_Подача2_Напольный обогрев" name_lv="Līkne 5p_Turpg. 2 grīdu apkure" name_tr="Curve5p_Out2Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1467" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In3Floor" name_en="Curve5p_Outdoort temp.3 Floor" name_fi="Käyrä5p_Ulkol.3_Lattial." name_sv="Kurva5p_Utet.3 Golv" name_et="Kõver5p_Välistemp.3 Põrandak." name_ru="Кривая5p_Наружная т.3_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa3 grīdu apkure" name_tr="Curve5p_In3Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1469" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out3Floor" name_en="Curve5p_Supply w.3 Floor" name_fi="Käyrä5p_Menov.3_Lattial." name_sv="Kurva5p_Framl.3 Golv" name_et="Kõver5p_küttevee 3 Põrandak." name_ru="Кривая5p_Подача3_Напольный обогрев" name_lv="Līkne 5p_Turpg. 3 grīdu apkure" name_tr="Curve5p_Out3Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1471" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_In4Floor" name_en="Curve5p_Outdoor temp.4 Floor" name_fi="Käyrä5p_Ulkol.4_Lattial." name_sv="Kurva5p_Utet.4 Golv" name_et="Kõver5p_Välistemp.4 Põrandak." name_ru="Кривая5p_Наружная т.4_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa 4 grīdu apkure" name_tr="Curve5p_In4Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1473" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out4Floor" name_en="Curve5p_Supply w.4 Floor" name_fi="Käyrä5p_Menov.4_Lattial." name_sv="Kurva5p_Framl.4 Golv" name_et="Kõver5p_küttevee 4 Põrandak." name_ru="Кривая5p_Подача4_Напольный обогрев" name_lv="Līkne 5p_Turpg. 4 grīdu apkure" name_tr="Curve5p_Out4Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1475" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve5p_Out5Floor" name_en="Curve5p_Supply w.5 Floor" name_fi="Käyrä5p_Menov.5_Lattial." name_sv="Kurva5p_Framl.5 Golv" name_et="Kõver5p_küttevee 5 Põrandak." name_ru="Кривая5p_Подача5_Напольный обогрев" name_lv="Līkne 5p_Turpg. 5 grīdu apkure" name_tr="Curve5p_Out5Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1477" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve_MinFloor" name_en="H1 Min limit" name_fi="L1 Minimiraja" name_sv="V1 Min gräns" name_et="K1 Alampiir" name_ru="О1 Мин.предел " name_lv="A1 Min.robeža" name_tr="H1 Min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1479" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl1_OutdoorCompCurves_Curve_MaxFloor" name_en="H1 Max limit" name_fi="L1 Maksimiraja" name_sv="V1 Max gräns" name_et="K1 Ülempiir" name_ru="О1 Макс.предел" name_lv="A1 Maks.robeža" name_tr="H1 Max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1481" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl1_RetwaterComp_RetWaterMinLimit" name_en="Return water freezing risk limit" name_fi="Paluuveden jäätymisvaarahälytys" name_sv="Returvatten frysrisk gräns" name_et="Tagastusvee külmumisohu piir" name_ru="Сигнал опасн.обмерз.обр.воды" name_lv="Atg. aizsalšanas riska robeža" name_tr="Return water freezing risk limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1280" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="25" />
      <point name="HeatingControl1_RetwaterComp_FrozingLimitDelay" name_en="Return water alarm delay" name_fi="Jäätymisvaarahälytyksen viive" name_sv="Returvatten larm fördröjning" name_et="Tagastusvee alarmi viivitus" name_ru="Задерж.сигн.опасн.обмерз.обр.воды" name_lv="Atg. trauksmes aizkaves laiks" name_tr="Return water alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1282" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="120" />
      <point name="HeatingControl1_RetwaterComp_RetWatCompFactor" name_en="Return water compensation" name_fi="Paluuveden kompensointisuhde" name_sv="Returvatten kompenserning" name_et="Tagastusvee kompenseerimine" name_ru="Компенсация обратной воды" name_lv="Atgaitas ūd. kompensācijas koeficients" name_tr="Return water compensation" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1284" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl1_DeviationAlarm1_DiffAlDelay" name_en="Deviation alarm delay" name_fi="Poikkeamahälytyksen viive" name_sv="Avvikelselarm fördröjning" name_et="Hälbealarmi viivitus" name_ru="Задержка сигнала несоответств." name_lv="Deviācijas trauksmes aizkaves laiks" name_tr="Deviation alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1286" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="120" />
      <point name="HeatingControl1_DeviationAlarm1_DiffAlarm" name_en="Supply water deviation alarm" name_fi="Menoveden poikkeamahälytys" name_sv="Framledn.vattnets avvikelselarm" name_et="Küttevee hälbealarm" name_ru="Сигн.несоотв. по воде на подаче" name_lv="Turpg. ūd. deviācijas trauksme" name_tr="Supply water deviation alarm" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1288" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="50" />
      <point name="HeatingControl1_DeviationAlarm1_OverTemp" name_en="Supply water high limit alarm" name_fi="Menoveden ylärajahälytys" name_sv="Framledningsvatten högnivålarm" name_et="Küttevee ülemise piiri alarm" name_ru="Сигн.по верх.пределу вод.подач." name_lv="Turpgaitas  pārkaršanas trauksme" name_tr="Supply water high limit alarm" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1290" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="40" max="100" />
      <point name="HeatingControl1_DeviationAlarm1_OverTempDelay" name_en="High limit alarm delay" name_fi="Ylärajahälytyksen viive" name_sv="Högnivålarm fördröjning" name_et="Ülemise piiri alarmi viivitus" name_ru="Задерж.сигн.по верх.пределу вод.подач." name_lv="Pārkaršanas trauksmes aizkaves laiks" name_tr="High limit alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1394" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_PArea" name_en="H2 P-area" name_fi="L2 P-alue" name_sv="V2 P-band" name_et="K2 P-ala" name_ru="О2 Зона Р" name_lv="A2 P-apgabals" name_tr="H2 P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="714" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="600" />
      <point name="HeatingControl2_ITime" name_en="H2 I-time" name_fi="L2 I-aika" name_sv="V2 I-tid" name_et="K2 I-aeg" name_ru="О2 Время I" name_lv="A2 I-laiks" name_tr="H2 I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="716" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="HeatingControl2_SupplyMaxChangeSpeed" name_en="H2 Supply w. max. speed of change" name_fi="L2 Menoveden maks. muutosnop." name_sv="V2 Framledn. max. ändring" name_et="K2 Küttev. maks. muutumiskiirus" name_ru="О2 Макс.скор.изм.под.воды" name_lv="A2 Turpg. ūd. setpunkta izmaiņu ātrums" name_tr="H2 Supply w. max. speed of change" pointtype="3" registertype="Holding" addressformat="S32" addressindex="718" categorytype="3" unit="°C/min" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="5.0" />
      <point name="HeatingControl2_ParallShift" name_en="Parallel shift" name_fi="Suuntaissiirto" name_sv="Parallellförskjutning" name_et="Paralleelnihe" name_ru="Параллельное смещение" name_lv="Paralēlā nobīde" name_tr="Parallel shift" pointtype="3" registertype="Holding" addressformat="S32" addressindex="720" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-15" max="15" />
      <point name="HeatingControl2_OperatingMode" name_en="Control mode" name_fi="Ohjaustapa" name_sv="Styrsätt" name_et="Juhtimisrežiim" name_ru="Способ управления" name_lv="Vadības režīms" name_tr="Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="739" categorytype="3" enum="0=Automaatti;1=Jatkuva normaalilämpö;2=Jatkuva lämmönpudotus;3=Jatkuva suuri lämmönpudotus;4=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl2_PumpSummerstopInUse" name_en="Pump summer stop" name_fi="Pumpun kesäpysäytys" name_sv="Pumpens sommarstopp" name_et="Pumba suvine seiskamine" name_ru="Отключ.насоса в летн.режиме" name_lv="Sūkņa vasaras apturēšana" name_tr="Pump summer stop" pointtype="3" registertype="Holding" addressformat="U16" addressindex="722" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_ParallShiftDampPoint" name_en="Parallel shift damping point" name_fi="Suuntaissiirron vaimennuspiste" name_sv="Dämning av parallellförskjutning" name_et="In1" name_ru="Attenuation of parallel shift" name_lv="A2 Paralēlās nobīd. slāpēšanas punkts" pointtype="3" registertype="Holding" addressformat="S32" addressindex="741" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_GenCompMin" name_en="General compensation min" name_fi="Yleiskompensoinnin aloitus" name_sv="Allmän kompensering min" name_et="Üldine min kompenseerimine" name_ru="Инициация общей компенсации" name_lv="Vispārīgās kompen. min." name_tr="General compensation min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="745" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_GenCompMax" name_en="In2" name_fi="Kompensointi max" name_sv="In2" name_et="In2" name_lv="Vispārīgās komp. maks." pointtype="3" registertype="Holding" addressformat="S32" addressindex="747" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_GenCompMaxVal" name_en="General compensation max effect" name_fi="Yleiskompensoinnin maksimi" name_sv="Allmän kompenseringens max. effekt" name_et="Üldise kompenseerimise max mõju" name_ru="Макс.воздейств.общ.компенс." name_lv="Vispārīgās komp. maks. ietekme" name_tr="General compensation max effect" pointtype="3" registertype="Holding" addressformat="S32" addressindex="749" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_GenCompMinEff" name_en="H2 Compensation min effect" name_fi="L2 Kompensoinnin minimi" name_sv="V2 Kompenseringens min. effekt" name_et="K2 Kompenseerimise min mõju" name_ru="O2 Минимум компенсации" name_lv="A2 Kompensācijas min. Ietekme" name_tr="H2 Compensation min effect" pointtype="3" registertype="Holding" addressformat="S32" addressindex="751" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_RoomSetp" name_en="Room temperature setting" name_fi="Huonelämpötilan asetusarvo" name_sv="Rumstemp. inställningsvärde" name_et="Toatemperatuur seadistus" name_ru="Устав.знач.комнат.температуры" name_lv="Telpas temperatūras iestatījums" name_tr="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="753" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="50" />
      <point name="HeatingControl2_BusCompensationIn" name_en="Input" name_fi="Väyläkompensointi" name_sv="Input" name_et="Input" name_lv="Input  A2 Tīkla kompensācija" pointtype="3" registertype="Holding" addressformat="S32" addressindex="755" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="HeatingControl2_BusCompMin" name_en="Bus compensation min" name_fi="Väyläkompensointi minimi" name_sv="Buss kompensering min" name_et="In1" name_ru="Bus compensation min" name_lv="Tīkla kompensācija min" pointtype="3" registertype="Holding" addressformat="S32" addressindex="757" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-30" max="0" />
      <point name="HeatingControl2_BusCompMax" name_en="Bus compensation max" name_fi="Väyläkompensointi maksimi" name_sv="Buss kompensering max" name_et="In2" name_ru="Bus compensation max" name_lv="Tīkla kompensācija maks" pointtype="3" registertype="Holding" addressformat="S32" addressindex="759" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="HeatingControl2_AutumnDryInUse" name_en="Autumn drying" name_fi="Syyskuivaus" name_sv="Hösttorkning" name_et="Sügiskuivatus" name_ru="Режим осуш.осен.период" name_lv="Rudens žāvēšana" name_tr="Autumn drying" pointtype="3" registertype="Holding" addressformat="U16" addressindex="761" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_AutumDryFloor" name_en="Autumn dry effect on supply water" name_fi="Syyskuivauksen vaik. menoveteen" name_sv="Hösttorknings effekt på framl. vatten" name_et="Sügiskuivatuse mõju kütteveele " name_ru="Воздейс.реж.осуш.осен.на Т.подач." name_lv="Rudens žāv. ietekme uz turpg. temp." name_tr="Autumn dry effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="762" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_ValveSummerCutOff" name_en="Valve summer close" name_fi="Venttiilin kesäsulku" name_sv="Ventilens sommarstängning" name_et="Ventiili suvine sulgumine" name_ru="Перекрытие клап. в лет.реж." name_lv="Vārsta vasaras aizvēršana" name_tr="Valve summer close" pointtype="3" registertype="Holding" addressformat="U16" addressindex="765" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_SummerFuncTempLimit" name_en="Summer function outdoor t. limit" name_fi="Kesätoiminnon ulkol. raja" name_sv="Sommarfunktion utetemp. gräns" name_et="Suvefunktsiooni välistemp. piir" name_ru="Предел.знач.Т.нар.возд. в лет.реж." name_lv="Vasaras funkcijas ārgaisa temp. limits" name_tr="Summer function outd.limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="766" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="10" max="35" />
      <point name="HeatingControl2_SummerFuncDisableLimit" name_en="Summer func. Inh. limit" name_fi="Kesätoiminnon estoraja" name_sv="Sommar funk.inhib.gräns" name_et="Suvefunktsiooni summutuspiir" name_ru="Предел.знач.блокировки лет.реж." name_lv="Vasaras funkc. izslēgšanas temp." name_tr="Summer func.inh.limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="772" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-10" max="20" />
      <point name="HeatingControl2_RetWaterCompInUse" name_en="H2 Return water compensation" name_fi="L2 Paluuvesikompensointi" name_sv="V2 Returvatten kompensering" name_et="K2 Tagastusvee kompens." name_ru="O2 Компенсация обратной воды" name_lv="A2 Atgaitas ūdens kompensācija" name_tr="H2 Return water compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="774" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_RoomCompInUseH2" name_en="Room compensation " name_fi="Huonekompensointi" name_sv="Rumskompensering" name_et="Toa kompenseerimine " name_ru="Соотношение комнатной компенсации" name_lv="Telpas kompensācija" name_tr="Room compenstation " pointtype="3" registertype="Holding" addressformat="U16" addressindex="775" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_SerialValveCtrl" name_en="Select" name_fi="Sarjasäätö" name_sv="Select" name_et="Select" name_lv=" Izpildmehānisma 2 pozīcija" pointtype="3" registertype="Holding" addressformat="U16" addressindex="776" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_AutumnDryRoomSetp" name_en="Effect of autumn dry" name_fi="Syyskuivaus" name_sv="Hösttorkning påverkan" name_et="Effect of autumn dry" name_ru="Effect of autumn dry" name_lv="Rudens žāv. ietekme uz telpas. temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="777" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="1.5" />
      <point name="HeatingControl2_AutumnDryRadiatorSetp" name_en="Autumn dry effect on supply water" name_fi="Syyskuivauksen vaik. menoveteen" name_sv="Hösttorknings effekt på framl. vatten" name_et="Sügiskuivatuse mõju kütteveele " name_ru="Воздейс.реж.осуш.осен.на Т.подач." name_lv="Rudens žāv. ietekme uz turpg. temp." name_tr="Autumn dry effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="779" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl2_HAEnable" name_en="Home/Away control" name_fi="Kotona/Poissa ohjaus" name_sv="Hemma/Borta styrning" name_et="Kodus/eemal juhtimine" name_ru="Управление Дома/Не дома " name_lv="Mājās / Ārpus mājām vadība" name_tr="Home/Away control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="783" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_OutdoorTempForecSel" name_en="Outdoor temperature forecast" name_fi="Ulkolämpötilan ennustetieto" name_sv="Utetemperaturens prognos" name_et="Välistemp. ennustamine" name_ru="Прогноз по темп.наруж.возд." name_lv="Ārg. temp. prognoze" name_tr="Outdoor temperature forecast" pointtype="3" registertype="Holding" addressformat="S32" addressindex="784" categorytype="3" enum="0=Ei käytössä;1=Käytössä" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl2_GenCompInUse" name_en="General compensation" name_fi="Yleiskompensointi" name_sv="Allmän kompensering" name_et="Üldine kompenseerimine" name_lv="Vispārīgā kompensācija" name_ru="Общая компенсация" name_tr="General compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="788" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_BusCompInUse" name_en="Bus compensation" name_fi="Väyläkompensointi" name_sv="Busskompensering" name_et="Siini kompenseerimine" name_ru="Компенсация по шине" name_lv="Tīkla kompensācija" name_tr="Bus compensation" pointtype="3" registertype="Holding" addressformat="U16" addressindex="789" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_BusCompFactor" name_en="Bus compensation factor" name_fi="Väyläkompensoinnin kerroin" name_sv="Buss kompenseringens faktor" name_et="B1" name_lv="Tīkla kompensācija koef." pointtype="3" registertype="Holding" addressformat="S32" addressindex="790" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl2_ManualPosition" name_en="H2 Manual position" name_fi="L2 Käsiajoasento" name_sv="V2 Manuell position" name_et="K2 Käsitsi positsioon" name_ru="O2 Положение ИМ в ручн.реж.управл." name_lv="A2 Rokas režīma pozīcija" name_tr="H2 Manual position" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1118" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_DTime" name_en="H2 D-time" name_fi="L2 D-aika" name_sv="V2 D-tid" name_et="K2 D-aeg" name_ru="О2 Время D" name_lv="A2 D-laiks" name_tr="H2 D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="680" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_GenCompFilter" name_en="Gen. compensation filtering" name_fi="Yleiskompensoinnin suodatus" name_sv="Allmän komp. filtertid" name_et="Kompenseerimise filtreerimine" name_ru="Фильтрация компенсации" name_lv="Kompensācijas filtrēšana" name_tr="Gen. compensation filtering" pointtype="3" registertype="Holding" addressformat="S32" addressindex="970" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="HeatingControl2_HeatinModeL2" name_en="H2 Type of heating" name_fi="L2 Lämmitystapa" name_sv="V2 Typ av uppvärmning sätt" name_et="K2 Kütterežiim" name_ru="O2 Режим отопления" name_lv="A2 Apkures līkne" name_tr="H2 Heating circuit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="556" categorytype="3" enum="0=Lattialämmitys;1=Patterilämmitys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_n_20" name_en="Output temperature when outdoor temperature is -20 °C" name_fi="Menoveden lämpötila kun ulkolämpötilan on -20 °C" name_sv="Framledn.vattnets temperatur när utetemperatur är -20 °C" name_et="K1 pealevoolu temp., kui välistemperatuur on -20 °C" name_ru="Т.на подаче при т.нар.возд. -20 °C" name_lv="Izvades temperatūra, kad ārgaisa temperatūra ir -20 °C" name_tr="Output temperature when outdoor temperature is -20 °C" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1339" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_in2" name_en="Curve outdoor temperature point 2" name_fi="Käyrän ulkolämpötilapiste 2" name_sv="punkt 2 utetemperatur" name_et="Küttekõvera välistemp. punkt 2" name_ru="Точка 2 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 2" name_tr="Curve outdoor temperature point 2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1341" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_out2" name_en="Heating water temperature at outdoor temperature point 2" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 2" name_sv="Framledn.vattnets temperatur  vid punkt 2 utetemperatur " name_et="Kütte pealevoolu temp. küttekõvera välistemp. punktis 2" name_ru="Т.на подаче в точ.2 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 2" name_tr="Heating water temperature at outdoor temperature point 2" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1343" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_in3" name_en="Curve outdoor temperature point 3" name_fi="Käyrän ulkolämpötilapiste 3" name_sv="punkt 3 utetemperatur" name_et="Küttekõvera välistemp. punkt 3" name_ru="Точка 3 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 3" name_tr="Curve outdoor temperature point 3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1345" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_out3" name_en="Heating water temperature at outdoor temperature point 3" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 3" name_sv="Framledn.vattnets temperatur  vid punkt 3 utetemperatur" name_et="Kütte pealevoolu temperatuur küttekõvera välistemperatuuri punktis 3" name_ru="Т.на подаче в точ.3 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 3" name_tr="Heating water temperature at outdoor temperature point 3" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1347" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_in4" name_en="Curve outdoor temperature point 4" name_fi="Käyrän ulkolämpötilapiste 4" name_sv="punkt 4 utetemperatur" name_et="Küttekõvera välistemperatuuri punkt 4" name_ru="Точка 4 кривой темп.нар.возд." name_lv="Līknes ārgaisa temperatūras punkts 4" name_tr="Curve outdoor temperature point 4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1349" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_out4" name_en="Heating water temperature at outdoor temperature point 4" name_fi="Menoveden lämpötila käyrän ulkolämpötilapisteessä 4" name_sv="Framledn.vattnets vid punkt 4 utetemperatur" name_et="Kütte pealevoolu temp. küttekõvera välistemperatuuri punktis 4" name_ru="Т.на подаче в точ.4 кривой Т.нар.возд." name_lv="Apkures ūdens temperatūra pie ārgaisa temperatūras punktā 4" name_tr="Heating water temperature at outdoor temperature point 4" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1351" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="42" max="65" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_out5" name_en="Output temperature when outdoor temperature is +20 °C" name_fi="Menoveden lämpötila kun ulkolämpötilan on +20 °C" name_sv="Framledn.vattnets när utetemperatur är +20 °C" name_et="K1 pealevoolu temp., kui välistemperatuur on +20 °C" name_ru="Темп.подаче при т.нар.возд. +20 °C" name_lv="Izvades temperatūra, kad ārgaisa temperatūra ir +20 °C" name_tr="Output temperature when outdoor temperature is +20 °C" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1353" categorytype="3" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_min_limit" name_en="Supply water minimum  value" name_fi="Menoveden lämpötilan minimiarvo" name_sv="Framledn.vattnets minimitemperatur" name_et="Kütte miinimum väärtus" name_ru="Миним.знач.темп.воды на подаче" name_lv="Izvades min. robeža" name_tr="Output minimum value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1355" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="20" max="60" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHReturnComp_max_limit" name_en="Supply water maximum value" name_fi="Menoveden lämpötilan maksimiarvo" name_sv="Framledn.vattnets maximitemperatur" name_et="Kütte maksimum väärtus" name_ru="Макс.знач.темп.воды на подаче" name_lv="Izvades maks. robeža" name_tr="Output maximum value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1357" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="50" max="70" />
      <point name="HeatingControl2_DHReturnTempComp_L2DhRetTempComp_P_value" name_en="H2 DH ret. water comp. P-area" name_fi="L2 KL paluulämpöt. kompens. P-alue" name_sv="V2 FJV returv. temp. komp. P-band" name_et="K2 KK tagasiv. temp. Komp. P-arv" name_ru="О2  ЦТС зона Р компенс.Т.обр.воды" name_lv="A2 Prim. kont. atg. komp. P-apgabals" name_tr="H1 DH ret. water comp. P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1359" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="HeatingControl2_DHReturnTempComp_L2DhRetTempComp_I_time" name_en="H2 DH ret. water comp. I-time" name_fi="L2 KL paluulämpöt. kompens. I-aika" name_sv="V2 FJV returv. temp. komp. I-tid" name_et="K2 KK tagasiv. temp. Komp. I-aeg" name_ru="О2 ЦТС время I компенс.Т.обр.воды" name_lv="A2 Prim. kont. atg. komp. I-laiks" name_tr="H1 DH ret. water comp. I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1361" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="HeatingControl2_DHReturnTempComp_L2DhReturnCompMAx" name_en="H2 DH return temp. max comp, " name_fi="L2 KL paluulämpötilan kompens. maks." name_sv="V2 FJV returtemp. max komp." name_et="K2 KK tagasiv. temp. max.kompens." name_ru="O2 ЦТС максимум компенс.Т.обр.воды" name_lv="A2 Prim. kont. atg. maks komp." name_tr="H1 DH Return max comp " pointtype="3" registertype="Holding" addressformat="S32" addressindex="1363" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_DHReturnTempComp_L2DHRetTempCompState" name_en="H2 DH return temp. comp," name_fi="L2 KL paluulämpötilan komp." name_sv="V2 FJV returtemp. komp." name_et="K2 KK tagasiv. temp. kompens." name_ru="О2 ЦТС компенсация обр.воды" name_lv="A2 Prim. kont. atg. kompensācija" name_tr="H2 DH return temp. comp" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1365" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_TimeControl2_OperatingModeAwayState" name_en="Temp.level on Away control" name_fi="Lämpötaso Poissa-ohjauksessa" name_sv="Temp. nivå på Borta status" name_et="Eemal-juhtimise temperatuuritase" name_ru="Темпер.режим управления Не дома" name_lv="Ārpus mājām rež. temp pazem." name_tr="Temp.level on Away control" pointtype="3" registertype="Holding" addressformat="S32" addressindex="792" categorytype="3" enum="0=Automaatti;1=Normaalilämpö;2=Lämmönpud.;3=Suuri lämmönp.;4=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl2_TimeControl2_BigTempDropRadiator" name_en="Big temp. drop" name_fi="Suuri lämmönpudotus" name_sv="Stor temp.sänkning" name_et="Suur temperatuurilangus" name_ru="Значит.понижение темпер." name_lv="Lielais temp. pazeminājums" name_tr="Big temp. drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="796" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_TimeControl2_SmallTempDropRadiator" name_en="Temp. drop" name_fi="Lämmönpudotus" name_sv="Temp. sänkning" name_et="Temp.langus" name_ru="Падение температуры" name_lv="Pazeminājums" name_tr="Temp. Drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="798" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_TimeControl2_PreHeatingValueFloor" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framledn.vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="S32" addressindex="800" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl2_TimeControl2_PreHeatingValueRadiator" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framledn.vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="S32" addressindex="802" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="HeatingControl2_TimeControl2_SmallTempDropFloor" name_en="Temp. drop" name_fi="Lämmönpudotus" name_sv="Temp. sänkning" name_et="Temp.langus" name_ru="Падение температуры" name_lv="Pazeminājums" name_tr="Temp. Drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="804" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_TimeControl2_BigTempDropFloor" name_en="Big temp. drop" name_fi="Suuri lämmönpudotus" name_sv="Stor temp.sänkning" name_et="Suur temperatuurilangus" name_ru="Значит.понижение темпер." name_lv="Lielais temp. pazeminājums" name_tr="Big temp. drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="806" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_TimeControl2_PreHeatingTime" name_en="Pre-increase time" name_fi="Esikorotusaika" name_sv="Snabbhöjning tid" name_et="Eeltõstmise aeg" name_ru="О1 Время предподогрева" name_lv="Pirms-paaugstinājuma laiks" name_tr="Pre-increase time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="808" categorytype="3" unit="h" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="10" />
      <point name="HeatingControl2_TimeControl2_PreHeatInUse" name_en="Supply water pre-increase" name_fi="Menoveden esikorotus" name_sv="Framl. vatten snabbhöjning" name_et="Küttevee eeltõstmine" name_ru="Предподогр.вод.подач." name_lv="Turpg. temp. pirms-paaugstinājums" name_tr="Supply water pre-increase" pointtype="3" registertype="Holding" addressformat="U16" addressindex="810" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_TimeControl2_BigTempDropRoom" name_en="Big temp. drop room temp." name_fi="Suuri lämmönpudotus huonel." name_sv="Stor temp.sänkning rumstemp." name_et="Suur temperatuurilangus toatemp." name_ru="Значит.понижение темпер. Комнатная т." name_lv="Lielais temp. pazeminājums telpas temp." name_tr="Big temp. drop room temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="686" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_TimeControl2_SmallTempDropRoom" name_en="Temp. drop room temp" name_fi="Lämmönpudotus huonel." name_sv="Temp. sänkning rumstemp." name_et="Temp.langus toatemp" name_ru="Падение температуры, Комнатная т." name_lv="Pazeminājums telpas temp." name_tr="Temp. drop room temp" pointtype="3" registertype="Holding" addressformat="S32" addressindex="723" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="40" />
      <point name="HeatingControl2_ConstructionComp_OutTempDelayDec" name_en="Radiat. heat.delay on outd.temp dec." name_fi="Patterilämmityksen hidastus ulkol. laskiessa" name_sv="Rad.värme fördr.på utetemp.sjunkn." name_et="Building specific delay time" name_lv=" Ārgaisa temp. aizkave tai samaz.(radiatoru apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="280" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_ConstructionComp_OutTempDelayInc" name_en="Radiat.heat.anticip.on outd.temp.incr." name_fi="Patterilämmityksen ennakointi ulkol. noustessa" name_sv="Rad.värme framförhålln.på utet.ökn." name_et="Building specific delay time" name_lv="Ārgaisa temp. aizkave tai paliel.(radiatoru apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="352" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_ConstructionComp_OutTempAnticInc" name_en="Building specific delay time" name_fi="Lattialämmityksen ennakointi ulkol. noustessa" name_sv="Buggnad specifik fördröjning tid" name_lv="Grīdas apk. prognoze temp. paliel.(grīdu apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="425" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_ConstructionComp_OutTempAnticDec" name_en="Building specific delay time" name_fi="Lattialämmityksen ennakointi ulkol. laskiessa" name_sv="Buggnad specifik fördröjning tid" name_lv="Grīdas apk. prognoze temp. samaz.(grīdu apkure)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="472" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_RoomComp_RoomCompMaxEffectFloor" name_en="Comp.max effect on supply water" name_fi="Kompens. max vaikutus menoveteen" name_sv="Komp.max effekt på framl. vatten" name_et="Kompenseerimise max mõju kütteveele" name_ru="Макс.воздейст.комп. на Т на подаче" name_lv="Komp. maks. ietekme uz turpg. temp." name_tr="Comp.max effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="819" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="HeatingControl2_RoomComp_RoomCompMaxEffectRadiator" name_en="Comp.max effect on supply water" name_fi="Kompens. max vaikutus menoveteen" name_sv="Komp.max effekt på framl. vatten" name_et="Kompenseerimise max mõju kütteveele" name_ru="Макс.воздейст.комп. на Т на подаче" name_lv="Komp. maks. ietekme uz turpg. temp." name_tr="Comp.max effect on supply water" pointtype="3" registertype="Holding" addressformat="S32" addressindex="821" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="HeatingControl2_RoomComp_RoomCompRatioFloor" name_en="Room compenstation ratio" name_fi="Huonekompensointisuhde" name_sv="Rumskompensering" name_et="Toa kompenseerimise kiirus" name_ru="Соотнош.комн.компенс." name_lv="Telpas kompensācijas koeficients" name_tr="Room compenstation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="823" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl2_RoomComp_RoomCompRatioRadiator" name_en="Room compenstation ratio" name_fi="Huonekompensointisuhde" name_sv="Rumskompensering" name_et="Toa kompenseerimise kiirus" name_ru="Соотнош.комн.компенс." name_lv="Telpas kompensācijas koeficients" name_tr="Room compenstation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="825" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl2_RoomComp_RoomIMaxEffectFloor" name_en="Input1" name_fi="I-säädön max vaik. menoveteen" name_sv="Input1" name_et="Input1" name_lv="I-laika maks. ietekme uz turpg. temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="827" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_RoomComp_RoomIMaxEffectRadiator" name_en="I control's max effect on sup wat" name_fi="I-säädön max vaik. menoveteen" name_sv="I regler max.effekt på framl.vatten" name_et="Input1" name_lv="I-laika maks. ietekme uz turpg. temp." pointtype="3" registertype="Holding" addressformat="S32" addressindex="829" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="15" />
      <point name="HeatingControl2_RoomComp_RoomITimeFloor" name_en="Room compensation adjustment time" name_fi="Huonekompens. korjausaika" name_sv="Rumskompenseringens justeringstid" name_et="Input1" name_ru="Room compensation adjustment time" name_lv="Telpas komp. laiks (I-laiks)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="831" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="7" />
      <point name="HeatingControl2_RoomComp_RoomITimeRadiator" name_en="Room compensation adjustment time" name_fi="Huonekompens. korjausaika" name_sv="Rumskompenseringens justeringstid" name_et="Input1" name_ru="Room compensation adjustment time" name_lv="Telpas komp. laiks (I-laiks)" pointtype="3" registertype="Holding" addressformat="S32" addressindex="833" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0.5" max="7" />
      <point name="HeatingControl2_RoomComp_RoomMeasDelay" name_en="Room temp.measurement delay" name_fi="Huonel. mitt. hidastusaika" name_sv="Rumstemp.mätningens fördröjning" name_et="Toatemperatuuri mõõtmise viivitusaeg" name_ru="Отлож.вр.измер.темп.наруж.возд." name_lv="Telpas temp. mērījuma aizkave" name_tr="Room temp.measurement delay time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="835" categorytype="3" unit="h" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="2" />
      <point name="HeatingControl2_OutdoorCompCurves_CurveTypeL2" name_en="Curve type" name_fi="Säätökäyrän tyyppi" name_sv="Typ av kurva" name_et="Kõvera tüüp" name_ru="Тип кривой регулирования" name_lv="Līknes tips" name_tr="Curve type" pointtype="3" registertype="Holding" addressformat="U16" addressindex="837" categorytype="3" enum="0=3-piste säätökäyrä;1=5-piste säätökäyrä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_n20Floor" name_en="Curve3p_Supply w._n20Floor" name_fi="Käyrä3p_Menov._-20_Lattial." name_sv="Kurva3p_Framl._n20_Golv" name_et="Kõver3p_küttevee_n20 Põrandak." name_ru="Кривая 3p_Подача._Наружная темп.-20_Напольное отопление" name_lv="Līkne 3p_Turpg. n20 grīdu apkure" name_tr="Curve3p_Out_n20Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="564" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve_5p_Out1Floor" name_en="Curve_5p_Supply w.1 Floor" name_fi="Käyrä5p_Menov.1_Lattial." name_sv="Kurva_5p_Framl.1 Golv" name_et="Kõver5p_küttevee 1 Põrandak." name_ru="Кривая_5p__Подача1_Напольный обогрев" name_lv="Līkne_5p_Turpg.1 grīdu apkure" name_tr="Curve_5p_Out1Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="662" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve_MinFloor" name_en="Min. limit" name_fi="Minimiraja" name_sv="Min.gräns" name_et="Alampiir" name_ru="Мин.предел" name_lv="Min. robeža" name_tr="Min. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="693" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve_MaxFloor" name_en="Max. limit" name_fi="Maksimiraja" name_sv="Max.gräns" name_et="Ülempiir" name_ru="Макс.предел" name_lv="Maks. robeža" name_tr="Max. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="697" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_0Floor" name_en="Curve3p_Supply w._0 Floor" name_fi="Käyrä3p_Menov._0 Lattial." name_sv="Kurva3p_Framl._0 Golv" name_et="Kõver3p_küttevee_Välistemp.0_Põrandak." name_ru="Кривая3p_Подача_Наружная т.0_напольный обогрев" name_lv="Līkne 3p_Turpg._Ārgaisa 0_ grīdu apkure" name_tr="Curve3p_Out_0Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="838" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_p20Floor" name_en="Curve3p_Supply w._p20 Floor" name_fi="Käyrä3p_Menov._p20_Lattial." name_sv="Kurva3p_Framl._p20 Golv" name_et="Kõver3p_küttevee_Välistemp.+20_Põrandak." name_ru="Кривая3p_Подача_Наружная т.+20_Напольный обогрев" name_lv="Līkne 3p_Turpg._Ārgaisa +20_ grīdu apkure" name_tr="Curve3p_Out_p20Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="840" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In2Floor" name_en="Curve5p_Outdoor temp.2 Floor" name_fi="Käyrä5p_Ulkol.2_Lattial." name_sv="Kurva5p_Utet.2 Golv" name_et="Kõver5p_Välistemp.2 Põrandak." name_ru="Кривая5p_Наружная т.2_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa 2 grīdu apkure" name_tr="Curve5p_In2Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="842" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out2Floor" name_en="Curve5p_Supply w.2 Floor" name_fi="Käyrä5p_Menov.2_Lattial." name_sv="Kurva5p_Framl.2 Golv" name_et="Kõver5p_küttevee 2 Põrandak." name_ru="Кривая5p_Подача2_Напольный обогрев" name_lv="Līkne 5p_Turpg. 2 grīdu apkure" name_tr="Curve5p_Out2Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="844" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In3Floor" name_en="Curve5p_Outdoort temp.3 Floor" name_fi="Käyrä5p_Ulkol.3_Lattial." name_sv="Kurva5p_Utet.3 Golv" name_et="Kõver5p_Välistemp.3 Põrandak." name_ru="Кривая5p_Наружная т.3_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa3 grīdu apkure" name_tr="Curve5p_In3Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="846" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out3Floor" name_en="Curve5p_Supply w.3 Floor" name_fi="Käyrä5p_Menov.3_Lattial." name_sv="Kurva5p_Framl.3 Golv" name_et="Kõver5p_küttevee 3 Põrandak." name_ru="Кривая5p_Подача3_Напольный обогрев" name_lv="Līkne 5p_Turpg. 3 grīdu apkure" name_tr="Curve5p_Out3Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="848" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In4Floor" name_en="Curve5p_Outdoor temp.4 Floor" name_fi="Käyrä5p_Ulkol.4_Lattial." name_sv="Kurva5p_Utet.4 Golv" name_et="Kõver5p_Välistemp.4 Põrandak." name_ru="Кривая5p_Наружная т.4_Напольный обогрев" name_lv="Līkne 5p_Ārgaisa 4 grīdu apkure" name_tr="Curve5p_In4Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="850" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out4Floor" name_en="Curve5p_Supply w.4 Floor" name_fi="Käyrä5p_Menov.4_Lattial." name_sv="Kurva5p_Framl.4 Golv" name_et="Kõver5p_küttevee 4 Põrandak." name_ru="Кривая5p_Подача4_Напольный обогрев" name_lv="Līkne 5p_Turpg. 4 grīdu apkure" name_tr="Curve5p_Out4Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="852" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out5Floor" name_en="Curve5p_Supply w.5 Floor" name_fi="Käyrä5p_Menov.5_Lattial." name_sv="Kurva5p_Framl.5 Golv" name_et="Kõver5p_küttevee 5 Põrandak." name_ru="Кривая5p_Подача5_Напольный обогрев" name_lv="Līkne 5p_Turpg. 5 grīdu apkure" name_tr="Curve5p_Out5Floor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="854" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_n20Radiator" name_en="Curve3p_Supply w._n20 Radiator" name_fi="Käyrä3p_Menov._n20_patteril." name_sv="Kurva3p_Framl._n20 Radiator" name_et="Kõver3p_küttevee_Välistemp.-20 Radiaatork." name_ru="Кривая3p_Подача_n20_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa -20 radiatoru apkure" name_tr="Curve3p_Out_n20Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="856" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_0Radiator" name_en="Curve3p_Supply w._0 Radiator" name_fi="Käyrä3p_Menov._0_patteril." name_sv="Kurva3p_Framl._0 Radiator" name_et="Kõver3p_küttevee_0 Radiaatork." name_ru="Кривая3p_Подача_0_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa 0 radiatoru apkure" name_tr="Curve3p_Out_0Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="858" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve3p_Out_p20Radiator" name_en="Curve3p_Supply w._p20 Radiator" name_fi="Käyrä3p_Menov._p20_patteril." name_sv="Kurva3p_Framl._p20 Radiator" name_et="Kõver3p_küttevee_Välistemp.+20 Radiaatork." name_ru="Кривая3p_Подача_p20_Радиаторное отопление" name_lv="Līkne 3p_Turpg._Ārgaisa +20_ radiatoru apkure" name_tr="Curve3p_Out_p20Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="860" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_CurveMinRadiator" name_en="H2 Min limit" name_fi="L2 Minimiraja" name_sv="V2 Min gräns" name_et="K2 Alampiir" name_ru="О2 Мин.предел " name_lv="A2 Min. robeža" name_tr="H2 Min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="862" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve_MaxRadiator" name_en="H2 Max limit" name_fi="L2 Maksimiraja" name_sv="V2 Max gräns" name_et="K2 Ülempiir" name_ru="О2 Макс.предел" name_lv="A2 Maks. robeža" name_tr="H2 Max limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="915" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="99" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve_5p_Out1Radiator" name_en="Curve_5p_Supply w.1 Radiator" name_fi="Käyrä5p_Menov.1_patteril." name_sv="Kurva5p_Framl.1 Radiator" name_et="Kõver5p_küttevee 1Radiaatork." name_ru="Кривая_5p_Подача1_Радиаторное отопление" name_lv="Līkne_5p_Turpg. 1 radiatoru apkure" name_tr="Curve_5p_Out1Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1036" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In2Radiator" name_en="Curve5p_Outdoor temp.2 Radiator" name_fi="Käyrä5p_Ulkol.2_patteril." name_sv="Kurva5p_Utet.2 Radiator" name_et="Kõver5p_Välistemp.2 Radiaatork." name_ru="Кривая5p_Наружная т.2_Радиаторное отопление" name_lv="Līkne_5p_Ārgaisa 2 radiatoru apkure" name_tr="Curve5p_In2Radistor" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1058" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out2Radiator" name_en="Curve5p_Supply w.2 Radiator" name_fi="Käyrä5p_Menov.2_patteril." name_sv="Kurva5p_Framl.2 Radiator" name_et="Kõver5p_küttevee 2 Radiaatork." name_ru="Кривая5p_Подача2_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 2 radiatoru apkure" name_tr="Curve5p_Out2Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1066" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In3Radiator" name_en="Curve5p_Outdoor temp.3 Radiator" name_fi="Käyrä5p_Ulkol.3_patteril." name_sv="Kurva5p_Utet.3 Radiator" name_et="Kõver5p_Välistemp.3 Radiaatork." name_ru="Кривая5p_Наружная т.3_Радиаторное отопление" name_lv="Līkne 5p_Ārgaisa 3_radiatoru apkure" name_tr="Curve5p_In3Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1070" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out3Radiator" name_en="Curve5p_Supply w.3 Radiator" name_fi="Käyrä5p_Menov.3_patteril." name_sv="Kurva5p_Framl.3 Radiator" name_et="Kõver5p_küttevee 3 Radiaatork." name_ru="Кривая5p_Подача3_Радиаторное отопление" name_lv="Līkne 5p_Turpg.3 radiatoru apkure" name_tr="Curve5p_Out3Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1072" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_In4Radiator" name_en="Curve5p_Outdoor temp.4 Radiator" name_fi="Käyrä5p_Ulkol.4_patteril." name_sv="Kurva5p_Utet.4 Radiator" name_et="Kõver5p_Välistemp.4 Radiaatork." name_ru="Кривая5p_Наружная т.4_Радиаторное отопление" name_lv="Līkne 5p_Ārgaisa 4 radiatoru apkure" name_tr="Curve5p_In4Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1074" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-20" max="20" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out4Radiator" name_en="Curve5p_Supply w.4 Radiator" name_fi="Käyrä5p_Menov.4_patteril." name_sv="Kurva5p_Framl.4 Radiator" name_et="Kõver5p_küttevee 4 Radiaatork." name_ru="Кривая5p_Подача4_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 4 radiatoru apkure" name_tr="Curve5p_Out4Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1076" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_OutdoorCompCurves_Curve5p_Out5Radiator" name_en="Curve5p_Supply w.5 Radiator" name_fi="Käyrä5p_Menov.5_patteril." name_sv="Kurva5p_Framl.5 Radiator" name_et="Kõver5p_küttevee 5 Radiaatork." name_ru="Кривая5p_Подача5_Радиаторное отопление" name_lv="Līkne 5p_Turpg. 5 radiatoru apkure" name_tr="Curve5p_Out5Radiator" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1078" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="HeatingControl2_RetwaterComp_RetWaterMinLimit" name_en="Return water freezing risk limit" name_fi="Paluuveden jäätymisvaarahälytys" name_sv="Returvatten frysrisk gräns" name_et="Tagastusvee külmumisohu piir" name_ru="Сигнал опасн.обмерз.обр.воды" name_lv="Atg. aizsalšanas riska robeža" name_tr="Return water freezing risk limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="917" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="5" max="25" />
      <point name="HeatingControl2_RetwaterComp_FrozingLimit" name_en="Return water alarm delay" name_fi="Jäätymisvaarahälytyksen viive" name_sv="Returvatten larm fördröjning" name_et="Tagastusvee alarmi viivitus" name_ru="Задерж.сигн.опасн.обмерз.обр.воды" name_lv="Atg. trauksmes aizkaves laiks" name_tr="Return water alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="919" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="120" />
      <point name="HeatingControl2_RetwaterComp_RetWatCompFactor" name_en="H2 Return water compensation ratio" name_fi="L2 Paluuveden kompensointisuhde" name_sv="V2 Returvattnets kompensering" name_et="K2 Tagastusvee kompenseerimine" name_ru="O2 Компенсация обратной воды" name_lv="A2 Atgaitas ūd. kompensācijas koeficients" name_tr="H2 Return water kompensation ratio" pointtype="3" registertype="Holding" addressformat="S32" addressindex="921" categorytype="3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="HeatingControl2_DeviationAlarm1_DiffAlDelay" name_en="Deviation alarm delay" name_fi="Poikkeamahälytyksen viive" name_sv="Avvikelselarm fördröjning" name_et="Hälbealarmi viivitus" name_ru="Задержка сигнала несоответств." name_lv="Deviācijas trauksmes aizkaves laiks" name_tr="Deviation alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="923" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="120" />
      <point name="HeatingControl2_DeviationAlarm1_DiffAlarm" name_en="Supply water deviation alarm" name_fi="Menoveden poikkeamahälytys" name_sv="Framledn.vattnets avvikelselarm" name_et="Küttevee hälbealarm" name_ru="Сигн.несоотв. по воде на подаче" name_lv="Turpg. ūd. deviācijas trauksme" name_tr="Supply water deviation alarm" pointtype="3" registertype="Holding" addressformat="S32" addressindex="925" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="1" max="50" />
      <point name="HeatingControl2_DeviationAlarm1_OverTemp" name_en="Supply water high limit alarm" name_fi="Menoveden ylärajahälytys" name_sv="Framledningsvatten högnivålarm" name_et="Küttevee ülemise piiri alarm" name_ru="Сигн.по верх.пределу вод.подач." name_lv="Turpgaitas  pārkaršanas trauksme" name_tr="Supply water high limit alarm" pointtype="3" registertype="Holding" addressformat="S32" addressindex="947" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="40" max="100" />
      <point name="HeatingControl2_DeviationAlarm1_OverTempDelay" name_en="High limit alarm delay" name_fi="Ylärajahälytyksen viive" name_sv="Högnivålarm fördröjning" name_et="Ülemise piiri alarmi viivitus" name_ru="Задерж.сигн.по верх.пределу вод.подач." name_lv="Pārkaršanas trauksmes aizkaves laiks" name_tr="High limit alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="949" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="120" />
      <point name="InputSelections_SensorSelUI13" name_en="SensorType" name_fi="Mittauksen valinta" pointtype="3" registertype="Holding" addressformat="S32" addressindex="605" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus, NTC10;6=Painekytkin;4=Painelähetin V;9=Painelähetin mA" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI12" name_en="SensorType" name_fi="Mittauksen valinta" pointtype="3" registertype="Holding" addressformat="S32" addressindex="607" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus, NTC10;6=Painekytkin;4=Painelähetin V;9=Painelähetin mA" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI14" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_et="Mõõtmise valik" name_ru="Выбор измерения" name_lv="Mērīj. izvēle" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="619" categorytype="3" enum="0=Ei käytössä;4=Yleiskompensointi, 0...10V;9=Yleiskompensointi, 0...20mA;6=Kotona/Poissa -kytkin" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI7" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_et="Mõõtmise valik" name_ru="Выбор измерения" name_lv="Mērīj. izvēle" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="640" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus;2=L2 Huonemittaus, NTC10;3=L2 Huonemittaus, 0...10V;5=L2 vaihdin KL paluu" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI4" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_et="Mõõtmise valik" name_ru="Выбор измерения" name_lv="Mērīj. izvēle" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="644" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus;2=L1 Huonemittaus, NTC10;3=L1 Huonemittaus, 0...10V;4=L1 vaihdin KL paluu" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelDI2_18" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_et="Mõõtmise valik" name_ru="Выбор измерения" name_lv="Mērīj. izvēle" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="932" categorytype="3" enum="0=Ei käytössä;4=Vesimäärämittaus;3=Energiamittaus" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI16" name_en="SensorType" name_fi="Mittauksen valinta" pointtype="3" registertype="Holding" addressformat="S32" addressindex="936" categorytype="3" enum="0=Ei käytössä;1=Indikointi;2=Hälytys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSel_DI1_17" name_en="SensorType" name_fi="Mittauksen valinta" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1396" categorytype="3" enum="0=Ei käytössä;1=P1 Hälytys;2=Yleishälytys;4=Vesimäärämittaus;3=Energiamittaus" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI10" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_lv="Mērīj. izvēle" name_ru="Выбор измерения" name_et="Mõõtmise valik" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1225" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus, NTC10;6=Kosketinhälytys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI15" name_en="SensorType" name_fi="Mittauksen valinta" pointtype="3" registertype="Holding" addressformat="S32" addressindex="934" categorytype="3" enum="0=Ei käytössä;1=Indikointi;2=Hälytys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSelUI11" name_en="Meas. selection" name_fi="Mittauksen valinta" name_sv="Val av mätning" name_lv="Mērīj. izvēle" name_ru="Выбор измерения" name_et="Mõõtmise valik" name_tr="Meas. selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1259" categorytype="3" enum="0=Ei käytössä;1=Vapaa mittaus, NTC10;6=Kosketinhälytys" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="InputSelections_SensorSel_UI11_DigInType" name_en="Digital input type" name_fi="Digitaalitulon tyyppi" name_sv="Digital ingång typ" name_et="Digitalsisendi tüüp" name_lv="Digitālās ieejas tips" name_ru="Тип цифрового входа" name_tr="Digital input type" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1261" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_UI10_DigInType" name_en="Digital input type" name_fi="Digitaalitulon tyyppi" name_sv="Digital ingång typ" name_et="Digitalsisendi tüüp" name_lv="Digitālās ieejas tips" name_ru="Тип цифрового входа" name_tr="Digital input type" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1227" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_OutSel_UI1_OutdoorTempBusSelect" name_en="Outdoor temp. from bus" name_fi="Ulkolämpötila väylältä" name_sv="Utetemp, från bus" name_et="Välistemperatuur siinist" name_ru="Т.нар.возд. по магист.шине " name_lv="Ārgaisa temp. no BUS" name_tr="Outdoor temp from bus" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1380" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_UI12_DigInType" name_en="Select" name_fi="Digitaalitulon tyyppi" name_sv="Select" name_et="Select" name_lv="UI12  izvēle" pointtype="3" registertype="Holding" addressformat="U16" addressindex="646" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_UI13_DigInType" name_en="Select" name_fi="Digitaalitulon tyyppi" name_sv="Select" name_et="Select" name_lv="UI 13  izvēle" pointtype="3" registertype="Holding" addressformat="U16" addressindex="648" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_DI1_DigInType" name_en="Input1" name_fi="Digitaalitulon tyyppi" name_sv="Input1" name_et="Input1" name_lv="D1 1 izvēle" pointtype="3" registertype="Holding" addressformat="U16" addressindex="942" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_DI1_EnergyPulseScale_DI1" name_en="Pulse input scaling" name_fi="Pulssitulon skaalaus" name_sv="Pulsingång skalning" name_et="Pulsi sisendi mastaapimine" name_ru="Масштабир.импульс.входа" name_lv="Pulsa ieejas kalibrēšana" name_tr="Pulse input scaling" pointtype="3" registertype="Holding" addressformat="S32" addressindex="930" categorytype="3" unit="kWh/pulse" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      <point name="InputSelections_SensorSel_DI1_EnergyCountSet_DI1" name_en="Value to be multiplied" name_fi="Laskurin alkuarvo" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="938" categorytype="3" unit="MWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="999999.9" />
      <point name="InputSelections_SensorSel_DI1_WaterCountSet" name_en="Counter init value" name_fi="Laskurin alkuarvo" name_sv="Värdet som man vill multiplicera" name_et="Value to be multiplied" name_ru="Value to be multiplied" pointtype="3" registertype="Holding" addressformat="S32" addressindex="940" categorytype="3" unit="m3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="999999.9" />
      <point name="InputSelections_SensorSel_DI1_SetCounter_DI1" name_en="Write" name_fi="Write" name_sv="Write" name_et="Write" name_ru="Write" pointtype="3" registertype="Holding" addressformat="U16" addressindex="615" categorytype="3" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_DI1_WaterPulseScale_DI1" name_en="Pulse input scaling" name_fi="Pulssitulon skaalaus" name_sv="Pulsingång skalning" name_et="Input0" name_ru="Input0" pointtype="3" registertype="Holding" addressformat="S32" addressindex="968" categorytype="3" unit="l/pulse" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      <point name="InputSelections_SensorSel_DI1_DI1DigAlarmPriority" name_en="Alarm priority" name_fi="Hälytyksen prioriteetti" name_sv="Alarm priority" name_et="Alarm priority" name_ru="Приоритет авар.сигн." name_lv="Alarm priority" name_tr="Alarm priority" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1513" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_SensorSel_UI15_DigInType" name_en="Input1" name_fi="Digitaalitulon tyyppi" name_sv="Input1" name_et="Input1" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1096" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_UI15_PumpAlarm_UI15DigAlarmPriority" name_en="Alarm priority" name_fi="Hälytyksen prioriteetti" name_sv="Alarm priority" name_et="Alarm priority" name_ru="Приоритет авар.сигн." name_lv="Alarm priority" name_tr="Alarm priority" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1515" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_SensorSel_DI22_EnergyPulseScale_DI2" name_en="Input0" name_fi="Pulssitulon skaalaus" name_sv="Input0" name_et="Input0" name_ru="Input0" pointtype="3" registertype="Holding" addressformat="S32" addressindex="815" categorytype="3" unit="kWh/pulse" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      <point name="InputSelections_SensorSel_DI22_EnergyCountSet_DI2" name_en="Value to be multiplied" name_fi="Laskurin alkuarvo" name_sv="Värdet som man vill multiplicera" pointtype="3" registertype="Holding" addressformat="S32" addressindex="817" categorytype="3" unit="MWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="999999.9" />
      <point name="InputSelections_SensorSel_DI22_WaterCountSet" name_en="Counter init value" name_fi="Laskurin alkuarvo" name_sv="Värdet som man vill multiplicera" name_et="Value to be multiplied" name_ru="Value to be multiplied" pointtype="3" registertype="Holding" addressformat="S32" addressindex="943" categorytype="3" unit="m3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="999999.9" />
      <point name="InputSelections_SensorSel_DI22_SetCounter_DI2" name_en="Write" name_fi="Write" name_sv="Write" name_et="Write" name_ru="Write" pointtype="3" registertype="Holding" addressformat="U16" addressindex="301" categorytype="3" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_DI22_WaterPulseScale_DI2" name_en="Pulse input scaling" name_fi="Pulssitulon skaalaus" name_sv="Pulsingång skalning" name_et="Pulsi sisendi mastaapimine" name_ru="Масштабир.импульс.входа" name_lv="Pulsa ieejas kalibrēšana" name_tr="Pulse input scaling" pointtype="3" registertype="Holding" addressformat="S32" addressindex="337" categorytype="3" unit="l/pulse" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="100" />
      <point name="InputSelections_SensorSel_UI16_DigInType" name_en="Input1" name_fi="Digitaalitulon tyyppi" name_sv="Input1" name_et="Input1" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1099" categorytype="3" enum="0=Sulkeutuva;1=Avautuva" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_SensorSel_UI16_PumpAlarm_UI16DigAlarmPriority" name_en="Alarm priority" name_fi="Hälytyksen prioriteetti" name_sv="Alarm priority" name_et="Alarm priority" name_ru="Приоритет авар.сигн." name_lv="Alarm priority" name_tr="Alarm priority" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1517" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_L1RoomScaling_UI4_VoltMin" name_en="Message MIN" name_fi="Viesti Min" name_sv="Signal MIN" name_et="Signaali MIN" name_ru="Сигнал Мин" name_lv="Ziņas Min." name_tr="LP sensor  min input" pointtype="3" registertype="Holding" addressformat="S32" addressindex="672" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_L1RoomScaling_UI4_TempMin" name_en="Temperature minmum" name_fi="Lämpötila Min" name_sv="Temperatur min" name_et="Temperatuuri miinimum" name_ru="Tемпература Мин " name_lv="Min. temperatūra" name_tr="Temperature minmum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="674" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="InputSelections_L1RoomScaling_UI4_VoltMax" name_en="Message MAX" name_fi="Viesti Max" name_sv="Signal MAX" name_et="Signaali MAX" name_ru="Сигнал Макс" name_lv="Ziņas Maks." name_tr="Temperature maksimum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="676" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_L1RoomScaling_UI4_TempMax" name_en="Temperature max" name_fi="Lämpötila Max" name_sv="Temperatur max" name_et="Temperatuuri maksimum" name_ru="Температура Макс." name_lv="Maks. temperatūra" name_tr="Temperature max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="678" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="InputSelections_PressScaling_UI13_PressMax" name_en="Measuring area" name_fi="Mittausalue" name_sv="Mätområde" name_et="Mõõtmisala" name_ru="Измерит.диапазон" name_lv="Mērījuma diapazons" name_tr="Measuring area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="708" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="InputSelections_PressScaling_UI13_PresMeas13Offser" name_en="Measurement adjustment" name_fi="Mittauksen korjaus" name_sv="Mätningens justering" name_et="Mõõtmise kohandamine" name_ru="Корректировка измер.парам." name_lv="Mērījuma koriģēšana" name_tr="Measurement adjustment" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1186" categorytype="3" unit="V" decimals="2" scaling="100" readacceslevel="5" writeacceslevel="3" min="-5" max="5" />
      <point name="InputSelections_HA_sync_HASwitchSet" name_en="Home-Away-control" name_fi="Kotona-Poissa -ohjaus" name_sv="Hemma-Borta-styrning" name_et="Kodus-Eemal-juhtimine" name_ru="Управл. Дома-Не дома" name_lv="Mājās - Ārpus mājām - vadība" name_tr="Home-Away-control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="649" categorytype="3" enum="0=Kotona;1=Poissa" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_GenCompScaling_UI14_VoltMin" name_en="Message MIN" name_fi="Viesti Min" name_sv="Signal MIN" name_et="Signaali MIN" name_ru="Сигнал Мин" name_lv="Ziņas Min." name_tr="LP sensor  min input" pointtype="3" registertype="Holding" addressformat="S32" addressindex="664" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_GenCompScaling_UI14_OutMin" name_en="HP sensor  min output" name_fi="Lähtö Min" name_sv="HP sensor  min utgång" name_et="HP andur min väljund" pointtype="3" registertype="Holding" addressformat="S32" addressindex="666" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_GenCompScaling_UI14_VoltMax" name_en="Message MAX" name_fi="Viesti Max" name_sv="Signal MAX" name_et="Signaali MAX" name_ru="Сигнал Макс" name_lv="Ziņas Maks." name_tr="Temperature maksimum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="668" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_GenCompScaling_UI14_OutMax" name_en="HP sensor  max output" name_fi="Lähtö Max" name_sv="HP sensor  max utgång" name_et="HP andur maks väljund" pointtype="3" registertype="Holding" addressformat="S32" addressindex="670" categorytype="3" unit="%" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_L2RoomScaling_UI7_VoltMin" name_en="Message MIN" name_fi="Viesti Min" name_sv="Signal MIN" name_et="Signaali MIN" name_ru="Сигнал Мин" name_lv="Ziņas Min." name_tr="LP sensor  min input" pointtype="3" registertype="Holding" addressformat="S32" addressindex="507" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_L2RoomScaling_UI7_TempMin" name_en="Temperature minmum" name_fi="Lämpötila Min" name_sv="Temperatur min" name_et="Temperatuuri miinimum" name_ru="Tемпература Мин " name_lv="Min. temperatūra" name_tr="Temperature minmum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="579" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="InputSelections_L2RoomScaling_UI7_VoltMax" name_en="Message MAX" name_fi="Viesti Max" name_sv="Signal MAX" name_et="Signaali MAX" name_ru="Сигнал Макс" name_lv="Ziņas Maks." name_tr="Temperature maksimum" pointtype="3" registertype="Holding" addressformat="S32" addressindex="638" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="InputSelections_L2RoomScaling_UI7_TempMax" name_en="Temperature max" name_fi="Lämpötila Max" name_sv="Temperatur max" name_et="Temperatuuri maksimum" name_ru="Температура Макс." name_lv="Maks. temperatūra" name_tr="Temperature max" pointtype="3" registertype="Holding" addressformat="S32" addressindex="642" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="-50" max="100" />
      <point name="InputSelections_PressScaling_UI12_Press1Max" name_en="Measuring area" name_fi="Mittausalue" name_sv="Mätområde" name_et="Mõõtmisala" name_ru="Измерит.диапазон" name_lv="Mērījuma diapazons" name_tr="Measuring area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="737" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="25" />
      <point name="InputSelections_PressScaling_UI12_PresMeas12Offset" name_en="Measurement adjustment" name_fi="Mittauksen korjaus" name_sv="Mätningens justering" name_et="Mõõtmise kohandamine" name_ru="Корректировка измер.парам." name_lv="Mērījuma koriģēšana" name_tr="Measurement adjustment" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1188" categorytype="3" unit=" V" decimals="2" scaling="100" readacceslevel="5" writeacceslevel="3" min="-5" max="5" />
      <point name="InputSelections_AnAlarm_UI10_AlarmDeayAnAlarmUI10" name_en="Entry delay" name_fi="Aktivoitumisviive" name_sv="Entry delay" name_lv="Trauksm. iesl. aizkave" name_ru="Entry delay" name_et="Entry delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1230" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="InputSelections_AnAlarm_UI10_LowLimitUI10Analog" name_en="UI 10  Alarm min limit" name_fi="UI 10 Hälytyksen alaraja" name_sv="UI 10  Larm min gräns" name_et="UI 10  Alarm alampiir" name_ru="UI 10  Alarm min limit" name_lv="UI 10 Trauksmes min. robeža" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1237" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="InputSelections_AnAlarm_UI10_HighLimitUI10Analog" name_en="UI 10  Alarm max limit" name_fi="UI 10  Hälytyksen yläraja" name_sv="UI 10  Larm max gräns" name_et="UI 10  Alarm ülempiir" name_ru="UI 10  Alarm max limit" name_lv="UI 10  Trauksmes maks. robeža" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1239" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="InputSelections_AnAlarm_UI10_UI10AnAlarmPriority" name_en="UI10 Alarm priority" name_fi="UI10 Hälytyksen prioriteetti" name_sv="UI10 Alarm priority" name_lv="UI10  Alarm priority" name_tr=" UI10 Alarm priority" name_et="UI10 Alarm priority" name_ru="UI10 Приоритет авар.сигн." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1519" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_DigAlarm_UI11_AlarmDelayDigAlaUI11" name_en="Entry delay" name_fi="Aktivoitumisviive" name_sv="Entry delay" name_lv="Trauksm. iesl. Aizkave" name_ru="Entry delay" name_et="Entry delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1268" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="InputSelections_DigAlarm_UI11_UI11DigAlarmPriority" name_en="UI11 Alarm priority" name_fi="UI11 Hälytyksen prioriteetti" name_sv="UI11 Alarm priority" name_lv="UI11  Alarm priority" name_tr=" UI11 Alarm priority" name_et="UI11 Alarm priority" name_ru="UI11 Приоритет авар.сигн." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1521" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_AnAlarm_UI11_AlarmDeayAnAlarmUI11" name_en="Entry delay" name_fi="Aktivoitumisviive" name_sv="Entry delay" name_lv="Trauksm. iesl. aizkave" name_ru="Entry delay" name_et="Entry delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1262" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="InputSelections_AnAlarm_UI11_LowLimitUI11Analog" name_en="UI 11 Alarm min limit" name_fi="U I11 Hälytyksen alaraja" name_sv="UI 11 Larm min gräns" name_et="UI 11 Alarm alampiir" name_ru="UI 11 Alarm min limit" name_lv="UI 11 Trauksmes min. robeža" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1264" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="InputSelections_AnAlarm_UI11_HighLimitUI11Analog" name_en="Free meas. UI 11 max limit" name_fi="Vapaa mittaus UI11 yläraja" name_sv="Free mätn. UI 11 max gräns" name_et="Vaba mõõt. UI11 ülempiir" name_ru="Free meas. UI 11 max limit" name_lv="Brīvais mērījums  UI 11 maks. robeža" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1266" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="-51" max="131" />
      <point name="InputSelections_AnAlarm_UI11_UI11AnAlarmPriority" name_en="UI11 Alarm priority" name_fi="UI11 Hälytyksen prioriteetti" name_sv="UI11 Alarm priority" name_lv="UI11  Alarm priority" name_tr=" UI11 Alarm priority" name_et="UI11 Alarm priority" name_ru="UI11 Приоритет авар.сигн." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1523" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_DigAlarm_UI10_AlarmDelayDigAlaUI10" name_en="UI10 Alarm entry delay" name_fi="UI10 Hälytyksen tuloviive" name_sv="UI10 Entry delay" name_lv="UI10 Trauksm. iesl. Aizkave" name_ru="UI10 Entry delay" name_et="UI10 Entry delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1228" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="300" />
      <point name="InputSelections_DigAlarm_UI10_UI10DigAlarmPriority" name_en="UI10 Alarm priority" name_fi="UI10 Hälytyksen prioriteetti" name_sv="UI10 Alarm priority" name_lv="UI10  Alarm priority" name_tr=" UI10 Alarm priority" name_et="UI10 Alarm priority" name_ru="UI10 Приоритет авар.сигн." pointtype="3" registertype="Holding" addressformat="S32" addressindex="1525" categorytype="3" enum="1=1 (Hätä);2=2 (Vaara);3=3 (Vika);4=4 (Huolto);5=5 (Info)" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="5" />
      <point name="InputSelections_RoomSel_UI7_H2RoomTempBusSelect" name_en="H2 Room temperature from bus" name_fi="L2 Huonelämpötila väylältä" name_sv="V2 Rumstemp. från buss" name_et="K2 Toatemperatuur siinist" name_ru="О2 Комн.темп. по магист.шине" name_lv="A2 Telpas temp. no BUS" name_tr="H2 room temp from bus" pointtype="3" registertype="Holding" addressformat="U16" addressindex="880" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_RoomSel_UI4_H1RoomTempBusSelect" name_en="H1 Room temp.  from bus" name_fi="L1 Huonelämpötila väylältä" name_sv="V1 Rumstemp. från buss" name_et="K1 Toatemperatuur siinist" name_ru="О1 Комн.темп. по магист.шине" name_lv="A1 Telpas temp. no BUS" name_tr="H1 Room temp from bus" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1107" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="InputSelections_AnAlarm_UI12_LowLimit" name_en="Pressure 1 min limit" name_fi="Painemittauksen 1 alaraja" name_sv="Tryck 1 min gräns" name_et="Rõhu 1 alampiir" name_ru="Сигнал по верх.пределу давления 1" name_lv="Spiediena 1 trauksm. min. robeža" name_tr="Pressure 1 min limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1431" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="InputSelections_AnAlarm_UI12_HiLimit" name_en="Pressure 1 max. limit" name_fi="Painemittauksen 1 yläraja" name_sv="Tryck 1 max gräns" name_et="Rõhu 1 ülempiir" name_ru="Сигнал по ниж. пределу давления 1" name_lv="Spiediena 1 trauksm. maks. robeža" name_tr="Pressure 1 max. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1433" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="InputSelections_AnAlarm_UI13_LowLimit" name_en="Pressure 2 min. limit" name_fi="Painemittauksen 2 alaraja" name_sv="Tryck 2 min gräns" name_et="Rõhu 2 alampiir" name_ru="Сигнал по ниж. пределу давления 2" name_lv="Spiediena 2 trauksm. min. robeža" name_tr="Pressure 2 min. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1425" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="InputSelections_AnAlarm_UI13_HiLimit" name_en="Pressure 2 max. limit" name_fi="Painemittauksen 2 yläraja" name_sv="Tryck 2 max gräns" name_et="Rõhu 2 ülempiir" name_ru="Сигнал по верх.пределу давления 2" name_lv="Spiediena 2 trauksm. maks. robeža" name_tr="Pressure 2 max. limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1427" categorytype="3" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="20" />
      <point name="DHW_Control_PArea" name_en="DHW P-area" name_fi="LV P-alue" name_sv="TV P-band" name_et="TV P-ala" name_ru="ГВС Зона Р" name_lv="K.ŪD. P-apgabals" name_tr="HW P-area" pointtype="3" registertype="Holding" addressformat="S32" addressindex="325" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="2" max="500" />
      <point name="DHW_Control_ITime" name_en="DHW I-time" name_fi="LV I-aika" name_sv="TV I-tid" name_et="TV I-aeg" name_ru="ГВС Время I" name_lv="K.ŪD. I-laiks" name_tr="HW I-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="327" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="300" />
      <point name="DHW_Control_DTime" name_en="DHW D-time" name_fi="LV D-aika" name_sv="TV D-tid" name_et="TV D-aeg" name_ru="ГВС Время D" name_lv="K.ŪD. D-laiks" name_tr="HW D-time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="329" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHW_Control_DHW_Setpoint" name_en="Domestic hot water setting value" name_fi="Käyttöveden asetusarvo" name_sv="Tappvarmvattnets inst. värde" name_et="Kodune kuuma vee seadeväärtus" name_ru="Уставочное значение ГВС" name_lv="Karstā ūdens temperatūras iestatījums" name_tr="Domestic hot water setting value" pointtype="3" registertype="Holding" addressformat="S32" addressindex="331" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="20" max="90" />
      <point name="DHW_Control_BoostPower" name_en="DHW Quick run" name_fi="LV Pika-ajo" name_sv="TV Snabbkörn" name_et="TV Kiirkäivitus" name_ru="ГВС Быстрый прогон" name_lv="K.ŪD. Ātrā darbība" name_tr="HW Quick run" pointtype="3" registertype="Holding" addressformat="S32" addressindex="333" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHW_Control_AnticipP" name_en="DHW Anticipating" name_fi="LV Ennakointi" name_sv="TV Anticipering" name_et="TV Ennustamine" name_ru="ГВС Упреждение" name_lv="K.ŪD. Prognoze" name_tr="HW Anticipating" pointtype="3" registertype="Holding" addressformat="S32" addressindex="335" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="1" max="250" />
      <point name="DHW_Control_SerialValveCtrl" name_en="Select" name_fi="Sarjasäätö" name_sv="Select" name_et="Select" name_lv=" Izpildmehānisma 2 pozīcija" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1253" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="DHW_Control_OperatingMode" name_en="Control mode" name_fi="Ohjaustapa" name_sv="Styrsätt" name_et="Juhtimisrežiim" name_ru="Способ управления" name_lv="Vadības režīms" name_tr="Control mode" pointtype="3" registertype="Holding" addressformat="S32" addressindex="259" categorytype="3" enum="0=Automaatti;4=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="-8388608" max="8388608" />
      <point name="DHW_Control_LVManualPosition" name_en="DHW Manual position" name_fi="LV Käsiajoasento" name_sv="TV Manuell position" name_et="TV käsitsi positsioon" name_ru="ГВС Положение ИМ в ручн.реж.управл." name_lv="K.ŪD. Rokas režīma pozīcija" name_tr="HW Manual position" pointtype="3" registertype="Holding" addressformat="S32" addressindex="883" categorytype="3" unit="%" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="100" />
      <point name="DHW_Control_DHWAlarmDelay" name_en="DHW over heat./low limit alarm delay" name_fi="LV ylilämpö/alaraja häl. viive" name_sv="TV överhettning /nedre gräns larm fördr." name_et="TV ülem/alam piir alarmi viivitus" name_ru="ГВС Задерж.сигн. по перегр.воде" name_lv="Zemākā/Pārkaršana trauksm. aizkave" name_tr="HW Over heating / low limit alarm delay" pointtype="3" registertype="Holding" addressformat="S32" addressindex="893" categorytype="3" unit="min" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="DHW_Control_DHWMaxAlarm" name_en="DHW over heating alarm limit" name_fi="LV ylilämpö hälytysraja" name_sv="TV Överhettninglarm gräns" name_et="TV ülekuumenemisalarmi piir" name_ru="ГВС Предел сигнала по перегр.воде" name_lv="K.ŪD. Pārkaršanas trauksmes robeža" name_tr="HW Over heating alarm limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="901" categorytype="3" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="3" min="65" max="120" />
      <point name="DHW_Control_AticipInUse" name_en="Anticipation control" name_fi="Ennakointisäätö" name_sv="Anticipering styrning" name_et="Ennustamise juhtimine" name_ru="Регулирование в реж. упреж­дения" name_lv="Prognozes vadība" name_tr="Anticipation control" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1162" categorytype="3" enum="0=Käytössä;1=Ei käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="DHW_Control_DHWSetValue_raise_dropSel" name_en="DHW increase/drop time prog." name_fi="LV pudotus-/korotusaikaohjelma" name_sv="TV Tidsprogram öka/sänka" name_et="TV tõstma/tilk ajaprogr." name_ru="ГВС Недел.прогр.пониж./повыш." name_lv="K.ŪD. paaugst./paz Laika programma" name_tr="DHW increase/drop time prog." pointtype="3" registertype="Holding" addressformat="U16" addressindex="1366" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="DHW_Control_DHWDropSetValue" name_en="Domestic hot water drop" name_fi="LV asetusarvon pudotuksen määrä" name_sv="Tappvarmvatten sänkning" name_et="Kodune kuuma vee langus" name_ru="ГВС Величина пониж.устав.знач. " name_lv="K.ŪD. temp. pazeminājums" name_tr="Domestic hot water drop" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1367" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="DHW_Control_DHWRaiseSetValue" name_en="Domestic hot water  increase" name_fi="LV asetusarvon korotuksen määrä" name_sv="Tappvarmvatten höjning" name_et="Koduse kuuma vee tõus" name_ru="ГВС Величина повыш.устав.знач. " name_lv="K.ŪD. temp. paaugstinājums" name_tr="Domestic hot water  increase" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1369" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="0" max="30" />
      <point name="DHW_Control_DHWLowLimitAlarmSetValue" name_en="DHW low limit alarm limit" name_fi="LV alaraja hälytysraja" name_sv="TV nedre larm gräns" name_et="TV alumine alarmi piir" name_ru="ГВС Предельные значения аварии" name_lv="K.ŪD. trauksmes zemākā robeža" name_tr="HW low limit alarm limit" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1439" categorytype="3" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="3" min="20" max="70" />
      <point name="H1ActuatorSel_ValveSummerFlushInUse" name_en="Valve summer flushing" name_fi="Venttiilin kesähuuhtelu" name_sv="Ventilens sommar sköljning" name_et="Ventiili suvine loputamine" name_ru="Промывка клапана в лет.реж." name_lv="Vārsta izskalošana vasarā" name_tr="Valve summer flushing" pointtype="3" registertype="Holding" addressformat="U16" addressindex="913" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="H1ActuatorSel_MotorDriver2_H1_valve2_RunTimeOpen" name_en="H1 Actuator 2 open running time" name_fi="L1 Toimil. 2 ajoaika auki" name_sv="V1 Ställdonets 2 driftstid öppna" name_et="K1 Aktuaatori 2 tööaeg avatud" name_ru="O1 Время откр. ИМ 2 " name_lv="A1 Izpildmeh 2. darbības laiks atveroties" name_tr="H1 Actuator 2 open running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="905" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      <point name="H1ActuatorSel_MotorDriver2_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="911" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="H1ActuatorSel_MotorDriver2_H1_valve2_RunTimeClose" name_en="H1 Actuator 2 close running time" name_fi="L1 Moottorin 2 ajoaika kiinni" name_sv="V1 Ställdonets 2 driftstid stängd" name_et="K1 Aktuaatori 2 tööaeg suletud" name_lv="A1 Izpildmehānisma 2 aizvēršanās laiks" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1489" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="500" />
      <point name="H1ActuatorSel_MotorDriver1_H1_valve1_t_Open" name_en="H1 Actuator open running time" name_fi="L1 Toimil. ajoaika auki" name_sv="V1 Ställdonets driftstid öppna" name_et="K1 Aktuaatori tööaeg avatud" name_ru="O1 Время откр. ИМ " name_lv="A1 Izpildmehānisma atvēršanās laiks" name_tr="H1 Actuator open running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="927" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H1ActuatorSel_MotorDriver1_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="955" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V;0=3-piste" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="H1ActuatorSel_MotorDriver1_H1_valve1_t_Close" name_en="H1 Actuator close running time" name_fi="L1 Toimil. ajoaika kiinni" name_sv="V1 Ställdonets driftstid stängd" name_et="K1 Aktuaatori tööaeg suletud" name_ru="O1 Время закр. ИМ" name_lv="A1 Izpildmehānisma aizvēršanās laiks" name_tr="H1 Actuator close running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1293" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="H2ActuatorSel_ValveSummerFlushInUse" name_en="Valve summer flushing" name_fi="Venttiilin kesähuuhtelu" name_sv="Ventilens sommar sköljning" name_et="Ventiili suvine loputamine" name_ru="Промывка клапана в лет.реж." name_lv="Vārsta izskalošana vasarā" name_tr="Valve summer flushing" pointtype="3" registertype="Holding" addressformat="U16" addressindex="887" categorytype="3" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="H2ActuatorSel_MotorDriver2_H2_valve2_RunTimeClose" name_en="H2 Actuator 2 close running time" name_fi="L2 Toimil. 2 ajoaika kiinni" name_sv="V2 Ställdonets 2 driftstid stängd" name_et="K2 Aktuaatori 2 tööaeg suletud" name_ru="O2 Время закр. ИМ 2" name_lv="A2  Izpildmehānisma 2 aizvēršanās laiks" name_tr="H2 Actuator 2 close running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="889" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      <point name="H2ActuatorSel_MotorDriver2_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="895" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="H2ActuatorSel_MotorDriver2_H2_valve2_RunTimeOpen" name_en="H2 Actuator 2 open running time" name_fi="L2 Moottorin 2 ajoaika auki" name_sv="V2 Ställdonets 2 driftstid öppna" name_et="K2 Aktuaatori 2 tööaeg avatud" name_lv="A2 Izpildmeh. 2 darbības laiks atveroties" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1487" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="500" />
      <point name="H2ActuatorSel_MotorDriver1_H2_valve1_t_Open" name_en="H2 Actuator open running time" name_fi="L2 Toimil. ajoaika auki" name_sv="V2 Ställdonets driftstid öppna" name_et="K2 Aktuaatori tööaeg avatud" name_ru="O2 Время откр. ИМ " name_lv="A2 Izpildmehānisma atvēršanās laiks" name_tr="" pointtype="3" registertype="Holding" addressformat="S32" addressindex="897" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="10" max="500" />
      <point name="H2ActuatorSel_MotorDriver1_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="903" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V;0=3-piste" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="H2ActuatorSel_MotorDriver1_H2_valve1_t_Close" name_en="H2 Actuator close running time" name_fi="L2 Toimil. ajoaika kiinni" name_sv="V2 Ställdonets driftstid stängd" name_et="K2 Aktuaatori tööaeg suletud" name_tr="" name_ru="O2 Время закр. ИМ" name_lv="A2 Izpildmehānisma aizvēršanās laiks" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1277" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="HWActuatorSel_MotorDriver2_HWValve2t_Open" name_en="DHW Actuator 2 open running time" name_fi="LV Toimil. 2 ajoaika auki" name_sv="TV Ställdonets 2 driftstid öppna" name_et="TV Aktuaatori 2 tööaeg avatud" name_ru="ГВС Время откр. ИМ 2" name_lv="K.ŪD. Izpildmeh. 2 darbības laiks atveroties" name_tr="HW Actuator 2 open running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="866" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="HWActuatorSel_MotorDriver2_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="872" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="HWActuatorSel_MotorDriver2_HWValve2t_Close" name_en="HW Actuator 2 close running time" name_fi="LV Moottorin 2 ajoaika kiinni" name_sv="TV Ställdonets 2 driftstid slut" name_et="TV Aktuaatori 2 tööaeg suletud" name_lv="K.ŪD. Izpildmehānisma 2 aizvēršanās laiks" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1483" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="HWActuatorSel_MotorDriver1_HWValve1t_Open" name_en="DHW Actuator open running time" name_fi="LV Toimil. ajoaika auki" name_sv="TV Ställdonets driftstid öppna" name_et="TV Aktuaatori tööaeg avatud" name_ru="ГВС Время откр. ИМ " name_lv="K.ŪD. Izpildmehānisma atvēršanās laiks" name_tr="HW Actuator open running time" pointtype="3" registertype="Holding" addressformat="S32" addressindex="874" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="HWActuatorSel_MotorDriver1_ActuatorConf" name_en="Actuator selection" name_fi="Toimilaitteen valinta" name_sv="Val av ställdon" name_et="Aktuaatori valimine" name_ru="Выбор исп.механизма" name_lv="Izpildmehānisma izvēle" name_tr="Actuator selection" pointtype="3" registertype="Holding" addressformat="S32" addressindex="885" categorytype="3" enum="1=0-10V;2=2-10V;3=10-0V;4=10-2V" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="4" />
      <point name="HWActuatorSel_MotorDriver1_HWValve1t_Close" name_en="DHW Actuator close running time" name_fi="LV Toimil. ajoaika kiinni" name_sv="TV Ställdonets driftstid slut" name_et="TV Aktuaatori tööaeg suletud" name_lv="K.ŪD.  Izpildmehānisma aizvēršanās laiks" name_tr="HW Actuator close running time" name_ru="ГВС Время закр. ИМ" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1485" categorytype="3" unit="s" scaling="1" readacceslevel="5" writeacceslevel="3" min="5" max="500" />
      <point name="RelayControl_Select_P2" name_en="Select" name_fi="P2 Ohjaustapa (L1)" name_sv="Select" name_et="Select" name_ru="Select" pointtype="3" registertype="Holding" addressformat="S32" addressindex="964" categorytype="3" enum="0=Ei käytössä;1=Automaatti;2=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="RelayControl_Select_P3" name_en="Select" name_fi="P3 Ohjaustapa (L2)" name_sv="Select" name_et="Select" name_ru="Select" pointtype="3" registertype="Holding" addressformat="S32" addressindex="966" categorytype="3" enum="0=Ei käytössä;1=Automaatti;2=Käsiajo" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="7" />
      <point name="RelayControl_Manual_P2" name_en="Input2" name_fi="P2 Käsajo" name_sv="Input2" name_et="Input2" name_ru="Input2" pointtype="3" registertype="Holding" addressformat="U16" addressindex="339" categorytype="3" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="RelayControl_Manual_P3" name_en="Input2" name_fi="P3 Käsiajo" name_sv="Input2" name_et="Input2" name_ru="Input2" pointtype="3" registertype="Holding" addressformat="U16" addressindex="406" categorytype="3" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="3" type="1" />
      <point name="SumAlarms_SumAlrInd_TRS2" name_en="Select" name_fi="Hälytyksen indikointi" name_sv="Select" name_et="Select" name_lv="Kopējā trauksme" pointtype="3" registertype="Holding" addressformat="S32" addressindex="1141" categorytype="3" enum="0=Ei käytössä;1=1-luokka;2=2-luokka;5=1- tai 2- luokka" scaling="1" readacceslevel="5" writeacceslevel="3" min="0" max="5" />
    </group>
    <group categorytype="2" name="Mittaukset" name_en="Measurements" name_fi="Mittaukset" name_sv="Mätningar" name_et="Mõõtmised" name_ru="Измерения" name_lv="Mērījumi" name_tr="Ölçümler ">
      <point name="AutumnDry_AverageOutTemp" name_en="Previous day's average outdoor temp" name_fi="Ulkolämpötilan edell. vrk:n keskiarvo" name_sv="Föregående dags utetemp. i genomsnitt" name_et="Eelmise päeva keskmine välistemp." name_ru="Сред.знач.Т.наруж.возд.предыд.суток" name_lv="Iepriekš. dienas vid. ārgaisa temp." name_tr="Previous day's average outdoortemp" pointtype="10" registertype="Holding" addressformat="S32" addressindex="270" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_ParallShiftEff" name_en="Effect of parallel shift" name_fi="Suuntaissiirron vaikutus" name_sv="Påverkan av parallellförskjutning" name_et="Paralleelnihke mõju" name_ru="Воздействие параллельного смещения" name_lv="Paralēlās nobīdes ietekme" name_tr="Effect of parallel shift" pointtype="10" registertype="Holding" addressformat="S32" addressindex="415" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_CalculatedSet" name_en="Calculated supply water setting" name_fi="Laskennall. menoveden asetusarvo" name_sv="Beräknad framledningstemp." name_et="Arvutuslik küttevee seadistus" name_ru="Расчёт.устав.знач.темп. на подаче" name_lv="Aprēķinātā turpgaitas temp." name_tr="Calculated supply water setting" pointtype="10" registertype="Holding" addressformat="S32" addressindex="419" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="HeatingControl1_RetWaterEff" name_en="Return water compensation" name_fi="Paluuveden kompensoinnin vaikutus" name_sv="Påverkan av returvattnets kompens." name_et="Tagastusvee kompenseerimine" name_ru="Воздействие компенсации по обр.воде" name_lv="Atgaitas temp. kompensācijas ietekme" name_tr="Return water compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="421" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_MinLimitEff" name_en="Min limit effect" name_fi="Minimirajan vaikutus" name_sv="Påverkan av min.gränsen" name_et="Alampiiri mõju" name_ru="Воздействие мин. ограничения" name_lv="Min. robežas ietekme" name_tr="Min limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="431" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_MaxLimitEff" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Påverkan av max.gränsen" name_et="Ülempiiri mõju" name_ru="Воздействие макс. ограничения" name_lv="Maks. robežas ietekme" name_tr="Max limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="433" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_SupplyLineTempFinal" name_en="Output" name_fi="Menoveden lämpötila säätimelle" name_sv="Output" name_et="Output" pointtype="10" registertype="Holding" addressformat="S32" addressindex="443" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_GenCompEff" name_en="General compensation effect" name_fi="Yleiskompensoinnin vaikutus" name_sv="Påverkan av allmän kompenseringen" name_et="Üldine kompenseerimise mõju" name_ru="Коррект.по врем.в реж.комп.комн.темп." name_lv="Vispārīgās kompensācijas ietekme" name_tr="General compensation effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="457" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_BusCompEff" name_en="Bus compensation effect" name_fi="Väyläkompensoinnin vaikutus" name_sv="Påverkan av  busskompenseringen" name_et="Siini kompenseerimise mõju" name_ru="Воздействие общей компенсации" name_lv="Tīkla kompensācijas ietekme" name_tr="Bus compensation effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="459" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_AutumnDryEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkningen" name_et="Sügiskuivatamise mõju" name_ru="Воздейств.функц.осуш. в осен.период" name_lv="Rudens žāvēšanas ietekme" name_tr="Effect of autumn drying" pointtype="10" registertype="Holding" addressformat="S32" addressindex="461" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_OutTempDelayEff" name_en="Outd.temp delay effect" name_fi="Ulkolämpötilahidastuksen vaikutus" name_sv="Påverkan av utetemp.fördröj." name_et="Välistemperatuuri viivituse mõju" name_ru="Воздейств.отлож.измер.темп.наруж.возд." name_lv="Ārgaisa temp. aizkaves ietekme" name_tr="Outd.temp delay effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="463" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_OutTempDelayed" name_en="Delayed outdoor temperature" name_fi="Hidastettu ulkolämpötilamittaus" name_sv="Fördröjd utetemperatur" name_et="Viivitusega välistemperatuur" name_ru="Отложенное измер.темп.нар.возд." name_lv="Aizkavētais ārgaisa temp. mērījums" name_tr="Delayed outdoor temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="470" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomCompEff" name_en="Effect of room compensation" name_fi="Huonekompensoinnin vaikutus" name_sv="Påverkan av rumskompenseringen" name_et="Toa kompenseerimise mõju" name_ru="Воздействие компенсации комн.темп." name_lv="Telpas kompensācijas ietekme" name_tr="Effect of room compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="474" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomCompIDrive" name_en="Room comp. Time adjustment" name_fi="Huonekompensoinnin aikakorjaus" name_sv="Påverkan av rumskomp. tidsjusteringen" name_et="Toa kompenseerimisaja reguleerimine" name_ru="Воздействие компенсации комн.темп." name_lv="Telpas kompensācijas laika koriģēšana" name_tr="Room comp.time adjustment" pointtype="10" registertype="Holding" addressformat="S32" addressindex="482" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomDropHigh" name_en="Time program effect on room temp." name_fi="Aikaohjelman vaikutus huonel." name_sv="Tidsprogram påverkan på rumstemp." name_et="Ajaprogrammi mõju toatemperatuurile" name_ru="Воздейст.времен.прогр. на комн.темп." name_lv="Laika prog. ietekme uz telpas temp." name_tr="Time program effect on  room temp." pointtype="10" registertype="Holding" addressformat="S32" addressindex="488" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomDropLow" name_en="RoomDropLow" name_fi="Aikaohjelman vaikutus huonelämpötilaan (pienipudotus)" name_lv="Temp. pazem. (telpas temp.)" pointtype="10" registertype="Holding" addressformat="S32" addressindex="490" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_AutumnDryRoomEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkning " name_et="Sügiskuivatamise mõju" name_ru="Воздейств.функц.осуш. в осен.период" name_lv="Rudens žāvēšanas ietekme" name_tr="Effect of autumn drying" pointtype="10" registertype="Holding" addressformat="S32" addressindex="558" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_AutumnDryEffToRoomSetp" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkningen" name_et="Sügiskuivatamise mõju" name_ru="Воздейств.функц.осуш. в осен.период" name_lv="Rudens žāvēšanas ietekme" name_tr="Effect of autumn drying" pointtype="10" registertype="Holding" addressformat="S32" addressindex="560" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_FollowCurve" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurvan" name_et="Küttevesi vastavalt küttekõverale" name_ru="В соответствии с кривой" name_lv="Pēc līknes" name_tr="According to curve" pointtype="10" registertype="Holding" addressformat="S32" addressindex="435" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomSetpReslut" name_en="Calculated room setting value" name_fi="Laskennall. huoneasetusarvo" name_sv="Beräknad rumstemperatur" name_et="Arvutuslik toatemp. seadistus" name_ru="Расчёт.устав.знач.темп. на подаче" name_lv="Aprēķinātā telpas temp." name_tr="Calculated room setting value" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1129" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_HASwitchEffect" name_en="Away -control effect" name_fi="Poissa -ohjauksen vaikutus" name_sv="Borta -styrning effekt" name_et="" name_lv="Mājās / Ārpus mājām – vadības ietekme" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1028" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomForceDrop" name_en="Force control effect" name_fi="Pakko-ohjauksen vaikutus" name_sv="Tvångsstyrningens effekt" name_et="Sundjuhtimise mõju" name_ru="Воздейств.принудит.управления" name_lv="Piespiedu vadības ietekme" name_tr="Force control effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1132" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_L1DHReturnCompEff" name_en="H1 DH return comp. effect " name_fi="L1 vaihdin KL paluukomp. vaik." name_sv="V1 FJV Retur ersätt effekt" name_et="K1 KK tagasivoolu kompens. mõju" name_ru="O1 DH Return comp effect " name_lv="A1 Prim. kont. atg. komp. Ietekme" name_tr="H1 DH Return comp effect " pointtype="10" registertype="Holding" addressformat="S32" addressindex="1295" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_L1RadiatorDelayEffect" name_en="Radiator heating Delay effect " name_fi="Patteril. hidastuksen vaikutus" name_sv="Radiator heating Delay effect " name_et="Radiator heating Delay effect " name_ru="Radiator heating Delay effect " name_lv="Ārgaisa temp. aizkaves ietekme (radiatoru apkure)" name_tr="Radiator heating Delay effect " pointtype="10" registertype="Holding" addressformat="S32" addressindex="548" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_L1FloorEffect" name_en="Floor heating anticipation effect" name_fi="Lattial. ennakoinnin vaikutus" name_sv="Floor heating anticipation effect" name_et="Floor heating anticipation effect" name_ru="Floor heating anticipation effect" name_lv="Grīdas apk. prognoze" name_tr="Floor heating anticipation effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="552" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl1_RoomComp_DelayedRoomTemp" name_en="H1 Delayed room temperature" name_fi="L1 Hidastettu huonelämpötilamittaus" name_sv="V1 Fördröjd rumstemperatur" name_et="Filtered output signal" name_ru="H1 Delayed room temperature" name_lv="A1 Aizkavēts telpas temp. mērījums" pointtype="10" registertype="Holding" addressformat="S32" addressindex="498" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_ParallShiftEff" name_en="Effect of parallel shift" name_fi="Suuntaissiirron vaikutus" name_sv="Påverkan av parallellförskjutning" name_et="Paralleelnihke mõju" name_ru="Воздействие параллельного смещения" name_lv="Paralēlās nobīdes ietekme" name_tr="Effect of parallel shift" pointtype="10" registertype="Holding" addressformat="S32" addressindex="266" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_CalculatedSet" name_en="Calculated supply water setting" name_fi="Laskennall. menoveden asetusarvo" name_sv="Beräknad framledningstemp." name_et="Arvutuslik küttevee seadistus" name_ru="Расчёт.устав.знач.темп. на подаче" name_lv="Aprēķinātā turpgaitas temp." name_tr="Calculated supply water setting" pointtype="10" registertype="Holding" addressformat="S32" addressindex="272" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="HeatingControl2_RetWaterEff" name_en="Return water compensation" name_fi="Paluuveden kompensoinnin vaikutus" name_sv="Påverkan av returvattnets kompens." name_et="Tagastusvee kompenseerimine" name_ru="Воздействие компенсации по обр.воде" name_lv="Atgaitas temp. kompensācijas ietekme" name_tr="Return water compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="274" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_MinLimitEff" name_en="Min limit effect" name_fi="Minimirajan vaikutus" name_sv="Påverkan av min.gränsen" name_et="Alampiiri mõju" name_ru="Воздействие мин. ограничения" name_lv="Min. robežas ietekme" name_tr="Min limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="282" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_MaxLimitEff" name_en="Max limit effect" name_fi="Maksimirajan vaikutus" name_sv="Påverkan av max.gränsen" name_et="Ülempiiri mõju" name_ru="Воздействие макс. ограничения" name_lv="Maks. robežas ietekme" name_tr="Max limit effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="320" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_SupplyLineTempFinal" name_en="Output" name_fi="Menoveden lämpötila säätimelle" name_sv="Output" name_et="Output" name_lv="Aprēķinātā turpgaitas temp." pointtype="10" registertype="Holding" addressformat="S32" addressindex="340" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_GenCompEff" name_en="General compensation effect" name_fi="Yleiskompensoinnin vaikutus" name_sv="Påverkan av allmän kompenseringen" name_et="Üldine kompenseerimise mõju" name_ru="Коррект.по врем.в реж.комп.комн.темп." name_lv="Vispārīgās kompensācijas ietekme" name_tr="General compensation effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="342" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_BusCompEff" name_en="Bus compensation effect" name_fi="Väyläkompensoinnin vaikutus" name_sv="Påverkan av  busskompenseringen" name_et="Siini kompenseerimise mõju" name_ru="Воздействие общей компенсации" name_lv="Tīkla kompensācijas ietekme" name_tr="Bus compensation effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="344" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_AutumnDryEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkningen" name_et="Sügiskuivatamise mõju" name_ru="Воздейств.функц.осуш. в осен.период" name_lv="Rudens žāvēšanas ietekme" name_tr="Effect of autumn drying" pointtype="10" registertype="Holding" addressformat="S32" addressindex="346" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_OutTempDelayEff" name_en="Outd.temp delay effect" name_fi="Ulkolämpötilahidastuksen vaikutus" name_sv="Påverkan av utetemp.fördröj." name_et="Välistemperatuuri viivituse mõju" name_ru="Воздейств.отлож.измер.темп.наруж.возд." name_lv="Ārgaisa temp. aizkaves ietekme" name_tr="Outd.temp delay effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="348" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_OutTempDelayed" name_en="Delayed outdoor temperature" name_fi="Hidastettu ulkolämpötilamittaus" name_sv="Fördröjd utetemperatur" name_et="Viivitusega välistemperatuur" name_ru="Отложенное измер.темп.нар.возд." name_lv="Aizkavētais ārgaisa temp. mērījums" name_tr="Delayed outdoor temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="350" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomCompEff" name_en="Effect of room compensation" name_fi="Huonekompensoinnin vaikutus" name_sv="Påverkan av rumskompenseringen" name_et="Toa kompenseerimise mõju" name_ru="Воздействие компенсации комн.темп." name_lv="Telpas kompensācijas ietekme" name_tr="Effect of room compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="354" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomCompIDrive" name_en="Room comp. Time adjustment" name_fi="Huonekompensoinnin aikakorjaus" name_sv="Påverkan av rumskomp. tidsjusteringen" name_et="Toa kompenseerimisaja reguleerimine" name_ru="Воздействие компенсации комн.темп." name_lv="Telpas kompensācijas laika koriģēšana" name_tr="Room comp.time adjustment" pointtype="10" registertype="Holding" addressformat="S32" addressindex="356" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomDropHigh" name_en="RoomDropHigh" name_fi="Aikaohjelman vaikutus huonel." name_lv="Lielais telpas  temp. pazeminājums" pointtype="10" registertype="Holding" addressformat="S32" addressindex="359" categorytype="2" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomDropLow" name_en="RoomDropLow" name_fi="Aikaohjelman vaikutus huonel." name_lv="Telpas temp. pazem" pointtype="10" registertype="Holding" addressformat="S32" addressindex="361" categorytype="2" unit="°C" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_AutumnDryRoomEff" name_en="Effect of autumn drying" name_fi="Syyskuivauksen vaikutus" name_sv="Påverkan av hösttorkningen" name_et="Sügiskuivatamise mõju" name_ru="Воздейств.функц.осуш. в осен.период" name_lv="Rudens žāvēšanas ietekme" name_tr="Effect of autumn drying" pointtype="10" registertype="Holding" addressformat="S32" addressindex="363" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_AutumnDryEffToRoomSetp" name_en="Output" name_fi="Syyskuivauksen vaikutus huoneasetusarvoon" name_sv="Output" name_et="Output" name_lv="Rudens žāv. ietekme uz telpas temp." pointtype="10" registertype="Holding" addressformat="S32" addressindex="365" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_FollowCurve" name_en="According to curve" name_fi="Käyrän mukaan" name_sv="Enligt kurvan" name_et="Küttevesi vastavalt küttekõverale" name_ru="В соответствии с кривой" name_lv="Pēc līknes" name_tr="According to curve" pointtype="10" registertype="Holding" addressformat="S32" addressindex="387" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomSetpResult" name_en="Calculated room setpoint" name_fi="Laskennall. huoneasetusarvo" name_sv="Beräknad rumstemperatur" name_et="Arvutuslik toa nimiväärtus" name_ru="Расчёт.устав.знач.темп. на подаче" name_lv="Aprēķinātā telpas temp." name_tr="Calculated room setpoint" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1122" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_HASwitchEffect" name_en="HADrop" name_fi="Poissa -ohjauksen vaikutus" name_lv="Mājās / Ārpus mājām - Temp. pazem." pointtype="10" registertype="Holding" addressformat="S32" addressindex="794" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomForceDrop" name_en="Force control effect" name_fi="Pakko-ohjauksen vaikutus" name_sv="Tvångsstyrningens effekt" name_et="Sundjuhtimise mõju" name_ru="Воздейств.принудит.управления" name_lv="Piespiedu vadības ietekme" name_tr="Force control effect" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1196" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_L2DHReturnCompEff" name_en="H2 DH return comp. effect " name_fi="L2 vaihdin KL paluukomp. vaik." name_sv="V2 FJV Retur ersätt effekt" name_et="K2 KK tagasivoolu kompens. mõju" name_ru="O2  ЦТС Return comp effect " name_lv="A2 Prim. kont. atg. komp. Ietekme" name_tr="H2 DH Return comp. effect " pointtype="10" registertype="Holding" addressformat="S32" addressindex="1328" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HeatingControl2_RoomComp_DelayedRoomTemp" name_en="H2 Delayed room temperature" name_fi="L2 Hidastettu huonelämpötilamittaus" name_sv="V2 Fördröjd rumstemperatur" name_et="Filtered output signal" name_ru="H2 Delayed room temperature" name_lv="A2 Aizkavēts telpas temp. mērījums" pointtype="10" registertype="Holding" addressformat="S32" addressindex="399" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_HAStatus_UI14" name_en="Home/Away switch status" name_fi="Kotona/Poissa kytkimen tila" name_sv="Hemma/Borta omkopplare status" name_et="Kodus/eemal lüliti seisund" name_ru="Положение перекл. Дома/Не дома" name_lv="Mājās / Ārpus mājām – Slēdža stāvoklis" name_tr="Home/Away switch status" pointtype="10" registertype="Holding" addressformat="U16" addressindex="501" categorytype="2" enum="0=Kotona;1=Poissa" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_PressSwitchMeas_UI13" name_en="Pressure switch 2 mode" name_fi="Painekytkimen 2 tila" name_sv="Tryck mätning 2 läge" name_et="Rõhulüliti 2  režiim" name_ru="Состояние датчика давления 2" name_lv="Spiediena releja 2 režīms" name_tr="Pressure switch 2 mode" pointtype="10" registertype="Holding" addressformat="U16" addressindex="502" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_PressSwitchMeas_UI12" name_en="Pressure switch 1 mode" name_fi="Painekytkimen 1 tila" name_sv="Tryckmätning 1 läge" name_et="Rõhulüliti 1 režiim" name_ru="Состояние датчика давления 1" name_lv="Spiediena releja 1 režīms" name_tr="Pressure switch 1 mode" pointtype="10" registertype="Holding" addressformat="U16" addressindex="504" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenCompMeas_UI14" name_en="General compensation" name_fi="Yleiskompensointi" name_sv="Allmän kompensering" name_et="Üldine kompenseerimine" name_ru="Общая компенсация" name_lv="Vispārīgā kompensācija" name_tr="General compensation" pointtype="10" registertype="Holding" addressformat="S32" addressindex="505" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_L2RoomMeasBusIn" name_en="L2RoomBusIn" name_fi="L2 Huonelämpötila väylältä" pointtype="10" registertype="Holding" addressformat="S32" addressindex="515" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_L2DhRetMeas_UI7" name_en="H2 DH Return" name_fi="L2 vaihdin KL paluu" name_sv="V2 FJV Returvattentemp." name_et="K2 KK Tagastus" name_ru="O2 т/о  ЦТС обр.контур" name_lv="A2 Prim.kont. Atgaitas" name_tr="H2 DH Return" pointtype="10" registertype="Holding" addressformat="S32" addressindex="570" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_L1RoomTempBusIn" name_en="L1RoomBusIn" name_fi="L1 Huonelämpötila väylältä" pointtype="10" registertype="Holding" addressformat="S32" addressindex="581" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_L1DhRetMeas_UI4" name_en="H1 DH Return" name_fi="L1 vaihdin KL paluu" name_sv="V1 FJV Returvattentemp." name_et="K1 KK Tagastus" name_ru="O1 т/о ЦТС обр.контур" name_lv="A1 Prim.kont. Atgaitas" name_tr="H1 DH Return" pointtype="10" registertype="Holding" addressformat="S32" addressindex="583" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_L1RoomMeas_UI4" name_en="Room temperature" name_fi="Huonelämpötila" name_sv="Rumstemp." name_et="Toatemperatuur" name_ru="Комнатная температура" name_lv="Telpas temperatūra" name_tr="Room temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="585" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="100" />
      <point name="InputSelections_PressureMeas_UI12" name_en="Pressure measurement 1" name_fi="Painemittaus 1" name_sv="Tryckmätning 1" name_et="Rõhu mõõtmine 1" name_ru="Давление 1" name_lv="Spiediena mērījums 1" name_tr="Pressure measurement 1" pointtype="10" registertype="Holding" addressformat="S32" addressindex="587" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="16" />
      <point name="InputSelections_PressureMeas_UI13" name_en="Pressure measurement 2" name_fi="Painemittaus 2" name_sv="Tryck mätning 2" name_et="Rõhu mõõtmine 2" name_ru="Давление 2" name_lv="Spiediena mērījums 2" name_tr="Pressure measurement 2" pointtype="10" registertype="Holding" addressformat="S32" addressindex="589" categorytype="2" unit="bar" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="16" />
      <point name="InputSelections_L2RoomMeas_UI7" name_en="Room temperature" name_fi="Huonelämpötila" name_sv="Rumstemperatur" name_et="Toatemperatuur" name_ru="Комнатная температура" name_lv="Telpas temperatūra" name_tr="Room temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="377" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_WaterVol_DI2_18" name_en="DI2 Water volume" name_fi="DI2 Vesimäärämittaus" name_sv="DI2 Vattenvolym" name_et="DI2 Veevoolu mõõtmine" name_ru="DI 2 Расход воды" name_lv="DI2 Ūdens tilpums" name_tr="DI2 Water flow measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="429" categorytype="2" unit="m3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_P1AlarmState_DI1_17" name_en="Pump 1 alarm" name_fi="Pumppu 1 hälytys" name_sv="Pump 1 larm" name_et="P1_Alarm" name_ru="Pump1 Alarm" name_lv="CS1 Sūknis" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1382" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenAlarmState_DI1_17" name_en="General alarm status" name_fi="Yleishälytyksen tila" name_sv="Allmänt larm status" name_et="Üldalarmi seisund" name_ru="Статус общего сигнала" name_lv="Vispārīgā trauksme režīms" name_tr="General alarm status" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1383" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_P3AlarmState_UI16" name_en="Pump 3 alarm" name_fi="Pumppu 3 hälytys" name_sv="Pump 3 larm" name_et="P_Alarm" name_ru="Pump3 Alarm" name_lv="CS3 Sūknis" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1385" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_WaterVol_DI1_17" name_en="DI1 Water volume" name_fi="DI1 Vesimäärämittaus" name_sv="DI1 Vattenvolym" name_et="DI1 Veevoolu mõõtmine" name_ru="DI 1 Расход воды" name_lv="DI1 Ūdens tilpums" name_tr="DI1 Water flow measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="427" categorytype="2" unit="m3" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_GenTempMeas_UI12" name_en="Meas.UI 12" name_fi="Mitt. UI 12" name_sv="Mätn. UI 12" name_et="Mõõtmine UI 12" name_ru="Изм. UI12" name_lv="Mērīj. UI 12" name_tr="Meas.UI 12" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1392" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_GenTempMeas_UI13" name_en="Meas. UI13" name_fi="Mitt. UI13" name_sv="Mätn. UI13" name_et="Mõõtmine UI13" name_ru="Изм. UI13" name_lv="Mērīj. UI13" name_tr="Meas. UI13" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1399" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_PressSwitchAlrState_UI12" name_en="Pressure alarm UI12" name_fi="Painehälytys UI12" name_sv="Tryck larm UI12" name_et="AlrState" name_ru="AlrState" name_lv="Spiediena trauksme UI12" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1233" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_PressSwitchAlrState_UI13" name_en="Pressure alarm UI13" name_fi="Painehälytys UI13" name_sv="Tryck larm UI13" name_et="AlrState" name_ru="AlrState" name_lv="Spiediena trauksme  UI13" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1234" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_PressureMeasAlrState_UI12" name_en="Pressure alarm UI12" name_fi="Painehälytys UI12" name_sv="Tryck larm UI12" name_et="AlrState" name_ru="AlrState" name_lv="Spiediena trauksme UI12" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1235" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_PressureMeasAlrState_UI13" name_en="Pressure alarm UI13" name_fi="Painehälytys UI13" name_sv="Tryck larm UI13" name_et="AlrState" name_ru="AlrState" name_lv="Spiediena trauksme  UI13" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1236" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_DigInState_DI1" name_en="P1 Alarm status" name_fi="P1 hälytyksen tila" name_sv="P1 Larm status" name_et="P1 alarmi seisund" name_ru="P1 hälytyksen tila" name_lv="CS1 Trauksmes stāvoklis" name_tr="P1 Alarm status" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1249" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_DigInState_UI16" name_en="P3 Pump mode" name_fi="P3 Pumpun tila" name_sv="P3 Pump läge" name_et="P3 Pumba režiim" name_ru="P3 Статус насоса" name_lv="CS3 sūkņis" name_tr="P3 Pump mode" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1411" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_EnergyMeas_DI2" name_en="DI2 Energy measurement" name_fi="DI2 Energiamittaus" name_sv="DI2 Energimätning" name_et="DI2 Energia mõõtmine" name_ru="DI2 Расход энергии" name_lv="DI2 Enerģijas mērījums" name_tr="DI2 Energy measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="318" categorytype="2" unit="MWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_EnergMeas_DI1" name_en="DI1 Energy measurement" name_fi="DI1 Energiamittaus" name_sv="DI1 Energimätning" name_et="DI1 Energia mõõtmine" name_ru="DI1 Расход энергии" name_lv="DI1  Enerģijas mērījums" name_tr="DI1 Energy measurement" pointtype="10" registertype="Holding" addressformat="S32" addressindex="311" categorytype="2" unit="MWh" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_SwitchMeas_UI10" name_en="Switch alarm state" name_fi="Kosketinhälytyksen tila" name_sv="Switch alarm state" name_et="Lüliti alarm režiim" name_ru="Полож.контакта ав.сигн." name_lv="Slēdža trauksmes stāvoklis" name_tr="Switch alarm state" pointtype="10" registertype="Holding" addressformat="U16" addressindex="730" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_SwitchInUseUI10" name_en="BinaryInUse" name_fi="Kosketinhälytys käytössä" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1212" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenMeasNtc10InUse_UI10" name_en="Ntc10InUse" name_fi="Yleismittaus Ntc-10 käytössä" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1213" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenTempMeas_UI10" name_en="Meas. UI10" name_fi="Mitt. UI 10" name_sv="Mätn. UI 10" name_et="Mõõtmine UI10" name_ru="Изм. UI10" name_lv="Mērīj.UI10" name_tr="Meas. UI10" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1214" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_P2AlarmState_UI15" name_en="Pump 2 alarm" name_fi="Pumppu 2 hälytys" name_sv="Pump 2 larm" name_et="P_Alarm" name_ru="Pump2 Alarm" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1384" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_DigInState_UI15" name_en="P2 Pump mode" name_fi="P2 Pumpun tila" name_sv="P2 Pump läge" name_et="P2 Pumba režiim" name_ru="P2 Статус насоса" name_lv="CS2 sūkņis mode" name_tr="P2 Pump mode" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1250" categorytype="2" enum="0=Seis;1=Käy" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_SwitchMeas_UI11" name_en="Switch alarm state" name_fi="Kosketinhälytyksen tila" name_sv="Switch alarm state" name_et="Lüliti alarm režiim" name_ru="Полож.контакта ав.сигн." name_lv="Slēdža trauksmes stāvoklis" name_tr="Switch alarm state" pointtype="10" registertype="Holding" addressformat="U16" addressindex="879" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_SwitchInUseUI11" name_en="Swirch alarm in use" name_fi="Kosketinhälytys käytössä" name_lv="Slēdža trauksme Lietot" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1243" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenMeasNtc10InUse_UI11" name_en="Ntc11InUse" name_fi="Yleismittaus Ntc-11 käytössä" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1244" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_GenTempMeas_UI11" name_en="Meas. UI 11" name_fi="Mitt. UI 11" name_sv="Mätn. UI 11" name_et="Mõõtmine UI11" name_ru="Изм. UI 11" name_lv="Mērīj. UI 11" name_tr="Meas. UI 11" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1245" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_FreeMeasureInUse_UI4" name_en="Free meassurement UI4 in use" name_fi="Vapaa mittaus UI4 käytössä" name_sv="Fri mätning UI4 in use" name_et="Vaba mõõtmine UI4 in use" name_lv="Brivais merijums Lietot__UI4 in use" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1279" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_L1DhRetMeasInUse_UI4" name_en="H1 DH Return in use" name_fi="L1 KL Paluu käytössä" name_lv="A2 Prim.kont. Atgaitas Lietot" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1297" categorytype="2" enum="0=Ei käytössä;1=Käytössä" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_UI4FreeMeasure" name_en="Free meas. UI4" name_fi="Vapaa mittaus UI4" name_sv="Fri mätning UI4" name_et="Vaba mõõtmine UI4" name_ru="Произвол.измерение UI4" name_lv="Brīvais mērījums UI 4" name_tr="Free meassurement UI4" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1330" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_UI7FreeMeasure" name_en="Free meas. UI7" name_fi="Vapaa mittaus UI7" name_sv="Fri mätning UI7" name_et="Vaba mõõtmine UI7" name_ru="Произвол.измерение UI7" name_lv="Brīvais mērījums UI 7" name_tr="Free meassurement UI7" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1332" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_FreeMeasureInUse_UI7" name_en="Free meassurement in use UI7" name_fi="Vapaa mittaus UI7 käytössä" name_sv="Free meassurement in use UI7" name_et="Free meassurement in use UI7" name_lv="Brivais merijums Lietot_UI7" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1334" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_OutTempFromBus" name_en="Outdoor temp from bus" name_fi="Ulkolämpötila väylältä" name_lv="Ārgaisa temp. no BUS" name_et="Välistemperatuur siinist" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1491" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_OutdoorTempOut" name_en="Outdoor temperature" name_fi="Ulkolämpötila" name_sv="Utetemperatur" name_et="Välistemperatuur" name_ru="Outdoor temperature" name_lv="Outdoor temperature" name_tr="Outdoor temperature" pointtype="10" registertype="Holding" addressformat="S32" addressindex="1493" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="-50" max="50" />
      <point name="InputSelections_SensorSel_DI1_GeneralAlarmName" name_fi="DI1 Yleishälytys" name_en="DI1 General alarm" name_sv="DI1 Allmänt larm" name_et="DI1 Üldalarm" name_lv="DI1 Vispārīgā trauksme" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1190" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_SensorSel_UI15_PumpAlarm_UI15AlarmName" name_fi="P2 Pumppu" name_en="P2 Pump alarm" name_sv="P2 Pump larm" name_et="P2 Pumba alarm" name_ru="H2 Насос" name_lv="CS2 Sūknis" name_tr="P2 Pump alarm" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1194" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_SensorSel_UI16_PumpAlarm_UI16AlarmName" name_fi="P3 Pumppu" name_en="P3 Pump alarm" name_sv="P3 Pump larm" name_et="P3 Pumba alarm" name_ru="H3 Насос" name_lv="CS3 Sūknis" name_tr="P3 Pump alarm" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1195" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_AnAlarm_UI10_UI10AlarmName" name_fi="KL Tulolämpötila" name_en="DH supply water temp." name_sv="FJV Framledn. temp." name_et="KK Küttevesi" name_ru="ЦТС Темп. на подаче" name_lv="Prim. kont. turpgaitas temp." name_tr="DH supply water temp." pointtype="10" registertype="Holding" addressformat="S32" addressindex="1217" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_DigAlarm_UI11_UI11AlarmName" name_fi="Kosketinhälytys UI11" name_en="Switch alarm UI11" name_sv="Koppling larm UI11" name_et="Lüliti alarm UI11" name_lv="Trauksmes relejs UI11" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1251" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_AnAlarm_UI11_UI11AlarmName" name_fi="KL Paluulämpötila" name_en="DH Return water temp." name_sv="FJV Returvattnets temp." name_et="KK Tagastusvesi" name_lv="Prim. kont. atgaitas temp." name_ru="ЦТС Обр.темпер." name_tr="DH Return water temp." pointtype="10" registertype="Holding" addressformat="S32" addressindex="1247" categorytype="2" unit="°C" decimals="1" scaling="10" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="InputSelections_DigAlarm_UI10_UI10AlarmName" name_fi="Kosketinhälytys (UI10)" name_en="Switch alarm (UI10)" name_sv="Koppling larm (UI10)" name_lv="Trauks. relejs (UI10)" name_et="Lüliti alarm (UI10)" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1216" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_RoomSel_UI7_RoomTempUI7InUse" name_en="Result of logical AND operation" name_fi="RoomTempUI7InUse" name_sv="Resultat av logisk AND-funktion" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1390" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="InputSelections_RoomSel_UI4_RoomTempUI4InUse" name_en="Result of logical AND operation" name_fi="RoomTempUI4InUse" name_sv="Resultat av logisk AND-funktion" pointtype="10" registertype="Holding" addressformat="U16" addressindex="1499" categorytype="2" enum="0=Off;1=On" readacceslevel="5" writeacceslevel="1" type="1" />
      <point name="H1ActuatorSel_MotorPos" name_en="Actuator control" name_fi="Toimilaiteohjaus" name_sv="Ställdon styrning" name_et="Aktuaatori juhtimine" name_ru="Управление ИМ" name_lv="Izpildmehānisma pozīcija" name_tr="Actuator control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="528" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1ActuatorSel_MotorPos2" name_en="Actuator control 2" name_fi="Toimilaiteohjaus 2" name_sv="Ställdon styrning 2" name_et="Aktuaatori juhtimine 2" name_ru="Управление ИМ 2" name_lv="Izpildmehānisma pozīcija 2" name_tr="Actuator control 2" pointtype="10" registertype="Holding" addressformat="S32" addressindex="530" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H1ActuatorSel_MotorPosReal" name_en="Actuator position" name_fi="Toimilaitteen asento" name_sv="Ställdonets läge" name_et="" name_ru="" name_lv="Izpildmehānisma pozīcija" pointtype="10" registertype="Holding" addressformat="S32" addressindex="534" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2ActuatorSel_MotorPos" name_en="Actuator control" name_fi="Toimilaiteohjaus" name_sv="Ställdon styrning" name_et="Aktuaatori juhtimine" name_ru="Управление ИМ 1" name_lv="Izpildmehānisma pozīcija" name_tr="Actuator control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="467" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2ActuatorSel_MotorPos2" name_en="Actuator control 2" name_fi="Toimilaiteohjaus 2" name_sv="Ställdon styrning 2" name_et="Aktuaatori juhtimine 2" name_ru="Управление ИМ 2" name_lv="Izpildmehānisma pozīcija 2" name_tr="Actuator control 2" pointtype="10" registertype="Holding" addressformat="S32" addressindex="476" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="H2ActuatorSel_MotorPosReal" name_en="Actuator position" name_fi="Toimilaitteen asento" name_sv="Ställdonets läge" name_et="" name_lv=" Izpildmehānisma pozīcija" pointtype="10" registertype="Holding" addressformat="S32" addressindex="478" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HWActuatorSel_MotorPos" name_en="Actuator control" name_fi="Toimilaiteohjaus" name_sv="Ställdon styrning" name_et="Aktuaatori juhtimine" name_ru="Управление ИМ 1" name_lv="Izpildmehānisma pozīcija" name_tr="Actuator control" pointtype="10" registertype="Holding" addressformat="S32" addressindex="401" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
      <point name="HWActuatorSel_MotorPos2" name_en="Actuator control 2" name_fi="Toimilaiteohjaus 2" name_sv="Ställdon styrning 2" name_et="Aktuaatori juhtimine 2" name_ru="Управление ИМ 2" name_lv="Izpildmehānisma pozīcija 2" name_tr="Actuator control 2" pointtype="10" registertype="Holding" addressformat="S32" addressindex="403" categorytype="2" unit="%" scaling="1" readacceslevel="5" writeacceslevel="1" min="0" max="0" />
    </group>
    <group categorytype="1" name="Käsiajo" name_en="Manual control" name_fi="Käsiajo" name_sv="Manuell styrning" name_et="käsijuhtimisrežiim" name_ru="Ручной режим" name_lv="Rokas vadība" name_tr="Manuel kontrol ">
      <point name="UI 1_mc" name_en="Outdoor temp. Manual control" name_fi="Ulkolämpötila Käsiajo" name_sv="Utetemperatur Manuell styrning" name_et="Välistemperatuur käsijuhtimisrežiim" name_ru="Наружная темп. Ручной режим" name_lv="Ārgaisa temp. Rokas vadība" name_tr="Outdoor temp. Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="284" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 2_mc" name_en="H1 Supply water Manual control" name_fi="L1 Menovesi Käsiajo" name_sv="V1 Framledningsv. Manuell styrning" name_et="K1 Küttevesi käsijuhtimisrežiim" name_ru="O1 Подача Ручной режим" name_lv="A1 Turpgaitas Rokas vadība" name_tr="Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="285" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 3_mc" name_en="Return water Manual control" name_fi="Paluuvesi Käsiajo" name_sv="Returvatten Manuell styrning" name_et="Tagastusvesi käsijuhtimisrežiim" name_ru="Темп. обратной воды  Ручной режим" name_lv="Atgaitas temperatūra Rokas vadība" name_tr="Return water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="286" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 4_mc" name_en="UI 4 Manual control" name_fi="UI 4 Käsiajo" name_sv="UI 4 Manuell styrning" name_et="UI 4 käsijuhtimisrežiim" name_ru="UI 4 Ручной режим" name_lv="UI 4: Brīvais mērī./ A1 Telpas temp./ A1 Prim.kont. Atgaitas Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="287" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 5_mc" name_en="H2 Supply water Manual control" name_fi="L2 Menovesi Käsiajo" name_sv="V2 Framledningsv. Manuell styrning" name_et="K2 Küttevesi käsijuhtimisrežiim" name_ru="O2 Подача Ручной режим" name_lv="A2 Turpgaitas Rokas vadība" name_tr="Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="288" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 6_mc" name_en="Return water Manual control" name_fi="Paluuvesi Käsiajo" name_sv="Returvatten Manuell styrning" name_et="Tagastusvesi käsijuhtimisrežiim" name_ru="Темп. обратной воды  Ручной режим" name_lv="Atgaitas temperatūra Rokas vadība" name_tr="Return water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="289" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 7_mc" name_en="UI 7 Manual control" name_fi="UI 7 Käsiajo" name_sv="UI 7 Manuell styrning" name_et="UI 7 käsijuhtimisrežiim" name_ru="UI 7 Ручной режим" name_lv="UI 7: Brīvais mērī./ A2 Telpas temp./ A2 Prim.kont. Atgaitas Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="290" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 8_mc" name_en="DHW Supply water Manual control" name_fi="LV Menovesi Käsiajo" name_sv="TV Framledningsv. Manuell styrning" name_et="TV Küttevesi käsijuhtimisrežiim" name_ru="ГВС Подача Ручной режим" name_lv="K.ŪD. Turpgaitas Rokas vadība" name_tr="Supply water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="291" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 9_mc" name_en="Circulation water Manual control" name_fi="Kiertovesi  Käsiajo" name_sv="Cirkulation  Manuell styrning" name_et="Ringlusvesi käsijuhtimisrežiim" name_ru="Циркуляционная вода Ручной режим" name_lv="Karstā ūdens cirkulācijas temp. Rokas vadība" name_tr="Circulation water Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="292" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 10_mc" name_en="UI10 Manual control" name_fi="UI10 Käsiajo" name_sv="UI10 Manuell styrning" name_et="UI10 käsijuhtimisrežiim" name_ru="UI 10 Ручной режим" name_lv="UI10: Brīvais mērījums. / Trauksmes relejs Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="293" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 11_mc" name_en="UI11 Manual control" name_fi="UI11 Käsiajo" name_sv="UI11 Manuell styrning" name_et="UI11 käsijuhtimisrežiim" name_ru="UI 11 Ручной режим" name_lv="UI11: Brīvais mērījums. / Trauksmes relejs Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="294" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 12_mc" name_en="UI 12 Manual control" name_fi="UI 12 Käsiajo" name_sv="UI 12 Manuell styrning" name_et="UI 12 käsijuhtimisrežiim" name_ru="UI 12 Ручной режим" name_lv="UI 12: Brīvais mērīj. / Spiediena relejs/Spiediena devējs Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="295" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 13_mc" name_en="UI 13 Manual control" name_fi="UI 13 Käsiajo" name_sv="UI 13 Manuell styrning" name_et="UI 13 käsijuhtimisrežiim" name_ru="UI 13 Ручной режим" name_lv="UI 13: Brīvais mērīj. / Spiediena relejs/Spiediena devējs Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="296" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 14_mc" name_en="UI 14 Manual control" name_fi="UI 14 Käsiajo" name_sv="UI 14 Manuell styrning" name_et="UI 14 käsijuhtimisrežiim" name_ru="UI 14 Ручной режим" name_lv="UI 14: Vispārīgā kompensācija/ Mājās / Ārpus mājām – Slēdzis Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="297" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 15_mc" name_en="UI 15 Manual control" name_fi="UI 15 Käsiajo" name_sv="UI 15 Manuell styrning" name_et="UI 15 käsijuhtimisrežiim" name_ru="UI 15 Ручной режим" name_lv="UI 15:Trauksme/ Indikācija Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="298" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="UI 16_mc" name_en="UI 16 Manual control" name_fi="UI 16 Käsiajo" name_sv="UI 16 Manuell styrning" name_et="UI 16 käsijuhtimisrežiim" name_ru="UI 16 Ручной режим" name_lv="UI 16: Trauksme/ Indikācija Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="299" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 1_mc" name_en="DI 1 Manual control" name_fi="DI 1 Käsiajo" name_sv="DI 1 Manuell styrning" name_et="DI 1 käsijuhtimisrežiim" name_ru="DI 1 Ручной режим" name_lv="DI 1: Trauks./ Vispārīgā trauks./Ūdens tilpums/Enerģijamēr. Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="233" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="DI 2_mc" name_en="DI 2 Manual control" name_fi="DI 2 Käsiajo" name_sv="DI 2 Manuell styrning" name_et="DI 2 käsijuhtimisrežiim" name_ru="DI 2 Ручной режим" name_lv="DI 2: Ūdens tilpums/Enerģijamērijum Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="234" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 1_mc" name_en="AO 1 Manual control" name_fi="Moottoriohjaus, jänniteviesti Käsiajo" name_sv="AO 1 Manuell styrning" name_et="AO 1 käsijuhtimisrežiim" name_ru="AO 1 Ручной режим" name_lv="AO1: A1  Izpildmehānisma pozīcija Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="303" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 2_mc" name_en="ValveCtrl2 Manual control" name_fi="Moottoriohjaus, jänniteviesti 2 Käsiajo" name_sv="ValveCtrl2 Manuell styrning" name_et="ValveCtrl2 käsijuhtimisrežiim" name_lv="AO2: A1 Izpildmehānisma pozīcija 2 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="304" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 3_mc" name_en="Valve control Manual control" name_fi="Moottoriohjaus, jänniteviesti Käsiajo" name_sv="Ventil styrning Manuell styrning" name_lv="AO3: A2 Izpildmehānisma pozīcija Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="305" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 4_mc" name_en="ValveCtrl2 Manual control" name_fi="Moottoriohjaus, jänniteviesti 2 Käsiajo" name_sv="ValveCtrl2 Manuell styrning" name_et="ValveCtrl2 käsijuhtimisrežiim" name_lv="Rudens žāv. ietekme uz turpg. temp. Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="306" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 5_mc" name_en="Output  Manual control" name_fi="Moottoriohjaus, jänniteviesti Käsiajo" name_lv="AO5: K.ŪD Izpildmehānisma pozīcija Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="307" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AO 6_mc" name_en="ValveCtrl2 Manual control" name_fi="Moottoriohjaus, jänniteviesti 2 Käsiajo" name_sv="ValveCtrl2 Manuell styrning" name_et="ValveCtrl2 käsijuhtimisrežiim" name_lv="AO6: K.ŪD Izpildmehānisma pozīcija 2 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="308" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 1_mc" name_en="TR 1 Manual control" name_fi="TR 1 Käsiajo" name_sv="TR 1 Manuell styrning" name_et="TR 1 käsijuhtimisrežiim" name_ru="TR 1 Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="309" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TR 2_mc" name_en="TR 2 Manual control" name_fi="TR 2 Käsiajo" name_sv="TR 2 Manuell styrning" name_et="TR 2 käsijuhtimisrežiim" name_ru="TR 2 Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="310" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TRS1_mc" name_en="TRS1 Manual control" name_fi="TRS1 Käsiajo" name_sv="TRS1 Manuell styrning" name_et="TRS1 käsijuhtimisrežiim" name_ru="TRS1 Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="313" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="TRS2_mc" name_en="TRS2 Manual control" name_fi="TRS2 Käsiajo" name_sv="TRS2 Manuell styrning" name_et="TRS2 käsijuhtimisrežiim" name_ru="TRS2 Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="314" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="AutumnDry_AverageOutTemp_mc" name_en="Previous day's average outdoor temp Manual control" name_fi="Ulkolämpötilan edell. vrk:n keskiarvo Käsiajo" name_sv="Föregående dags utetemp. i genomsnitt Manuell styrning" name_et="Eelmise päeva keskmine välistemp. käsijuhtimisrežiim" name_ru="Сред.знач.Т.наруж.возд.предыд.суток Ручной режим" name_lv="Iepriekš. dienas vid. ārgaisa temp. Rokas vadība" name_tr="Previous day's average outdoortemp Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="358" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_CalculatedSet_mc" name_en="Calculated supply water setting Manual control" name_fi="Laskennall. menoveden asetusarvo Käsiajo" name_sv="Beräknad framledningstemp. Manuell styrning" name_et="Arvutuslik küttevee seadistus käsijuhtimisrežiim" name_ru="Расчёт.устав.знач.темп. на подаче Ручной режим" name_lv="Aprēķinātā turpgaitas temp. Rokas vadība" name_tr="Calculated supply water setting Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="569" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RetWaterEff_mc" name_en="Return water compensation Manual control" name_fi="Paluuveden kompensoinnin vaikutus Käsiajo" name_sv="Påverkan av returvattnets kompens. Manuell styrning" name_et="Tagastusvee kompenseerimine käsijuhtimisrežiim" name_ru="Воздействие компенсации по обр.воде Ручной режим" name_lv="Atgaitas temp. kompensācijas ietekme Rokas vadība" name_tr="Return water compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="573" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_MinLimitEff_mc" name_en="Min limit effect Manual control" name_fi="Minimirajan vaikutus Käsiajo" name_sv="Påverkan av min.gränsen Manuell styrning" name_et="Alampiiri mõju käsijuhtimisrežiim" name_ru="Воздействие мин. ограничения Ручной режим" name_lv="Min. robežas ietekme Rokas vadība" name_tr="Min limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="599" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_MaxLimitEff_mc" name_en="Max limit effect Manual control" name_fi="Maksimirajan vaikutus Käsiajo" name_sv="Påverkan av max.gränsen Manuell styrning" name_et="Ülempiiri mõju käsijuhtimisrežiim" name_ru="Воздействие макс. ограничения Ручной режим" name_lv="Maks. robežas ietekme Rokas vadība" name_tr="Max limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="602" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_SupplyLineTempFinal_mc" name_en="Output Manual control" name_fi="Menoveden lämpötila säätimelle Käsiajo" name_sv="Output Manuell styrning" name_et="Output käsijuhtimisrežiim" pointtype="3" registertype="Holding" addressformat="U16" addressindex="609" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_BusCompEff_mc" name_en="Bus compensation effect Manual control" name_fi="Väyläkompensoinnin vaikutus Käsiajo" name_sv="Påverkan av  busskompenseringen Manuell styrning" name_et="Siini kompenseerimise mõju käsijuhtimisrežiim" name_ru="Воздействие общей компенсации Ручной режим" name_lv="Tīkla kompensācijas ietekme Rokas vadība" name_tr="Bus compensation effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="610" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_AutumnDryEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkningen Manuell styrning" name_et="Sügiskuivatamise mõju käsijuhtimisrežiim" name_ru="Воздейств.функц.осуш. в осен.период Ручной режим" name_lv="Rudens žāvēšanas ietekme Rokas vadība" name_tr="Effect of autumn drying Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="611" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_OutTempDelayEff_mc" name_en="Outd.temp delay effect Manual control" name_fi="Ulkolämpötilahidastuksen vaikutus Käsiajo" name_sv="Påverkan av utetemp.fördröj. Manuell styrning" name_et="Välistemperatuuri viivituse mõju käsijuhtimisrežiim" name_ru="Воздейств.отлож.измер.темп.наруж.возд. Ручной режим" name_lv="Ārgaisa temp. aizkaves ietekme Rokas vadība" name_tr="Outd.temp delay effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="612" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_OutTempDelayed_mc" name_en="Delayed outdoor temperature Manual control" name_fi="Hidastettu ulkolämpötilamittaus Käsiajo" name_sv="Fördröjd utetemperatur Manuell styrning" name_et="Viivitusega välistemperatuur käsijuhtimisrežiim" name_ru="Отложенное измер.темп.нар.возд. Ручной режим" name_lv="Aizkavētais ārgaisa temp. mērījums Rokas vadība" name_tr="Delayed outdoor temperature Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="613" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomCompEff_mc" name_en="Effect of room compensation Manual control" name_fi="Huonekompensoinnin vaikutus Käsiajo" name_sv="Påverkan av rumskompenseringen Manuell styrning" name_et="Toa kompenseerimise mõju käsijuhtimisrežiim" name_ru="Воздействие компенсации комн.темп. Ручной режим" name_lv="Telpas kompensācijas ietekme Rokas vadība" name_tr="Effect of room compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="616" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomCompIDrive_mc" name_en="Room comp. Time adjustment Manual control" name_fi="Huonekompensoinnin aikakorjaus Käsiajo" name_sv="Påverkan av rumskomp. tidsjusteringen Manuell styrning" name_et="Toa kompenseerimisaja reguleerimine käsijuhtimisrežiim" name_ru="Воздействие компенсации комн.темп. Ручной режим" name_lv="Telpas kompensācijas laika koriģēšana Rokas vadība" name_tr="Room comp.time adjustment Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="622" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomDropHigh_mc" name_en="Time program effect on room temp. Manual control" name_fi="Aikaohjelman vaikutus huonel. Käsiajo" name_sv="Tidsprogram påverkan på rumstemp. Manuell styrning" name_et="Ajaprogrammi mõju toatemperatuurile käsijuhtimisrežiim" name_ru="Воздейст.времен.прогр. на комн.темп. Ручной режим" name_lv="Laika prog. ietekme uz telpas temp. Rokas vadība" name_tr="Time program effect on  room temp. Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="623" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomDropLow_mc" name_en="RoomDropLow Manual control" name_fi="Aikaohjelman vaikutus huonelämpötilaan (pienipudotus) Käsiajo" name_lv="Temp. pazem. (telpas temp.) Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="624" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_AutumnDryRoomEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkning  Manuell styrning" name_et="Sügiskuivatamise mõju käsijuhtimisrežiim" name_ru="Воздейств.функц.осуш. в осен.период Ручной режим" name_lv="Rudens žāvēšanas ietekme Rokas vadība" name_tr="Effect of autumn drying Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="702" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_FollowCurve_mc" name_en="According to curve Manual control" name_fi="Käyrän mukaan Käsiajo" name_sv="Enligt kurvan Manuell styrning" name_et="Küttevesi vastavalt küttekõverale käsijuhtimisrežiim" name_ru="В соответствии с кривой Ручной режим" name_lv="Pēc līknes Rokas vadība" name_tr="According to curve Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="603" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomSetpReslut_mc" name_en="Calculated room setting value Manual control" name_fi="Laskennall. huoneasetusarvo Käsiajo" name_sv="Beräknad rumstemperatur Manuell styrning" name_et="Arvutuslik toatemp. seadistus käsijuhtimisrežiim" name_ru="Расчёт.устав.знач.темп. на подаче Ручной режим" name_lv="Aprēķinātā telpas temp. Rokas vadība" name_tr="Calculated room setting value Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1153" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_HASwitchEffect_mc" name_en="Away -control effect Manual control" name_fi="Poissa -ohjauksen vaikutus Käsiajo" name_sv="Borta -styrning effekt Manuell styrning" name_et=" käsijuhtimisrežiim" name_lv="Mājās / Ārpus mājām – vadības ietekme Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1128" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomForceDrop_mc" name_en="Force control effect Manual control" name_fi="Pakko-ohjauksen vaikutus Käsiajo" name_sv="Tvångsstyrningens effekt Manuell styrning" name_et="Sundjuhtimise mõju käsijuhtimisrežiim" name_ru="Воздейств.принудит.управления Ручной режим" name_lv="Piespiedu vadības ietekme Rokas vadība" name_tr="Force control effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1148" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_L1DHReturnCompEff_mc" name_en="H1 DH return comp. effect  Manual control" name_fi="L1 vaihdin KL paluukomp. vaik. Käsiajo" name_sv="V1 FJV Retur ersätt effekt Manuell styrning" name_et="K1 KK tagasivoolu kompens. mõju käsijuhtimisrežiim" name_ru="O1 DH Return comp effect  Ручной режим" name_lv="A1 Prim. kont. atg. komp. Ietekme Rokas vadība" name_tr="H1 DH Return comp effect  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1298" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_L1RadiatorDelayEffect_mc" name_en="Radiator heating Delay effect  Manual control" name_fi="Patteril. hidastuksen vaikutus Käsiajo" name_sv="Radiator heating Delay effect  Manuell styrning" name_et="Radiator heating Delay effect  käsijuhtimisrežiim" name_ru="Radiator heating Delay effect  Ручной режим" name_lv="Ārgaisa temp. aizkaves ietekme (radiatoru apkure) Rokas vadība" name_tr="Radiator heating Delay effect  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="554" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_L1FloorEffect_mc" name_en="Floor heating anticipation effect Manual control" name_fi="Lattial. ennakoinnin vaikutus Käsiajo" name_sv="Floor heating anticipation effect Manuell styrning" name_et="Floor heating anticipation effect käsijuhtimisrežiim" name_ru="Floor heating anticipation effect Ручной режим" name_lv="Grīdas apk. prognoze Rokas vadība" name_tr="Floor heating anticipation effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="555" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl1_RoomComp_DelayedRoomTemp_mc" name_en="H1 Delayed room temperature Manual control" name_fi="L1 Hidastettu huonelämpötilamittaus Käsiajo" name_sv="V1 Fördröjd rumstemperatur Manuell styrning" name_et="Filtered output signal käsijuhtimisrežiim" name_ru="H1 Delayed room temperature Ручной режим" name_lv="A1 Aizkavēts telpas temp. mērījums Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="626" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_CalculatedSet_mc" name_en="Calculated supply water setting Manual control" name_fi="Laskennall. menoveden asetusarvo Käsiajo" name_sv="Beräknad framledningstemp. Manuell styrning" name_et="Arvutuslik küttevee seadistus käsijuhtimisrežiim" name_ru="Расчёт.устав.знач.темп. на подаче Ручной режим" name_lv="Aprēķinātā turpgaitas temp. Rokas vadība" name_tr="Calculated supply water setting Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="405" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RetWaterEff_mc" name_en="Return water compensation Manual control" name_fi="Paluuveden kompensoinnin vaikutus Käsiajo" name_sv="Påverkan av returvattnets kompens. Manuell styrning" name_et="Tagastusvee kompenseerimine käsijuhtimisrežiim" name_ru="Воздействие компенсации по обр.воде Ручной режим" name_lv="Atgaitas temp. kompensācijas ietekme Rokas vadība" name_tr="Return water compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="445" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_MinLimitEff_mc" name_en="Min limit effect Manual control" name_fi="Minimirajan vaikutus Käsiajo" name_sv="Påverkan av min.gränsen Manuell styrning" name_et="Alampiiri mõju käsijuhtimisrežiim" name_ru="Воздействие мин. ограничения Ручной режим" name_lv="Min. robežas ietekme Rokas vadība" name_tr="Min limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="480" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_MaxLimitEff_mc" name_en="Max limit effect Manual control" name_fi="Maksimirajan vaikutus Käsiajo" name_sv="Påverkan av max.gränsen Manuell styrning" name_et="Ülempiiri mõju käsijuhtimisrežiim" name_ru="Воздействие макс. ограничения Ручной режим" name_lv="Maks. robežas ietekme Rokas vadība" name_tr="Max limit effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="500" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_SupplyLineTempFinal_mc" name_en="Output Manual control" name_fi="Menoveden lämpötila säätimelle Käsiajo" name_sv="Output Manuell styrning" name_et="Output käsijuhtimisrežiim" name_lv="Aprēķinātā turpgaitas temp. Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="518" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_BusCompEff_mc" name_en="Bus compensation effect Manual control" name_fi="Väyläkompensoinnin vaikutus Käsiajo" name_sv="Påverkan av  busskompenseringen Manuell styrning" name_et="Siini kompenseerimise mõju käsijuhtimisrežiim" name_ru="Воздействие общей компенсации Ручной режим" name_lv="Tīkla kompensācijas ietekme Rokas vadība" name_tr="Bus compensation effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="523" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_AutumnDryEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkningen Manuell styrning" name_et="Sügiskuivatamise mõju käsijuhtimisrežiim" name_ru="Воздейств.функц.осуш. в осен.период Ручной режим" name_lv="Rudens žāvēšanas ietekme Rokas vadība" name_tr="Effect of autumn drying Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="525" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_OutTempDelayEff_mc" name_en="Outd.temp delay effect Manual control" name_fi="Ulkolämpötilahidastuksen vaikutus Käsiajo" name_sv="Påverkan av utetemp.fördröj. Manuell styrning" name_et="Välistemperatuuri viivituse mõju käsijuhtimisrežiim" name_ru="Воздейств.отлож.измер.темп.наруж.возд. Ручной режим" name_lv="Ārgaisa temp. aizkaves ietekme Rokas vadība" name_tr="Outd.temp delay effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="532" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_OutTempDelayed_mc" name_en="Delayed outdoor temperature Manual control" name_fi="Hidastettu ulkolämpötilamittaus Käsiajo" name_sv="Fördröjd utetemperatur Manuell styrning" name_et="Viivitusega välistemperatuur käsijuhtimisrežiim" name_ru="Отложенное измер.темп.нар.возд. Ручной режим" name_lv="Aizkavētais ārgaisa temp. mērījums Rokas vadība" name_tr="Delayed outdoor temperature Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="540" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomCompEff_mc" name_en="Effect of room compensation Manual control" name_fi="Huonekompensoinnin vaikutus Käsiajo" name_sv="Påverkan av rumskompenseringen Manuell styrning" name_et="Toa kompenseerimise mõju käsijuhtimisrežiim" name_ru="Воздействие компенсации комн.темп. Ручной режим" name_lv="Telpas kompensācijas ietekme Rokas vadība" name_tr="Effect of room compensation Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="659" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomCompIDrive_mc" name_en="Room comp. Time adjustment Manual control" name_fi="Huonekompensoinnin aikakorjaus Käsiajo" name_sv="Påverkan av rumskomp. tidsjusteringen Manuell styrning" name_et="Toa kompenseerimisaja reguleerimine käsijuhtimisrežiim" name_ru="Воздействие компенсации комн.темп. Ручной режим" name_lv="Telpas kompensācijas laika koriģēšana Rokas vadība" name_tr="Room comp.time adjustment Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="695" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomDropHigh_mc" name_en="RoomDropHigh Manual control" name_fi="Aikaohjelman vaikutus huonel. Käsiajo" name_lv="Lielais telpas  temp. pazeminājums Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="699" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomDropLow_mc" name_en="RoomDropLow Manual control" name_fi="Aikaohjelman vaikutus huonel. Käsiajo" name_lv="Telpas temp. pazem Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="700" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_AutumnDryRoomEff_mc" name_en="Effect of autumn drying Manual control" name_fi="Syyskuivauksen vaikutus Käsiajo" name_sv="Påverkan av hösttorkningen Manuell styrning" name_et="Sügiskuivatamise mõju käsijuhtimisrežiim" name_ru="Воздейств.функц.осуш. в осен.период Ручной режим" name_lv="Rudens žāvēšanas ietekme Rokas vadība" name_tr="Effect of autumn drying Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="701" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_FollowCurve_mc" name_en="According to curve Manual control" name_fi="Käyrän mukaan Käsiajo" name_sv="Enligt kurvan Manuell styrning" name_et="Küttevesi vastavalt küttekõverale käsijuhtimisrežiim" name_ru="В соответствии с кривой Ручной режим" name_lv="Pēc līknes Rokas vadība" name_tr="According to curve Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="711" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomSetpResult_mc" name_en="Calculated room setpoint Manual control" name_fi="Laskennall. huoneasetusarvo Käsiajo" name_sv="Beräknad rumstemperatur Manuell styrning" name_et="Arvutuslik toa nimiväärtus käsijuhtimisrežiim" name_ru="Расчёт.устав.знач.темп. на подаче Ручной режим" name_lv="Aprēķinātā telpas temp. Rokas vadība" name_tr="Calculated room setpoint Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1134" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_HASwitchEffect_mc" name_en="HADrop Manual control" name_fi="Poissa -ohjauksen vaikutus Käsiajo" name_lv="Mājās / Ārpus mājām - Temp. pazem. Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1127" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomForceDrop_mc" name_en="Force control effect Manual control" name_fi="Pakko-ohjauksen vaikutus Käsiajo" name_sv="Tvångsstyrningens effekt Manuell styrning" name_et="Sundjuhtimise mõju käsijuhtimisrežiim" name_ru="Воздейств.принудит.управления Ручной режим" name_lv="Piespiedu vadības ietekme Rokas vadība" name_tr="Force control effect Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1161" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_L2DHReturnCompEff_mc" name_en="H2 DH return comp. effect  Manual control" name_fi="L2 vaihdin KL paluukomp. vaik. Käsiajo" name_sv="V2 FJV Retur ersätt effekt Manuell styrning" name_et="K2 KK tagasivoolu kompens. mõju käsijuhtimisrežiim" name_ru="O2  ЦТС Return comp effect  Ручной режим" name_lv="A2 Prim. kont. atg. komp. Ietekme Rokas vadība" name_tr="H2 DH Return comp. effect  Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1335" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="HeatingControl2_RoomComp_DelayedRoomTemp_mc" name_en="H2 Delayed room temperature Manual control" name_fi="L2 Hidastettu huonelämpötilamittaus Käsiajo" name_sv="V2 Fördröjd rumstemperatur Manuell styrning" name_et="Filtered output signal käsijuhtimisrežiim" name_ru="H2 Delayed room temperature Ручной режим" name_lv="A2 Aizkavēts telpas temp. mērījums Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="713" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressSwitchMeas_UI13_mc" name_en="Pressure switch 2 mode Manual control" name_fi="Painekytkimen 2 tila Käsiajo" name_sv="Tryck mätning 2 läge Manuell styrning" name_et="Rõhulüliti 2  režiim käsijuhtimisrežiim" name_ru="Состояние датчика давления 2 Ручной режим" name_lv="Spiediena releja 2 režīms Rokas vadība" name_tr="Pressure switch 2 mode Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="591" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressSwitchMeas_UI12_mc" name_en="Pressure switch 1 mode Manual control" name_fi="Painekytkimen 1 tila Käsiajo" name_sv="Tryckmätning 1 läge Manuell styrning" name_et="Rõhulüliti 1 režiim käsijuhtimisrežiim" name_ru="Состояние датчика давления 1 Ручной режим" name_lv="Spiediena releja 1 režīms Rokas vadība" name_tr="Pressure switch 1 mode Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="592" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_L2DhRetMeas_UI7_mc" name_en="H2 DH Return Manual control" name_fi="L2 vaihdin KL paluu Käsiajo" name_sv="V2 FJV Returvattentemp. Manuell styrning" name_et="K2 KK Tagastus käsijuhtimisrežiim" name_ru="O2 т/о  ЦТС обр.контур Ручной режим" name_lv="A2 Prim.kont. Atgaitas Rokas vadība" name_tr="H2 DH Return Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="593" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_L1DhRetMeas_UI4_mc" name_en="H1 DH Return Manual control" name_fi="L1 vaihdin KL paluu Käsiajo" name_sv="V1 FJV Returvattentemp. Manuell styrning" name_et="K1 KK Tagastus käsijuhtimisrežiim" name_ru="O1 т/о ЦТС обр.контур Ручной режим" name_lv="A1 Prim.kont. Atgaitas Rokas vadība" name_tr="H1 DH Return Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="597" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_L1RoomMeas_UI4_mc" name_en="Room temperature Manual control" name_fi="Huonelämpötila Käsiajo" name_sv="Rumstemp. Manuell styrning" name_et="Toatemperatuur käsijuhtimisrežiim" name_ru="Комнатная температура Ручной режим" name_lv="Telpas temperatūra Rokas vadība" name_tr="Room temperature Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="598" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressureMeas_UI12_mc" name_en="Pressure measurement 1 Manual control" name_fi="Painemittaus 1 Käsiajo" name_sv="Tryckmätning 1 Manuell styrning" name_et="Rõhu mõõtmine 1 käsijuhtimisrežiim" name_ru="Давление 1 Ручной режим" name_lv="Spiediena mērījums 1 Rokas vadība" name_tr="Pressure measurement 1 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="600" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressureMeas_UI13_mc" name_en="Pressure measurement 2 Manual control" name_fi="Painemittaus 2 Käsiajo" name_sv="Tryck mätning 2 Manuell styrning" name_et="Rõhu mõõtmine 2 käsijuhtimisrežiim" name_ru="Давление 2 Ручной режим" name_lv="Spiediena mērījums 2 Rokas vadība" name_tr="Pressure measurement 2 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="601" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_WaterVol_DI2_18_mc" name_en="DI2 Water volume Manual control" name_fi="DI2 Vesimäärämittaus Käsiajo" name_sv="DI2 Vattenvolym Manuell styrning" name_et="DI2 Veevoolu mõõtmine käsijuhtimisrežiim" name_ru="DI 2 Расход воды Ручной режим" name_lv="DI2 Ūdens tilpums Rokas vadība" name_tr="DI2 Water flow measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="575" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_P1AlarmState_DI1_17_mc" name_en="Pump 1 alarm Manual control" name_fi="Pumppu 1 hälytys Käsiajo" name_sv="Pump 1 larm Manuell styrning" name_et="P1_Alarm käsijuhtimisrežiim" name_ru="Pump1 Alarm Ручной режим" name_lv="CS1 Sūknis Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1386" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenAlarmState_DI1_17_mc" name_en="General alarm status Manual control" name_fi="Yleishälytyksen tila Käsiajo" name_sv="Allmänt larm status Manuell styrning" name_et="Üldalarmi seisund käsijuhtimisrežiim" name_ru="Статус общего сигнала Ручной режим" name_lv="Vispārīgā trauksme režīms Rokas vadība" name_tr="General alarm status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1387" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_P3AlarmState_UI16_mc" name_en="Pump 3 alarm Manual control" name_fi="Pumppu 3 hälytys Käsiajo" name_sv="Pump 3 larm Manuell styrning" name_et="P_Alarm käsijuhtimisrežiim" name_ru="Pump3 Alarm Ручной режим" name_lv="CS3 Sūknis Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1389" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_WaterVol_DI1_17_mc" name_en="DI1 Water volume Manual control" name_fi="DI1 Vesimäärämittaus Käsiajo" name_sv="DI1 Vattenvolym Manuell styrning" name_et="DI1 Veevoolu mõõtmine käsijuhtimisrežiim" name_ru="DI 1 Расход воды Ручной режим" name_lv="DI1 Ūdens tilpums Rokas vadība" name_tr="DI1 Water flow measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="481" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenTempMeas_UI12_mc" name_en="Meas.UI 12 Manual control" name_fi="Mitt. UI 12 Käsiajo" name_sv="Mätn. UI 12 Manuell styrning" name_et="Mõõtmine UI 12 käsijuhtimisrežiim" name_ru="Изм. UI12 Ручной режим" name_lv="Mērīj. UI 12 Rokas vadība" name_tr="Meas.UI 12 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1402" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenTempMeas_UI13_mc" name_en="Meas. UI13 Manual control" name_fi="Mitt. UI13 Käsiajo" name_sv="Mätn. UI13 Manuell styrning" name_et="Mõõtmine UI13 käsijuhtimisrežiim" name_ru="Изм. UI13 Ручной режим" name_lv="Mērīj. UI13 Rokas vadība" name_tr="Meas. UI13 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1404" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressSwitchAlrState_UI12_mc" name_en="Pressure alarm UI12 Manual control" name_fi="Painehälytys UI12 Käsiajo" name_sv="Tryck larm UI12 Manuell styrning" name_et="AlrState käsijuhtimisrežiim" name_ru="AlrState Ручной режим" name_lv="Spiediena trauksme UI12 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1412" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressSwitchAlrState_UI13_mc" name_en="Pressure alarm UI13 Manual control" name_fi="Painehälytys UI13 Käsiajo" name_sv="Tryck larm UI13 Manuell styrning" name_et="AlrState käsijuhtimisrežiim" name_ru="AlrState Ручной режим" name_lv="Spiediena trauksme  UI13 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1413" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressureMeasAlrState_UI12_mc" name_en="Pressure alarm UI12 Manual control" name_fi="Painehälytys UI12 Käsiajo" name_sv="Tryck larm UI12 Manuell styrning" name_et="AlrState käsijuhtimisrežiim" name_ru="AlrState Ручной режим" name_lv="Spiediena trauksme UI12 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1414" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_PressureMeasAlrState_UI13_mc" name_en="Pressure alarm UI13 Manual control" name_fi="Painehälytys UI13 Käsiajo" name_sv="Tryck larm UI13 Manuell styrning" name_et="AlrState käsijuhtimisrežiim" name_ru="AlrState Ручной режим" name_lv="Spiediena trauksme  UI13 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1415" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_DigInState_DI1_mc" name_en="P1 Alarm status Manual control" name_fi="P1 hälytyksen tila Käsiajo" name_sv="P1 Larm status Manuell styrning" name_et="P1 alarmi seisund käsijuhtimisrežiim" name_ru="P1 hälytyksen tila Ручной режим" name_lv="CS1 Trauksmes stāvoklis Rokas vadība" name_tr="P1 Alarm status Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1416" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_DigInState_UI16_mc" name_en="P3 Pump mode Manual control" name_fi="P3 Pumpun tila Käsiajo" name_sv="P3 Pump läge Manuell styrning" name_et="P3 Pumba režiim käsijuhtimisrežiim" name_ru="P3 Статус насоса Ручной режим" name_lv="CS3 sūkņis Rokas vadība" name_tr="P3 Pump mode Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1418" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_EnergyMeas_DI2_mc" name_en="DI2 Energy measurement Manual control" name_fi="DI2 Energiamittaus Käsiajo" name_sv="DI2 Energimätning Manuell styrning" name_et="DI2 Energia mõõtmine käsijuhtimisrežiim" name_ru="DI2 Расход энергии Ручной режим" name_lv="DI2 Enerģijas mērījums Rokas vadība" name_tr="DI2 Energy measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="300" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_EnergMeas_DI1_mc" name_en="DI1 Energy measurement Manual control" name_fi="DI1 Energiamittaus Käsiajo" name_sv="DI1 Energimätning Manuell styrning" name_et="DI1 Energia mõõtmine käsijuhtimisrežiim" name_ru="DI1 Расход энергии Ручной режим" name_lv="DI1  Enerģijas mērījums Rokas vadība" name_tr="DI1 Energy measurement Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="550" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SwitchMeas_UI10_mc" name_en="Switch alarm state Manual control" name_fi="Kosketinhälytyksen tila Käsiajo" name_sv="Switch alarm state Manuell styrning" name_et="Lüliti alarm režiim käsijuhtimisrežiim" name_ru="Полож.контакта ав.сигн. Ручной режим" name_lv="Slēdža trauksmes stāvoklis Rokas vadība" name_tr="Switch alarm state Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1219" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SwitchInUseUI10_mc" name_en="BinaryInUse Manual control" name_fi="Kosketinhälytys käytössä Käsiajo" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1220" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenMeasNtc10InUse_UI10_mc" name_en="Ntc10InUse Manual control" name_fi="Yleismittaus Ntc-10 käytössä Käsiajo" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1221" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenTempMeas_UI10_mc" name_en="Meas. UI10 Manual control" name_fi="Mitt. UI 10 Käsiajo" name_sv="Mätn. UI 10 Manuell styrning" name_et="Mõõtmine UI10 käsijuhtimisrežiim" name_ru="Изм. UI10 Ручной режим" name_lv="Mērīj.UI10 Rokas vadība" name_tr="Meas. UI10 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1222" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_P2AlarmState_UI15_mc" name_en="Pump 2 alarm Manual control" name_fi="Pumppu 2 hälytys Käsiajo" name_sv="Pump 2 larm Manuell styrning" name_et="P_Alarm käsijuhtimisrežiim" name_ru="Pump2 Alarm Ручной режим" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1388" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_DigInState_UI15_mc" name_en="P2 Pump mode Manual control" name_fi="P2 Pumpun tila Käsiajo" name_sv="P2 Pump läge Manuell styrning" name_et="P2 Pumba režiim käsijuhtimisrežiim" name_ru="P2 Статус насоса Ручной режим" name_lv="CS2 sūkņis mode Rokas vadība" name_tr="P2 Pump mode Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1417" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SwitchMeas_UI11_mc" name_en="Switch alarm state Manual control" name_fi="Kosketinhälytyksen tila Käsiajo" name_sv="Switch alarm state Manuell styrning" name_et="Lüliti alarm režiim käsijuhtimisrežiim" name_ru="Полож.контакта ав.сигн. Ручной режим" name_lv="Slēdža trauksmes stāvoklis Rokas vadība" name_tr="Switch alarm state Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1252" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SwitchInUseUI11_mc" name_en="Swirch alarm in use Manual control" name_fi="Kosketinhälytys käytössä Käsiajo" name_lv="Slēdža trauksme Lietot Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1254" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenMeasNtc10InUse_UI11_mc" name_en="Ntc11InUse Manual control" name_fi="Yleismittaus Ntc-11 käytössä Käsiajo" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1255" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_GenTempMeas_UI11_mc" name_en="Meas. UI 11 Manual control" name_fi="Mitt. UI 11 Käsiajo" name_sv="Mätn. UI 11 Manuell styrning" name_et="Mõõtmine UI11 käsijuhtimisrežiim" name_ru="Изм. UI 11 Ручной режим" name_lv="Mērīj. UI 11 Rokas vadība" name_tr="Meas. UI 11 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1256" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_FreeMeasureInUse_UI4_mc" name_en="Free meassurement UI4 in use Manual control" name_fi="Vapaa mittaus UI4 käytössä Käsiajo" name_sv="Fri mätning UI4 in use Manuell styrning" name_et="Vaba mõõtmine UI4 in use käsijuhtimisrežiim" name_lv="Brivais merijums Lietot__UI4 in use Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1299" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_L1DhRetMeasInUse_UI4_mc" name_en="H1 DH Return in use Manual control" name_fi="L1 KL Paluu käytössä Käsiajo" name_lv="A2 Prim.kont. Atgaitas Lietot Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1300" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_UI4FreeMeasure_mc" name_en="Free meas. UI4 Manual control" name_fi="Vapaa mittaus UI4 Käsiajo" name_sv="Fri mätning UI4 Manuell styrning" name_et="Vaba mõõtmine UI4 käsijuhtimisrežiim" name_ru="Произвол.измерение UI4 Ручной режим" name_lv="Brīvais mērījums UI 4 Rokas vadība" name_tr="Free meassurement UI4 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1336" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_UI7FreeMeasure_mc" name_en="Free meas. UI7 Manual control" name_fi="Vapaa mittaus UI7 Käsiajo" name_sv="Fri mätning UI7 Manuell styrning" name_et="Vaba mõõtmine UI7 käsijuhtimisrežiim" name_ru="Произвол.измерение UI7 Ручной режим" name_lv="Brīvais mērījums UI 7 Rokas vadība" name_tr="Free meassurement UI7 Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1337" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_FreeMeasureInUse_UI7_mc" name_en="Free meassurement in use UI7 Manual control" name_fi="Vapaa mittaus UI7 käytössä Käsiajo" name_sv="Free meassurement in use UI7 Manuell styrning" name_et="Free meassurement in use UI7 käsijuhtimisrežiim" name_lv="Brivais merijums Lietot_UI7 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1338" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SensorSel_DI1_GeneralAlarmName_mc" name_fi="DI1 Yleishälytys Käsiajo" name_en="DI1 General alarm Manual control" name_sv="DI1 Allmänt larm Manuell styrning" name_et="DI1 Üldalarm käsijuhtimisrežiim" name_lv="DI1 Vispārīgā trauksme Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1198" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SensorSel_UI15_PumpAlarm_UI15AlarmName_mc" name_fi="P2 Pumppu Käsiajo" name_en="P2 Pump alarm Manual control" name_sv="P2 Pump larm Manuell styrning" name_et="P2 Pumba alarm käsijuhtimisrežiim" name_ru="H2 Насос Ручной режим" name_lv="CS2 Sūknis Rokas vadība" name_tr="P2 Pump alarm Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1199" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_SensorSel_UI16_PumpAlarm_UI16AlarmName_mc" name_fi="P3 Pumppu Käsiajo" name_en="P3 Pump alarm Manual control" name_sv="P3 Pump larm Manuell styrning" name_et="P3 Pumba alarm käsijuhtimisrežiim" name_ru="H3 Насос Ручной режим" name_lv="CS3 Sūknis Rokas vadība" name_tr="P3 Pump alarm Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1200" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_AnAlarm_UI10_UI10AlarmName_mc" name_fi="KL Tulolämpötila Käsiajo" name_en="DH supply water temp. Manual control" name_sv="FJV Framledn. temp. Manuell styrning" name_et="KK Küttevesi käsijuhtimisrežiim" name_ru="ЦТС Темп. на подаче Ручной режим" name_lv="Prim. kont. turpgaitas temp. Rokas vadība" name_tr="DH supply water temp. Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1224" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_DigAlarm_UI11_UI11AlarmName_mc" name_fi="Kosketinhälytys UI11 Käsiajo" name_en="Switch alarm UI11 Manual control" name_sv="Koppling larm UI11 Manuell styrning" name_et="Lüliti alarm UI11 käsijuhtimisrežiim" name_lv="Trauksmes relejs UI11 Rokas vadība" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1258" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_AnAlarm_UI11_UI11AlarmName_mc" name_fi="KL Paluulämpötila Käsiajo" name_en="DH Return water temp. Manual control" name_sv="FJV Returvattnets temp. Manuell styrning" name_et="KK Tagastusvesi käsijuhtimisrežiim" name_lv="Prim. kont. atgaitas temp. Rokas vadība" name_ru="ЦТС Обр.темпер. Ручной режим" name_tr="DH Return water temp. Manuel kontrol " pointtype="3" registertype="Holding" addressformat="U16" addressindex="1257" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_DigAlarm_UI10_UI10AlarmName_mc" name_fi="Kosketinhälytys (UI10) Käsiajo" name_en="Switch alarm (UI10) Manual control" name_sv="Koppling larm (UI10) Manuell styrning" name_lv="Trauks. relejs (UI10) Rokas vadība" name_et="Lüliti alarm (UI10) käsijuhtimisrežiim" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1223" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
      <point name="InputSelections_RoomSel_UI7_RoomTempUI7InUse_mc" name_en="Result of logical AND operation Manual control" name_fi="RoomTempUI7InUse Käsiajo" name_sv="Resultat av logisk AND-funktion Manuell styrning" pointtype="3" registertype="Holding" addressformat="U16" addressindex="1500" categorytype="3" enum="0=Automaatti;1=Käsiajo" readacceslevel="5" writeacceslevel="3" />
    </group>
    <group categorytype="4" name="Hälytykset" name_en="Alarms" name_fi="Hälytykset" name_sv="Larm" name_et="Alarmid" name_ru="Аварийные сигналы" name_lv="Trauksmes" name_tr="Alarmlar ">
      <point name="SensorFaultAlarm__UI_1" name_en="Sensor fault  Outdoor temperature" name_fi="UI1: Anturivika  Ulkolämpötila" name_sv="Sensorfel  Utetemperatur" name_et="Anduri viga – välistemperatuur" name_ru="Неисправность датчика Наружная темп." name_lv="Sensora kļūda: Ārgaisa temperatūra" name_tr="Sensor fault  Outdoor temperature" pointid="SensorFaultAlarm__UI_1" refpointid="OutTemp.M" addressindex="517" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2838" severity="2" alarmid="#A2838" pointtype="14" />
      <point name="SensorFaultAlarm__UI_2" name_en="Sensor fault  H1 Supply water" name_fi="UI2: Anturivika L1 Menovesi" name_sv="Sensorfel  V1 Framledningsvatten" name_et="Anduri viga – K1 Küttevesi" name_ru="Неисправность датчика  O1 Подача" name_lv="Sensora kļūda: A1 Turpgaitas temp." name_tr="Sensor fault  H1 Supply water" pointid="SensorFaultAlarm__UI_2" refpointid="Heating1Supply.M" addressindex="520" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2839" severity="1" alarmid="#A2839" pointtype="14" />
      <point name="SensorFaultAlarm__UI_3" name_en="Sensor fault  H1 Return water" name_fi="UI3: Anturivika  L1 Paluuvesi" name_sv="Sensorfel V1 Returvatten" name_et="Anduri viga – K1 Tagastusvesi" name_ru="Неисправность датчика O1 Темп. обратной воды " name_lv="Sensora kļūda: A1  Atgaitas temperatūra" name_tr="Sensor fault  H1 Return water" pointid="SensorFaultAlarm__UI_3" refpointid="Heating1Retun.M" addressindex="524" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2840" severity="1" alarmid="#A2840" pointtype="14" />
      <point name="SensorFaultAlarm__UI_8" name_en="Sensor fault DHW Supply water" name_fi="UI8: Anturivika  LV Menovesi " name_sv="Sensorfel  TV Framledn.vatten" name_et="Anduri viga – TV Küttevesi" name_ru="Неисправность датчика  ГВС Подачаr" name_lv="Sensora kļūda: K.ŪD. Turpgaitas temp." name_tr="Sensor fault HW Supply water" pointid="SensorFaultAlarm__UI_8" refpointid="HotWatSupply.M" addressindex="533" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2841" severity="1" alarmid="#A2841" pointtype="14" />
      <point name="SensorFaultAlarm__UI_9" name_en="Sensor fault  DHW Circulation" name_fi="UI9: Anturivika LV Kiertovesi " name_sv="Sensorfel  TV Cirkulation" name_et="Anduri viga – TV Ringlus" name_ru="Неисправность датчика ГВС Circulation" name_lv="Sensora kļūda:  K.ŪD. Cirkulācijas temp." name_tr="Sensor fault  HW Circulation" pointid="SensorFaultAlarm__UI_9" refpointid="HotWatRet.M" addressindex="551" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2842" severity="1" alarmid="#A2842" pointtype="14" />
      <point name="SensorFaultAlarm__UI_5" name_en="Sensor fault  H2 Supply water" name_fi="UI5: Anturivika L2 Menovesi" name_sv="Sensorfel  V2 Framledningvatten" name_et="Anduri viga – K2 Küttevesi" name_ru="Неисправность датчика O2 Подача" name_lv="Sensora kļūda: A2 Turpgaitas temp." name_tr="Sensor fault  H2 Supply water" pointid="SensorFaultAlarm__UI_5" refpointid="Heating2Supply.M" addressindex="658" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2843" severity="1" alarmid="#A2843" pointtype="14" />
      <point name="SensorFaultAlarm__UI_6" name_en="Sensor fault  H2 Return water" name_fi="UI6: Anturivika L2 Paluuvesi" name_sv="Sensorfel  V2 Returvatten" name_et="Anduri viga – K2 Tagastusvesi" name_ru="Неисправность датчика   O2 Темп. обратной воды " name_lv="Sensora kļūda: A2  Atgaitas temperatūra" name_tr="Sensor fault  H2 Return water" pointid="SensorFaultAlarm__UI_6" refpointid="Heating2Return.M" addressindex="692" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2844" severity="1" alarmid="#A2844" pointtype="14" />
      <point name="SensorFaultAlarm__UI_4" name_en="Sensor fault  UI 4" name_fi="UI4: Anturivika" name_sv="Givarerfel  UI 7" name_et="Anduri viga – UI 4" name_ru="Неисправность датчика  UI4" name_lv="UI 4: Sensora kļūda" name_tr="Sensor fault  UI 4" pointid="SensorFaultAlarm__UI_4" refpointid="Room1/GenTemp.M" addressindex="1178" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2847" severity="2" alarmid="#A2847" pointtype="14" />
      <point name="SensorFaultAlarm__UI_7" name_en="Sensor fault  UI 7" name_fi="UI 7: Anturivika" name_sv="Givarerfel  UI 7" name_et="Anduri viga – UI 7" name_ru="Неисправность датчика  UI7" name_lv="UI 7: Sensora kļūda" name_tr="Sensor fault  UI 7" pointid="SensorFaultAlarm__UI_7" refpointid="Room2/GenTemp.M" addressindex="1179" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2848" severity="2" alarmid="#A2848" pointtype="14" />
      <point name="SensorFaultAlarm__UI_12" name_en="Sensor fault  UI 12" name_fi="UI12: Anturivika" name_sv="Givarerfel  UI 12" name_et="Anduri viga – UI 12" name_ru="Неисправность датчика  UI12" name_lv="UI 12: Sensora kļūda" name_tr="Sensor fault  UI 12" pointid="SensorFaultAlarm__UI_12" refpointid="Pressure1/GenTemp.M" addressindex="1180" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2849" severity="2" alarmid="#A2849" pointtype="14" />
      <point name="SensorFaultAlarm__UI_13" name_en="Sensor fault  UI 13" name_fi="UI13: Anturivika" name_sv="Givarerfel  UI 13" name_et="Anduri viga – UI 13" name_ru="Неисправность датчика  UI13" name_lv="UI 13: Sensora kļūda" name_tr="Sensor fault  UI 13" pointid="SensorFaultAlarm__UI_13" refpointid="Pressure2/GenTemp.M" addressindex="1184" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2850" severity="2" alarmid="#A2850" pointtype="14" />
      <point name="SensorFaultAlarm__UI_10" name_en="Sensor fault  UI10" name_fi="Anturivika  UI10" name_sv="Givarefel  UI10" name_et="Sensori viga  UI10" name_ru="Неисправность датчика  UI 10" name_lv="Sensora kļūda  UI10" name_tr="Sensor fault  UI10" pointid="SensorFaultAlarm__UI_10" refpointid="GenAl/GenTemp/UI10.M" addressindex="1272" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2147" severity="2" alarmid="#A2147" pointtype="14" />
      <point name="SensorFaultAlarm__UI_11" name_en="Sensor fault  UI11" name_fi="Anturivika  UI11" name_sv="Givarefel  UI11" name_et="Sensori viga  UI11" name_ru="Неисправность датчика  UI 11" name_lv="Sensora kļūda  UI11" name_tr="Sensor fault  UI11" pointid="SensorFaultAlarm__UI_11" refpointid="GenAl/GenTemp/UI11.M" addressindex="1273" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2148" severity="2" alarmid="#A2148" pointtype="14" />
      <point name="HeatingControl1_RetwaterComp_RetWaterFrozingAlr_A" name_en="H1 Freezing risk" name_fi="L1 Jäätymisvaara" name_sv="V1 Frysrisk" name_et="K1 Külmumisoht" name_ru="O1 Опасность обмерзания" name_lv="A1 Aizsalšanas risks" name_tr="H1 Freezing risk" pointid="HeatingControl1.RetwaterComp.RetWaterFrozingAlr_A" addressindex="1193" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2854" severity="1" alarmid="#A2854" pointtype="14" />
      <point name="HeatingControl1_DeviationAlarm1_DeviationAlarm_A" name_en="H1 Supply water deviation alarm" name_fi="L1 Menoveden poikkeamahälytys" name_sv="V1 Framledningvatten avvikelselarm" name_et="K1 Küttevee hälbealarm" name_ru="O1 Сигн.несоотв. по воде на подаче" name_lv="A1 Trauksme par turpg. temp. novirzēm" name_tr="H1 Supply water deviation alarm" pointid="HeatingControl1.DeviationAlarm1.DeviationAlarm_A" addressindex="1232" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2855" severity="1" alarmid="#A2855" pointtype="14" />
      <point name="HeatingControl1_DeviationAlarm1_Alarm" name_en="H1 Overheating alarm" name_fi="L1 Ylilämpöhälytys" name_sv="V1 Överhettningslarm" name_et="K1 Ülekuumenemise alarm" name_ru="O1 Авария по перегреву" name_lv="A1 Pārkaršanas trauksme" name_tr="H1 Overheating alarm" pointid="HeatingControl1.DeviationAlarm1.Alarm" addressindex="1292" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2856" severity="1" alarmid="#A2856" pointtype="14" />
      <point name="HeatingControl2_RetwaterComp_RetWaterFrozingAlr_A" name_en="H2  Freezing risk" name_fi="L2 Jäätymisvaara" name_sv="V2 Frysrisk" name_et="K2 Külmumisoht" name_ru="О2 Опасность обмерзания" name_lv="A2 Aizsalšanas risks" name_tr="H2  Freezing risk" pointid="HeatingControl2.RetwaterComp.RetWaterFrozingAlr_A" addressindex="959" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2851" severity="1" alarmid="#A2851" pointtype="14" />
      <point name="HeatingControl2_DeviationAlarm1_DeviationAlarm2_A" name_en="H2 Supply water deviation alarm" name_fi="L2 Menoveden poikkeamahälytys" name_sv="V2 Framledn.vattnets avvikelselarm" name_et="K2 Küttevee hälbealarm" name_ru="O2 Сигн.несоотв. по воде на подаче" name_lv="A2 Trauksme par turpg. temp. novirzēm" name_tr="H2 Supply water deviation alarm" pointid="HeatingControl2.DeviationAlarm1.DeviationAlarm2_A" addressindex="972" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2852" severity="1" alarmid="#A2852" pointtype="14" />
      <point name="HeatingControl2_DeviationAlarm1_Alarm" name_en="H2 Overheat alarm " name_fi="L2 Ylilämpöhälytys" name_sv="V2 Överhettningslarm " name_et="K2 Ülekuumenemise alarm " name_ru="O2 Авария по перегреву" name_lv="A2 Pārkaršanas trauksme" name_tr="H2 Overheat alarm " pointid="HeatingControl2.DeviationAlarm1.Alarm" addressindex="973" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2853" severity="1" alarmid="#A2853" pointtype="14" />
      <point name="InputSelections_SensorSel_DI1_P1Alarm_DI1_17_A" name_en="DI1 alarm" name_fi="DI1 Hälytys" name_sv="DI1 larm" name_et="DI1 Alarm" name_ru="DI1 Авария" name_lv="DI1 Trauksme" name_tr="DI1 alarm" pointid="InputSelections.SensorSel_DI1.P1Alarm_DI1_17_A" refpointid="InputSelections.SensorSel_DI1.P1_Alarm" addressindex="1100" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2857" severity="1" alarmid="#A2857" pointtype="14" />
      <point name="InputSelections_SensorSel_DI1_GenAlarm_DI1_17_A" name_en="DI1 Alarm" name_fi="DI1 Hälytys" name_sv="DI1 Larm" name_et="DI1 Alarm" name_ru="DI1 Авария" name_lv="DI1 Trauksme" name_tr="DI1 Alarm" pointid="InputSelections.SensorSel_DI1.GenAlarm_DI1_17_A" refpointid="InputSelections.SensorSel_DI1.GeneralAlarmName" addressindex="1144" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2858" severity="1" alarmid="#A2858" pointtype="14" />
      <point name="InputSelections_SensorSel_UI15_PumpAlarm_P2Alarm_UI15_A" name_en="UI15 Alarm" name_fi="UI15 Hälytys" name_sv="UI15 Larm" name_et="UI15 alarm" name_ru="UI15 Авария по насосу" name_lv="UI15 Trauksme" name_tr="UI15 Alarm" pointid="InputSelections.SensorSel_UI15.PumpAlarm.P2Alarm_UI15_A" refpointid="InputSelections.SensorSel_UI15.PumpAlarm.UI15AlarmName" addressindex="1150" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2859" severity="1" alarmid="#A2859" pointtype="14" />
      <point name="InputSelections_SensorSel_UI16_PumpAlarm_P3Alarm_UI16_A" name_en="UI16 Alarm" name_fi="UI16 Hälytys" name_sv="UI16 Larm" name_et="UI16 Alarm" name_ru="UI16 Авария" name_lv="UI16 Trauksme" name_tr="UI16 Alarm" pointid="InputSelections.SensorSel_UI16.PumpAlarm.P3Alarm_UI16_A" refpointid="InputSelections.SensorSel_UI16.PumpAlarm.UI16AlarmName" addressindex="1181" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2860" severity="1" alarmid="#A2860" pointtype="14" />
      <point name="InputSelections_DigAlarm_UI13_SwitchAlarm_A" name_en="Pressure switch alarm (UI13)" name_fi="Painekytkinhälytys (UI13)" name_sv="Tryck koppling larm (UI13)" name_et="Survelüliti alarm (UI13)" name_ru="Авария прессостата (UI13)" name_lv="Spiediena slēdža trauksme (UI13)" name_tr="Pressure switch alarm (UI13)" pointid="InputSelections.DigAlarm_UI13.SwitchAlarm_A" refpointid="InputSelections.DigAlarm_UI13.AlrState" addressindex="1435" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2861" severity="1" alarmid="#A2861" pointtype="14" />
      <point name="InputSelections_DigAlarm_UI12_SwitchAlarm_A" name_en="Pressure switch alarm (UI12)" name_fi="Painekytkinhälytys (UI12)" name_sv="Tryck koppling larm (UI12)" name_et="Survelüliti alarm (UI12)" name_ru="Авария пресостата (UI12)" name_lv="Spiediena slēdža trauksme (UI12)" name_tr="Pressure switch alarm (UI12)" pointid="InputSelections.DigAlarm_UI12.SwitchAlarm_A" refpointid="InputSelections.DigAlarm_UI12.AlrState" addressindex="1436" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2862" severity="1" alarmid="#A2862" pointtype="14" />
      <point name="InputSelections_AnAlarm_UI10_AnAlarmUI10_A" name_en="Free measurement (UI10)" name_fi="Vapaa mittaus (UI10)" name_sv="Fri mätning (UI10)" name_et="Free measurement (UI10)" name_ru="Произвол.измерение   (UI10)" name_lv="Brīvais mērījums (UI10)" name_tr="Free measurement (UI10)" pointid="InputSelections.AnAlarm_UI10.AnAlarmUI10_A" refpointid="InputSelections.AnAlarm_UI10.UI10AlarmName" addressindex="1242" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="3034" severity="1" alarmid="#A3034" pointtype="14" />
      <point name="InputSelections_DigAlarm_UI11_SwitchAlarmUI11_A" name_en="Switch alarm (UI11)" name_fi="Kosketinhälytys (UI11)" name_sv="Koppling larm (UI11)" name_et="Lüliti alarm (UI11)" name_ru="Авария по контакту (UI11)" name_lv="Trauksmes relejs (UI11)" name_tr="Switch alarm (UI11)" pointid="InputSelections.DigAlarm_UI11.SwitchAlarmUI11_A" refpointid="InputSelections.DigAlarm_UI11.UI11AlarmName" addressindex="1271" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="3035" severity="1" alarmid="#A3035" pointtype="14" />
      <point name="InputSelections_AnAlarm_UI11_AnAlarmUI11_A" name_en="Free measurement (UI11)" name_fi="Vapaa mittaus (UI11)" name_sv="Fri mätning (UI11)" name_et="Vaba mõõtmine  (UI11)" name_ru="Произвол.измерение (UI11)" name_lv="Brīvais mērījums (UI11)" name_tr="Free measurement (UI11)" pointid="InputSelections.AnAlarm_UI11.AnAlarmUI11_A" refpointid="InputSelections.AnAlarm_UI11.UI11AlarmName" addressindex="1270" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2866" severity="1" alarmid="#A2866" pointtype="14" />
      <point name="InputSelections_DigAlarm_UI10_SwitchAlarmUI10_A" name_en="Switch alarm (UI10)" name_fi="Kosketinhälytys (UI10)" name_sv="Koppling larm (UI10)" name_et="Lüliti alarm (UI10)" name_ru="Авария по контакту (UI10)" name_lv="Trauksmes relejs (UI10)" name_tr="Pressure switch alarm (UI10)" pointid="InputSelections.DigAlarm_UI10.SwitchAlarmUI10_A" refpointid="InputSelections.DigAlarm_UI10.UI10AlarmName" addressindex="1241" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2999" severity="1" alarmid="#A2999" pointtype="14" />
      <point name="InputSelections_RoomSel_UI7_L2RoomTempAlr_A" name_en="Room temperature H2" name_fi="Huonelämpötila L2" name_sv="Rumstemperatur V2" name_et="Toatemperatuur K2" name_ru="Комнатная температура О2" name_lv="Telpas temperatūra A2" name_tr="Room temperature H2" pointid="InputSelections.RoomSel_UI7.L2RoomTempAlr_A" refpointid="InputSelections.RoomSel_UI7.RoomTemp" addressindex="1183" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2863" severity="2" alarmid="#A2863" pointtype="14" />
      <point name="InputSelections_RoomSel_UI4_L1RoomTempAlr_A" name_en="Room temperature H1" name_fi="Huonelämpötila L1" name_sv="Rumstemp. V1" name_et="Toatemperatuur K1" name_ru="Комнатная температура О1" name_lv="Telpas temperatūra A1" name_tr="Room temperature H1" pointid="InputSelections.RoomSel_UI4.L1RoomTempAlr_A" refpointid="InputSelections.RoomSel_UI4.RoomTemp" addressindex="1182" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2864" severity="2" alarmid="#A2864" pointtype="14" />
      <point name="InputSelections_AnAlarm_UI12_AnAlarm_A" name_en="Pressure alarm (UI12)" name_fi="Painehälytys (UI12)" name_sv="Tryck larm (UI12)" name_et="Survealarm (UI12)" name_ru="Авария по давлению (UI12)" name_lv="Spiediena trauksme (UI12)" name_tr="Pressure alarm (UI12)" pointid="InputSelections.AnAlarm_UI12.AnAlarm_A" addressindex="1438" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="3000" severity="1" alarmid="#A3000" pointtype="14" />
      <point name="InputSelections_AnAlarm_UI13_AnAlarm_A" name_en="Pressure alarm (UI13)" name_fi="Painehälytys (UI13)" name_sv="Tryck larm (UI13)" name_et="Survealarm (UI13)" name_ru="Авария по давлению (UI13)" name_lv="Spiediena trauksme (UI13)" name_tr="Pressure alarm (UI13)" pointid="InputSelections.AnAlarm_UI13.AnAlarm_A" addressindex="1437" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2865" severity="1" alarmid="#A2865" pointtype="14" />
      <point name="DHW_Control_DHWHighLimitAlarm_A" name_en="DHW Overheating alarm" name_fi="LV Ylilämpöhälytys" name_sv="TV Överhettningslarm" name_et="TV Ülekuumenemise alarm" name_ru="ГВС Авария по перегреву" name_lv="K.ŪD. Pārkaršanas trauksme" name_tr="HW Overheating alarm" pointid="DHW_Control.DHWHighLimitAlarm_A" addressindex="953" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="2867" severity="1" alarmid="#A2867" pointtype="14" />
      <point name="DHW_Control_DHWLowLimitAlarm_A" name_en="DHW low limit alarm" name_fi="LV alarajahälytys" name_sv="TV nedre gräns larm" name_et="TV alumine piir alarm" name_ru="ГВС предел тревоги низкой" name_lv="K.ŪD. Trauksmes min. robeža" name_tr="HW low limit alarm" pointid="DHW_Control.DHWLowLimitAlarm_A" addressindex="1378" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="3120" severity="1" alarmid="#A3120" pointtype="14" />
      <point name="MyApplication_OutTempFromBusAlarm_A" name_en="Outdoor temperature from bus alarm" name_fi="Ulkolämpötila väylältä hälytys" name_sv="Utetemperatur från busslarm" name_et="Välistemperatuur siinist" name_ru="Темп.наруж.возд.от магистрал.шины" name_lv="Ārgaisa temp. no BUS " name_tr="Outdoor temperature from bus alarm" pointid="MyApplication.OutTempFromBusAlarm_A" addressindex="1503" mask="1" addressackmask="2" addressprioritymask="28" addressgroupmask="480" readacceslevel="5" writeacceslevel="3" ackindex="56" transferackindex="107" ackvalue="1223" severity="1" alarmid="#A1223" pointtype="14" />
    </group>
  </groups>
</controllertemplate>